1 Zen House A Case Study on Design, Construction and Cost/benefit Analysis of a High Performance Home Presentation for Net Zero Networking & Exchange CHBA Net Zero Energy Housing Council May 13, 2015 Ottawa by: Arthur LO Insightful Healthy Homes Inc.
2 Design A tailored-designed and custom-built 2 ½ storeys single family home -finished floor area 3942 sq. ft. plus 740 sq. ft. heated crawl space House owners requirements: highest energy performance possible with a healthy and comfortable living environment, and is albeit built on the cost within their budget limit. economically viable but practical interior finishings, home appliances, and lighting and plumbing fixtures. Large room in their dream home which would be used for occasional meditation gatherings the exterior look of the house should reflect their religious beliefs.
3 Curb Appeal The house is designed for ZEN style: The aesthetic appeal of the house demonstrates the ideals and insights of ZEN -balance, stability, tranquility, and nature. symmetrical front of the house represents balance. lower-and upper-storeysare proportioned to achieve stability Clear and simple exterior finishes show tranquility Natural stone steps on front stairs and two round columns in solid wood at the porch highlight the natural theme. Feature rocks on white gravel on both sides of front stair emphasize the ZEN style.
4 Design for Energy Efficiency Day-lighting South facing clerestory windows near top of family room in upper floor bring in day lighting to the central part of upper floor Sun light through the clerestory windows shines on the white walls and reflects through the lower windows on the upper floor into the Great Room, bringing daylight to main floor
5 Natural ventilation In shoulder seasons, outdoor air temperature provide the occupants with thermal comfort solely by natural ventilation through the house. The south-facing windows in the Great Room on main floor, the windows in the Family Room on upper floor, and the motorized window at top of the stairs will facilitate free air flow to enhance natural ventilation. This natural ventilation is activated by opening the motorized window at top of the stair (the highest operable window in the house) by use of a remote
6 Building Envelope and Systems Foundation: 3 TYPE 2 EPS RIGID INSULATION BOARD SA WATERPROOFING MEMBRANE (AB) 6 CONCRETE IN INSULATED CONCRETE FORM, ICF ½ DRYWALL LOW-PERMEANCE LOW-VOC WATER-BASED PAINT, <30 ng/(pa.s.m^2) (VB) EFFECTIVE R-VALUE = 30.5
7 Base Slab FLOOR FINISHING 4 THICK CONCRETE SLAB SEALED 6 mil POLY (AB & VB) 3 TYPE 2 EPS RIGID INSULATION BOARD MIN. 4 GRAVEL COMPACTED SOIL BASE EFFECTIVE R-VALUE = 12.0
8 Wall assembly: ¾ lstucco ¾ AIR SPACE 1X3 TREATED STRAPPING 2 R8 ROXUL COMFORT BOARD AIR-TIGHT TYVEK HOUSE WRAP (AB) ½ PLYWOOD WALL SHEATHING 2X6 O.C. WITH DOUBLE TOP PLATE AND 2 STUDS CORNER 5.5 R22 BATT INSULATION ½ 5DRYWALL LOW-PERMEANCE LOW-VOC WATER- BASED PAINT, <30 ng/(pa.s.m^2) (VB) EFFECTIVE R-VALUE = 25.7
10 Windows and Doors FIXED, AWNING, CASEMENT WINDOWS OR FRENCH DOORS VINYL FRAME TRIPLE GLAZING LOW-E COATING ARGON GAS INFILL INSULATED SPACER
11 Heating and cooling High efficient cold climate air source heat pump (Mitsubishi Zuba-Central, heating HSPF 9.4, cooling EER 12.0 SEER 15.00) Forced air system Two zones control (one for basement and the other for main and upper floors) to better control the room temperatures at different thermal conditions.
12 Air Filter A MERV 13 bag filter is installed in the HVAC duct system -see the metal box holding the bag filter at the return side of air handler. Air handler fan will run continuously to circulate air inside the house while passing air through the filter to achieve the best air quality.
