1 S10I / S20I / S30I Solar Light Controller USER MANNUAL Thank you very much for selecting our product! This manual offers important information and suggestions with respect to installation, use and troubleshooting, etc. Please read this manual carefully before using the product and pay attention to the safety recommendations in it. Specification Summary Nominal system voltage 12 / 24VDC* Maximum PV input voltage 50V Nominal charge / discharge current S10I 10A S20I 20A S30I 30A * The controller will recognize the system rated voltage when start up. If the battery voltage is lower than 18V, it will recognize the system as 12V. If the battery voltage is greater than 18V, it will recognize the system as 24V.
2 1 Important Safety Information Save These Instructions This manual contains important safety, installation and operating instructions. The following symbols are used throughout this manual to indicate potentially dangerous conditions or mark important safety instructions, please take care when meeting these symbols. WARNING: Indicates a potentially dangerous condition. Use extreme caution when performing this task. CAUTION: Indicates a critical procedure for safe and proper operation of the controller. NOTE: Indicates a procedure or function that is important for the safe and proper operation of the controller. General Safety Information Read all of the instructions and cautions in the manual before beginning installation. There are no user serviceable parts inside the controller. Do not disassemble or attempt to repair it. Install external fuses/breakers as required. Disconnect the solar module and fuse/breakers near to battery before installing or adjusting the controller. Do not allow water to enter the controller. Confirm that power connections are tightened to avoid excessive heating from loose connection. 2 General Information 2.1 Product Overview Thank you for selecting LandStar series solar light controller that adopts the most advanced digital technique and operates fully automatically. The Pulse Width Modulation (PWM) battery charging can greatly increase the lifetime of battery. It has various unique functions and quite easy to use, such as: 12/24V automatic recognition High efficient Series PWM charging, increase the battery lifetime and improve the solar system performance. Use MOSFET as electronic switch, without any mechanical switch Widely used, automatically recognize day/night. Digital LED menu, only one key solve all setting simply Intelligent timer function with 1-15 hours option Unique dual timer function, enhance the flexibility of street light system. Gel, Sealed and Flooded battery type option. Adopt temperature compensation, correct the charging and discharging parameters automatically and improve the battery lifetime. Electronic protection: Overheating, over charging, over discharging, overload, and short circuit. Reverse protection: any combination of solar module and battery.
3 The controller is for off-grid solar system, especially in solar light system, and protects the battery from being over charged by the solar module and over discharged by the loads. The charging process has been optimized for long battery life and improved system performance. The comprehensive self-diagnostics and electronic protection functions can prevent damage from installation mistakes or system faults. Though the controller is easy to operate and use, please take your time to read this manual and become familiar with it. This will help you make full use of all the functions and improve your solar PV system. 2.2 Product Features Figure 2-1 Land Star characteristics 1 Charging status LED indicator An LED indicator that shows charging status and also indicates when a solar input fault condition exists 2 Battery status LED indicator An LED indicator that shows battery status 3 Load status LED indicator An LED indicator that shows load status 4 Temperature Sensor Measure ambient temperature and make temperature compensation for charging and discharging. 5 LED digital display Display the load work mode and status 6 Solar Module Terminals Connect solar modules. 7 Battery Terminals Connect batteries. 8 Load Terminals Connect loads. 9 Setting button (in manual mode used for load ON/OFF) Set load work mode and select battery type. 3 Installation Instructions 3.1 General Installation Notes Read through the entire installation section first before beginning installation. Be very careful when working with batteries. Wear eye protection. Have fresh water available to wash and clean any contact with battery acid. Uses insulated tools and avoid placing metal objects near the batteries. Explosive battery gasses may be present during charging. Be certain there is sufficient ventilation to release the gasses.
