1 Contents: Introduction UFH-ZONE-R UFH-EXTRAZONE -R Connection of a thermostat (UFH-THERM-R) o Joining of a thermostat with UFH-ZONE-R or UFH-EXTRAZONE-R Connection of a digital thermostat (UFH-THERM -RD) o Joining of a digital thermostat with UFH-ZONE-R or UFH-EXTRAZONE -R Connection of an electrothermal motor UFH-ACT230NC2, UFH-ACT230NC4 or UFH- ACT24NC4 Connecting diagram Detailed information: o o o o UFH-THERM -R thermostat Technical characteristics LED indication Adjustment range limitation Calibration of the thermostat Digital thermostat (UFH-THERM -RD) Technical characteristics Connection of a floor sensor LCD display Installer s menu Description of the distinctive modes Timer/receiver: Characteristics LCD display Distinctive modes Setting-up of a user programme Installation menu Electrothermal motors UFH-ACT230NC2 UFH-ACT230NC4 UFH-ACT24NC2
2 UFH-ZONE-R This control unit enables you to receive signals from 6 radio-controlled room thermostats, by which all areas may be controlled. Besides, this module can also serve as timer for more (max. 10) non-programmable room thermostats. The programming of the timer and communication setting-up between sender and receiver proceeds in a very simple way. Control unit Timer and receiver Antenna As soon as 1 room thermostat detects a heat request, a built-in relay activates the pump and boiler. Extension possibility for 4 extra room thermostats, by using the optional extension module UFH- EXTRAZONE-R
3 Picture: UFH-ZONE-R Boiler and pump contact Supply voltage 230VAC or 24VAC Zone 1, 2, 3, 4, 5 and 6 Supply voltage 230VAC or 24VAC The unit has to be connected to the mains voltage (being 230VAC or 24VAC 50-60Hz). Because of electrocution danger, it is recommended not to do this until all thermostats and electrothermal motors have been connected. If you choose for a mains voltage of 24VAC, you can only connect electrothermal motors of the UFH- ACT24NC2 type to it. If you choose for a mains voltage of 230VAC, both types UFH-ACT230NC2 and UFH-ACT230NC4 can be connected. Zone 1, 2, 3, 4, 5 and 6: Each zone is provided with 2 pairs of terminals for the connection of electrothermal motors. Attention: only 2 motors maximally may be connected per pair (so: 4 motors per room thermostat). Boiler and pump contact: 2 pairs of dead terminals to control the boiler and pump. Attention: both contacts open and close at the same moment. Extension for extra zones: The control unit can be extended with an optional module UFH-EXTRAZONE-R. This module enables you to install 4 extra room thermostats and their accompanying electrothermal motors. The UFH-EXTRAZONE-R doesn t have to be separately provided with supply voltage. The supply voltage for the UFH-EXTRAZONE-R is provided by the UFH-ZONE-R.
4 Picture: UFH-EXTRAZONE-R: Connection between UFH-ZONE -R and UFH-EXTRAZONE -R: The black surfaces on the UFH-zone-R have to be linked with the forked terminals of the UFH- EXTRAZONE-R. This can be done by pushing the terminals through the white housing over the printed-circuit board. Because of electrocution danger, it is recommended to do this before connecting the UFH-ZONE-R to the mains supply. Attention: the UFH-EXTRAZONE -R has to be installed between the control unit and the timer/receiver. See picture below. Picture: UFH-ZONE -R and UFH-EXTRAZONE -R UFH-EXTRAZONE -R UFH-ZONE-R
5 Connection of a radio-controlled room thermostat (UFH-THERM -R): RF 1 1. Put the thermostatic switch in the centre position. 2. Put the timer - by using the < and > keys - in the comfort mode ( ) 3. Push the OK button then; keep pushing the OK while pushing the < at the same time. (You have reached the installer s menu now) 4. Push on - once now; you have reached the RF initialisation menu now. The utmost left LED is blinking. 5. By using the + and - keys, you can select and deselect respectively a zone. If you select a zone with the + key, the LED of the concerned zone keeps lighting up and the LED of the next zone starts blinking. If you deselect a zone with the - key, the LED of the concerned zone turns out and the LED of the next zone starts blinking. (You can select several zones for 1 room thermostat) 6. If you have selected the zones you want to connect with the room thermostat, put the thermostat switch in the comfort mode position. At this moment, a radio link is created between the thermostat and the receiver. On the LCD display of the timer, a double bar appears below and the LEDs of the selected zones turn out. 7. Repeat the above mentioned steps until you have connected all room thermostats with the desired zones. 8. Push on the OK key of the timer during 5 seconds now in order to leave the installer s menu. 9. Put the timer in the AUTO mode in order to activate the programmes.