13 Hot Water High efficient gas water boiler with indirect tank (IBC VFC , 95% AFUE)
14 Ventilation Eneready 2000 HRV Whisper Power grills with PoshTimezone switches at all bathrooms HRV supply integrated with the heating supply ducts. HRV exhaust in dedicated HRV exhaust ducts All HRV ducts were tested on site before drywall to ensure air-tightness.
15 Lighting 70% of lighting fixtures in LED light 20% of lighting fixtures in CFL Motion-sensor control for exterior lights Appliances and other electrical equipment All new home electric appliances, including fridge, dishwasher, range, hood fan, washer and dryer in are Energy Star rating.
16 Construction Foundation Fabric footing forms save time and materials in footing construction. prevent common moisture problems in basement due to wicked up moisture by capillary action from footing through concrete wall into basement living spaces. act as air barrier under footing connecting the 6 mil poly (air barrier) underneath base slab with the waterproofing membrane (air barrier) on the outside face of foundation wall.
17 Foundation Insulated concrete form (ICF) with 2.25 thick EPS on both sides of the 6 concrete core save both time and material in foundation wall construction. higher insulation and perform better moisture-proofing than normal basement wall construction As an energy conservation measure, a layer of 3 EPS insulation board was installed on the waterproofing membrane in full height on the outside face of foundation wall.
18 Unlike normal construction, the house wrap has to be sealed and taped at all joints between each sheet of house wrap
19 The house wrap has to be sealed and taped between the house wrap and other members of the building envelope, such as doors, windows, and all penetrations through the wall e.g. water pipe and wires.
20 The house wrap was installed on the wall sheathing using staples with plastic caps. This could minimize the number of staples used, thus minimizing the number of penetration through the air barrier, while holding the house wrap securely in place.
21 This photo shows different elements and stages of construction at the exterior wall: 1) sealed house wrap at top right corner, 2) exterior insulation board at top center and 3) rain screen strapping as lower level.
23 Windows installation Because of the additional 2 thick exterior insulation, the weatherproof and air seal work in window installation for the Zen House are different from normal construction. The differences are: Addition of metal flashing at window sill Bigger metal flashing at window head Extra wood trims around the windows
25 Step 2 apply a 4 wide flashing below the window sill (do not staple the bottom each of the flashing)
26 Step 3 install a treated wood block below window sill (to support the metal flashing of window sill)
27 Step 4 tape the corners, window sill, wooden block
28 Step 5 apply trim flashings around the rough opening Step 5 apply trim flashings around the rough opening
29 Step 6 install the window
30 Step 7 install the metal head flashing and apply tape along the top edge of the flashing
31 Step 8 install the metal window sill flashing below window and on the wooden block
32 Step 9 install house wrap around the window, tape and seal all joints
33 Step 10 install the 2 insulation board on the house wrap
34 Step 11 install rain screen strapping
35 Step 12 Install trims around the window Step 13 add another metal flashing on top of top window trim (diagram not shown)
38 Ceiling under roof House wrap MUST be fully supported on both faces during its servicing life in order to ensure its long term integrity as air barrier. At ceiling under roof, house wrap (a flexible membrane) is only supported by roofing trusses or joists (at 24 or 16 on center), -no full support at its top surface Therefore, house wrap is not suitable as air barrier at ceiling under roof. (It is used as air barrier on the vertical surfaces of the building envelope only). Rigid material, e.g. taped drywall, which has the strength to ensure long term integrity is more suitable as air barrier at ceiling under roof.
39 To ensure the continuity of air barrier, the house wrap at top of exterior wall was wrapped from outside passing between two top plates to the inside of the wall and was then well taped along its edge on the internal face of the lower top plate.
40 Gasket was stapled along the taped end of house wrap on the top plate of exterior walls under roof. Gasket was also installed along the top plate of all interior walls under roof. Drywall boards were installed on the ceilings and walls with close space drywall screws along the top edges of drywall. With the taping at all drywall corners, the drywall and gaskets act together as air barrier sealing off air leakage to/from the open space in roof.