4 Avoid direct sunlight and do not install in locations where water can enter the controller. Loose power connections and/or corroded wires may result in resistive connections that melt wire insulation, burn surrounding materials, or even cause fire. Ensure tight connections and use cable clamps to secure cables and prevent them from swaying in mobile applications. Use with Gel, Sealed or Flooded batteries only. Battery connection may be wired to one battery or a bank of batteries. The following instructions refer to a singular battery, but it is implied that the battery connection can be made to either one battery or a group of batteries in a battery bank. Select the system cables according to 3A/mm2 current density 3.2 Mounting NOTE: When mounting the controller, ensure free air through the controller heat sink fins. There should be at least 6 inches (150 mm) of clearance above and below the controller to allow for cooling. If mounted in an enclosure, ventilation is highly recommended. WARNING: Risk of explosion! Never install the controller in a sealed enclose with flooded batteries! Do not install in a confined area where battery gassed can accumulate. Step 1: Choose Mounting Location Locate the controller on a vertical surface protected from direct sun, high temperature, and water. And make sure good ventilation. Step 2: Check for clearance Place the controller in the location where it will be mounted. Verify that there is sufficient room to run wires and that there is sufficient room above and below the controller for air flow. 150mm(5.9inche)s 150mm(5.9inche) Warm air Cool air Step 3: Mark Holes Use a pencil or pen to mark the four (4) mounting hole locations on the mounting surface. Step 4: Drill Holes Remove the controller and drill 4.5mm holes in the marked locations. Step 5: Secure Controller Place the controller on the surface and align the mounting holes with the drilled holes in step 4. Secure the controller in place using the mounting screws. 3.3 Wiring NOTE: A recommended connection order has been provided for maximum safety during
5 installation. NOTE: The controller is a common positive ground controller. CAUTION: Don t connect the loads with surge power exceeding the ratings of the controller. CAUTION: For mobile applications, be sure to secure all wiring. Use cable clamps to prevent cables from swaying when the vehicle is in motion. Unsecured cables create loose and resistive connections which may lead to excessive heating and/or fire. Step1: Battery Wiring WARNING: Risk of explosion or fire! Never short circuit battery positive (+) and negative (-) or cables. Before battery is connected, make sure that battery voltage is greater than 6V so as to start up the controller. If system is 24V, make sure battery voltage is not less than 18V. System voltage can only be automatically recognized when controller start up for the first time. When install fuse, make sure that the biggest distance between the fuse holder and the positive terminal of battery is 150mm.Do not insert a fuse at this time. Step 2: Load Wiring The controller loads can be connected to such electrical equipments as lights, pumps, motors and others. Controller offers power to loads through the battery voltage. Connect the positive (+) and negative (-) of loads to controller load terminals. An in-line fuse holder should be wired in series in the load positive (+) or negative (-) wire as show in Figure 3-3. Do not insert a fuse at this time. If wiring the load connection to a load distribution panel, each load circuit should be fused separately. The total load draw should not exceed the load rated current of controller. Step 3: Solar wiring WARNING: Risk of electric shock! Exercise caution when handling solar wiring. The solar module(s) high voltage output can cause severe shock or injury. Cover the solar module(s) from the sun before installing solar wiring. The controller can accept12v, 24V nominal off-grid solar module(s). Grid-tie solar module(s) may be used if the open circuit voltage of solar module doesn t exceed the Maximum PV input voltage of the controller. The solar module(s) work voltage must be equal to or greater than the system voltage. Step 4: Confirm Wiring Double-check the wiring in step1 through 3. Confirm correct polarity at each connection. Verify that all six terminals are tightened.
6 Step 5: Install Fuse Install a suitable fuse in each fuse holder in the following order : 1. Battery circuit 2. Load circuit Step 6: Confirm power on When battery power is applied and the controller starts up, the battery LED indicator will be green. If the controller doesn't start up, or the battery status LED error exists, please refer to section 5 for troubleshooting. 4 Operation 4.1 PWM Technology (Series Pulse Width Modulation) The controller adopts the advanced series pulse width modulation. With range of 0-100%, it can charge the battery quickly and stably under any condition of solar photovoltaic system. The operating principle of PWM charging mode is as follows: The battery is firstly charged with pulse current and recharged after it stops charging for a while. It is repeated in this way for several times till the battery is fully charged. Intermissions allow some oxygen and hydrogen generated by chemical reaction can be chemically combined again and then absorbed, which can eliminate concentration polarization and ohm polarization naturally, and reduce the internal pressure of the battery. Consequently, it makes next charging smooth and the more power is charged to the battery. Intermittent pulse current charging mode makes battery have more time to react, which reduces the gassing volume and makes battery improve the acceptance rate of charging current. 