6 How to connect a room thermostat: Open the thermostat: 1. Remove the temperature scale 2. Loosen the screw 3. Remove the front plate Place the thermostat in a suitable room: Place the thermostat at a height of 1.5 m Avoid direct sunlight Don t fix the thermostat on an external wall Closing of the thermostat 1. Place the front plate 2. Fasten the front plate with the screw 3. Replace the temperature scale as before
7 Connection of a radio-controlled digital room thermostat (UFH-THERM -D): o Put the timer in the comfort mode ( ) by using the < and > keys. o o Push the OK button then, keep pushing the OK while pushing the < at the same time. (You have reached the installer s menu now) Push - once now; you have reached the RF initialisation menu now. The utmost left LED blinks. o o o o By using the + and - keys you can select and deselect respectively a zone. If you select a zone with the + key, the LED of the concerned zone keeps lighting up and the LED of the next zone starts blinking. If you deselect a zone with the - key, the LED of the concerned zone turns out and the LED of the next zone starts blinking. (You can select several zones for 1 room thermostat). If you have selected the zones you want to connect with the room thermostat, push the OK key of the digital thermostat during 5 seconds. The UFH-THERM-RD is now sending radio signals to the timer. If a double bar appears at the bottom of the timer display, push again shortly on the OK key of the thermostat. The LEDs of the selected zones turn out now. Repeat the above mentioned steps until all room thermostats are connected with the desired zones. Push the OK key of the timer now during 5 seconds in order to leave the installer s menu. Put the timer in the AUTO mode in order to activate the programmes.
8 Open a thermostat: 1. Remove the white protecting cap 2. Loosen the screw 3. Remove the front plate Place the thermostat in a suitable room: Place the thermostat at a height of 1.5 m Avoid direct sunlight Don t fix the thermostat on an external wall Close the thermostat 1 Place the front plate 2 Fasten the front plate with the screw 3 Replace the white protecting cap as before
9 Connection of an electrothermal motor UFH-ACT230NC2, UFH-ACT230NC4 or UFH-ACT24NC2 Each zone is provided with 2 pairs of terminals for the connection of an electrothermal motor. Only 1 motor maximally may be connected per pair of terminals. So: 2 electrothermal motors per zone (or per room thermostat). In case of an electrothermal motor with auxiliary contact (UFH-230NC4), you only have to connect the blue and brown wire onto the terminals. Terminals for electrothermal motor
10 Connecting diagram: RF 1
11 Detailed information: UFH-THERM -R room thermostat This radio-controlled room thermostat has been especially created for floor heating systems. Each room thermostat has a personal digital code that excludes jamming from room thermostats in the neighbourhood. There is a switch at the side of the room thermostat by means of which the thermostat can be put into 3 modes, namely: - comfort - night reduction - OFF The thermostat has an LED indication, showing the heating-up phase and radio transmission. The temperature adjustment can be limited or blocked. Technical characteristics: Accuracy of the measured temperature: Adjustment range: Regulation: Autonomous feeding: Frequency: Protection class: Dimensions: 0.1 C + 5 C to 30 C Proportional link of 2 C for a cycle of 15 min. 2 batteries of 3V, type CR2430, life span 2 years MHz, <10mW IP30 80 x 80 x 31 mm LED indication: Green blinking: Red: Red blinking: Radio transmission Heating-up phase based on the environmental temperature The battery has to be replaced
12 Adjustment range limitation: Calibration of the thermostat:
13 UFH-THERM -RD Digital wireless room thermostat This radio-controlled room thermostat with LCD display has been especially created for floor heating systems. Each room thermostat has a personal digital code that excludes jamming from room thermostats in the neighbourhood. By pressing a key, the room thermostat can be easily put into 3 modes, namely: - comfort - night reduction - OFF Display of the desired temperature and room temperature. Can be equipped with an optional floor sensor (UFH-SENSOR) to limit the temperature of the floor. This room thermostat has also an extended installers menu. Following parameters can be adjusted: - Display of C or F - Selection between heating and cooling system - Adjustment of the time cycle (proportional regulation) - Regulation of the amplitude in C or F (proportional regulation) - Possibility to put the pump into operation once a day. - Option between environmental and floor temperature - Setting-up of the temperature limits of the floor sensor Technical characteristics: Accuracy of the measured temperature: Adjustment range: Autonomous feeding: Frequency: Protection class: Dimensions: 0.1 C + 5 C to 37 C, in steps of 0.5 C 2 batteries of 3V, type CR2430, life span 2 years MHz, <10mW IP30 80 x 80 x 31 mm Adjustment of the optional floor sensor: In order to prevent floor heating from being switched off by the thermostat when sunlight is coming in, or to prevent floor temperature from rising too much so that the comfortable feeling disappears, the room thermostats can be equipped with this optional floor sensor. Terminals for floor sensor Connect the sensor with the terminals provided for that purpose; the parameters of the floor sensor can be adjusted in the installer s menu (see installer s menu below).
