1 Instruction Bulletin Z B PowerLogic Sub Display (SMD and SMDOPN) CONTENTS Introduction... 2 Parts of the Sub Display... 3 Dimensional Drawing... 4 Installation... 5 Mounting the SMD... 5 Mounting the SMDOPN... 6 Communications... 8 Downstream Devices... 9 Upstream Devices... 9 Terminating the Last Device in the Downstream Daisy Chain Power Connection Setup Entering the Password Initializing a System Viewing the Setup Mode Submenus Monitoring Mode Viewing and Resetting Alarms Troubleshooting and Maintenance Changing the Battery Changing the Fuse Quick Reference Menu Tree Specifications Mounting Template
2 PowerLogic Sub Display (SMD and SMDOPN) Introduction INTRODUCTION Z B The PowerLogic Sub Display (SMD and SMDOPN) is a comprehensive electrical sub metering display (Figure 1). With the display, you can view electrical parameters with one networked LCD. In addition to viewing system data on the display itself, you can also view data on a remote PC via a network connection. Touch pad buttons provide a convenient way to view downstream devices on the power monitoring network. The display is RS-485 Modbus RTU compatible. It has additional RS-485 and RS-232 Modbus ports for networking to additional displays or to a master PC. Figure 1 The Sub Display SUB METER DISPLAY (Setup) (Alarm) Next Previous Hold Reading Scroll The display provides local indication of all power system parameters from the compatible meters connected downstream. All system parameters and alarms can transmit to the network operations center by means of Modbus RTU protocol. The display supports the following multiple sensors: ENERCEPT s Branch Circuit Monitors (BCM42 and BCMSC) Multi-Circuit s (MCM8364) Alta Labs Network Temperatures and Humidity Sensors (HXO-485, TXO-485, and HXO/T-485) Schneider Electric All Rights Reserved.
3 Z B PowerLogic Sub Display (SMD and SMDOPN) Introduction Parts of the Sub Display Figure 2 shows the parts of the display, while Table 1 describes these parts. Figure 2 Parts of the Display RX TX RX TX Table 1 Parts Description of the Display Part Vac 200 ma fast fuse Fused power connection for circuit protection. 2 Lithium battery Onboard clock backup. Description 3 Power transformer Linear power supply for reliability and low noise Vac power supply terminals 2-wire, 120 Vac, 60 Hz, line to neutral. 5 Auxiliary input status LED Indicates alarm condition for the auxiliary input. 6 Membrane switch pin connector Connection point for push button panel. 7 Upstream RS-232 input jack Connection point for upstream RS-232 network Vdc power port Alternate 12 Vdc connection point for use with plug-in wall-mount transformer or power supply. (Auxiliary input is disabled if 12 Vdc power is used.) 9 Upstream RS-485 connection point Terminal for upstream RS-485 network. 2- or 4-wire compatible. 10 Downstream RS-485 connection point Terminal for downstream RS-485 network. 2- or 4-wire compatible. 11 Membrane switch ribbon cable (From customer-supplied face plate) 12 Status LED Green = Normal Operation. No network devices are in warning or critical alarm mode. Yellow = One or more network devices are in warning alarm mode. Red = One or more network devices are in critical alarm more or the auxiliary input is active. 13 Liquid crystal display High-resolution LCD with adjustable backlight Schneider Electric All Rights Reserved. 3
4 PowerLogic Sub Display (SMD and SMDOPN) Introduction Z B Dimensional Drawing 8.0 (204 mm) (4x) (7 mm) 8.0 (204 mm) 5.0 (127 mm) 1.5 (38 mm) 4.0 (102 mm) 7.0 (178 mm) 0.5 (13 mm) Schneider Electric All Rights Reserved.
5 Z B INSTALLATION PowerLogic Sub Display (SMD and SMDOPN) Installation DANGER HAZARD OF ELECTRIC SHOCK, EXPLOSION, OR ARC FLASH Apply appropriate personal protective equipment (PPE) and follow safe electrical work practices. See NFPA 70E. This equipment must be installed and serviced only by qualified personnel. Turn off all power supplying this equipment and the equipment it is to be mounted inside before working on or inside equipment. Always use a properly rated voltage sensing device to confirm that power is off. Replace all device doors and covers before turning on power to this equipment. Failure to observe these instructions will result in death or serious injury. Mounting the SMD The SMD ships pre-assembled in a UL508 listed equipment enclosure. The enclosure is equipped with knockouts for power and communication conduit attachments and requires no field assembly except for enclosure mounting. Front View (Display Screen) Back View (Mounting Holes) Figure 3 Mounting the Display 2011 Schneider Electric All Rights Reserved. 5
6 (Setup) (Alarm) PowerLogic Sub Display (SMD and SMDOPN) Installation Z B Mounting the SMDOPN The SMDOPN is an open board product that requires field mounting in an enclosure or panel. To mount the display in a panel enclosure, refer to Figure 5 and Figure 6 and follow these steps: 1. Ensure that the display is not connected to power and turn off all power supplying the equipment it is to be mounted inside before working on or inside the equipment. 2. Use a properly rated voltage sensing device to confirm that power is off. 3. Using the template provided with your SMDOPN as a guide, drill holes and cut openings in the panel or enclosure. 4. Thread the membrane switch ribbon cable (A) through the rectangular opening. 5. Mount the display faceplate (B) onto the panel. Figure 4 Mounting the Display in a Panel Chassis Display Faceplate (B) SUB METER DISPLAY Membrane Switch Ribbon Cable (A) Panel Door Next Previous Hold Reading Scroll 6. Secure the faceplate by screwing four threaded stand-offs (C) into the faceplate studs from the inside of the door. 7. Attach the display (D) to the threaded studs using the four #6-32 screws (E) provided Schneider Electric All Rights Reserved.