4.2 Battery Charging Information Bulk Charge In this stage, the battery voltage has not yet reached boost voltage and 100% of available solar power is used to charge the battery. Boost Charge When the battery has recharged to the Boost voltage setpoint, constant-voltage regulation is used to prevent heating and excessive battery gassing.the Boost stage remains 120 minutes and then goes to Float Charge. Float Charge After the battery is fully charged in Boost voltage stage, the controller reduces the battery voltage to Float voltage set point. When the battery is fully recharged, there will be no more chemical reactions and all the charge current transmits into heat and gas at this time. Then the controller reduces the voltage to the floating stage, charging with a smaller voltage and current. It will reduce the temperature of battery and prevent the gassing, also charging the battery slightly at the same time. The purpose of Float stage is to offset the power consumption caused by self consumption and small loads in the whole system, while maintaining full battery storage capacity. In Float stage, loads can continue to draw power from the battery. In the event that the system load(s) exceed the solar charge current, the controller will no longer be able to maintain the battery
7 at the Float setpoint. Should the battery voltage remains below the Boost setpoint, the controller will exit Float stage and return to Bulk charge. Equalize Charge WARNING: Risk of explosion! Equalizing flooded battery can produce explosive gases, so well ventilation of battery box is necessary. NOTE: Equipment damage! Equalization may increase battery voltage to the level damaging to sensitive DC loads. Ensure that all load allowable input voltages are greater than the equalizing charging set point voltage. NOTE: Equipment damage! Over-charging and excessive gas precipitation may damage the battery plates and activate material shedding on them. Too high an equalizing charge or for too long may cause damage. Please carefully review the specific requirements of the battery used in the system. Certain types of batteries benefit from periodic equalizing charge, which can stir the electrolyte, balance battery voltage and complete chemical reaction. Equalizing charge increases the battery voltage, higher than the standard complement voltage, which gasifies the battery electrolyte. If the battery is being over discharged, the solar controller will automatically turn to equalize charging stage, and the equalize stage remain 120mins. Equalize charge and boost charge are not carried out constantly in a full charge process to avoid too much gas precipitation or overheating of battery. 4.3 LED Indicators Charging Status LED indicator Battery Status LED indicator Figure 4-2 LED indicators Charging status indicator GREEN ON when charging normal, GREEN FLASHING when solar modul low power. Please refer to section 5 for troubleshooting. Charging Status LED indicator Table 4-1 Color Indicator Charging Status Green On Solid Normal Green Flashing Low power Battery status indicator GREEN FLASHING whenever sunlight is available for battery charging GREEN ON when battery full RED ON when battery under voltage
8 RED FLASHING when battery over discharged Please refer to section 5 for troubleshooting. Battery status LED indicator Table 4-2 Color Indicator Battery Status Green Flashing Charging Green On solid Full Red On solid Under voltage Red Flashing Over discharged Load status indicator: RED ON when load output normal RED FALSHING when the load amp is 1.25times of rated current for 60 seconds, or the load amp is 1.5 times of rated current for 5 seconds (overload); or load amp is more than 3.5 times of rated current(short Circuit). Please refer to section 5 for trouble shooting. Load status LED indicator Table 4-3 Color Indicator Load status Red On Solid Normal Red Flashing Overload or short circuit 4.4 Setting Operation. Load Control Settings 1. Dusk to Dawn When solar module voltage goes below the point of NTTV (Night Time Threshold Voltage) at sunset, the controller will recognize the starting voltage and turn on the load after 10 minutes delay. When solar module voltage goes above point of DTTV (Day Time Threshold Voltage), the solar controller will recognize the starting voltage and turn off the load after 10 minutes delay. 2. Light ON + Timer When solar module voltage goes below the point of NTTV (Night Time Threshold Voltage) at sunset; the solar controller will recognize the starting voltage and turn on the load after 10 minutes delay. The load will be on for several hours which users set through LED digital tube. The controller has dual timer function. Please refer to table 4-5 Load Work Mode Settingǁ. 3. Test mode This mode is the same as Dusk to Dawn. But there is no 10 minutes delay when controller recognizes the starting voltage. When below the starting voltage, the controller will turn on the load, if higher, it will turn off load. The test mode makes it easy to check the system installation. 4. ON/OFF mode This mode is to turn ON and OFF the load by manual.
9 Load Work Mode Setting Work mode led digital tube display: When the led digital tube is not display, Press the setting button "MODE" more than 5 seconds, and keep on press it once more,led digital tube will be changed once among 0 b1 J0 S5 F0 H0 q0 8.8.,its means Load work mode Battery type Load start-up delay Optical sensitivity Float charging voltage Low voltage reconnect voltage Low voltage disconnect voltage Restore factory Settings. Setting operation: Press the setting button "MODE" more than 5 secondsand setting indicators will be changed once among 0 b1 J0 S0 F0 H0 q When you want to change`s setting indicator is on, press the setting button for more than 5 seconds till the LED digital tube flashes. Then press the setting button till the desired number appears according to the following table. The setting is finished when the digital tube stop flashing. work mode Table 4-5 Led Ranges Function Describe Load work mode b1 b1-b3 Battery type J0 J0-J9 Load start-up delay Default 0= Dusk to Dawn 1-15= Light ON + Timer 16= ON/OFF mode 17= Test mode Default DefaulB1= Sealed lead acid battery B2= Flooded battery B3= Gel battery Default J0 10min J1=increase 10min J9=increase 90min S5 S0-S9 Optical sensitivity Default S5(5v load on,6v load off) S4=all reduce 0.2V 4.8V load on,5.8v load off S6=all increase 0.2V 5.2V load on,6.2v load off F0 F0 - F9 F0. - F9. Float charging voltage Default F0(13.8V) F1= increase 0.1V F9= increase 0.9V F1.= reduce 0.1V