14 LCD display: 1 : Function mode 2 : Burner into operation display 3 : Cooling system into operation display 4 : Replace the batteries (only for the RF model) 5 : When lighted up, 6 shows the environmental temperature 6 : Measured temperature or adjusted temperature 7 : Parameter installation: description Installer s menu: Push the OK button during 5 seconds, use the and keys then in order to select the parameter installation to be adapted. Push the OK button to walk through the parameters or to adapt the value. If the value blinks, you can modify it with and. Press the and key at the same time to return to the works settings. Push OK to confirm. N of the parameter Description of the parameter Rf Radio signal is sent out, press OK shortly to stop and leave the menu JO C/ F display J1 Cooling installation Cy Proportional integral regulation value time cycle in minutes (standard: 15 minutes) bp Proportional integral regulation value amplitude in degrees C/ F (standard: 2 C/3.6 F) J5 Select PMP to let operate the pump once a day (if the pump hasn t functioned one day) J6 Air: air temperature adjustment J7 reg (proportional integral) or HYs (0.3 K Hysteresis) to choose the regulation type Cp C/ F Display (standard: 2.0 C/3.6 F) Ao Adaptation environmental sensor display measured environmental value Fo Adaptation floor sensor display measured floor value FL Limitation of the floor temperature lower limit (standard 5 C/41 F); works only if the floor sensor has been connected. FH Limitation of the floor temperature upper limit (standard 28 C/82 F); works only if the floor sensor has been connected. Clr Push OK during 5 sec. in order to choose works settings for all parameters.
15 Description of distinctive modes: RF 1 Mode COMFORT Use this function to set your installation into comfort mode Use the and keys to adjust the comfort temperature The comfort temperature of the thermostat is unlimitedly maintained Afterwards, the environmental temperature is displayed again Mode REDUCED TEMPERATURE Use this function to put your installation into reduced temperature mode Use the and keys to adjust the reduced temperature The reduced temperature of the thermostat is unlimitedly maintained Afterwards, the environmental temperature is displayed again Mode OFF Use this function to switch off your heating installation. The display is empty now. (Attention: Your installation may freeze now). The parameters are kept. Timer Characteristics: Guarantees wireless communication, equipped with an active antenna. Average receiving range in residential environments: 50 m. 7 days, to be programmed separately per zone Provided with 9 works programmes and 12 user programmes (to be programmed yourself) Graphic programme rendition Temperature display in each zone Comfort mode / reduced temperature / frost protection Mode holidays Programming is maintained during long current interruptions The clock continues to operate during 3 hours of current interruption
16 Distinctive installation parameters LCD-display Holiday mode Temperature has been adapted manually Heat request Temperature use + / - to adapt temperature Environmental temperature MENU use to change mode Day of the week Time Graphic programme rendition Mode COMFORT: If selected, each zone follows the temperature which is adjusted on the local thermostat. If you push the OK button, you can read the temperature in the selected zone. Mode AUTOMATIC: If selected, the timer follows the programme which you programmed/selected for each zone. Sun = Room thermostat adjusted temperature. Moon = Room thermostat adjusted temperature - 4 C. REDUCED TEMPERATURE mode: If selected, the temperature is reduced in each zone. Room thermostat adjusted temperature - 4 C. FROST PROTECTION mode: If selected, the installation is frost-protected. With the +/- keys, you can adjust the anti-freeze temperature. In each zone, the temperature will be at least equal to the anti-freeze temperature.