41 Air Test Post drywall test To study air seal performance of the house wrap All drywall was installed and taped, all openings through the building envelope, such as venting ducts and hood fans, were closed. The air test would show the air seal performance of the house wrap at walls, taped drywall at ceiling under roof, poly under base slab, and all windows and doors. Test result: Pa and in^2 10 Pa.
42 Final test The final air test was conducted after the completion of the house. Under the new R2000 requirements, all openings cannot be closed during the air test. These openings in Zen House include two hood fans, the intake and exhaust ducts of HRV, two dryer vent ducts, one hot water boiler vent duct. Test result: Pa and in^2 10 Pa The result indicated the effect of the above openings on the overall air tightness of the house.
43 Energy Conservation Measures (ECM) 2 broader approaches Provide higher insulation and better air-tightness of the building to reduce heat loss, reducing the energy required to keep the building in a livable condition Increase the efficiency of mechanical systems, lighting and home appliances, so that they can use less energy to perform their functions.
44 These two broader approaches can be carried out through 9 energy conservation measures (ECM) 1. Increase insulation of the foundation wall 2. Increase insulation of base slab 3. Increase insulation to above grade exterior wall 4. Increase insulation of roof 5. Upgrade windows and doors 6. Improve air-tightness of the house 7. Upgrade the efficiency of heating and cooling system 8. Upgrade the efficiency of domestic hot water system 9. Use higher efficient lighting and home appliances
45 ECMs adopted in Zen House The energy performance of a particular ECM is found by analyzing the Baseline house with the additional of that ECM using energy simulation software HOT2000 The additional cost for ECMs is based on the actual expenditure record from the Zen House project
46 ECM #1 Location: Foundation wall Baseline construction: 8 concrete wall plus 2x4 R12 furring wall inside Upgrade: Use ICF wall and add 3 EPS insulation on outside face of wall Annual energy saving: kwh Additional cost: $4,494.31
47 ECM #2 Location: Foundation base slab Baseline construction: 2 wide 3 EPS insulation under slab along foundation walls Upgrade: 3 EPS insulation under whole base slab Annual energy saving: kwh Additional cost: $1, Note: many municipalities have required insulation under whole base slab if radiant floor heating is installed. In this case, this is not an ECM
48 ECM #3 Location: Exterior wall above grade Baseline construction: 2x6 R22 wall Upgrade: Add 2 mineral wool semi-rigid insulation board on outside of exterior walls. Annual energy saving: kwh Additional cost: $13,070.77
49 ECM #4 Location: Roof Baseline construction: R40 for both sflatand sloping ceiling roofs Upgrade: No upgrade is adopted in Zen House due to high cost Annual energy saving: 0 kwh Additional cost: $0
50 ECM #5 Location: All windows Baseline construction: Double glazing, clear glass, air infill, vinyl frame Upgrade: triple glazing, low-e coating, argon gas infill, insulated spacer, vinyl frame Annual energy saving: kwh Additional cost: $2,500.00
51 ECM #6 Location: Building envelope Baseline construction: normal air-tight construction, ACH = Pa Upgrade: high performance air-tight construction, ACH = Pa (actual air test result of ZEN House) Annual energy saving: kwh Additional cost: $3,539.44
52 ECM #7 Location: Heating System Baseline equipment: high efficient (90%) condensing gas furnace Upgrade: cold climate air source heat pump, heating HSPF 9.4, cooling, EER 12.0, SEER Annual energy saving: kwh Additional cost: $5,400.00
53 ECM #8 Location: Domestic hot water system Baseline equipment: medium efficient gas hot water tank Upgrade: condensing high efficient (90%) hot water boiler Annual energy saving: kwh Additional cost: $2,471.00