10 F9.= reduce 0.9V H0 H0 -H9 H0. -H9. Low voltage reconnect voltage Default H0(12.6V) H1=increase 0.1V H9=increase 0.9V H1.=reduce 0.1V H9.=reduce 0.9V q0 q0 -q9 q0. -q9. Low voltage disconnect voltage Default q0(11.1v) q1= increase 0.1V q9= increase 0.9V q1.= reduce 0.1V q9.= reduce 0.9V Restore factory Settings Restore factory Settings Load work mode 0 Table 4-6 Describe LED digital No. Dusk to Dawn, Load will be on all night 0 Load will be on for 1 hour after ten minutes delay since sunset 1 Load will be on for 2 hours after ten minutes delay since sunset 2 Load will be on for 3 hours after ten minutes delay since sunset 3 Load will be on for 4 hours after ten minutes delay since sunset 4 Load will be on for 5 hours after ten minutes delay since sunset 5 Load will be on for 6 hours after ten minutes delay since sunset 6 Load will be on for 7 hours after ten minutes delay since sunset 7 Load will be on for 8 hours after ten minutes delay since sunset 8 Load will be on for 9 hours after ten minutes delay since sunset 9 Load will be on for 10 hours after ten minutes delay since sunset 10 Load will be on for 11 hours after ten minutes delay since sunset 11 Load will be on for 12 hours after ten minutes delay since sunset 12 Load will be on for 13hours after ten minutes delay since sunset 13
11 Load will be on for 14 hours after ten minutes delay since sunset 14 Load will be on for 15 hours after ten minutes delay since sunset 15 ON/OFF mode 16 TEXT mode 17 5 Protection, Troubleshooting and Maintenance 5.1 Protection PV Array Short Circuit If PV array short circuit occurs, clear it to resume normal operation. Load Overload If the load current exceeds the maximum load current rating, the controller will disconnect the load. The greater the overload, the faster the load will be disconnected. A small overload could take a few minutes to disconnect. Overloading must be cleared up through reapply power or pressing the setting button. Load Short Circuit Fully protected against load wiring short-circuit. After one automatic load reconnect attempt, the fault must be cleared by reapply power or pressing the setting button. PV Reverse Polarity Fully protection against PV reverse polarity, no damage to the controller will result. Correct the miswire to resume normal operation. Battery Reverse Polarity Fully protection against battery reverse polarity, no damage to the controller will result. Correct the miswire to resume normal operation. Damaged Local Temperature Sensor If the temperature sensor short-circuited or damaged, the controller will be charging or discharging at the default temperature 25 to prevent the battery damaged from overcharging or over discharged. Overheating Protection If the temperature of the controller heat sink exceeds 85 C, the controller will automatically start the overheating protection. 5.2 Troubleshooting Trouble Shooting Table 5-1 Faults Possible reasons Troubleshooting Charging LED indicator off during daytime when sunshine falls on PV modules properly. PV array disconnection Check that PV and battery wire connections are correct and tight.
12 Battery LED indicators are RED Battery LED indicators RED color flashing and loads not working. Red Load LED indicator flashing Battery under voltage Battery over discharged Over load or short circuit Load output is normal,, charging LED indicator will return to green automatically when fully charged. The controller cut off the output automatically, LED indicator will return to green automatically when fully charged. Overload: Please reduce the load and press the button once, the controller will clear it; Short circuit: please press the button, the controller will resume to work. Notes: No LED indicator. Measure battery voltage with multimeter. Min.6V can start up the controller. Notes: No charging status LED indicator with normal connection. Measure the input voltage of solar module, the input voltage must be higher than battery voltage! 5.3 Maintenance The following inspections and maintenance tasks are recommended at least two times per year for best controller performance. Check that the controller is securely mounted in a clean and dry environment. Check that the air flow and ventilation around the controller is not blocked. Clear all dirt or fragments on the heat sink. Check all the naked wires to make sure insulation is not damaged for serious solarization, frictional wear, dryness, insects or rats etc. Maintain or replace the wires if necessary. Tighten all the terminals. Inspect for loose, broken, or burnt wire connections. Check and confirm that LED digital tube is consistent with required. Pay attention to any troubleshooting or error indication.take necessary corrective action. Confirm that all the system components are ground connected tightly and correctly. Confirm that all the terminals have no corrosion, insulation damaged, high temperature or burnt/discolored sign, tighten terminal screws to the suggested torque. Inspect for dirt, insects and corrosion, and clear up. Check and confirm that lightning arrester is in good condition. Replace a new one in time to avoid damaging of the controller and even other equipments. 6 Warranty