17 Mode OFF: Select this mode if you want to turn off the heating installation. The timer will first of all turn off the installation and then itself. The clock continues to work another 3 hours; the programmes are kept in memory. The timer can be activated by pressing any random button. Attention: If you choose this mode, your installation may freeze. Mode CLOCK : Select this menu to adjust the time. use +/ - to set minutes, push on OK then use +/ - to set hours, push on OK then use +/ - to set the actual day (1 = Monday), push on OK then Mode PROGRAMMING: By pushing the +/- keys, the zone number starts blinking. (***) use +/ - to select a zone or a user programme with < and > you can look at the other days of the programme Programme number Shows the daily programme If you select a zone (1 to 12) and push on OK then, you can select a weekly programme that has to be followed by this zone. When the programme number is blinking: With < and > another day of the weekly programme is shown Use +/- to select a programme Shows the daily programme When you select a works programme (P1 to P9 (included)) or a user programme (U1 to U10 (included)) and then you push on OK, this programme will follow the AUTO mode.
18 Works programmes: P1: Morning, evening and in the weekend P2: Morning, noon, evening and in the weekend P3: Day and weekend P4: Evening and in the weekend P5: Morning, evening P6: Morning, afternoon and in the weekend P7: 7h-19h (office) P8: 8h-19h and Saturday (shop) P9: Weekend (weekend house) User programme setting-up: If you choose for a user menu (U1-U12) in (***), you can, after having pressed OK, program a whole week. Day Hour on cursor position With the + key, you select the comfort mode With the key, you select the reduced mode With the < and > you are walking through the programming bar; if a complete day is programmed, push the OK to go to the following day. If you push the OK button on the seventh day, this will bring you to the main menu. In phase (***), you can link your programme to the desired zone now. Installer s menu: Go with the < > keys to the comfort mode. Keep pushing on OK and press < at the same time. You have reached the installer s menu now. With +/- you can select the desired parameter; push OK to adapt the parameter. Parameters: F.0 PROG/EASY Select PROG for an extended menu Select EASY for a limited menu, only: - comfort - reduced temperature - frost protection - holiday mode F.1 BUZZ/no If you choose for BUZZ, a sound signal is generated when contact with a room thermostat is lost. F.2 NC/NO actuator Select NC if you use normally closed actuators
19 Select NO if you use normally open actuators RF 1 F.3 ACtU/no Actuator exercise Choose ACtU if you want to open the actuators during 5 minutes daily, if there is no heat request during 24 h. J.0 C/ F temperature display J.1 12h/24h time display J.2 --:15/--:8 time cycle in minutes Choose --:8 if you have an installation that thermally reacts slowly. J K/1.2 K proportional link Choose 1.2 K only if you have an installation that thermally reacts quickly. J.5 PUMP/no pump test Choose PUMP in order to activate the pump during 2 minutes a day (at 12h), if there is no heat request during 24 h. J.6 ItCS/no Intelligent Temperature Control System Choose ItSC if you want to use intelligent software, taking into account the distinctive parameters, which are influencing the heating-up and cooling-down time of each zone. Consequently, each zone will be warmed up optimally with a minimum of energy costs. UFH-ACT230NC2 Electrothermal motor 230V, normally closed (NC) Attachment M30 x 1.5 Description: This electrothermal ON/OFF motor is used for automation of manifolds of type V-06 and VH-06. The motor is addressed by a room thermostat or regulation unit. Operation: The operation is based on a thermostatic wax element, which is activated by an electrical signal (230V) originating from a room thermostat or regulation unit. The wax element is warmed up by this electrical signal, which results in expansion. This expansion activates opening and closing of a zone. The motor is provided with a transparent zone which visualizes the status. (RED = valve closed, BLACK = valve opened) Technical characteristics: Supply voltage: 230V alternating voltage Frequency: 60Hertz Consumption: 2.5Watt Starter current: 0.25A x 0.5sec Initial opening and closing time: 90s Final opening and closing time: 3min. Protection class: IP44 Operating temperature: 0 to 50 C Storage temperature: -25 to 60 C Maximal liquid temperature: 110 C Nominal clamping force: 140N