54 ECM #9 Location: Lighting and appliances Baseline equipment: normal lighting and appliances Upgrade: 70% LED lighting, 20% CFL lighting, energy star appliances and water saving plumbing fixtures Annual energy saving: kwh Additional cost: $1,000.00
55 ECM Cost-benefit Analysis - Initial Cost ECM Additional cost Annual energy saved (kwh) cost to save 1 kwh ICFplus 3 EPS to foundation wall $4, $1.71 3" EPS under base slab $1, $2.63 2" exterior Roxul to exterior wall $13, $3.26 Roof insulation from R40 to R50 NA NA NA Windows - Triple glazing $2, $1.15 Air-tightness - to R2000 standard $3, $0.51 Cold weather air source heat pump $5, $0.27 High efficient hot water tank $2, $1.13 Energy efficient lighting& appliances $1, $0.28
56 ECM has different service life Future electricity rate forecast based on BC Hydro 2011 IRP Technical Advisory Committee, Integrated Resource Plan, Long- Term Rate Forecast 2010 BC Hydro Residential Rate, Tier 1: $0.067 Assumed inflation 2.1% Use Equivalent-Annual-Annuity Approach
57 ECM Cost-benefit Analysis Service Life ECM Service life IRR Equivalent-Annual- Annuity (cents) ICF plus 3 EPS to foundation wall 50 5% " EPS under base slab 50 3% " exterior Roxul to exterior wall 50 2% 0.41 Roof insulation from R40 to R50 50 NA NA Windows - Triple glazing 30 6% 3.29 Air-tightness - to R2000 standard 40 15% 7.66 Cold weather air source heat pump 25 27% 6.56 High efficient hot water tank 25 5% 2.18 Energy efficient lighting& appliances 10 23% 4.01
58 Annual Green House Gas Emission (tonne): (11.688) ECM Service life GHG Reduction in Service Life Additional cost Add. Cost to save 1 tonne GHG ICFplus 3 EPS to foundation wall $4, $ " EPS under base slab $1, $ " exterior Roxulto exterior wall $13, $ Roof insulation from R40 to R50 50 NA NA NA Windows - Triple glazing $2, $ Air-tightness -to R2000 standard $3, $87.87 Cold weather air source heat pump $5, $ High efficient hot water tank $2, $ Energy efficient lighting& appliances $1, $62.58
59 Energy Performance of Zen House Site Energy in Heating Mode Only Estimated Annual Space Heating Energy Consumption (kwh): ( ) Ventilator Electrical Consumption: Heating Hours (kwh): (512.04) Estimated Annual DHW Heating Energy Consumption (kwh): ( ) ESTIMATED ANNUAL SPACE + DHW ENERGY CONSUMPTION (kwh): ( ) LESS 79% Eneguide Rating: 88 Note: Figures in bracket are Baseline House results
60 Annual Estimated Energy Consumption by Devices Site Energy in Heating Mode Only kwh Heating A/C HRV + fan DHW Appliance Total Baseline Zen House Zen House to baseline percentage 11% 0% 191% 43% 78% 33%
61 Baseline Heating A/C HRV + fan DHW Appliance Zen House
62 Estimated Annual Fuel Consumption Costs Site Energy in Heating Mode Only Electricity Gas Total Saving Saving in Percentage Baseline $ $1, $2, Zen House $ $ $1, $ %
63 Financial A analysis Total additional Cost for Energy Upgrade = $33, Mortgage for $33, Mortgage rate: 4.74% Amortization: 25 years Monthly payment = $ Annual payment = $2, Compare with Annual Fuel Consumption Costs: Heating mode only: $ Heat and Cooling mode: $1,030.72
64 Discussion Primary energy Cost effect due to fuel Air-conditioning Energy bill saving vs mortgage payment for additional cost for energy upgrade
research highlight June 2012 Technical Series 12-103 Highly Energy Efficient Building Envelope Retrofits for Houses introduction In Canada approximately 30% of all energy is consumed in buildings, with
District of Houston 250-845-2238 2014 British Columbia Building Code Changes A District of Houston interpretation of the 2014 Building Code Changes for 9.36 & 9.32 The following changes reflect the most
BPC Green Builders Green building for new and existing homes Health Comfort Energy Mechanical Systems Installed HVAC Systems Primary energy source large, roof mounted, solar thermal array (AET flat plate)