7 Z B PowerLogic Sub Display (SMD and SMDOPN) Communications 8. Connect the membrane switch ribbon cable (A) to the membrane switch pin connector (F). Figure 5 Display Components Back of Display Faceplate (B) Faceplate studs Panel Enclosure of Cutout Threaded Stand-offs (C) #6-32 Screws (E) Display (D) Opening in Panel for Membrane Switch Ribbon Cable Membrane Switch Ribbon Cable (A) Membrane Switch Pin Connector (F) 2011 Schneider Electric All Rights Reserved. 7
8 PowerLogic Sub Display (SMD and SMDOPN) Communications Z B COMMUNICATIONS The display resides on a Modbus network as a pass-through device (Figure 7). It provides an upstream and downstream communication connection. This allows for flexible data retrieval as the upstream options include RS-232 or RS-485. Figure 8 shows the downstream and upstream wiring scheme. Figure 6 Upstream Monitoring Network Option Control Panel or PC To additional Displays Upstream RS-485 or RS-232 (Setup) SUB METER DISPLAY (Alarm) Next Display Next Previous Hold Reading Scroll SUB METER DISPLAY Downstream RS-485 (Setup) (Alarm) Next Previous Hold Reading Scroll Display Up to 63 (physical) or 246 (logical) devices Enercept MCM8364 Branch Current Monitor Other Modbus Devices Multi-Circuit End of Line Resistor 100 Ohms Schneider Electric All Rights Reserved.
9 Z B PowerLogic Sub Display (SMD and SMDOPN) Communications Downstream Devices Upstream Devices Observe these guidelines for downstream devices communications wiring: Connect devices on a daisy chain from the downstream RS-485 port. The display can support 32 devices with a maximum distance of 4000 ft. (1,219 m) to the last device. For devices on the daisy chain, follow the device distance limitations recommended by the manufacturer. Each device must have a unique address. The last device must be terminated with a terminator (Square D part no. 3090MCTAS485 or 100 ohm resistor). Observe these guidelines for upstream devices communications wiring: NOTE: Connection to upstream RS-485 or RS-232 ports will disable the front infrared port. A master computer or additional Sub Displays can be connected on a daisy chain to the upstream RS-485 port. The maximum distance from the first upstream device to the last is 4000 ft. (1,219 m). Each device on this upstream connection as well as those downstream must have a unique address. The last upstream device must be terminated with a terminator (Square D PN 3090MCTAS485 or 100 ohm resistor). Figure 7 Wiring of Downstream and Upstream Devices RS-232 Pinout: DCE, no handshaking DB-9 connection: pin 2: Transmitted data from display pin 3: Received data into display pin 5: Signal ground RX TX RX TX Master or Slave (Upstream Devices) 4-Wire RS485 Downstream RS232 Upstream Slave (Downstream Device) TX TX+ SHLD RX RX+ TX TX+ TX TX+ SHLD RX RX+ TX TX+ SHIELD 4-Wire RS485 Upstream SHIELD OR Master or Slave (Upstream Devices) OR Slave (Downstream Device) TX TX+ SHLD RX RX+ TX TX+ 2-Wire RS 485 Downstream TX TX+ SHLD RX RX+ TX TX+ 2-Wire RS485 Upstream SHIELD SHIELD SHIELD SHIELD 2011 Schneider Electric All Rights Reserved. 9
10 PowerLogic Sub Display (SMD and SMDOPN) Communications Z B Terminating the Last Device in the Downstream Daisy Chain Terminate the downstream network using the 3090MCTAS485 terminator to ensure reliable communications. Refer to Figure 9 and follow these steps: 1. Insert the wires of the daisy chain as shown in Figure 8 and insert the wires of the terminator into the holes of the RS-485 communications connector. 2. Using a small flat blade screwdriver, tighten the connector screws. 3. Plug the communications connector into the communications port of the last device on the daisy chain. Figure 8 Installing the 3090MCTAS485 Terminator TX TX+ SHLD RX RX+ TX TX Schneider Electric All Rights Reserved.