20 UFH-ACT230NC4 Electrothermal motor 230V, normally closed (NC), with auxiliary contact. Attachment M30 x 1.5 Description: This electrothermal ON/OFF motor is used for automation of manifolds of type V-06 and VH-06. The motor is addressed by a room thermostat or regulation unit. The pump is addressed by an auxiliary contact. Operation: The operation is based on a thermostatic wax element, which is activated by an electrical signal (230V) originating from a room thermostat or regulation unit. The wax element is warmed up by this electrical signal, which results in expansion. This expansion activates opening and closing of a zone. The motor is provided with a transparent zone which visualizes the status. (RED = valve closed, BLACK = valve opened) Technical characteristics: Supply voltage: 230V alternating voltage Frequency: 60Hertz Consumption: 2.5Watt Starter current: 0.25A x 0.5sec Initial opening and closing time: 90s Final opening and closing time: 3min. Protection class: IP44 Operating temperature: 0 to 50 C Storage temperature: -25 to 60 C Maximal liquid temperature: 110 C Nominal clamping force: 140N Maximal switching current of the auxiliary contact: 700mA at 250 (AC) UFH-ACT24NC2 Electrothermal motor 24V, normally closed (NC) Attachment M30 x 1.5 Description: This electrothermal ON/OFF motor is used for automation of manifolds of type V-06 and VH-06. The motor is addressed by a room thermostat or regulation unit. Operation: The operation is based on a thermostatic wax element, which is activated by an electrical signal (24V) originating from a room thermostat or regulation unit. The wax element is warmed up by this electrical signal, which results in expansion. This expansion activates opening and closing of a zone. The motor is provided with a transparent zone which visualizes the status. (RED = valve closed, BLACK = valve opened) Technical characteristics: Supply voltage: 24V alternating voltage Frequency: 60Hertz Consumption: 2.5Watt Starter current: 0.25A x 0.5sec Initial opening and closing time: 90s Final opening and closing time: 3min. Protection class: IP44 Operating temperature: 0 to 50 C Storage temperature: -25 to 60 C Maximal liquid temperature: 110 C Nominal clamping force: 140N
DUAL SENSING DIGITAL THERMOSTAT PRODUCT INSTRUCTIONS www.rehau.com Construction Automotive Industry SCOPE This guide gives instruction regarding REHAU Programmable Digital Thermostat installation and operation.
3 072 RDJ10RF RCR10/433 Wireless room temperature controller with 24-hour time switch and LCD Programmable, for heating systems RDJ10RF/SET Operating modes: Automatic, Comfort, Energy Saving, and Frost
INSTALLATION MANUAL EKRTR EKRTETS 1 2 1 2 3 60 87 170 161 ±1.5 m >0.2 m 3 5 4 34 125 4 5 28 50 EKRTR EKRTETS Contents Read this manual attentively before starting up the unit. Do not throw it away. Keep
W Ith I ntelligent Control S Ave E lectricity INTELLIGENT HOT WATER CYLINDER CONTROL INSTRUCTION MANUAL Thank you for purchasing our controller Before operating and installation carefully read all instructions.
TB6980/TB7980 1. Introduction The TB6980/TB7980 digital thermostats provide proportional plus integral individual space temperature control in zoned commercial HVAC systems such as hydronic and pressure
CM702 PROGRAMMABLE THERMOSTAT FEATURES Attractive slim, modern styling makes it ideal for location in any type of home. 24-hour heating program. Up to 4 daily independent time and temperature level changes
HCE80/HCC80/HCE80R/HCC80R UNDERFLOOR HEATING-ZONEING CONTROLLERS PRODUCT DATA FEATURES Easy and fast installation because the new wiring design Pluggable terminals for fast wiring connection because clamp
Instructions *087R9781* *VIKTG202* Danfoss can accept no responsibility for possible errors in catalogues, brochures and other printed material. Danfoss reserves the right to alter its products without
EK908FHL - Thermostat for floor heating EK908FHL is a programmable thermostat designed for floor warming application or helping to limit floor temperature. This thermostat can be used for hot water radiant
8400 Series Thermostats Safety & Installation Instructions READ AND SAVE THESE INSTRUCTIONS 61000652D 8400 Tstat Install.indd 1 Table of contents Installation Installation location recommendations... 3
