1 Software Release For DF6000/CF3000/FX6000 Site Installer Network Card
2 DF6000/CF3000/FX6000 Software Updates Latest Version: Display Loop: (14) Engineering Change Note : 1163 Site Installer : Engineering Change Note : 1164 Network Card : 6.6 Engineering Change Note : 1165 Date: 15/10/10 DF6000/CF3000/FX6000 Analogue Addressable Panel Important: These versions of Software loop and Display are compatible with previous versions (See tables below). Main features / Improvements Better touch screen responsiveness. Faster indication of fire/faults during printing mode Added panel network filtering. (This feature will be explained in the latest release of Cooper fault finding guide). Enabling all will not fail if some outputs cannot be enabled, it will simply enable all that. Accept commands from both HyperTerminal and PanelComm. Network disabling of sounder 1 and sounder 2 removed in order to comply with the new EN54 pt A1:2006. Added evacuate locking feature (this feature will be explained in the latest release of Cooper fault finding guide). Disabling a zone on a panel will disable that zone on all panels in the network. Web server can get zone/address text information from the panel. Australia Fire Brigade screen will now show address OR zone information depending on an option set on menu(this feature will be explained in the latest release of Cooper fault finding guide). Added loop repeater command either loop or network to mute the internal buzzer from the main panel. (This feature will be explained in the latest release of Cooper fault finding guide). Viewing of the status of T1/T2 timer. This feature will be explained in the latest release of Cooper fault finding guide). 2
3 Indication of day/night mode on main display. This feature will be explained in the latest release of Cooper fault finding guide). Added new fan control features according to the new Australian standard AS1668. (This feature will be explained in the latest release of Cooper fault finding guide) Web server can request all disablement information for the panel over the network Added a toggle on to enable/disable all outputs (panel + loop). (This feature will be explained in the latest release of Cooper fault finding guide). Added UL 864 Pt 9 requirements (feature available at access level 3). Add German local requirement on FBF & FAT interfaces. Site monitor can request various system data from panel (Web server feature). Improved support for Non Fire input. Updated Polish requirement. Polish font (codepage 1250). Extra characters on Polish keyboard Uploading log in Polish now has correct characters displayed on PC. Polish language now prints correctly. For Polish, technical input activation turns on an LED. Bug Fixes All panels now send at least one loop to Site Installer to get round a problem with how it stores zone data. Auxiliary board type is no longer reset on auto learn. On download from PC to panel, the panel preserves settings not overwritten by the download. When CDR data is reset (auto learn etc), FPE, FRE and sounder disablement flags are cleared. Now shows correct count of zones in system details. Filled in missing characters from central European font. Corrected some problems with Czech and Slovak. Fixed bug displaying fires and pre-alarms incorrectly on screen-cover level 1 screen. For the central European font, the panel will now attempts to re-map the non displayable characters when in text mode. 3
4 Font no longer reset after screen calibration. Fixed bug on "go to" screen, if you did not select a loop it would not work, loop now defaults to 1. Buzzer beeps only when user hits a control that does something, rather than when they touch the screen. Fixed bug where the level 1 "Accept fire" button was not working, it was going to another screen. Fixed bug in sending pre-alarm across network, type was not being sent. Fixed bug in detecting when a zone had become disabled by disabling all its devices. Fixed bug in printing of panel disablements (FRE, FPE, sounders). Fixed bug displaying panel number of the analogue value screen. Fixed bug displaying the enable/disable status of sounders on the level 2 menu. Analogue level test function importing wrong fault values for heat devices, causing heats to fault with value <10. Fixed a bug in the Disable All menu Fixed a problem with list of zones, if there is a gap, it does list all zones. Fixed a problem with Australian FB screen as it would always initially show disabled address count as 0. MCOM devices on loop4 activated by zones outside of populated list, sub address indexer not reinitialised for loop driver 2 downloadh Auto config not locating ID mismatches. 4
