# Lambda Tuning the Universal Method for PID Controllers in Process Control

Save this PDF as:

Size: px
Start display at page:

Download "Lambda Tuning the Universal Method for PID Controllers in Process Control"

## Transcription

1 Lambda Tuning the Universal Method for PID Controllers in Process Control Lambda tuning gives non-oscillatory response with the response time (Lambda) required by the plant. Seven industrial examples show the relevance and simplicity of this method. Will Lambda tuning work in your process control loop? by Mark T. Coughran PID Proportional+Integral+Derivative--is by far the most common feedback control algorithm in the process industries. Many control engineers are asked to choose the P, I, and D controller tuning parameters. Often we are faced with one or more of these six common challenges: Process Challenge Requirement Lambda (λ) Tuning Solution Oscillation with as-found tuning First-order setpoint response or critically Any λ >> T d damped load response Need minimum variability on PV Fast response of control loop; shift λ = 3*T d (minimum robust λ) variability to Output Surge vessel to absorb variability; need Slow response of liquid level control loop λ LEVEL as large as possible minimum variability on Output Cascade configuration Slave loop must respond faster than λ MASTER >> λ SLAVE master loop Physically coupled or interacting Uncouple the loop dynamics λ LOOP B >> λ LOOP A processes Multiple streams into blending vessel All inflows respond at same speed to inventory control λ FLOW A = λ FLOW B = λ FLOW N Given these challenges, what is a systematic and practical way to find the optimal parameters? Don t confuse yourself with arcane statistics; use your knowledge of the plant. Start with the purpose of the loop, possible interactions with other loops, and the ability of the process to respond to the controller (the process dynamics). For example, there are practically no control loops in the process industries whose purpose is to oscillate. To comply with the production objectives of the plant, and to prevent interactions between loops, most loops need to respond in a certain amount of time. Learning which loops need to be fast and which need to be slow will make your tuning efforts more valuable to the plant. Finally, the process dynamics (MANUAL response) will limit how fast you can make the closed loop (AUTO) response. Load Set Point (SP) + - Σ Controller Output Process Process Value (PV) Figure 1. Basic feedback control loop.

2 Lambda tuning has proven successful in thousands of control loops covering the following process control applications: feedback control loops (Figure 1) in continuous and batch processes. PID controllers of all types--dcs, PLC, single-loop, pneumatic--from all manufacturers. physical processes including flow, pressure (liquids and gases), level (liquids and solids), temperature (heat exchange, mixing, reaction), and composition (density, ph, stack O 2, dissolved oxygen, etc.). process industries including chemicals, refining, oil & gas, power, life sciences, pulp & paper, metals & mining, and pipeline. the environments of brownfield plant optimization, greenfield plant startup, design and simulation of control systems, and education. Lambda Tuning Concepts Lambda tuning is a model-based method related to Internal Model Control and Model Predictive Control. The math behind it uses pole-zero cancellation to achieve the desired closed loop response. However, to apply the method you need only simple arithmetic--as in Figure 2--if your process dynamics fit any of the following models: a) First Order b) Integrator c) Integrator, First Order Lag d) Integrator, First Order Lead e) Integrator, Non-Minimum Phase f) Second Order, Overdamped g) Second Order, Underdamped h) Second Order, Lead i) Second Order, Lead with Overshoot j) Second Order, Non-Minimum-Phase Each process model includes dead time. Types a) and f) j) are self-regulating; that is, for an output step, the PV eventually settles at a new value. The process dynamics model is typically identified from step testing in MANUAL mode (open loop). Step tests also help to identify the nonlinearities in the process response, such as dead band in control valves, which may be a greater problem than the as-found controller tuning. We assume the controller block in Figure 1 contains a PID algorithm. The process block includes the final control element or slave loop, the process to be controlled (chemistry, hydraulics, thermal energy, etc.) and the sensor/transmitter. Lambda tuning gives a non-oscillatory response to setpoint changes and load disturbances. You choose the response time (Lambda or λ) to fit the control strategy and the unit production objectives. Most of the processes in your plant will fit either the first order model or the integrator model.

3 a) First-Order Process Dynamics: if the process has the following self-regulating open loop response b) Integrator Process Dynamics: if the process has the following integrating open loop response then we define Lambda (λ) as the closed loop time constant after a setpoint step. Time constant has the familiar meaning of the time to reach 63% of the final value. For simplicity, we show here the closed loop response with negligible dead time: then we define a critically damped load response with Lambda (λ) equal to the arrest time. For simplicity, we show here the closed loop response with negligible dead time: To accomplish this in the PID controller, we set Proportional Gain = To accomplish this in the PID controller, we set Proportional Gain Integral Time = τ Integral Time = 2λ+T d Derivative Time = 0 (none) Derivative Time = 0 (none) Figure 2. Lambda tuning method for the two simplest and most common process responses. The process response, in particular the dead time T d, limits how small you can make λ. For further explanation of the math, see the References. The process models shown in Figure 2 are built into some control system tuning tools. The ideal tool would include process model identification, the arithmetic for Lambda tuning, recommendations for choice of Lambda, and predicted setpoint and load responses.