11 Z B POWER CONNECTION PowerLogic Sub Display (SMD and SMDOPN) Power Connection DANGER HAZARD OF ELECTRIC SHOCK, EXPLOSION, OR ARC FLASH Apply appropriate personal protective equipment (PPE) and follow safe electrical work practices. See NFPA 70E. This equipment must be installed and serviced only by qualified personnel. Turn off all power supplying this equipment and the equipment it is to be mounted inside before working on or inside equipment. Always use a properly rated voltage sensing device to confirm that power is off. Replace all device doors and covers before turning on power to this equipment. Failure to observe these instructions will result in death or serious injury. To make the power connection, use either 120 Vac 2-wire or 12 Vdc connection as shown in Figure 10. Figure 9 Power Connection Options Option #1 power wiring 120 Vac Option #2 power wiring 12 Vdc RX TX RX TX Note: Internal fusing is not active on the 12 Vdc input Schneider Electric All Rights Reserved. 11
12 PowerLogic Sub Display (SMD and SMDOPN) Setup Z B SETUP Entering the Password Use the Setup Mode to initialize and configure the display to the application requirements. The password for setup mode is, Previous, Previous,, Next, Next as shown in Figure 11. This password is fixed and cannot be changed. Figure 10 Entering the Password for Setup Mode To Enter Press Simultaneously Enter Password SET UP MODE and * * * * * * * (, Previous, Previous,, Next, Next) Initializing a System Viewing the Setup Mode Submenus To initialize a system, you must perform the Setup communications and Find s actions. See Setup Communications Submenu and Find s Submenu. Once you are in the setup mode, press Next or Previous buttons to view submenus and then press for the submenu you want. Figure 12 illustrates setup mode button functions. Figure 11 Setup Mode Button Functions Press Show next submenu. Show previous submenu. a submenu. monitoring. Setup Mode Submenus View System Info Find s Review meters Setup Communications Setup Operation The following are the setup mode submenus: View System Info Submenu In setup mode, View System Info is the first submenu to display. View System Info for viewing information only (not modifying) such as the serial number or the customer support phone number. See Figure Schneider Electric All Rights Reserved.
13 Z B PowerLogic Sub Display (SMD and SMDOPN) Setup Figure 12 View System Info Button Functions VIEW SYSTEM INFO Show next parameter. Show previous parameter. setup mode menu. Model Serial number RS Rev OS Rev Memory Clock System Info Unit model number. Unit serial number. Reset system firmware revision number Operating system firmware revision number Amount of non-volatile memory Indicates presence of a real-time clock. Customer support number Contact support information. Setup Operation Submenu Setup Operation to adjust operational parameters. Set backlight brightness for optimum visibility. You can set output relay and auxiliary input parameters based on the contact configuration of any (optional) remote devices. You can set the display to automatically rotate through the readings or you can rotate manually. See Monitoring Mode on page 11 for details. Refer to Figure 14 for Setup Operation parameters. Figure 13 Setup Operation Button Functions SETUP OPERATION Show next parameter. Show previous parameter. Save setting and go to next parameter. setup menu. Operation Parameters Backlight Brightness (0-9), 0 = Backlight OFF) Output Relays (ALARM = OPEN, ALARM = CLOSED) Auxiliary Input (ALARM = OPEN, ALARM = CLOSED) Rotate Parameters (YES, NO). See Monitoring Mode Setup Communications Submenu Setup Communications to adjust communications parameters. You must set downstream communications parameters to match the communications parameters of the downstream devices. When using an upstream master PC or control panel, you must set the appropriate Modbus address and upstream communications parameters. Refer to Figure 15. Figure 14 Setup Communication Button Functions Communication Parameters SETUP COMMUNICATIONS Show next parameter. Show previous parameter. Save setting and go to next parameter. setup menu. Modbus Address (1-247) Upstream Type (RS-485, RS-232, Infrared) Upstream Duplex (2-wire, 4-wire). See Notes 1, 2. Upstream Baudrate (2400, 4800, 9600, 19,200). See Note 2. Upstream Parity (NONE, ODD, EVEN). See Note 2. Downstream Duplex (2-wire, 4-wire) Downstream Baudrate (2400, 4800, 9600, 19,200) Downstream Parity (NONE, ODD, EVEN) Notes: 1. Parameter not available for RS Parameter not available for Infrared Schneider Electric All Rights Reserved. 13
14 PowerLogic Sub Display (SMD and SMDOPN) Setup Z B Find s Submenu From Setup mode, selecting Find s initiates a search and identifies devices on the network. Exit the search by pressing any key. To make sure all meters are accounted for, do not exit until all active addresses have been counted. Unsupported devices will be designated as unknown device and parameters will not be displayed. See Specifications section for supported devices. Review s Submenu From Setup mode, selecting Review s allows you to review all attached devices detected by the display. When you press REVIEW METERS, you see the first device found in the network. If the display does not detect any devices, you get a No s message. The following are example displays of devices detected by the FIND METERS function: Example Display for an MCM6384 AD=002 BRD1 MTR7 MULTI-CRCT PRW 8 where AD=002 indicates Modbus address 2, BRD1 is the board name, and MTR7 is the meter name. Example Display for a BCM42 Monitor AD=061 BRD1 BRANCH CRCT AMPS where AD=061 indicates Modbus address 061 and BRD1 is the board name. Example Display for an Alta RH/Temp Sensor AD=216 ALTA RH/TEMP Example Display for an Unsupported Device AD=123 UNKNOWN DEVICE Press Next to view the next meter. Continue pressing Next to scroll through the devices. Press to return to the setup menu Schneider Electric All Rights Reserved.