13 The LandStar charge controller is warranted to be free from defects for a period of ONE (1) years from the date of shipment to the original end user. We will, at its option, repair or replace any such defective products. Claim procedure: Before requesting warranty service, check the Operation Manual to be certain that there is a problem with the controller. Return the defective product to us with shipping charges prepaid if problem cannot be solved. Provide proof of date and place of purchase. To obtain rapid service under this warranty, the returned products must include the model, serial number and detailed reason for the failure, the module type and size, type of batteries and system loads. This information is critical to a rapid disposition of your warranty claim. his warranty does not apply under the following conditions: 1. Damage by accident, negligence, abuse or improper use. 2. PV or load current exceeding the ratings of product. 3. Unauthorized product modification or attempted repair 4. Damaged occurring during shipment. 5. Damage results from acts of nature such as lightning, weather extremes 6. Irreclaimable mechanical damage. 7 Technical specifications Electrical Parameters Table 7-1 Description Parameter Nominal System Voltage 12 / 24VDC Auto work Battery Voltage Range 6-36V Rated Battery Current S10I 10A S20I 20A S30I 30A Charge Circuit Voltage Drop 0.26V Discharge Circuit Voltage 0.15V Drop Self-consumption 6mA Thresh old Voltage Parameters Table7-2 Description NTTV (Night Time Threshold Voltage) DTTV (Day Time Threshold Voltage) Parameter 5V; x2/24v 6V; x2/24v Temperature Compensation Coefficient Table7-3 Description Parameter Temperature Compensation -25mV/ /12V(25 ref) Coefficient(TEMPCO)*
14 * Compensation of equalize, boost, float and boost reconnect voltage
15 YSMART TECHNOLOGY CO.,LTD website:www.ysmart-tech.com Phone: Battery Voltage Parameters (temperature at 25 ) Table 7-4 Charging Parameters Battery charging setting Sealed Flooded Gel Over Voltage Disconnect Voltage 15.5V; x2/24v Charging Limit Voltage 15.0V;x2/24V Equalize Charging Voltage 14.6V; 2/24V 14.8V; 2/24V 14.4V; 2/24V Boost Charging Voltage 14.4V; 2/24V 14.6V; 2/24V 14.2V; 2/24V Float Charging Voltage Boost Reconnect Charging Voltage 13.8V;x2/24V 13.2V;x2/24V Low Voltage Reconnect Voltage Under voltage warning reconnect voltage 12.6V;x2/24V 12.2V;x2/24V Under Voltage Warning Voltage 12V; x2/24v Add:No. 30 XinFeng Road,Potoubei Village,Ailian Town,Longgang Dist,Shenzhen 51872,P.R. China
16 YSMART TECHNOLOGY CO.,LTD website:www.ysmart-tech.com Phone: Low Voltage Disconnect Voltage Discharging Limit Voltage Equalize duration 11.1V;x2/24V 10.8V;x2/24V 60min Boost duration 60min Environmental parameters Table 7-5 Environmental parameters Parameter Working temperature -35 to +55 Storage temperature -35 to +80 Humidity 10%-90% NC Enclosure IP30 S10I/S20I/S30I Mechanical parameters Table 7-6 Mechanical Parameter Parameter Overall dimension 133(5.24)x70(2.75)x34(1.34) mm/inches Mounting dimension 126(4.96) x 50(1.97) mm/inches Mounting hole size Φ4.5 Terminal 6mm2 Net weight 0.15kg Final interpretation right of the manual belongs to our company. Any changes without prior notice! Add:No. 30 XinFeng Road,Potoubei Village,Ailian Town,Longgang Dist,Shenzhen 51872,P.R. China
Tracer-1206RN / 1210RN / 1215RN Maximum Power Point Tracking Solar Charge Controller INSTRUCTION MANUAL Thank you very much for selecting our product! This manual offers important information and suggestions
EPSOLAR Utility model patent NO. 201120064092.1 Tracer-2210RN / 2215RN Maximum Power Point Tracking Solar Charge Controller INSTRUCTION MANUAL Thank you very much for selecting our product! This manual
EPSOLAR LS1024B / LS2024B/ LS3024B Solar Charge Controller USER MANUAL Thank you very much for selecting our product! This manual offers important information and suggestions with respect to installation,
View Star series Solar Charge Controller INSTRUCTION MANUAL Thank you very much for selecting our product! This manual offers important information and suggestions with respect to installation, use and
EPsolar itracer Series Maximum Power Point Tracking Solar Charge Controller OPERATION MANUAL Thank you very much for selecting our product! This manual offers important information and suggestion about
12 Volt 30 Amp Digital Solar Charge Controller User s Manual WARNING Read carefully and understand all INSTRUCTIONS before operating. Failure to follow the safety rules and other basic safety precautions
MASSPOWER MPPT Solar charge controller Installation and Operation Manual Block 5, Lingyun Industrial Park, No.1177,Lingyun Road, Ningbo National Hi-Tech Zone Ningbo,zhejiang,China. Post:315000 TEL:+86-574-86699988
12 Volt 30 Amp Digital Solar Charge Controller Installation & Operation Manual This 30Amp charge controller is designed to protect your 12Volt Lead-acid or Gel-cell battery from being overcharge by solar
Wind/Solar Hybrid Street Light Controller User Manual Model: HY-WSC04-12AWM, HY-WSC04-12/24AWM, HY-WSC06-24AWM, HY-WSC06-48AWM 1. Product Introduction The wind/solar hybrid street light controller is an
EPsolar etracer series Network Maximum Power Point Tracking Solar Charge Controller OPERATION MANUAL Models: ET2415N ET3415N ET4415N ET6415N Thank you very much for selecting our product! This manual offers
Manual for Fire Suppression & Methane Detection System Fogmaker North America Post address: 150 Gordon Dr Exton, PA 19341 Delivery address: 150 Gordon Dr Exton, PA 19341 Tel: 610-265-3610 Fax: 610-265-8327
Charge Regulator SCR 12 Marine Manual Many thanks for purchasing a superwind product. The SCR 12 Marine is a charge regulator of highest quality and will perfectly and reliably charge your batteries for
BRAVER UPS (Uninterruptible Power System) User s Manual Safety CAUTION! This UPS utilizes voltages that may be hazardous. Do not attempt to disassemble the unit. The unit contains no user replaceable parts.