5 Loop Software History Log Date Version Comments 15/08/ See above 15/09/ Auto learn locking function Supports Fan controls. Technical Input/Technical Output Supports Non Fire Input Added HMO (House of Multiple Occupancy) requirements as per BS5839 Pt6 Support New EN54 pt2 requirements. (Disable address moved to access level 3 and Disable LED now is off when delay are implemented) Download analogue values and Event Log to PC. T1/T2 can be Disable using panel clock or a loop addressable device. AVF programmable 10 to 30s AVF programmable by zone Added Bell tone on Class Change Pre-addressed Auto learn Added German feature on FAT Added Polish requirements Approved to latest EN54 pt 2 :1997 +A1:2006 and EN54 pt 4: A1:2002+A2: /08/ Double Knock 2 devices within a Zone (addressable loop devices as well as panel outputs), Calibration of Touch Screen: This feature has been removed from the power up menu as well as during reset due to various complaints. Touch screen calibration is only possible by either Panel com or activation of Class Change input during Panel power up. Test Device on Output modules, Support Technical timers. Increase the number of Devices alarm LED s to 24, Support Russian, Afrikaans, Vietnamese, Finnish, & Greek languages. Panel default to Cooper Logo, Disable Buzzer at Access level 4 Support T1/T2 features (Swedish as well as Standard), Call point override facility for T1/T2,T1/T2 override using programmable input on site installer, Support Swedish Fire Brigade Interface with zone/address location Printer monitoring (Paper and head up), Extended walk test (led remains on for 20 seconds), Added Australian tone on addressable sounders, Added overload Fault on Loop when the load current is too high. (EN54 pt13 requirement) Added "abnormal comms" Fault Condition, when the loop communication is (EN54 Pt13). Support FAT interface (Fire Brigade interface on the network)two network protocols V1&V2 (V1 standard protocol, V2 standard+ FAT interface)update Display software using PC. Display Program can be erased from panel via HyperTerminal. Press Ctrl-X, then Y.Once erased, it can be programmed via RS232 with "PanelProg". Added above features as per ECN 20/07/ Implemented Autolearn per loop, Integrations of Faults, 5
6 Loop Software History Log. Cont. Date Version Comments 16/03/ Update delete device, updated programmer, capacity 127 network panels. Alarm verification on detectors 12/02/ Italian mode overrides sounder programming, update on T1/T2. Evacuation with no aux not setting the FRE Flag 23/10/ Global output disabled for commissioning access level 4 fixed 22/09/ Czech T1/T2 applied to panel outputs 13/09/ Czech T1/T2 updated, now tests for day night mode, if night mode T1/T2 timers are ignored. 10/08/ Sounder disablements from aux boards-now disables only sounder outputs FPE disablement, now disablement all panel outputs exclude sounders and panel FRE 27/07/ Australian no longer latches. Read types from network fire command Set up day/night mode 26/05/ Australian mode now exist inside the UK version SP40 Voice Evac interface now recognized. Australian variant with key switch T1/T2 implemented for Czech 6
7 Display Software History Log : (Micro Board) Date Version Comments 15/08/ See above 15/09/09 3,03.19 Auto learn locking function Supports Fan controls,technical Input/Technical output Supports Non Fire Input Added HMO (House of Multiple Occupancy) requirements as per BS5839 Pt6 Support New EN54 pt2 requirements (Disable address moved to access level 3 and disable LED now is off when delay are implemented) Download analogue values and Event Log to PC T1/T2 can be Disable using panel clock or a loop addressable device AVF programmable 10 to 30s AVF programmable by zone Added Bell tone on Class Change Pre-addressed Auto learn Added German feature on FAT Added Polish requirements Approved to latest EN54 pt 2 :1997 +A1:2006 and EN54 pt 4: A1:2002+A2: /08/ Calibration of touch screen: This feature has been removed from the power up menu as well as during reset due to various complaints. Touch screen calibration is only possible by either panel com or activation of class Change input during panel power up. Test device on output modules, support technical timers. Increase the number of devices alarm LED s to 24, support Russian, Afrikaans, Vietnamese, Finnish, & Greek languages. Panel default to Cooper Logo, Disable Buzzer at Access level 4. Support T1/T2 features (Swedish as well as Standard ),Call point override facility for T1/T2,T1/T2 override using programmable input on site installer, Support Swedish Fire Brigade Interface with zone/address location. Printer monitoring (Paper and head up), Extended walk test (led remains on for 20 seconds), Added Australian tone on addressable sounders, Added overload Fault on Loop when the load current is too high. (EN54 pt13 requirement). Added "abnormal comms" fault condition, when the loop communication is (EN54 Pt13). Support FAT interface (Fire Brigade interface on the network)two network protocols V1&V2 (V1 standard protocol, V2 standard+ FAT interface) update display software using PC. Display Program can be erased from panel via HyperTerminal. Press Ctrl-X, then Y. Once erased, it can be programmed via RS232 with "PanelProg". Added above features as ECN 7