15 Z B PowerLogic Sub Display (SMD and SMDOPN) Setup Monitoring Mode Monitoring is the default mode for the Sub Display. You can set up the display to automatically rotate (scroll) through parameters or you can set it to display a selected parameter continuously. You do this by selecting either Yes or No for Rotate Parameters in the Setup Operation submenu (see Figure 14. When set to Yes for Rotate Parameters, the display automatically rotates through the parameters of all supported devices and updates every four seconds. You can press to hold a reading to allow time to manually record the reading. When the reading is in hold, it will not be updated. Press any other button to return to monitoring mode (the display resumes automatically rotating through parameters of all supported devices). Figure 16 shows the monitoring mode button functions. Figure 15 Monitoring Mode Button Functions MONITORING MODE Go to next parameter set. Go to previous parameter set. Hold the present reading when in automatic rotation mode (the display flashes). Pressing any other button releases the reading. Go to next meter. Viewing and Resetting Alarms Alarm mode provides a means of viewing and resetting warning and critical alarms on the downstream network. To enter the alarm mode, press the and buttons simultaneously. Figure 17 shows the alarm mode button functions. Figure 16 Alarm Mode Button Functions To Enter ALARM MENU Press Simultaneously and View next alarm. Reset currently displayed alarm. Exit alarm display Schneider Electric All Rights Reserved. 15
16 PowerLogic Sub Display (SMD and SMDOPN) Troubleshooting and Maintenance Z B TROUBLESHOOTING AND MAINTENANCE WARNING HAZARD OF ELECTRIC SHOCK, EXPLOSION OR ARC FLASH Apply appropriate personal protective equipment (PPE) and follow safe electrical work practices. See NFPA 70E. Turn off all power supplying this equipment and the equipment it is mounted inside before working on or inside equipment. Always use a properly rated voltage sensing device to confirm that power is off. Replace onboard lithium backup battery only with the same or equivalent type recommended by the manufacturer. Dispose of battery according to the manufacturer s instructions. Failure to follow these instructions can result in death or serious injury. If the display does not illuminate, check the fuses and voltage connections. Changing the Battery To change the onboard lithium backup battery (item 2, Figure 2 on page 3), follow these steps: 1. Verify that the power supply to the display is turned off. 2. Remove the old lithium battery, taking care not to short the battery terminals. 3. Install the new lithium battery (same or equivalent type recommended by the manufacturer). 4. Turn on the power supply to the display. Changing the Fuse If the fuse is blown, use only 250 Vac / 200 ma, Fast, 5x20 mm. Follow these steps to replace it: 1. Verify that the power supply to the display is turned off. 2. Remove the old fuse and replace it with the new one. 3. Turn on the power supply to the display Schneider Electric All Rights Reserved.
17 Z B PowerLogic Sub Display (SMD and SMDOPN) Quick Reference Menu Tree QUICK REFERENCE MENU TREE Figure 16 provides a quick reference menu tree. Figure 17 Quick Reference Menu Tree MONITORING Show next parameter Show previous parameter Hold reading Go to next meter To Enter ALARM MENU Press simultaneously and Press Show next alarm Clear alarm monitoring To Enter SET UP MENU Press simultaneously and Enter Password Press * * * * * * * (, Previous, Previous,, Next, Next) Show next submenu Show previous submenu Go to submenu or start action monitoring 1st Submenu VIEW SYSTEM INFO Show next info item Show previous submenu monitoring Info Items Model Number/Serial Number Version/Revision Installed Options Veris Support Phone Number FIND METERS 2nd Submenu Any key to return to setup menu REVIEW METERS 3rd Submenu Show next meter setup menu 4th Submenu 5th Submenu SETUP COMMUNICATIONS Increment parameter Increment parameter Decrement parameter SETUP OPERATION Decrement parameter Go to next parameter Go to next parameter setup menu setup menu Communication Parameters Modbus Address (1-247) Upstream Type (RS-485, RS-232, Infrared) Upstream Duplex (2-wire, 4-wire)*** Upstream Baud (2400, 4800, 9600, 19200)** Upstream Parity (NONE, ODD, EVEN)** Downstream Duplex (2-wire, 4-wire) Downstream Baud (2400, 4800, 9600, 19200) Downstream Parity (NONE, ODD, EVEN) Setup Operation Parameters Backlight Brightness (0-9, 0=Backlilght OFF) Output Relays (ALARM=OPEN, ALARM = CLOSED) Auxiliary Input (ALARM = OPEN, ALARM = CLOSED) Rotate Parameters (YES, NO) 2011 Schneider Electric All Rights Reserved. 17