REMOTE METER TM Installation and Operation Manual. Digital Remote Meter for Monitoring System Performance. Version: RM-1 1098 Washington Crossing Road Washington Crossing, PA 18977 USA www.morningstarcorp.com
User s Manual AURORA 1.2K/2.2K Uninterruptible Power System Safety CAUTION This UPS utilizes voltages that may be hazardous. Do not attempt to disassemble the unit. The unit contains no user serviceable
USER S MANUAL MaxPower 400-600 UPS Uninterruptible Power System 28-2MAXPO0018 IMPORTANT SAFETY INSTRUCTIONS SAVE THESE INSTRUCTIONS This manual contains important instructions for models MaxPower 400 and
YSmart Technology Co.,Ltd GWV Series Grid Tie Microinverter User Manual The copyright of this user manual belong to YSmart TechnologyCompany Limited. Without the written permission of the copyright holder,
EN Manual Solar Fountain Mobile Phone Charger Copyrights 2008 Victron Energy B.V. All Rights Reserved This publication or parts thereof may not be reproduced in any form, by any method, for any purpose.
Solar Home System User Manual AEHSHS0110W2L Solar Home System 2 Lamps All rights reserved Specifications subject to change without prior notice 2 Dear Customer, Thank you for purchasing Schneider Electric
SOLAR ELECTRIC MODULE ES-124 & ES-62T Owners Manual and Installation Guide circuit. Reverse connection will damage the module and may result in fire. CAUTIONS Solar electric modules produce DC electricity
Digital echo-charge Owner s Manual Xantrex Digital echo-charge Battery Charger Thank you for purchasing a Xantrex Digital echo-charge. Xantrex Technology Inc. takes pride in manufacturing quality products
Solar Controller / Battery Charger User s Manual 1 Congratulations! You have made an excellent choice by purchasing this high quality KORR PWM solar controller which has been manufactured to the highest
Solar charger controller User s Manual Contents Important safety instructions... 6 1. Product description... 8 1.1 General description... 8 1.2 Features... 8 1.3 Maximum setpoint voltage limit... 8 1.4
543-0032-00, 943-0032-00 User s Manual 1 Comfort Alert Diagnostics Faster Service And Improved Accuracy The Comfort Alert diagnostics module is a breakthrough innovation for troubleshooting heat pump and
MANUAL CONGRATULATIONS on the purchase of your new CTEK professional battery management unit. This unit is part of a range of professional battery chargers from CTEK SWEDEN AB. It represents the latest
WITH TWO BATTERY CHARGING EPSOLAR s duo-battery charging solar controller, For RVs, Caravans,and boats. Adjust options: 1. Battery type selection. 2. Two battery charging priority(from 0-100%) 3. Charging
Battery Power Inverters Renogy 500W 1000W 2000W Pure Sine Wave Inverter Manual 2775 E. Philadelphia St., Ontario, CA 91761 1-800-330-8678 1 Version 1.1 Important Safety Instructions Please save these instructions.