1 How Old and New Houses Use Energy Total Consumption per Household, 2001 120 100 2: RENOVATION - CONCORD, MA million per household 80 60 40 20 Space Heating Electric Air Conditioning Water Heating Refrigerators
R-H-DI1 INSULATION BATT NR-E-IB1 Avoid Using Batt Insulation With Metal Framing Batt insulation should not be used with metal framing systems. Although it is common to see fiberglass batt insulation installed
POLICY Page 1 of 5 SUBMITTAL REQUIREMENTS FOR ONE AND TWO FAMILY DWELLINGS, ADDITIONS AND RENOVATIONS All submittals shall be site specific and designed to the provisions of the 2012 International Residential
Moisture Aside from structural concerns, the most important consideration for foundation design is moisture. No client wants a wet basement. No client wants a damp basement. No client wants mold in their
Home Energy Evaluation Report for Fritz Kreiss and Catherine McQueen May 2008 Wisconsin Area PO BOX 115 Lake Geneva, WI 53147 CELL (414) 550-4765 Home Performance with ENERGY STAR Evaluation Report Customer
ECHO System for Basements Homeowners looking for more space are all too familiar with the cold, damp and dingy basement. Now, the Enclosure Conditioned Housing (ECHO) System TM, winner of the Ottawa-Carleton
Wise Energy Guide solutions & tips 32 AIR SEALING Is your house leaking money? six Building envelope solutions and simple tips If your home is like most, the greatest amount of heat loss is from air leakage;
IECC Compliance Guide for Homes in Virginia Amended Version of 2012 International Energy Conservation Code July 14, 2014 Climate Zone Since the entire state of Virginia falls in the IECC Climate Zone 4,
2009 IECC Update International Energy Conservation Code Scope The code applies to both residential and commercial buildings. In the code, the United States is divided into eight climate zones which are
building science.com 2006 Building Science Press All rights of reproduction in any form reserved. Renovating Your Building America Report - 0309 2003 (revised 2007) Building Science Corporation Abstract:
Selecting Energy-Efficient Windows E N E R I N F O A D V I S O R S E R I E S Key Points Improving the energy performance of windows is important, since windows are the least insulated surface of most homes.
Low-cost Construction for High-energy Savings Brian J. Wimmer Construction Manager Rochester Area Habitat for Humanity firstname.lastname@example.org Objectives: 1. Control air & moisture in high-performance, low-cost
TechSpecs A builder s blueprint for construction technologies January 2013 The Closed Crawl Space: Making the Transition Climate Zones 3A & 4A C B A E D H G F A. Wood Floor Framing - p. 2 B. Foundation
energy-saving checklist a guide for rental property owners taking responsibility As an individual, your efficient use of energy brings benefits such as lower bills, improved comfort levels in your home
Qualifying Homes ENERGY STAR Qualified Homes, Version 3 (Rev. 03) The following homes are eligible to earn the ENERGY STAR: Single-family homes; Units in multi-family buildings that are three stories or
NCMA TEK National Concrete Masonry Association an information series from the national authority on concrete masonry technology CONCRETE MASONRY FOUNDATION WALL DETAILS TEK 5-3A Details (2003) Keywords:
24.301.161 INCORPORATION BY REFERENCE OF INTERNATIONAL ENERGY CONSERVATION CODE (1) The Department of Labor and Industry adopts and incorporates by reference the International Code Council's International
Additions and Alterations Addition and alteration construction is a miscellaneous grouping of home improvement and renovation projects that are generally geared toward the enhancement of an existing principal
Chapter 2: Foundations Crawlspace [V502.1.2] Vents. Vents in the crawlspace help keep floor insulation and floor framing dry. Crawlspace vents also reduce the potential for radon buildup under the floor.