4 Process Plant Examples Let s look at several examples from process plants. In each example, Lambda has a clear physical meaning. We begin with self-regulating process dynamics. Figure 3 shows a typical result for flow loops. Figure 3. Closed loop flow rate control of Natural Gas Liquids through a control valve into a depropanizer column. The PID controller executes in a DCS. The process model is self-regulating first order plus dead time. The dead time (occurring both in open loop and closed loop) is mostly due to nonlinearity in the response of the control valve. Robustness of the controller tuning takes into account that the process dynamics (process gain, dead time, and time constant) may change considerably at other process conditions. For robustness it is wise to choose Lambda equal to a generous multiple of the dead time. Note we chose λ=3*t d in the above case. Figure 4. Pressure control of lubricating oil pumped from a reservoir to the propylene compressor of an olefins unit. Maintaining the oil pressure is critical to operation of the unit. The pressure is controlled by routing part of the flow back to the reservoir through a bypass control valve. The PID executes in a pneumatic controller, where the oil is connected directly to the controller sensing element and the output (3-15 psig) goes to a pneumatic positioner on the bypass valve. This example shows that we can make the closed loop response very fast if the open loop process response is fast and the plant requires fast loop response. Note however that our choice of Lambda was again no smaller than 3*T d.

5 Integrating processes are often critical to the performance and profitability of the plant. For integrating processes, it is difficult to guess a combination of Proportional and Integral settings that will not cause oscillation. A systematic tuning method is needed to obtain both stability and performance. The first integrating process example is a level controller with no slave flow loop. Figure 5. Level control in an oilfield produced water treatment tank. The PID executes in a PLC with output going to a variable speed pump on the inflow piping. The outflow is controlled by a separate pump which establishes the load on the level loop. The process model is integrator. The as-found tuning caused large oscillations in AUTO, so the operator kept the level controller in MANUAL. For the data shown here with Lambda tuning, the level PV initially is returning to SP after a load disturbance; hence inflow slightly greater than outflow. Then a step occurs on the load flow (outflow); note the inflow responds with a smooth increase. The arrest time or Lambda is the time for the PV to reach maximum deviation and begin returning to SP. After reaching steady state, there will be no oscillation. We chose Lambda = 240 to keep the level PV away from the alarm limits for large disturbances. For applications where tight level control is needed, a smaller Lambda value can be chosen. In boiler drum level control, for example, the PV alarms are quite close to SP. The next integrating process example is from a different process industry and a much smaller vessel.

6 Figure 6. Dissolved Oxygen (DO) control in a 2-liter bioreactor. The PV is measured as % saturation of the solution. Output of the DO controller goes to a slave flow loop that sparges oxygen (O 2 ) into the bioreactor and is tuned for Lambda = 20 seconds. CO 2 flows into the reactor to control the ph; however, it also tends to displace the O 2, making CO 2 the load variable. The process model (measured in MANUAL) is integrator. The PID controller executes in a DCS. The chosen Lambda will maintain the DO adequately close to SP as the culture evolves--and the oxygen demand varies--in this batch application. It also complies with the cascade rule, λ MASTER >> λ SLAVE. So far, for integrating processes, we have only examined the load response. If the controller is any of the default standard PID types, if integral action is used in the controller, and if the process integrates, then a setpoint step will cause an overshoot with any tuning method. Figure 7. Reactor pressure control in the gasoline hydrotreater unit of a refinery. The PID controller executes in a DCS with standard structure, and output goes to a control valve on the outlet of the reactor. The process model (measured in MANUAL mode) is integrator.

8 The examples with cascade control pointed out the need to prevent interaction between the master and slave loops. Lambda tuning is the only method that provides explicitly for this requirement; we simply choose λ MASTER >> λ SLAVE. Another common type of physical interaction that needs loop decoupling involves multiple control valves piped in series. For example, a chemical plant had process water with a pressure letdown from 2500 to 600 psig, a second letdown from 600 to 150 psig, followed by a flow loop. To get all the loops in AUTO with good system performance, we chose the respective Lambda values at 6 seconds, 30 seconds, and 80 seconds. Summary We have illustrated Lambda tuning in several different process plants with various types of PID controllers and various control objectives. In each case, we achieved a smooth response with the appropriate response time (Lambda or λ) ranging from 0.6 to 3000 seconds. The method accounts for the ability of the process to respond to the controller (process dynamics), the purpose of the loop, and interactions with other loops. To our initial question, Will Lambda tuning work in your process control loop?, you should now be able to answer yes. The most important user requirement is to choose the response time λ according to the unit objectives and the process constraints. The math is simple; training and tools are available. But if you want an oscillatory response or an arbitrary response time, you will need to find a different method. References W. L. Bialkowski, page 1235 in The Control Handbook, edited by W. S. Levine, CRC Press and IEEE Press, W. L. Bialkowski, page in Process/Industrial Instruments and Controls, 5 th edition, edited by G.K. McMillan, McGraw-Hill, B. Janvier & W.L. Bialkowski, Lambda Tuning The How and Why, PAPTAC 91 st Annual Meeting, Emerson Educational Services Courses 9030 and 9032, US/brands/edservices/plantoptimization/processcontrol/Pages/9032.aspx. Mark T. Coughran is a senior process control consultant with Emerson Process Management.