18 Z B PowerLogic Sub Display (SMD and SMDOPN) Specifications SPECIFICATIONS Table 2 General Specifications Type Operating Temperature Range Storage Temperature Range 20 C to 70 C AC Power Source AC Power Voltage Tolerance AC Power Frequency AC Power Termination Description 0 to 50 C (< 95% relative humidity, non-condensing) Dedicated 120 Vac, line-to-neutral, Fused, 200 ma at 250 Vac 5x20 mm Fast + 10/-25% ( Vac) 50/60 Hz 2-position cage clamp terminal block (max. wire size 12 gauge) Alternate DC Power Source 12 Vdc unfused (Auxiliary input disabled) Upstream Network Communications Interface Protocol Baud Rate Parity Communication Format RS-485, RS-232, or infrared Modbus RTU User-selectable 2400, 4800, 9600, 19,200 (infrared fixed at 9600) User-selectable NONE, ODD, EVEN (infrared fixed at NONE) 8-data-bits, 1-start-bit, 1-stop-bit RS-485 1/4-load transceivers Duplex is user-selectable 2-wire or 4-wire 5-position depluggable connector Downstream Network Communications Interface Protocol Duplex Load RS-485 Modbus RTU User-selectable 2-wire or 4-wire 1/4-load transceivers Baud Rate User-selectable 2400, 4800, 9600, 19,200 Parity Communication Format Termination LCD Size Backlight Supported Modbus Devices User-selectable NONE, ODD, EVEN 8-data-bits, 1-start-bit, 1-stop-bit 5-position depluggable connector 1 x 4 inch visible area, 2 lines x 16 characters per line Green, User-adjustable brightness in 10 steps Enercept s Multi-Circuit Monitor (MCM8364) Branch Current Monitor (BCM42) Alta Labs Network Temperature/Humidity Sensors (HXO-485, TXO-485, HXO/T-485) 2011 Schneider Electric All Rights Reserved. 18
19 MOUNTING TEMPLATE The following template may be used as a guide when installing the display. Schneider Electric Power Monitoring and Control 295 Tech Park Drive, Suite 100 LaVergne, TN (615) Document# Z B March 2011 As standards, specifications and designs develop from time, always ask for confirmation of the information given in this publication. Power Monitoring and Control, ION, ION Enterprise, and Modbus are either trademarks or registered trademarks of Schneider Electric or its affiliates. Other marks used herein may be the property of their respective owners Schneider Electric - All Rights Reserved.
Generator Meter Model: VAAFH Installation/Operation Manual I) Introduction The VAAFH is an ideal monitor system for 240/120 generators and grid power sources and provides monitor of load balancing on the
LAUREL ELECTRONICS, INC. Laureate Quadrature Encoder Position & Rate Meter Features Accepts low-level differential or single-ended 5V logic level outputs from quadrature encoders Quadrature count x1, x2
Vroom CANBUS USER INTERFACE WITH LCD GRAPHIC DISPLAY AND WITH TEMPERATURE AND HUMIDITY SENSOR ENGLISH HARDWARE MANUAL ver. 1.00 CODE 114VROOHWE00 page 1 of 22 Important Important Read these instructions
MAKING MODERN LIVING POSSIBLE AK-SC255 On-Site Installation Guide DANFOSS ELECTRONIC CONTROLS & SENSORS How to Use This Guide Read this Guide completely as you install and start up your new AK-SC 255 controller.
This Quick Start Guide is designed to familiarize the user with the connection and configuration of the DTS-305 DIN rail mounted single / 3 phase power & energy meter with RS-485 or TCP communications.
INSTRUCTION MANUAL IM670-U v0.1 COMPALARM C2C ALARM SYSTEM GENERAL Compact alarm system, with a basic module of 12 signals Multiple modules coupling possibility Easy printing of the alarm points description
DX4010V2 EN Installation Instructions RS-232/USB Serial Interface Module DX4010V2 Installation Instructions Trademarks Trademarks BlackBox is either a registered trademark or a trademark of BlackBox Corporation
Infrastructure Management & Monitoring For Business-Critical Continuity Liebert AC4 User Manual TABLE OF CONTENTS 1.0 INTRODUCTION 1.1 Methods of Viewing and Configuring the Liebert AC4..............................