8 Display Software History Log : (Micro Board). Cont. Date Version Comments 20/07/ Implemented all the above functions Auto learn per loop Added Next/Previous buttons on the Test & Analogue value screens Facility to remove integration of Fault at access level 3 for speed of fault findings/commissioning If a sounder is added without PC programming, it will default to Global alarm Facility to remove Call point ID Text a access level 3.This is mainly used if a call point is used for other application. Implemented Spanish/Latvian/Croatian languages Updated Italian/Hungarian/Czech/Polish 22/11/ Add Slovak & Slovenian language 13/09/ Change maximum output per loop to /07/ Send device text across network Australian Fire Brigade Australian brigade Screen reset is now global rather than local Sounder Enable/Disable in German prints correctly Analogue values in German prints correctly 26/05/ When Fire Brigade screen appears backlight is always turned on In the Brigade colors release, the Fire Brigade has labels denoting the color of various buttons and indications When auto learn was done, the language was set back to English 8
9 DF6000/CF3000/FX6000 Site Installer Latest Version: Engineering Change Note : 1164 These versions of Site Installer are compatible with previous versions. Site Installer Features Swedish, French, Dutch, Slovakian translations. Retrieve event log and analogue values. Screen grab, firmware upload, erase CDR, screen calibration. New interface improvement for ease of use (i.e Text manager). Add support for RF panel and RF devices. Integrated and improved logo upload. Screen grab, firmware upload, erase CDR, screen calibration. Support for configuring the mimic repeater and Fan control. Support updating and programming of panel display software (No need for a programmer). Improvements and additions to the sanity checking. Added UL 864 9th edition requirements. Added support for device 254 (Reserved address). 9
10 Site Installer History Log Date Version Comments 15/08/ See above features Support Mimic Repeater Support updating panel display software Sanity Checks Add French, Dutch and Swedish update Panel Com Commands Log retrieval and storage 15/09/ Support for different editions of SI with varying panel support Move to SQL Server Compact Edition (64bit support) Calibrate screen/panel Com part of Site installer Retrieve event log and analogue values Integrated fan controller PAVA output Integrated commission transfer solution.net resources for translations and right-to-left text support Integrated and improved logo upload 10
11 DF6000/CF3000/FX6000 Network Card Latest Version : 6.6 Engineering Change Note : 1165 These versions of network card are compatible with previous versions. Features The card now check for acknowledgment after sending a message to the panel before removing the message from the buffer card. Network monitoring will now start after power up without requiring a master panel soft reset. Repeat timer value changed to 48ms. Network History Log Date Version Comments 15/10/ See above features 20/07/ Recompiled for Rev. 2c pcb. 19/09/06 4b Minimum slave timeout set to 30s 18/09/06 4a If number of panels is < 50, slave timeout defaults to 300s 13/09/06 4 Slave timeout now scales with number of panels 07/02/06 3a Maximum number of panels increased to /07/05 3 Monitoring now activated only if number of panels > 1 09/11/04 2 Added ability to switch between master and slave modes 08/10/04 1 Monitoring now continues after a reset. 11
12 Head Office Sales Tel: Fax: Technical Tel: Fax: Export Tel: Fax: Service Tel: Fax: Web: Head Office Cooper Lighting and Safety Ltd Wheatley Hall Road Doncaster South Yorkshire DN2 4NB CC1838
GAI-TRONICS A division of Hubbell Ltd VoIP Telephones Configuration Guide: Firmware version 3 (The previous versions of this manual, for firmware versions 1 & 2, remain available) Document Ref: 502-20-0119-001
IP Telephony Contact Centers Mobility Services Avaya IP Deskphones 9620/9620L, 9630, 9640, 9650/ 9650C connected to Integral Enterprise Bedienungsanleitung Operating User Manual instructions Version 1.1-022010
Total Connect TM 2.0 Online Help Guide Hints for use: When viewing in a web browser, hit F11 to toggle full screen mode. Use the bookmarks panel or table of contents to jump to the desired topic. Select
INTERACT TM Pro Pro 8i AT User s Manual Table of Contents CHAPTER 1: INTRODUCTION SERVICE AND SUPPORT...1 Technical Support...1 Sales and Customer Service...1 Product returns...1 IMPORTANT SAFETY INFORMATION...2
Aspire VoIP Feature Supplement 2.00 Technical Support Web Site: http://ws1.necii.com (registration is required) This manual has been developed by NEC America. It is intended for the use of its customers
Thecus N8900 series N12000 series N16000 series N5550/N6850/N8850/N10850 N7700PRO V2/N8800PRO V2 User s Manual Copyright and Trademark Notice Thecus and other names of Thecus products are registered trademarks
WF-3620/WF-3640 User's Guide Contents WF-3620/WF-3640 User's Guide... 13 Product Basics... 14 Setting Up the Control Panel... 14 Control Panel Buttons and Lights... 15 Status Icons... 16 Status Button...