Intelligent Solar Charge Controller Solar30 User s Manual Please read this instruction carefully before using it. SOLAR30 12V/24V AUTO WORK 1 Product introduction This controller is a kind of intelligent
AGS Owner's Manual Xantrex Automatic Generator Start Control System TABLE OF CONTENTS INTRODUCTION...3 Main Features...3 Safety Summary...3 THINGS YOU SHOULD KNOW...4 THEORY OF OPERATION...5 System...5
( 5A, 12V/24V Output, Double Mode ) 1. Introduction: This controller is suitable for 12V and 24V solar photovoltaic system. The charge and discharge current is 5A. The maximum solar panel for 12V system
Mobile Data Power Model: MDP-25 Topic Section Features... 2 Operational Features Summary... 2 Back-up Battery Power Internal Charger Voltage Spike Protection RF Noise Filtering Warning of Imminent Loss
Engineering Production Sales LEAD CRYSTAL Valve-regulated lead-crystal batteries Energy storage Cells User Manual www.axcom-battery-technology.de info@.axcom-battery-technology.de Chapter 1: 1. Introduction
LESTRONIC DV AUTOMATIC 12 OR 2 VOLT DUAL OUTPUT DUAL MODE BATTERY CHARGER MODEL 16350 TYPE 12/2EL0-10ET PLEASE SAVE THESE IMPORTANT SAFETY AND OPERATING INSTRUCTIONS For correct operation of the equipment,
Extended warranties are available for purchase at www.progressivedyn.com Installation and Operation Guide for PD4000 Series Power Control Center Member Thank you for selecting Progressive Dynamics as your
powered by Portable Solar Kits Owner s Manual Veuillez visiter gpelectric.com pour la version française de ce manuel de l utilisateur Visite gpelectric.com para la versión en español de este manual del
B Installation & Maintenance Instructions MM-414 Series 150E and 157E Low Water Cut-Off/Pump Controllers For Steam Boilers and Other Level Control Applications A Typical Applications: Primary or secondary
MODE ALARM Portable Air Conditioner OWNER S MANUAL Read these instructions before use 8 Model: MF08CESWW Voltage rating: 115V~60Hz Power rating : 800W Customer Support : 1-800-474-2147 For product inquiries
MX MANUAL CONGRATULATIONS to the purchase of your new professional switch mode battery charger. This charger is included in a series of professional chargers from CTEK SWEDEN AB and represents the latest
IMPORTANT! - YOU'RE SOLAR READY SOLAR POWER - THE NEW WAY TO RV! Your RV is PRE-WIRED for SOLAR POWER! Benefits of Solar Zamp Solar Portable Solar Kit Maximize Battery Life Electrical Independence Green,
TECHNICAL DATA & SERVICE MANUAL INDOOR UNIT: AW52AL AW64AL SPLIT SYSTEM AIR CONDITIONER Model No. Product Code No. AW52AL 387030095 AW64AL 387030096 0.8180.463.0 07/05 IMPORTANT! Please read before installation
WARNING: This Unit employs Components that tend to produce arcs or sparks To prevent fire or explosion, do not install in compartments containing batteries or flammable materials - SHOCK HAZARD. DO NOT
FILE: IM_091-120-12E-20 Rev A., 05-06-08 INSTRUCTION MANUAL AUTO CHARGE 3 STEP AUTOMATIC BATTERY CHARGER R MODEL #091-120-12E-20 for ODYSSEY AGM BATTERIES CAUTION This charger is calibrated to the ODYSSEY
ATLAS DC solar home system Model: CSFDC-20-1218B1 CSFDC-30-1224B1/CSFDC-30-1224B2 CSFDC-50-1233B1/CSFDC-50-1233B2 2 3 WARNING To ensure that you use the system correctly and safely, please read the following
Wind/solar hybrid controller Key Features: 1. U.S. imports of products based on expert-level micro controller and dedicated control software; 2. With battery overcharge over discharge reverse protection;tan
ADI 9510-B Advantium 2 Plus Alarm INSTALLATION AND OPERATING INSTRUCTIONS Carefully Read These Instructions Before Operating Carefully Read These Controls Corporation of America 1501 Harpers Road Virginia
BB800 Off-Grid Solar System KEY PRODUCT FEATURES Control Box & Charge Controller 1000W of Solar Panels 4x200Ah of SLA Batteries in series 2KW Inverter Output Power Solar Panel & Battery Mounting Our entry
ALL WEATHER W-SERIES QUARTZ TUBE ELECTRIC INFRARED RADIANT HEATER TABLE OF CONTENTS: INSTALLATION USE & CARE MANUAL IMPORTANT INFORMATION Assembly Instructions 2 Wiring Instructions 2 Outdoor Installation
Single Phase Soft Starter Installation & Operating Manual 6/02 Table of Contents Section 1 General Information................................................... 1 1 General Description................................................