3 067 RDF310.2, RDF310.21 RDF410.21 Flush-mounted Room Temperature Controllers with LCD for 2-pipe fan coil units for use with compressors in DX type equipment RDF310 RDF410 Output for on / off valve actuator
evohome Wireless Radiator Zoning Kit Installation & User Guide Getting the most from your evohome system Installation & User Guide 1 Getting the most from your evohome system Thanks for choosing an evohome
ELECTRICAL HEATER INTEGRATED THERMOSTATS Class I Thermostat Electronic thermostat with proportional regulation to be integrated in electrical heater, protected by earth. Basic or 2 orders pilot wire (Eco
Installation and User Guide TYXIA Wireless receiver TYXIA RF 642-1 channel DELTA DORE Bonnemain - 35270 COMBOURG - France E-mail : firstname.lastname@example.org Unit compliant with the requirements of directives:
T5000 T000 LCD Digital Fan Coil Thermostat T000 LCD Digital Fan Coil Thermostat T000 LCD Digital Fan Coil Thermostats are designed to control heating, cooling, or year round air conditioning unit in Commercial,
Alpha Climatic Programmable Modulating Boiler Energy Manager Part No 3.022144 (Hard Wired) Part No 3.022143 (Radio Frequency) Installation and User Instructions 1. Description The Alpha Climatic energy
3060 electro-mechanical programmer for controlling heating & hot water Installation & User Instructions Index Installation Product specification 3 Installation 4 Wiring 4-5 User Your programmer 6 Programming
TICS - Total Integrated Control Strategy Mid Range System Underfloor Heating & Cooling Control Solutions Energy efficient Heating and cooling TICS - Mid Range System Mid Range System TICS Mid Range Install
Wireless Control Systems Accessories Leading the way in intelligent automation contents Range Overview Typical Installations Transmitters Combined Modules Accessories Programming Switching & Dimmer Functions
MAKING MORN LIVING POSSIBLE Danfoss heating living connect Installation and User Guide Contents 1.0 System overview... 3 2.0 Overview of display and control buttons... 3 3.0 Installation - step by step...
RTC2 BACnet FAN COIL CONTROLLER / THERMOSTAT BACnet Enabled C-030 BAC 07/10 Description The RTC2 temperature controller incorporates a LCD display and is specifically designed for zone temperature control
3 346 Temperature Controller (Heat Pumps) RWD34 RWD44 For comfort control in HVAC & R systems Standalone electronic controller Programmable controller with preconfigured applications Two universal inputs
ATS-220 AUTOMATIC TRANSFER SWITCH CONTROL UNIT OPERATOR S MANUAL For Use in 208 to 240 Volts Single and 3 Phase ATS Systems With 110Volt AC or DC Control Motors and selenoids 4501 NW 27 ave Miami FL 33142
INSTALLATION AND MAINTENANCE Specifications: is suitable for floor heating systems, Power Supply AC 120/ 240V,50/60Hz Maximum Load 15A, resistive Maximum Power 1800W at 120VAC; 3600W at 240VAC GFI Class
ELECTRIC CENTRAL HEATING FLOW BOILER EKCO.T Used product can t be treated as general communal waste. Disassembled appliance has to be delivered to the collection point of electrical and electronic equipment
TF428 Series Digital Thermostat Fan Coil Unit Control Features SPECIFICATION DATA General The TF428 series digital thermostat is designed for 3-speed fan and valve control in a fan coil system, including:
2 242 Room temperature controller for in-wall mounting with one weekly operating mode including individual 24-hour modes and three 24-hour modes, cooling function REV26 Mains-independent room temperature
Devices Clima-phone - TECHNICAL CHARACTERISTICS 01913 - Electronic GSM timer-thermostat Supply voltage: 120-230 V~, 50-60 Hz. 2 AAA NiMH 1,2 V rechargeable batteries (supplied) in order to operate during
ADI Modules - Integrated Domestic Automation Weather and control units ADI MODULES Radio controlled equipment for automating doors and windows, rolling shutters, lights, fans, solenoids and small domestic
Vroom CANBUS USER INTERFACE WITH LCD GRAPHIC DISPLAY AND WITH TEMPERATURE AND HUMIDITY SENSOR ENGLISH HARDWARE MANUAL ver. 1.00 CODE 114VROOHWE00 page 1 of 22 Important Important Read these instructions
3 003 Room hermostat RAA30 Adjustable room thermostat for heating only or cooling only systems Room thermostat with manual O/OFF switch wo-position control witching voltage AC 24 250 V Use he RAA30 room
COMPUTHERM Q7 Programmable, digital room thermostat Operating Instructions GENERAL DESCRIPTION OF THE THERMOSTAT The COMPUTHERM Q7 type switched-mode room thermostat is suitable to regulate the overwhelming