First Time Home Buyers Energy Efficiency Workshop Guide Why is efficiency important when buying a home? Affordability: lower utility bills Environmental responsibility: reduces your carbon footprint and
Basement Finishing Guide Community Development Department Building Inspections Division 5200 85 th Avenue North / Brooklyn Park, MN 55443 Phone: (763) 488-6379 / Fax: (763) 493-8171 6/15 www.brooklynpark.org
Vision Home Inspection 324 Rams Run Shepherdsville KY 40165-7877 Inspector: James McFadden Property Inspection Report Client(s): Property address: Inspection date: View report summary This report is the
ROOFS, SNOW AND ICE DAMS The Problem Ice dams are a common roof performance problem in cold climate buildings. Simply put, they are ridges of ice and icicles caused by melt water from further up the roof
CLIENT Inspection Report 271 Front St. Alert Bay, B.C. Island Building Inspections 2013 V ANCOUVER I SLAND B. C. Elevation Photos For the Property at 271 Front Street Alert Bay, BC ELEVATION PICTURES Front
2012 Ontario Building Code Requirements for New Construction Bradford West Gwillimbury Building Division March 5, 2012 1 Ontario Building Code changes Applicable to permits applied for after December 31,
www.citiesinspection.com October 5, 2015 Dear Client, On 9/14/2015, Cities Inspection Service, Inc. completed a building inspection of the property located at 123 Oak Street, Someplace, Minnesota for you.
THE DISTRICT MUNICIPALITY OF MUSKOKA ONTARIO RENOVATES PROGRAM FOR HOMEOWNERS ELIGIBLE REPAIR PROJECT PARAMETERS 1. To have your project considered and payment processed, all projects requiring a Building
March 14, 2007 Re: Installation of Bay, Bow and Garden Windows Attached are the Atrium Companies, Inc recommendation for the installation of bay, bow and garden windows. These instructions were developed
Arch itectu ral Te sting Inc. XYZ Corporation 23 June 2008 Project Waterproofing Handbook Working Set Rev. 0 Project Address: 8888 Main Street York, PA 88888 Prepared By: Architectural Testing 4 Rancho
LEGALETT HVAC DESIGN FEE SCHEDULE (revised April 17, 2012) Background In the past Legalett has simply supplied warm floors for comfortable living. However, 2012 Building Code changes in Ontario make it
ENERGY STAR Qualified New Homes Thermal Enclosure Checklist & Water Management Checklist Eli Caudill ENERGY STAR Version 3 Tighter Standards Whole Home Approach Better, More Sustainable Construction Surpasses
The better way to build TM Installation Manual FOUNDATION SIPs & FROST WALLS SIPs February 2016 PWF FOUNDATION & FROST WALL SIPs Installation Manual Table of Contents Topics General Requirements...................................
Air Sealing Air Infiltration Reduction/Blower Door Guided Program Operations Air Sealing Door Weatherstrip Kit Program Operations Air Sealing Exhaust Fan Damper Incidental Repair Air Sealing Dryer Duct
City of Duluth Preparation for 2015 Residential Code Changes Discussion with Local Builders and Designers Thank you for taking the time to join us today. We know you are busy and your time is valuable.