### Best Practices for Controller Tuning

Best Practices for Controller Tuning George Buckbee, P.E. ExperTune, Inc. 2009 ExperTune, Inc. Page 1 Best Practices for Controller Tuning George Buckbee, P.E., ExperTune Inc. 2009 ExperTune Inc Summary

### Enhancing Process Control Education with the Control Station Training Simulator

Enhancing Process Control Education with the Control Station Training Simulator DOUG COOPER, DANIELLE DOUGHERTY Department of Chemical Engineering, 191 Auditorium Road, Room 204, U-222, University of Connecticut,

### Sensing and Control. A Process Control Primer

Sensing and Control A Process Control Primer Copyright, Notices, and Trademarks Printed in U.S.A. Copyright 2000 by Honeywell Revision 1 July 2000 While this information is presented in good faith and

### HC900 Boiler Control. Background. Solution. Application Brief Industry: Manufacturing

HC900 Boiler Control Application Brief Industry: Manufacturing Background Until recent years, only the largest boilers could justify sophisticated boiler controls. Now high fuel costs and occasional limited

### Instrumentation and Process Control. Boiler Control. Courseware Sample 85993-F0

Instrumentation and Process Control Boiler Control Courseware Sample 85993-F0 A INSTRUMENTATION AND PROCESS CONTROL BOILER CONTROL Courseware Sample by the staff of Lab-Volt Ltd. Copyright 2010 Lab-Volt

### PID Tuning Guide. A Best-Practices Approach to Understanding and Tuning PID Controllers. First Edition by Robert C. Rice, PhD

PID Tuning Guide A Best-Practices Approach to Understanding and Tuning PID Controllers First Edition by Robert C. Rice, PhD Technical Contributions from: Also Introducing: Table of Contents 2 Forward 3

### Introduction. Chapter 1. 1.1 The Motivation

Chapter 1 Introduction 1.1 The Motivation Hydroelectric power plants, like real systems, have nonlinear behaviour. In order to design turbine controllers, it was normal practice in the past, when computer

### Performance Monitor Improves Performance of FCC At a Refiner in Anacortes, WA

Performance Monitor Improves Performance of FCC At a Refiner in Anacortes, WA By Tom Kinney, ExperTune Inc. www.expertune.com ABSTRACT The benefit of model predictive control or MPC can only be achieved

### HC900 for Boiler Control Applications

HC900 for Boiler Control Applications Background Until recent years, only the largest boilers could justify sophisticated boiler controls. Now high fuel costs make it necessary to improve boiler efficiency

### FAST METHODS FOR SLOW LOOPS: TUNE YOUR TEMPERATURE CONTROLS IN 15 MINUTES

FAST METHODS FOR SLOW LOOPS: TUNE YOUR TEMPERATURE CONTROLS IN 15 MINUTES Michel Ruel P.E. President, TOP Control Inc 4734 Sonseeahray Drive 49, Bel-Air St, #103 Hubertus, WI 53033 Levis Qc G6W 6K9 USA

### EECE 460 : Control System Design

EECE 460 : Control System Design PID Controller Design and Tuning Guy A. Dumont UBC EECE January 2012 Guy A. Dumont (UBC EECE) EECE 460 PID Tuning January 2012 1 / 37 Contents 1 Introduction 2 Control

### Reliability Modeling Software Defined

Reliability Modeling Software Defined Using Titan Reliability Modeling Software May 30, 2014 Prepared by: The Fidelis Group 122 West Way, Suite 300 Lake Jackson, TX 77566 Fidelis Group, LLC All Rights

### Control of an industrial process using PID control blocks in automation controller

Control of an industrial process using PID control blocks in automation controller by Michel Van Dessel 1 1 Abstract Many continuous industrial processes can be controlled using programmable automation

### Plant Wide Performance Monitor Bridges Resource Gap

Plant Wide Performance Monitor Bridges Resource Gap Presented at ISA2003, Houston, TX October, 2003 Tom Kinney ExperTune Inc. Hubertus, WI www.expertune.com Copyright 2003 Instrumentation, Systems and