Page 1 of 6 Application Proportional 0-10V or 3-position modulating or On/ Off control of Frese OPTIMA Compact valves in heating, ventilating and air conditioning systems. The actuator can be mounted on
2 522 Heating Controller Series B RVL470 Multifunctional heating controller for use in residential and non-residential buildings; suitable for weather-dependent flow temperature control of heating zones
AUTOMATE RF40s REMOTE INSTRUCTIONS RF40s Single Channel Remote Control / With Timer P/N: RB24-905-06900 LCD Screen UP CH (-) TIME SETTING BUT- DOWN CH () TIME CONFIRMATION BUT- STOP MODE BUTTON WEEK MANUAL
Wireless Detection System with unique detectors for smaller applications RCP6 B wireless fire control panel microprocessor controlled 433 MHz 6 zones up to 100 radio addressable devices linkable 4 potential-free
Operation 3M-30 Day Time of day Target Temperature Time Slot Touch Screen Current Room Temperature Thermostat Mode Statement of use: The 3M-30 can be used with millivolt, 24VAC, single and 2 stage conventional
Operating instructions for built-in electronic timers with Day and Week programms Series 884 Attention: This operating manual is destined for our OEM customers and is intended as a basis for the instruction
Document No. 19-49 RDF Series Room Temperature Controllers Product Description Room Temperature Controllers with LCD for twopipe (with and without an electrical heater) and fourpipe fan coil units. Installation
SERVICE INSTRUCTION SPLIT TYPE ROOM AIR CONDITIONER WALL MOUNTEDtype INVERTER Models Indoor unit Outdoor unit ASYG07LECA ASYG09LECA ASYG12LECA ASYG14LECA AOYG07LEC AOYG09LEC AOYG12LEC AOYG14LEC R410A CONTENTS
Selecting the right controls for your automated lubrication system is one of the last steps in the design process. Several different models may be chosen to control power-operated pumps, depending on the
Radio Thermostat Clock Part Number: 30800009 Installation & User Instructions Suitable for all Ferroli Combination Boilers 2 Short Description Short description Radio Thermostat Clock - Transmitter The
2 726 Temperature controller for duo-zone ducted systems RRV852 Multifunctional controller used for central control of ducted HVAC systems in combination with QAX850 and QAW850 room units. Duo-zone model
1 General information 1.1 About this manual This manual describes the installation, function and operation of an integrated solar control system, which is suitable for split pressurized solar heating system.
Going green Smart HVAC - ECOclimate www.ekonhome.com Simply Smart ECOclimate Thermostat Fan Coil Central AirCon Control Fan Coil or Central Air Condition combined with 2 Loads Light Switch. Add Optional
- Saves energy - Guarantees an even room temperature - Suitable for central water heating systems - Many types of measurements and alarm functions - GSM remote use Intelligent heating controller for your
Wireless 7 Day Programmable Room Thermostat Cat. No. TRT037 Transmitter Receiver Operating & Installation Instructions What is a programmable room thermostat? an explanation for householders A programmable
COOLING or HEATING ANALOG or PWM Art. 119914 631001A TOTAL AUTOMATION GENERAL TRADING CO. LLC SUITE NO.506, LE SOLARIUM OFFICE TOWER, SILICON OASIS, DUBAI. UAE. Tel. +971 4 392 6860, Fax. +971 4 392 6850
TM 4.-inch Back-Up Camera Model No.: PKC0BU4 Owner s Manual and Warranty Information Read these instructions completely before using this product. Retain this Owner s Manual for future reference. INTRODUCTION
AQUATROL Zone Synchronizing Programmable Relay Boiler Controls AQ25A USER OPERATION AND MAINTENANCE WARNING Risk of electrical shock. Can cause severe injury, property damage or death. Only trained, experienced,
Installation Guide TH3210D Non-programmable Digital Thermostat Product Application This thermostat provides electronic control of 24 VAC heat pump systems with auxiliary heat (2 heat/1 cool). Power Type
3 576 ACR2.44/ALG Fan-coil controller for wall mounting ACR2.44 Pulse width modulated (PWM) valve outputs for thermal actuators, AC 23 V P or PI control behaviour selectable 3-speed fan control, automatic
Welcome To INSTALLATION GUIDE 1 Contents Introduction... 3 In The Box... 4 Display... 5 Before You Start... 6 Installation Overview... 7 Professional Assistance... 7 Abbreviations... 8 Installation Details...
comfort at your command Carrier has met temperature control needs worldwide with its thermostats. Carrier thermostats provide computer-like intelligence with extremely simple operation in an elegant package.