Instruction Bulletin 63249-420-317A1 01/2009 POWERLINK RS232 to 485 Converter for use with POWERLINK G3 Systems INTRODUCTION SAFETY PRECAUTIONS The POWERLINK G3 Controllers are used to control the operation
LAUREL ELECTRONICS, INC. Laureate Quadrature Encoder Position & Rate Meter Features Accepts low-level differential or single-ended 5V logic level outputs from quadrature encoders Quadrature count x1, x2
Cellular Modem Installation Guide This installation guide describes how to install and set up a GSM cellular modem for use as a communication gateway for the SolarEdge device (inverter or Safety and Monitoring
SolarEdge RS485 Expansion Kit Installation Guide Version 1.0 Disclaimers Disclaimers Important Notice Copyright SolarEdge Inc. All rights reserved. No part of this document may be reproduced, stored in
RSC232 Communication Converter Installation and Operation Manual LIMITED WARRANTY The manufacturer offers the customer a 24-month functional warranty on the instrument for faulty workmanship or parts from
Instruction Bulletin 63230-216-244B1 LaVergne, TN, USA MCS025 Sync-Check Module Installation Sheet Retain for future use. DANGER HAZARD OF ELECTRIC SHOCK, EXPLOSION, OR ARC FLASH Only qualified electrical
This quick start guide provides, basic installation information, drawings, first time power-on instructions, and short descriptions of key terms and concepts for installing the EntraGuard Platinum Telephone
COMPU TER PROCE SS CONTRO L S technical bulletin Overview Control Techniques Variable-Speed Drive (VSD) Interface The E2 RX, BX, and CX series of controllers features integration with several models of
MANUAL PC1000R INFO@APART-AUDIO.COM Features The APart PC1000R is a professional multisource CD/USB/SD card music player, equipped with balanced and unbalanced analog outputs, coaxial and optical digital
Technical Specification Sheet Document No. 149-188P25 Rev. 6 March, 2000 Unitary Controller The Unitary Controller can operate as an independent stand-alone controller, or can be connected to the APOGEE
PC1000RMKII Instruction manual PC1000RMKII Instruction manual 3 PC1000RMKII Manual 4 MEDIA PLAYER Features The Apart PC1000RMKII is a professional multisource CD/USB/SD card music player, equipped with
PF2100 4-20mA Input Card Instruction Manual v1.0 by Ryan Northcott Table of Contents Description... 1 Level Current Loop... 2 Pressure Current Loop... 2 Auxiliary Current Loop... 2 Quick Start Checklist...
Setting Up the ZigBee Ethernet Gateway MAN-01-00030-1.4 This manual describes how to install and set up ZigBee communication between a SolarEdge device (Inverters or Safety and Monitoring Interface) and
00% electricity Generating set controller RGK 60 Large graphic screen for measurement and 5-language help prompt display Operating mode selection touch keys Manual control of stand-by generating set Load
Instruction Sheet 1-2003 Automatic Transfer Switch FT-10 Network Control Communications Module (CCM-T) Kit 541 0811 PURPOSE OF KIT A CCM-T is used to monitor and control an automatic transfer switch. The
MPBB1 Uploader user manual 1997-2000 Martin Professional A/S, Denmark. All rights reserved. No part of this manual may be reproduced, in any form or by any means, without permission in writing from Martin
EMBEDDED ACCESS CONTROL Hardware Installation Guide Lenel goentry Hardware Installation Guide, product version 1.00. This guide is item number DOC- ENHW-ENU, revision 1.003, April 2009 Copyright 2009 Lenel
Section F The conversion of Analogue signals to digital is an important part of many control systems. So is the conversion of serial data between various standards (RS, RS485 and RS4 for example). www.weidmüller.com.au
ENET-710 ENET-710 - Ethernet Module JAN / 06 ENET-710 FOUNDATION E N E T 7 1 0 ME smar www.smar.com Specifications and information are subject to change without notice. Up-to-date address information is
LIGHTING CONTROL PANELS 4 AND 8 RELAYS INSTALLATION INSTRUCTIONS INSTALLATION OVERVIEW The installation instructions contained in this document are provided as a guide for proper and reliable installation.
1 de 7 1. Introduction This Technical Note explains how to configure the Modbus Gateway for Vantage Pro2. The Modbus Gateway allows the easy connection of a PLC (Programmable Logic Controller), RTU (Remote
68 Flexible, high specification system Choice of 1, 2, 4 or 8 zones Simple one-shot auto-reset user test facility Approved to EN54 Maintenance free poly switch circuit protection, with auto reset Class
5731 Benjamin Center Drive Tampa, Florida 33634 Phone:813.349.1900 Fax:813.349.1907 Version: A Release Date: 2013-07-24 READ THIS MANUAL CAREFULLY AND KEEP IT ACCESSIBLE FOR FURTHER REFERENCE! USE AS DIRECTED:
REV. A Applied Electronics Commercial Dimming System UPDATE NOTICE This notice is to inform the end user of an additional feature added to this DP12/2400 dimming unit. This unit has been outfitted with
Instruction Bulletin PowerLogic Tenant Metering Software Installation Guide 63230-504-200A4 LaVergne, TN, USA Replaces 63230-504-200A3 Retain for future use. Use this installation guide when you install
February 2015 February 2015 Application Note - Connecting an Electricity Meter to SolarEdge Devices (Europe and APAC) This document describes how to connect an electricity meter to a SolarEdge device (inverters,
INSTALLATION GUIDE Card Reader & Controller with KIM Swipe Reader for Solitaire 850 / 950 / 850L Learnlok PK2930 Card Reader and Controller Model 3.5 with KIM Swipe Reader Table of Contents 1. Features..................................