### Jump Start: Aspen HYSYS Dynamics V7.3

A Brief Tutorial (and supplement to training and online documentation) Glenn Dissinger, Product Director, Aspen Technology, Inc. Julie Levine, Associate Product Marketing Professional, Aspen Technology,

### Using Wireless Measurements in Control Applications

Using Wireless Measurements in Control Applications Terry Blevins, Mark Nixon, Marty Zielinski Emerson Process Management Keywords: PID Control, Industrial Control, Wireless Transmitters ABSTRACT Wireless

### Modelling and Simulation of the Freezing Systems and Heat Pumps Using Unisim Design

Modelling and Simulation of the Freezing Systems and Heat Pumps Using Unisim Design C. Patrascioiu Abstract The paper describes the modeling and simulation of the heat pumps domain processes. The main

### JD Edwards EnterpriseOne Bulk Stock Industry & Overview

JD Edwards EnterpriseOne Bulk Stock Industry & Overview 2 The following is intended to outline our general product direction. It is intended for information purposes only, and may

### Tips for burner modulation, air/fuel cross-limiting, excess-air regulation, oxygen trim and total heat control

Boiler control Tips for burner modulation, air/fuel cross-limiting, excess-air regulation, oxygen trim and total heat control Boilers are often the principal steam or hot-water generators in industrial

### Control Device Requirements Charts For Oil and Gas Handling and Production Facilities

Device Charts For Oil and Gas Handling and Production Facilities Purpose/Scope: The purpose of this document is to provide standardized guidance for use by the regulated community and air permit reviewers,

### ISA108 Intelligent Device Management (IDM)

ISA108 Intelligent Device Management (IDM) Intelligent Digital Devices - Have Self-Diagnostics and More Eight-channel two-wire temperature transmitter Intelligent two-wire on/off valve 2 Fully integrated

### Current Loop Tuning Procedure. Servo Drive Current Loop Tuning Procedure (intended for Analog input PWM output servo drives) General Procedure AN-015

Servo Drive Current Loop Tuning Procedure (intended for Analog input PWM output servo drives) The standard tuning values used in ADVANCED Motion Controls drives are conservative and work well in over 90%

### Refinery Planning & Scheduling - Plan the Act. Act the Plan.

Refinery Planning & Scheduling - Plan the Act. Act the Plan. By Sowmya Santhanam EXECUTIVE SUMMARY Due to the record high and fluctuating crude prices, refineries are under extreme pressure to cut down

### HEAT RECOVERY OPTIONS FOR DRYERS AND OXIDIZERS

HEAT RECOVERY OPTIONS FOR DRYERS AND OXIDIZERS William K. Scullion, Application Engineering Leader, MEGTEC Systems, De Pere, WI Introduction Competitive pressures continuously motivate us to examine our

### PSAC/SAIT Well Testing Training Program Learning Outcomes/Objectives Level B

s/objectives Level B CHEM 6014: Properties and Characteristics of Natural Gases Discuss the pertinent properties and uses of natural gases as they occur in gas processing. 1. Describe the physical properties

### IPB-IB ELECTRIC ACTUATORS FOR INDUSTRIAL PROCESS CONTROL INDUSTRIAL STEAM BOILERS. BECK VIDEO Scan w/ Smartphone

IPB-IB R ELECTRIC ACTUATORS FOR INDUSTRIAL PROCESS CONTROL INDUSTRIAL STEAM BOILERS BECK VIDEO Scan w/ Smartphone 1 Increasing Business Pressures Necessitate Boiler Control Improvements Today s industrial

### Controller Design using the Maple Professional Math Toolbox for LabVIEW

Controller Design using the Maple Professional Math Toolbox for LabVIEW This application demonstrates how you can use the Maple Professional Math Toolbox for LabVIEW to design and tune a Proportional-Integral-Derivative

### PIDControlfor the future

PIDControlfor the future Haruo TAKATSU Yokogawa Electric Corporation! 1! Agenda! 2! Discussion Items 1. Will PID control continue to be used in the future? Market Survey in Japan 2. When and why is derivative

### ARCHITECTURE OF INDUSTRIAL AUTOMATION SYSTEMS

ARCHITECTURE OF INDUSTRIAL AUTOMATION SYSTEMS Abdu Idris Omer Taleb M.M., PhD Majmaah University, Kingdom of Saudia Arabia Abstract This article is aimed to name the levels of industrial automation, describes

### FULL ELECTRICAL LNG PLANTS: HIGHEST AVAILABILITY AND ENERGY EFFICIENCY THROUGH OVERALL SYSTEM DESIGN

FULL ELECTRICAL LN PLANTS: HIHEST AVAILABILITY AND ENERY EFFICIENCY THROUH OVERALL SYSTEM DESIN Dr. Edwin Lerch Siemens A Infrastructure and Cities Sector, IC S SE PTI, ermany Phone: 49-9131-7-34052 Fax:

### Dynamic Models Towards Operator and Engineer Training: Virtual Environment

European Symposium on Computer Arded Aided Process Engineering 15 L. Puigjaner and A. Espuña (Editors) 2005 Elsevier Science B.V. All rights reserved. Dynamic Models Towards Operator and Engineer Training:

### Practical Process Control For Engineers and Technicians

Practical Process Control For Engineers and Technicians THIS BOOK WAS DEVELOPED BY IDC TECHNOLOGIES WHO ARE WE? IDC Technologies is internationally acknowledged as the premier provider of practical, technical

### INTRUSION PREVENTION AND EXPERT SYSTEMS

INTRUSION PREVENTION AND EXPERT SYSTEMS By Avi Chesla avic@v-secure.com Introduction Over the past few years, the market has developed new expectations from the security industry, especially from the intrusion

### Non Linear Control of a Distributed Solar Field

Non Linear Control of a Distributed Solar Field Rui Neves-Silva rns@fct.unl.pt Universidade Nova de Lisboa ACUREX Solar Field 2 Parabolic through collector 3 Solar plant scheme The action on the pump s

### Terry Blevins Principal Technologist Emerson Process Management Austin, TX

Terry Blevins Principal Technologist Emerson Process Management Austin, TX QUALITY CONTROL On-line Decision Support for Operations Personnel Product quality predictions Early process fault detection Embedded

### MODELBASED DIAGNOSTICS, MAINTENANCE ON DEMAND AND DECISION SUPPORT ON BOILERS

MODELBASED DIAGNOSTICS, MAINTENANCE ON DEMAND AND DECISION SUPPORT ON BOILERS Erik Dahlquist 1), Björn Widarsson 1) 2) and Anders Avelin 1) 1)Mälardalen University, Västerås, Sweden 2) Fjärrvärmebyrån

### Gas Detection for Refining. HA University

Gas Detection for Refining HA University Refinery Process and Detection Needs Refining i Crude Oil Final Products Coke Asphalt Waxes, Lubricating Oils and Greases Kerosene, Jet Fuel, Diesel Fuel, Home

### Monitoring and Control Tools for Implementing PAT

Supplement to Monitoring and Control Tools for Implementing PAT Terry Blevins and James Beall AUTHORS Innovations in process analysis and control offer significant opportunities for improving pharmaceutical

### Intelligent control system with integrated electronic expansion valves in an air-conditioning system operating at a Telecom telephone exchange

Intelligent control system with integrated electronic expansion valves in an air-conditioning system operating at a Telecom telephone exchange ING. TOMMASO FERRARESE Thermodynamics Laboratory Engineer

### Example. Fluid Power. Circuits

Example Fluid Power Circuits To Enhance Symbol Reading Skills To Work On Circuit Reading Skills With Answers HI LO Pump Circuit 18 A1 B1 17 16 15 13 Set 14 2,000 PSI PG2 Set 500 PSI 12 11 7 8 10 PG1 9

### INCREASING THE EFFICIENCY OF BOILER OPERATION BY CONTROLLING DRUM LEVEL WITH BFP SCOOP OPERATION

INCREASING THE EFFICIENCY OF BOILER OPERATION BY CONTROLLING DRUM LEVEL WITH BFP SCOOP OPERATION IN THREE ELEMENT MODE 1 Aditya Sindhu, 2 Aashish Bhaskar and 3 Avdesh Bhardawaj 1 Department of EEE, MAIT,

### Maximizing return on plant assets

Maximizing return on plant assets Manufacturers in nearly every process industry face the need to improve their return on large asset investments. Effectively managing assets, however, requires a wealth

ECSE 4440 Control System Engineering Fall 2001 Project 3 Controller Design in Frequency Domain TA 1. Abstract 2. Introduction 3. Controller design in Frequency domain 4. Experiment 5. Colclusion 1. Abstract

### Cooking at the Speed of light!

Cooking at the Infrared Cooking & Colouring Infrabaker is a modular infrared continuous cooking system developed by Infrabaker International. The machine is designed to cook and/or put colour on a wide

### IGEMA BOILER LEVEL & TDS CONTROLS

IGEMA BOILER LEVEL & TDS CONTROLS IGEMA offers boiler level and TDS control products of the highest quality standard, being certified to ISO 9001. Made in Germany, IGEMA products are manufactured in compliance

### Raffaele Rea GE-Bayer Specialties Srl - Termoli Paolo Belli, Nunzio Bonavita ABB PS&S SpA - Genova ABB - 1 -

Raffaele Rea GE-Bayer Specialties Srl - Termoli Paolo Belli, Nunzio Bonavita ABB PS&S SpA - Genova ABB - 1 - Agenda An Innovative Approach to Control Loop Performance Assessment Why Control Loop Condition