R-H-DI1 INSULATION BATT Pressure or Friction Fit Insulation should be cut to fit snugly against studs on all sides, and should completely fill the cavity with no air gaps. Cut lengths of insulation should
Comment Form on Gut Rehabilitation Alternatives Name: Organization: Email: Instructions Submission: Please submit this form to email@example.com by October 10 th, 2012 with the subject line
SAVE ENERGY AT HOME INSULATE AND AIR SEAL Check the roof insulation level and add insulation to maintain minimum R-38 (6 of blown cellulose or equal). Use R-19 between frame or R-10 rigid insulation for
Thank you for considering as you prepare to build! Enclosed in this new construction planning packet you ll find examples of forms, samples, and other information you ll submit with your loan application:
Basements are Changing John Straube, Ph.D., P.Eng Basements: New & Retrofit Energy Efficient, Durable, Healthy Increasingly used as living space Not a root /coal cellar anymore! High quality space expected
This report presents the findings and recommendations of the assessment of energy use and environmental stewardship of Arlington Street Church, Boston, MA. As stewards of the earth it is important that
first look at GigaCrete s revolutionary new New Construction GigaHouse GigaHouse Utilizing GigaPanel What is GigaCrete GigaCrete is a family of products based on low carbon footprint Green ceramic binders
AIR INFILTRATION AND ENERGY EFFICIENCY IN YOUR HOME When you think about the energy efficiency of a home, things like the heating and cooling system and insulation readily come to mind. These are certainly
Crawford Inspection Services C.C.B. # 76914 www.crawfordinspections.com Portland Area PO Box 665 West Linn, OR 97068 Ph: (503) 650-6957 Salem Area 5434 River Rd. N; #192 Keizer, OR 97303 Ph: (503) 362-5809
BUILDING PERMIT SPECIFICATIONS The below noted requirements are based upon La Plata County Building Code. These specifications are not intended as a complete set of requirements, but are intended to provide
A bout your house CE 28c before you start Renovating Your Basement Moisture Problems Mold and decay on floor joists and sill plates Stuffy air, high humidity, poor air circulation Water draining in from
#1) BEFORE Purchasing Land Here Is A Checklist Of Things You Should Check Zoning laws Deed restrictions on home size, foundation style, roof pitch, etc. Suitability (slope, wetland issues, etc.) Accessibility
To be used as a first home visit for note taking. Visit www.homeinspectiondirect.com for more tips and information about buying a home and hiring a home inspector. This form in no way replaces a professional
Atlantic Post and Beam Construction 1245 Hanwell Rd. Fredericton, NB. E3C 1A6 www.atlanticpostandbeam.ca Tel: (506) 450-5445 Prefabricated/Modular Timber frame Home / Cottage: At Atlantic Post and Beam,
BUDGETING The budgeting information provided is offered for rough estimating purposes. We have provided you with typical life expectancies where possible. For specific quotes, contact at least three appropriate
7 th Annual North American Passive House Conference September 27-30, 2012 Denver CO Performance of 8 Passive House Envelopes in Cold Climates Rolf Jacobson, LEED AP CSBR, University of Minnesota ZEB, Norwegian
Electrical for Detached Garages: Updated Feb 19, 2016 for 2015 CE Code in force Jan. 1, 2016 * Garage construction requires permits (electrical, building) * Permits must be applied for at the time. * Dial
Single Section and Double Section Homes SM-01 All New 20 Wides Now Available! SM-08 Units shown with optional features SM-01-4814 42 Bedrooms 41 Bathrooms 648 Sq. Ft. SM-01-5214 42 Bedrooms 41 Bathrooms
MINNESOTA ENERGY CODE COMPLIANCE COLLABORATIVE 2015 Minnesota Residential Energy Code (MR 1322) SIGNIFICANT CHANGES INCLUDING CODE COMMENTARY (July 15, 2015 Update) Note: The following information contains
DETAILED SCOPE OF WORK FOR THE NETCONG ELEMENTARY SCHOOL The Netcong Board of Education Netcong, Morris County New Jersey Roof Replacement Project Health and Safety Renovation Projects Roof Replacement
Greenhouse Gas Implications of HVAC Upgrades in Multi-Unit Residential Buildings J A NUARY 2015 INTRODUCTION This Research Report explores best practices and approaches for reducing greenhouse gas (GHG)
City of Ann Arbor PLANNING & DEVELOPMENT SERVICES CONSTRUCTION SERVICES Mailing: 301 E. Huron Street P.O. Box 8647 Ann Arbor, Michigan 48107-8647 Location: Larcom City Hall First Floor 301 E. Huron St.