Firmware version: 1.10 Issue: 7 AUTODIALER GD30.2 Instruction Manual Firmware version: 2.0.1 Issue: 0.6 Version of the GPRS transmitters configurator: 22.214.171.124 Date of issue: 07.03.2012 TABLE OF CONTENTS
SAT-1 Thermostat COOL FAN DRY HEAT AUTO SLEEP SWING AUTO ZONE SUN MON TUE WED THU FRI SAT HEATER ON OFF ERR UNIT USER'S OPERATING INSTRUCTIONS CONTENTS Introduction 3 Features Summary 3 Display 4 Operation
Stove Guard Kit User Manual Innohome improves the Safety of your Home. inno home www.innohome.com Stove Guard Kit User Manual Stove Guard Kit User Manual Congratulations! You now own one of the most intelligent
Inwall Room Temperature Unit TM11B01KNX TM11B11KNX TM11B21KNX Product Handbook Product: Inwall Room Temperature Unit Order Code: TM11B01KNX TM11B11KNX TM11B21KNX Application Program ETS: TM11B_1KNX Inwall
B.IQ push button 3-5gang with RTR and Functional description: Push button functionality: Depending on the parameterized software, the B.IQ push button RTR (Room Temperature Regulator) will send telegrams
ROBERTS Sound for Generations CR9971 2 Band Auto Set Dual Alarm Clock Radio Please read this manual before use Contents Contents... 1 Controls...2-5 Switching on... 6 Setting the time manually... 6 Setting
1 ERROR CODES AND APPLIANCE MESSAGES... 3 1.1 Complete overview of all error codes (in order)... 3 Automatic switch-off... 3 Display is dark and any individual LEDs are lit... 3 E 005... 3 E 011... 3 E
TP5000 Si Range Electronic 5/2 day programmable room thermostat Mains, Battery and RF versions Certification Mark GB Installation and GB Index Index Installation Instructions 3-14 Product Specification
SERVICE INSTRUCTION SPLIT TYPE ROOM AIR CONDITIONER Universal Floor / Ceiling Duct / Cassette Wall Mounted / Floor type INVERTER MULTI R410A Models Indoor unit Outdoor unit AB*14LBAJ AB*18LBAJ AB*F14LAT
230 V~ 369813a 1 07.02.15 The 230 V~ room thermostat adds temperature control to the LutronR hotel guestroom control solution. Controls 2-pipe, 4-pipe, and 3 fan-speed fan coil units. Compatible with LutronR
Installation Guide TH4210D Programmable Thermostat Product Application This thermostat provides electronic control of 24 VAC heat pump systems with auxiliary heat (2 heat/1 cool). Power Type Battery power
SOLO User Guide Programmable Dual Voltage Thermostat Description The SOLO thermostat is designed to control the temperature of a floor heating system for both 120-volt and 240-volt applications. The thermostat
DC/AC CLAMP METER Model CM-01 USERS MANUAL PROVA INSTRUMENTS INC. EN 61010-2-032 CAT II 600V CAT III 300V Pollution Degree 2 SYMBOLS showed on the clamp meter or in this manual: Caution, risk of danger.
THERMONET UNDERFLOOR HEATING STANDARD THERMOSTAT KIT STOCK CODE 5260 STANDARD THERMOSTAT KIT 1.0 KIT CONTENTS Parts included: 1 x Thermostat 1 x Wall plate 2 x Mounting box screws 1 x Floor temperature
MAKING MODERN LIVING POSSIBLE living connect Installation and User Guide Danfoss Heating Solutions 2 living connect Thank you for buying a Danfoss product Danfoss Heating Solutions 3 Contents 1. System
Installation Guide TH3110D Non-programmable Digital Thermostat Product Application This thermostat provides electronic control of 24 VAC single-stage heating and cooling systems, or 750 mv heating systems.
Specifications Supply Voltage 240VAC @ 0.07Amps or 24VAC @ 0.380Amps Relays 240V @ 12A max (resistive) / Comp1,2,3, Aux Ht, Rv O/B) Fuses (Equipment) 15 Amps Maximum 3AG Control Range Minus 10 to 50C Control