### Optimization of Natural Gas Processing Plants Including Business Aspects

Page 1 of 12 Optimization of Natural Gas Processing Plants Including Business Aspects KEITH A. BULLIN, Bryan Research & Engineering, Inc., Bryan, Texas KENNETH R. HALL, Texas A&M University, College Station,

### Achieving consistency in multisite installations of PlantTriage.

Achieving consistency in multisite installations of PlantTriage. Peter Thomas Control Specialists Ltd - UK Authorized Solution Provider for ExperTune Inc Benefits. Facilitates site-site comparisons. Creates

### C. starting positive displacement pumps with the discharge valve closed.

KNOWLEDGE: K1.04 [3.4/3.6] P78 The possibility of water hammer in a liquid system is minimized by... A. maintaining temperature above the saturation temperature. B. starting centrifugal pumps with the

### Perform Common Process Loop Control Algorithms

Perform Common Process Loop Control Algorithms Using the PIDE Instruction Introduction This white paper discusses how to use the features inherent in the Enhanced PIDE instruction in the RSLogix 5000 Function

### AMEC 6007: Linear Velocity and Acceleration Learning Outcome. CHEM 6012: Oil and Gas Compositions and Sales Specifications Learning Outcome

s/objectives Level F ADMN 6044: Post Job Management It is important to know the proper procedures for closing out a job so that rigging and equipment is maintained for future use and personnel are adequately

### EUROTHERM MASTER COMMUNICATIONS 5000 Series with Master Communications for unsurpassed access to process data everywhere

EUROTHERM MASTER COMMUNICATIONS 5000 Series with Master Communications for unsurpassed access to process data everywhere CONNECTIONS MADE EASY The 5180V, 5100V and 5000B now all support Modbus Master Communications

### Microcontroller-based experiments for a control systems course in electrical engineering technology

Microcontroller-based experiments for a control systems course in electrical engineering technology Albert Lozano-Nieto Penn State University, Wilkes-Barre Campus, Lehman, PA, USA E-mail: AXL17@psu.edu

### How does solar air conditioning work?

How does solar air conditioning work? In a conventional air conditioning system; The working fluid arrives at the compressor as a cool, low-pressure gas. The compressor is powered by electricity to squeeze

### Industrial IT Process Data Management. Advanced IT Tools for Building Information Systems in the Process Industry

Industrial IT Process Data Management Advanced IT Tools for Building Information Systems in the Process Industry Solutions Meeting Challenging Industrial Requirements Based on Extensive Experience Process

### Uniformance Asset Sentinel. Advanced Solutions. A real-time sentinel for continuous process performance monitoring and equipment health surveillance

Uniformance Asset Sentinel Advanced Solutions A real-time sentinel for continuous process performance monitoring and equipment health surveillance What is Uniformance Asset Sentinel? Honeywell s Uniformance

### VALIDATION, MODELING, AND SCALE-UP OF CHEMICAL LOOPING COMBUSTION WITH OXYGEN UNCOUPLING

VALIDATION, MODELING, AND SCALE-UP OF CHEMICAL LOOPING COMBUSTION WITH OXYGEN UNCOUPLING A research program funded by the University of Wyoming School of Energy Resources Executive Summary Principal Investigator:

### Heat Trace Fundamentals. Monte Vander Velde, P.E. President, Interstates Instrumentation

Heat Trace Fundamentals Monte Vander Velde, P.E. President, Interstates Instrumentation Contents Introduction... 3 Purpose of Heat Trace... 3 Types of Heat Trace... 4 Steam Trace vs. Electric Trace...

### Terminology and Symbols in Control Engineering

Technical Information Terminology and Symbols in Control Engineering 1 Part 1 Fundamentals Technical Information Part 1: Fundamentals Part 2: Self-operated Regulators Part 3: Control Valves Part 4: Communication

### MANAGING ASSETS USING PERFORMANCE SUPERVISION

MANAGING ASSETS USING PERFORMANCE SUPERVISION Michel Ruel P.E. President, Top Control Inc. mruel@topcontrol.com 49, Bel-Air, suite 103 Lévis, Qc G6V 6K9 Canada ABSTRACT In today s highly competitive worldwide

### Fuel Treatment and Conditioning Systems

RULES FOR CLASSIFICATION OF Ships PART 6 CHAPTER 14 NEWBUILDINGS SPECIAL EQUIPMENT AND SYSTEMS ADDITIONAL CLASS Fuel Treatment and Conditioning Systems JULY 2006 This chapter has been amended since the

### Industry Solution. Integrated Upstream Asset Management

Industry Solution Integrated Upstream Asset Industry Solution > Integrated Upstream Asset The vibrant upstream oil and gas industry is investing large amounts of capital in the pursuit of new reserves/resource

### TwinCAT NC Configuration

TwinCAT NC Configuration NC Tasks The NC-System (Numeric Control) has 2 tasks 1 is the SVB task and the SAF task. The SVB task is the setpoint generator and generates the velocity and position control