*00151* FEATURES Automatic taper of charge rate for superior battery life through good equalization of cells and low water use rate. Silicon diodes with inherent surge protection operated at a conservative
Builder MODEL 1010 Series Non-Programmable Single Stage Heat/Cool Thermostat USER MANUAL Compatible with low voltage single stage gas, oil or electric heating or cooling systems, including single stage
Instruction Sheet 07-2013 Installation Instructions for Alarm Module Kit A043F059 1 Introduction The information contained within is based on information available at the time of going to print. In line
Website: www.andico.com.au Service manual CAUTION - BEFORE SERVICING THE UNIT, READ THE SAFETY - PRECAUTIONS IN THIS MANUAL. - ONLY FOR AUTHORISED SERVICE PERSONNEL. MODELS: MPK1-09CR-QB8 MPK1-12ER-QB6
DONGGUAN SHENGYANG INDUSTRIAL CO., LTD SY WMVC Smart Grid Tie Microinverter User Manual Dongguan Shengyang Industrial Co., Ltd. ADD: No. 1 Shangxin Road, New Village, Xin An Community, Chang An Town, Dongguan
Revision Level: 01 Revision Date: 07/07/2011 Please read all instructions carefully to help ensure a correct and SAFE installation of your Second Wind Ultraviolet Germicidal Air Purifier. Failure to do
PRO370D 65A Mbus MID DIN rail three phase four wire energy meter User manual Version 1.03 1 Safety instructions... 3 2 Foreword... 4 3 CE certificates... 5 4 MID certificate... 7 5 Performance criteria...
BC-5000 BATTERY CAPACITY TESTER OPERATIONS MANUAL COFKO LLC. COPYRIGHT 2010 1 UNPACKING As you unpack your new BC-5000 battery capacity tester, inspect the tester for signs of shipping damage. If shipping
EaglePicher Technologies, LLC Commercial Power P.O. Box 47 Joplin, MO 6482 (417) 623-8 email@example.com Carefree Sealed Lead Acid (SLA) MSDS EaglePicher s Carefree lead acid batteries are
Series 510 Submersible Level Transmitters The Series 510 Submersible Level Transmitters are solid state instruments designed for direct submergence into many types of liquid for quick, accurate and reliable
RV Battery Savvy To properly maintain and extend the life of your RV batteries you need to have a basic understanding of what a battery is and how it works. Batteries used in RVs are lead acid batteries.
PSDC 08128 v.1.2 PSDC 12V/8A/8x1A Power supply for up to 8 analog cameras PTC/TOPIC. EN** Edition: 9 from 25.05.2015 Supersedes the edition: 8 from 12.12.2014 the 8x 1A/12V DC power output for powering
30W SOLAR CHARGING STATION USER MANUAL & PRODUCT SPECIFICATIONS Model: SDP-Y-30W Thank you for choosing the Solarland Solar charging station. Please read this manual carefully before setting up and using
Oil and Coolant Circulating Heating System Model - OCSM Installation & Operation Manual 216280-000 REV 2 Identifying Your System The HOTSTART heating system is designed to heat fluids for use in marine
SOLAR PANEL 12 & 24 VDC INSTRUCTIONS REIMANN & GEORGER CORPORATION MARINE PRODUCTS BUFFALO, NY P/N 6114200 08/15/14 1 SPECIFICATIONS 1.1 TECHNICAL DATA Model 4110020 3641357 Solar Panel Operating Voltage
DC Inline Watt Meter RENOGY 150A High Precision Watt Meter and Power Analyzer 0 2775 E. Philadelphia St., Ontario CA 91761 1-800-330-8678 Important Safety Instructions Please save these instructions. This
All about the Use & Care of your Iron Important Safeguards... 2 Iron Safety Instructions... 3 Parts and Features...4 TA B L E O F C O N T E N T S Using Your Iron...6 Cleaning and Maintenance... 8 Warranty...9
RI-215A Operator s Manual Part Number: 71-0045RK Revision 0 Released: 10/3/05 Warranty RKI Instruments, Inc., warrants gas alarm equipment sold by us to be free from defects in materials and workmanship,
TruPower-Portable-500W Solar Starter kit This Solar starter kit is an easy to use solar power supply system that is the complete solution for all your solar power needs. It is a solar generator that converts
Europasolar GmbH Uses sun energy and environmental awareness intelligence Solar Charger LR 122430 Mounting instruction Read instructions carefully! Cordial congratulation on the acquisition of this loading
SDX Submersible Depth Transmitter User Manual January 2011 USER INFORMATION Stevens makes no warranty as to the information furnished in these instructions and the reader assumes all risk in the use thereof.
7 Watt Solar Charger Solar Panel Owner s Manual Warning: Read carefully and understand all ASSEMBLY AND OPERATION INSTRUCTIONS before operating. Failure to follow the safety rules and other basic safety
Mini Power Bank and Charger Owner s Manual Please read before using this equipment. Your charger is ETL listed to UL standards and meets all applicable FCC standards. WARNING: To reduce the risk of fire
USER GUIDE TURBOCORD TM PORTABLE CHARGER 120V/240V: DUAL VOLTAGE AeroVironment EV Solutions 2013 AeroVironment, Inc. All rights reserved. AeroVironment, EV Solutions, and the AeroVironment logo are trademarks