Keypad D222 Installation Instructions 1.0 Description The D222 Keypad (Figure 1) is a low-profile, surface-mount, three-wire unit with four hard-wired expansion points for use with Bosch Security Systems
Page 1 of 8 1. DESCRIPTION The Viking VFR400 is a microprocessor based multi-hazard releasing control panel for use on preaction, deluge, Surefire and Firecycle multicycle sprinkler systems, MX-1230 Fire
instalert 2 units to cover any application instalert 18 (ia18): 18 x 28 full matrix instalert 24: (ia24): 24 x 60 full matrix Size, Weight without battery ia18: 30 x 20 x 2.74, 29 lbs ia24: Folds to fits
Installing the RDSP-3000A-NIST Master Clock. Ethernet Connect the RJ-45 connector to a TCP/IP network. Equipment The following equipment comes with the clock system: RDSP-3000A-NIST Master Clock Module.
DEVICES COVERED IN THIS DOCUMENT: 4940 Alarm Kit (ALT, ALM, ALL) 2-649-0168 Latch Monitor Switch 2-649-1090 Tamper Switch OVERVIEW Page 1 of 8 ALARM KIT INSTALLATION STEP ONE Disassemble device if it was
GETTING STARTED CHAPTER 1 In This Chapter... Manual Overview.........................1 2 SOLO Temperature Controller Introduction......1 3 SOLO Temperature Controller Specifications.....1 5 Manual Overview
Process & TEMPERATURE LIMIT Controllers NOVA PD57 Series Thermocouple, RTD, & Process Input Universal Power Supply 124 VAC Latching Relay High or Low Limit Control 1 Latching Relay & 1 Alarm Relay Retransmitting
Troubleshooting and Diagnostics The troubleshooting and diagnostics guide provides instructions to assist in tracking down the source of many basic controller installation problems. If there is a problem
EQUIPMENT SPECIFICATIONS IC-1600 Intelligent Controller The IC-1600 Intelligent Controller is a fully intelligent panel that has a complete database on board. It operates in conjunction with the Access
Square D Clipsal DIN-Rail Four-Channel Auxiliary Input Unit SLCLE5504AUX for Use with Wired C-Bus Networks Instruction Bulletin Retain for future use. Square D Clipsal DIN-Rail Four-Channel Auxiliary Input
General Purpose IO for Integrators -1- TABLE OF CONTENTS Table of Contents Technical Data 3 Standard Operation 4 Inputs 4 Outputs 4 Analog Output Calibration 4 Bandrate 4 Master Timer Clock Function for
MODEL NUMBER: ISC910-1-0-GB-XX ISC911-5-0-GB-XX IXP20 CONTROLLER SPECIFICATIONS Working Environment Plastic Housing... Power ImproX IXP20 Controller INSTALLATION MANUAL Designed to work in an indoor (dry)
ENV909 kwh Meter Modbus Metering System 1 Programming Meters fitted with the Modbus option have two additional stages in the front panel programming menu. Baud Rate Unique Modbus Address A V In programming
Model 201 Wiegand Touchpad Reader Installation Guide P/N 460353001C 15AUG11 2011 UTC Fire & Security. All rights reserved. This document may not be copied in whole or in part or otherwise reproduced without
Fire Fighter Phone System Installation Instructions Introduction This publication describes the installation procedure for the Fire Fighter s Phone on a 4100U or a 4100ES Fire Alarm Control Panel (FACP).
Master Catalog 125 Clocks Section C Product/Technical Bulletin C-7355 Issue Date 0895 C-7355 Digital Series 7-Day Time Clocks The C-7355 Digital Series 7-Day Time Clocks provide an economical control solution
026-1711 Rev 4 10-NOV-2010 E2 and Square D Smart Breaker Panel Installation and Operation Manual Retail Solutions 3240 Town Point Dr. NW Suite 100 Kennesaw, GA 30144 Phone: 770-425-2724 Fax: 770-425-9319
Remote Control Cut Off Switch NEFA20 Plus F1 Installation Guide Please read this entire guide before beginning the installation! Supplied Parts Antenna NEFA20 F1 Plus Cutoff Switch Protective Covers DIN
RI-215A Operator s Manual Part Number: 71-0045RK Revision 0 Released: 10/3/05 Warranty RKI Instruments, Inc., warrants gas alarm equipment sold by us to be free from defects in materials and workmanship,
to RS422/RS485 Isolated Universal Converter 1. Introduction The converts serial data from the standard to either RS422 or RS485. Features: Universal converter can be used with both and other manufacturer
RS232C < - > RS485 CONVERTER S MANUAL Model: LD15U INTRODUCTION Milestone s model LD-15U is a RS232 to RS 485 converter is designed for highspeed data transmission between computer system and or peripherals
Operation Wireless Monitoring System Models: PowerScan Wireless Monitor GM29535 GM29536 TP-6223 10/05a Product Identification Information Record the product identification information in the spaces below
AWM910 Owner s Manual COMPACT DISC PLAYER PUSH 1 2 3 4 5 6 RPT SCAN RDM H M PUSH PWR VOL ALARM SET ON/OFF EQ T/F AUD RADIO CD COMPACT MUSIC SYSTEM MUTE AUX BAND CD AUX IN A B A+B JENSEN AWM910 Thank You!