### Boiler Efficiency. Charles Stark Department of Poultry Science. charles_stark@ncsu.edu

Reducing Energy Cost Through Boiler Efficiency Charles Stark Department of Poultry Science North Carolina State University charles_stark@ncsu.edu Use of trade names in this publication does not imply endorsement

### USER-INITIATED NOTIFICATION: A CONCEPT FOR AIDING THE MONITORING ACTIVITIES OF PROCESS CONTROL OPERATORS

USER-INITIATED NOTIFICATION: A CONCEPT FOR AIDING THE MONITORING ACTIVITIES OF PROCESS CONTROL OPERATORS Stephanie Guerlain and Peter Bullemer Honeywell Technology Center Minneapolis, MN Monitoring activities

### Energy Efficient Operations and Maintenance Strategies for Boilers

Energy Efficient Operations and Maintenance Strategies for Boilers Large, complex and widely used, industrial boilers are major consumers of fuel. Proper operations and maintenance (O&M) procedures must

### Temperature Transmitter TTX300

coo Interface Description COM/TTX300/FF-EN Temperature Transmitter TTX300 FOUNDATION Fieldbus Contents Blinder Text Temperature Transmitter TTX300 Interface Description COM/TTX300/FF-EN 01.2010 Manufacturer:

### LECTURE 28 to 29 ACCUMULATORS FREQUENTLY ASKED QUESTIONS

LECTURE 28 to 29 ACCUMULATORS FREQUENTLY ASKED QUESTIONS 1. Define an accumulator and explain its function A hydraulic accumulator is a device that stores the potential energy of an incompressible fluid

### Engineering Recommendation on: Accumulators Revised 6-17-99 Issued January 10, 1979 Page 1 of 7

Issued January 10, 1979 Page 1 of 7 Accumulators have long been recognized by the industry as an effective means of maintaining good system balance by storing excess refrigerant as the condenser or evaporator

### Fundamentals of Mass Flow Control

Fundamentals of Mass Flow Control Critical Terminology and Operation Principles for Gas and Liquid MFCs A mass flow controller (MFC) is a closed-loop device that sets, measures, and controls the flow of

### How is Dew Point Measured Reliably?

How is Dew Point Measured Reliably? Air compression increases vapor pressure and thus dew point. = water vapor Vapor pressure Frost point Saturation - 0 C + Dew point Monitoring with alarming and real

### Continuous flow direct water heating for potable hot water

Continuous flow direct water heating for potable hot water An independently produced White Paper for Rinnai UK 2013 www.rinnaiuk.com In the 35 years since direct hot water systems entered the UK commercial

### Technical Information POWER PLANT CONTROLLER

Technical Information POWER PLANT CONTROLLER Content The Power Plant Controller offers intelligent and flexible solutions for the control of all PV power plants in the megawatt range. It is suitable for

### Energy Efficiency in Steam Systems

Energy Efficiency in Steam Systems Fundamentals of Energy Efficiency: An Introductory Workshop April 2008 John S. Raschko, Ph.D. Mass. Office of Technical Assistance www.mass.gov/envir/ota (617) 626-1093

### Laundry Hot Water Systems

TECHNICAL BULLETIN HE-2020 Laundry Hot Water Systems Commercial/Institutional Applications using Helitherm Heat Exchangers AERCO INTERNATIONAL, INC. 159 PARIS AVE., NORTHVALE, NJ 07647 (201) 768-2400 FAX

### This is a Master s degree level apprenticeship which includes academic learning combined workplace learning and training.

Power Engineer Degree Apprenticeship The UK s energy sector is integral to the prosperity and stability of the UK economy as a whole, delivering an absolutely fundamental service for all its citizens.

### Boiler Control Solution. Boiler Control Solution. Instruments and Solution for Automatic Boiler Control LF3BUSS02-00EN. www.yokogawa.

Boiler Control Boiler Control Instruments and for Automatic Boiler Control LF3BUSS02-00EN www.yokogawa.com Best for Automatic Boiler C Sensors and controllers for the efficiency and environmental performance

### Basics electronic speed Governor

Basics electronic speed Governor 1 MAN B&W Diesel Aktiengesellschaft, Augsburg Why do we need Governors? Power sources must be controlled to be converted to useful work. Uncontrolled prime movers, not

### The Piping System Model a New Life Cycle Document. Elements of the Piping System Model

Piping System Model as a Life Cycle Document White Paper Introduction When designing piping systems, a variety of documents are created providing the details necessary to design, purchase, build, and test

### Liquids Pipeline Leak Detection and Simulation Training

Liquids Pipeline Leak Detection and Simulation Training April 2010 / White paper Make the most of your energy Summary Executive summary... p 1 Introduction... p 2 CPM methods for pipeline leak detection...