IP Office 3.2 Phone Installation Guide 15-601042 Issue 11e (27th June 2006) 2006 Avaya Inc. All Rights Reserved. Notice While reasonable efforts were made to ensure that the information in this document
GoldMine Mobile Edition Installation and User Guide Version 9.0 Rev: 90-10-24-11 5675 Gibraltar Drive Pleasanton, CA 94588 USA TEL: 800.776.7889 www.frontrange.com Copyright 2011 FrontRange Solutions USA
SNS-SF064 SNS-SF032 SNS-SF016 SNS-SF008 SNS-SF004 SNS-SF001 User Guide SAMSUNG NETWORK RECORDING SERVER SOFTWARE ware v1.2 imagine the possibilities Thanks you for purchasing this Samsung product. To receive
VeriTrax AS-215 AC-215's PC management software Software Users Guide August 07 Version 2.05.03 Copyright and Version Number Information in this document, including URL and other Internet Web site references,
NAUTIZ X7 Manual NAUTIZ X7 Manual Trademarks Microsoft, Windows, the Windows logo, Windows Media, Outlook and ActiveSync are registered trademarks or trademarks of Microsoft Corporation in the United States
GoldMine Premium Edition Administrator Guide Version 9.0 Rev: 90-04-26-10 5675 Gibraltar Drive Pleasanton, CA 94588 USA TEL: 800.776.7889 www.frontrange.com Copyright 2010 FrontRange Solutions USA Inc.
User Guide for the Polycom SoundPoint IP 450 Phone SIP 3.2 July 2009 1725-12495-001 Rev. B Trademark Information POLYCOM, the Polycom Triangles logo and the names and marks associated with Polycom s products
Technical Bulletin 43565 Using Polycom SoundPoint IP and Polycom SoundStation IP Phones with Asterisk Introduction This document provides introductory information on how to use Polycom SoundPoint IP phones
REACH-IT Industry User Manual Part 02 - Sign-up and account management 2 REACH-IT Industry User Manual Version: 2.1 Version Changes 2.1 April 2014 Updates related to REACH-IT 2.7 regarding Terms and Conditions,
OfficeServ Call User Manual Every effort has been made to eliminate errors and ambiguities in the information contained in this guide. Any questions concerning information presented here should be directed
Copyright 2007 Pirelli Broadband Solutions S.p.A. All rights reserved. This document contains Pirelli proprietary and confidential information. No part of this document may be copied, reprinted or reproduced
8/18/60/128/500/504/512 User Guide Table of Conts Introduction ------------------------------------------------------------------------------------------vii KEYPAD INFORMATION ----------------------------------------------------------------------------
Grandstream Networks, Inc. DP715/DP710 DECT Cordless IPPhone This page is intentionally left bank DP715/DP710 USER MANUAL Index GNU GPL INFORMATION... 4 CHANGE LOG... 5 CHANGES FROM 18.104.22.168 USER MANUAL...
GE Healthcare Life Sciences UNICORN start 1.0 User Manual Table of Contents Table of Contents 1 Introduction... 1.1 Important user information... 1.2 User documentation... 1.3 UNICORN start overview...