TCP/IP MODULE CA-ETHR-A INSTALLATION MANUAL w w w. c d v g r o u p. c o m CA-ETHR-A: TCP/IP Module Installation Manual Page Table of Contents Introduction...5 Hardware Components... 6 Technical Specifications...
2800 Series POS System Installation Guide Congratulations on your purchase of UTC RETAIL s innovative 2800 Series POS System! This fully integrated point-of-sale hardware solution, with its modular design
IS5025/5030/5035 Installation Guide Installing the Switch in the Rack Minimum and Maximum Rack Depth for these switches Make sure that the Installation kit you have is compatible with your rack. To use
Data Bulletin 1210DB0002R3/05 03/2005 LaVergne, TN, USA Communications Wiring for POWERLINK G3 Systems Class 1210 Retain for future use. ABOUT THIS BULLETIN This data bulletin describes the proper wiring
8400 Series Thermostats Safety & Installation Instructions READ AND SAVE THESE INSTRUCTIONS 61000652D 8400 Tstat Install.indd 1 Table of contents Installation Installation location recommendations... 3
Options for ABB drives, converters and inverters User s manual FDPI-02 diagnostics and panel interface Table of contents Table of contents 3 1. FDPI-02 diagnostics and panel interface Safety..............................................
Mega128-DEVelopment Board Progressive Resources LLC 4105 Vincennes Road Indianapolis, IN 46268 (317) 471-1577 (317) 471-1580 FAX http://www.prllc.com GENERAL The Mega128-Development board is designed for
USB-SSR08 Specifications Document Revision 1.2, February, 2010 Copyright 2010, Measurement Computing Corporation Typical for 25 C unless otherwise specified. Specifications in italic text are guaranteed
Installation and User Guide 458-UNI8 8-Channel Universal Dimmer Module Introduction The 458/UNI8 is an 8-channel universal, digital transistor, dimmer module. Each channel s mode can be selected for either
Sense +V Tx Rx LAN LINK Over ARCNET KBaud BACnet Rx BACnet Tx Archive Valid Port S Tx Port S Rx Low Battery Network- Enhanced Access Default MSTP PTP = Download Required on Rnet and Port S IP Address IP
Section TELEPHONE AUTOMATIC DIALER SYSTEM PART 1 GENERAL 1.01 SYSTEM DESCRIPTION A. Design Requirements: 1. Electronic monitoring system shall interface plant alarms to public telephone system or cellular
E90463 PB101556 The EGX100 serves as an Ethernet gateway for PowerLogic System devices and for any other communicating devices utilizing the Modbus protocol. The EGX100 gateway offers complete access to
Electronics Ltd Presenting Power, Intelligence... with a sense of feeling By Appointment to Her Majesty The Queen Supplier of Fire Detection Equipment Kentec Electronics Ltd. Dartford Plug in slots K772
Square D Clipsal Two-Channel DIN-Rail DALI Gateway SLC5502DAL for Use with C-Bus Wired Networks Instruction Bulletin Retain for future use. Square D Clipsal Two-Channel DIN-Rail DALI Gateway 63249-420-226A1
Troubleshooting Tips Lifestyle SA-2 & SA-3 Amplifier Refer to the Lifestyle SA-2 & SA-3 Amplifier service manuals, part number 271720 for schematics, PCB layouts and parts lists. Preventative Repair Measures
1 VIDI + System Controller for OPUS DC Power Systems Product description VIDI is the advanced monitoring and control device for OPUS DC Power Systems. It delivers intelligence, an easy user interface and
Back-UPS Pro 1300/1500 Installation and Operation Inventory Safety Do not install the Back-UPS in direct sunlight, in excessive heat, humidity, or in contact with fluids. Connect the battery bu059a bu058a
Instruction Bulletin EAV85226 08/2014 Wiser Panel Meter, Model Number WISERCTPM200 Installer s Guide Retain for future use. Product Description Kit Contents The Wiser Panel Meter is for use in energy management
Communicate and view data from meters with one simple device PowerLogic EGX300 integrated gateway-server Web Monitoring Communications Plug and Play Plug into your energy usage with a simple mouse click