### HYDRAULIC ACCUMULATOR. Energy buffering applications APPLICATIONS OSP 035. Applications with short term high quantity oil requirements

HYDRAULIC ACCUMULATOR APPLICATIONS OSP 035 Energy buffering applications Energy saving - the capacity of buffering energy is one of the main features of OLAER hydraulic accumulators. Hydraulic installations

### SIMULATION AND CONTROL OF BATCH REACTORS

THESES OF THE PhD DISSERTATION SIMULATION AND CONTROL OF BATCH REACTORS dr. Lajos Nagy Supervisor: dr. Ferenc Szeifert CSc, associate professor University of Veszprém Department of Process Engineering

### V. ENERGY SAVINGS IN INDUSTRY

V. ENERGY SAVINGS IN INDUSTRY A. Energy Use in Industry Industry is the major user of energy in modern society, accounting for roughly 40% of final energy use. Coal or oil are heavily used, especially

### Pressurized Water Reactor B&W Technology Crosstraining Course Manual. Chapter 9.0. Integrated Control System

Pressurized Water Reactor B&W Technology Crosstraining Course Manual Chapter 9.0 Integrated Control System TABLE OF CONTENTS 9.0 INTEGRATED CONTROL SYSTEM... 1 9.1 Introduction... 1 9.2 General Description...

### General Electric Systems Technology Manual. Chapter 2.8. Reactor Water Cleanup System

General Electric Systems Technology Manual Chapter 2.8 Reactor Water Cleanup System TABLE OF CONTENTS 2.8 REACTOR CLEANUP SYSTEM... 1 2.8.1 Introduction... 2 2.8.2 System Description... 2 2.8.3 Component

### Harmonics and Noise in Photovoltaic (PV) Inverter and the Mitigation Strategies

Soonwook Hong, Ph. D. Michael Zuercher Martinson Harmonics and Noise in Photovoltaic (PV) Inverter and the Mitigation Strategies 1. Introduction PV inverters use semiconductor devices to transform the

GE Mine Performance powered by Predix Increase throughput and availability If you re like most mining companies, you need to improve both your processes and your equipment availability to optimize throughput

### MOBILE ROBOT TRACKING OF PRE-PLANNED PATHS. Department of Computer Science, York University, Heslington, York, Y010 5DD, UK (email:nep@cs.york.ac.

MOBILE ROBOT TRACKING OF PRE-PLANNED PATHS N. E. Pears Department of Computer Science, York University, Heslington, York, Y010 5DD, UK (email:nep@cs.york.ac.uk) 1 Abstract A method of mobile robot steering

### UOP Career Development. Career development program for mechanical and civil engineers

UOP Career Development Career development program for mechanical and civil engineers MAKING OUR WORLD SAFER AND MORE SECURE, MORE COMFORTABLE AND ENERGY EFFICIENT, AND MORE INNOVATIVE AND PRODUCTIVE Our

### Chromatograph Maintenance and Troubleshooting Class # 5050

Chromatograph Maintenance and Troubleshooting Class # 5050 Shane Hale Business Development Manager Emerson Process Management Gas Chromatographs Division 5650 Brittmoore Drive Houston, TX 77041 USA Introduction

### CHAPTER 1: GENERAL APPLICABILITY

CHAPTER 1: GENERAL APPLICABILITY 1.1 INTRODUCTION The purpose of this chapter is to help you determine if you are subject to Part 68, the risk management program rule. Part 68 covers you if you are: The

### Control Valve Training Course Program

Control Valve Training Course Program LEARNINGPATH LEARNINGPATH Vocational training covers the basics and fundamentals but if the plant personnel do receive hands on experience with the measurement products

### ENERGY TRANSFER SYSTEMS AND THEIR DYNAMIC ANALYSIS

ENERGY TRANSFER SYSTEMS AND THEIR DYNAMIC ANALYSIS Many mechanical energy systems are devoted to transfer of energy between two points: the source or prime mover (input) and the load (output). For chemical

### Tadahiro Yasuda. Introduction. Overview of Criterion D200. Feature Article

F e a t u r e A r t i c l e Feature Article Development of a High Accuracy, Fast Response Mass Flow Module Utilizing Pressure Measurement with a Laminar Flow Element (Resistive Element) Criterion D200

### PID Control. Chapter 10

Chapter PID Control Based on a survey of over eleven thousand controllers in the refining, chemicals and pulp and paper industries, 97% of regulatory controllers utilize PID feedback. Desborough Honeywell,

### On-Site Risk Management Audit Checklist for Program Level 3 Process

On-Site Risk Management Audit Checklist for Program Level 3 Process Auditor name: Date: I. Facility Information: Facility name: Facility location: County: Contact name: RMP Facility I.D. Phone Number:

### globe reactions made easy Process perfection

globe reactions made easy Process perfection Benefits More reactions in less time: The Globe oil drain unit and quick clamp allow single hand vessel changes in seconds Space saving: 50ml, 100ml, 250ml,