Key energy-efficient features of your new home Your thermal envelope The thermal envelope, or shell, of your home (walls, roof and floor) is designed to keep you dry and comfortable. It protects you from
DIVISION OF CAPITAL ASSET MANAGEMENT AND MAINTENANCE THE COMMONWEALTH OF MASSACHUSETTS STANDARD SPECIFICATIONS MGL CHAPTER 149A CM-AT-RISK PROJECTS DIVISION 00 - PROCUREMENT AND CONTRACTING REQUIREMENTS
City of St. Charles Basement Finish or Remodel Building & Code Enforcement Division 2 East Main Street St. Charles IL 60174 630.377.4406 (Office) 630.443.4638 (Fax) http://www.stcharlesil.gov Please direct
about your house CE 28 c Before You Start Renovating Your Basement Moisture Problems Mold and decay on floor joists and sill plates Stuffy air, high humidity, poor air circulation Water draining in from
Selling your home Does Wall Township require an inspection by the building department on resale of a home? No. We do not require a Certificate of Continued Occupancy on the resale of home. A Smoke Detector,
Department of Health and Human Services, Division of Public Health Occupational and Environmental Epidemiology Branch 1912 Mail Service Center, Raleigh, North Carolina 27699-1912 BUILDING ASSESSMENT QUESTIONNAIRE
1 Sealing Air Leaks in Your Home Housing Fact Sheet What is Air Leakage? Air leakage, or infiltration, is outside air that enters uncontrollably through cracks and openings in the walls, ceilings and floors
Alberta Allied Roofing Association Asphalt Shingle Application Requirements Section 1 Roof Decks 1.1 General Asphalt Shingles are not permitted to be installed directly over rigid insulation. When Asphalt
Home Improvements Basement development What you need to know. calgary.ca/dba call 3-1-1 I plan to finish my basement. Do I need a Building Permit? A Building Permit is required for basement alterations
Home Energy Evaluation Report Nate Begeman, 1550 Saint Francis Dr San Jose, CA 95125 Air Infiltration Current Air Leakage 2,852 Current Air Changes Per Hour 0.91 Recommended Air Changes Per Hour 0.35 Percent
Energy Efficient Home Construction TABLE OF CONTENTS ENERGY SAVINGS - TWO PLANS... 1 REQUIRED FEATURES CHART... 2 THE ELECTRIC HEAT PUMP... 4 ELECTRIC HEATING COST CHART... 5 AIR SEALING... 6 INSULATION...
INTRODUCTORY INFORMATION TABLE OF CONTENTS 00 0101 PROJECT TITLE PAGE PROCUREMENT REQUIREMENTS (PROJECT MANUAL) Tab A - Invitation for Bids Tab B - Instructions to Bidders Tab C Bid Form for General Bids
New Hampshire Residential Energy Code Application for Certification of Compliance for New Construction, Additions and/or Renovations (EC-1 Form) Minimum Provisions Effective Date: April 1, 2010 Owner/Owner
BUILDING CODE GUIDELINE FOR MECHANICAL INSPECTIONS Building Code compliance is the obligation of design professionals and/or contractors. Plan Review and Inspection Guidelines are intended to be used by
4658.4500 PLUMBING SYSTEMS; NEW CONSTRUCTION. Subpart 1. Installation. All plumbing systems must be installed and tested according to this chapter and chapter 4715, the Minnesota Plumbing Code. Subp. 2.
4 Installation Requirements 9 4.1 Code Reference The authority having jurisdiction should be referenced to determine what law, ordinance or code shall apply in the use of flexible duct. Ducts conforming
Glossary of Heating, Ventilation and Air Conditioning Terms Air Change: Unlike re-circulated air, this is the total air required to completely replace the air in a room or building. Air Conditioner: Equipment
BUILDING CODEACT, 1992 RULING OF THE MINISTER OF MUNICIPAL AFFAIRS AND HOUSING Pursuant to clause 29(l)(b) of the Building Code Act, 1992. as amended, the Director of the Building and Development Branch
In accordance with the Department of Labor and Industry s statute 326.0981, Subd. 11, This educational offering is recognized by the Minnesota Department of Labor and Industry as satisfying 1.5 hours of