1 Wind/solar hybrid controller Key Features: 1. U.S. imports of products based on expert-level micro controller and dedicated control software; 2. With battery overcharge over discharge reverse protection;tan fan with auto unloading auto brake manually brake speed detection over-speed protection; Load short-circuit protection overload protection;solar reverse polarity protection;all protection does not damage any parts 3. Solar and Wind use buck MPPT function,;with a float,constant voltage,current limiting charging function;wind speed and braking recovery time can be set and modified; 4. Batteries with precision temperature compensation; 5. All the control uses the industrial chip, in the cold, high temperature, damp environment to run freely. At the same time, use a crystal oscillator for timing control, timing control precision 6. Using the intuitive LED digital display, a key type operation can complete all settings, the setting time and nixie tube display digital is corresponding to each other, and show more intuitive 7. Fully waterproof, pure aluminum housing designed to increase awareness of environmental failure prevention, and to achieve good cooling effect, can effectively extend the service life of the controller
2 Controller panel Figure: System Description: This controller is designed for wind turbines and solar power DC power supply system,street lighting system design,and the use of special computer chip intelligent controller One-touch touch switches,complete all operations and settings Wind control with speed unloading constant voltage current limiting floating charge auto unloading auto brake function; Set the Fan speed detection method: Z:Set parameters; N:Rated speed fan/minute; D:Number of pole pairs; Z = (N*D)/60 Wind opportunity brakes several situations: 1. Battery is fully charged,stop charging protection; 2. Manual brake controller;
3 3. Wind speed protection brakes; Automatic release braking conditions to be met: 1. The battery voltage is lower than the charge return voltage; 2. Braking time has reached the brake Recovery Time; Solar control with reverse polarity protection,reverse charge protection,constant voltage limiting charge,floating charge,light control function; Load short-circuit protection overload protection; The LED indicator function definition: The wind charging indicator The solar charging indicator Light color system Light color system / No bright No charge / No bright No charge Charging Charging green Normally on green Normally on normally normally Battery is fully Red Normally on Brake status green 1/2Hz flash charged Battery status indicator Light color system Green 1/4Hz Flash Over-high Load indicator Green 1/2Hz flash Full Light color system Green Normally on Normal / No bright No output Yellow Normally on Lower Green Normally on Normal Red Normally on Too low Green 1/2Hz flash Output overload Red 1/2Hz flash Ultra-low Green 1/4Hz flash Output short
4 Installation Instructions: 1. Controller solidly fixed. L * W * H = 120 mm 93 mm 28 mm; 2. Wire preparation: It is recommended to use strands insulated copper wire. Firstly, make sure the length of the cord, secondly, ensure the installation location in the circumstances, thirdly, try to minimize the connection length to reduce power consumption. According to not more than 4A/mm² in accordance with the current density of selected cross-sectional area of copper wire, the controller side of the first strip 5mm of insulation should be shucked off. 3. Access to the battery connection terminals on the controller battery,note + - pole,do not reverse;if the connection is correct, Battery indicator should be lighted, according to buttons to check. Otherwise, need to check the connection. In case of reverse, will not burn any part of the insurance and damage any part of controller, fuse only as the end protection of a controller itself to protect the amount of internal short circuit damage 4. Connect the wire of load to the controller output, and pay attention to +, -, do not be reverse. Otherwise, it would burn appliances out 5. Photovoltaic cells wires is connected, first connect solar panels termination to the controller, and then the other end is connected to solar panels. Pay attention to +, -, do not be reverse. If it is a sunny day, charging indicator light should be bright. Otherwise, there is need to check the connection 6. Wind turbines wire connection,communication,regardless of the direction of wind turbines leads,free access to;
5 Special advising:charged controller,never happened solar terminals shorted,short-circuit operation! Buttons definition: Short Button: press the button for < 1.5s, like ; Long Button: press the button for > 1.5s, like ; LED digital display and setting mode relations correspond to set the table LED display Ten Bits 0 01 To To To To To 9 Working code ( Ten ) Time control mode Night lighting time Morning light time Delay time of turning on Wind speed setting Bits Wind speed setting Ten Working code ( Bits ) Normally open Light-off open + 1 To 12 hour delay Chen Liang open+ 0 To 270 Minute delay Range from 0 minutes to 27 minutes Corresponding from 1 to 9 Calculation ( Bits ) Multiplied by 24Hour Multiplied by 1Hour Multiplied by 30Minute Multiplied by Corresponding from 0 to 9 Multiplied by 1 3minutes Corresponding from 0 to 9 Multiplied by 10
6 6 0 To 9 Wind speed setting Hundred Corresponding from 0 to 9 Multiplied by To 9 Wind brake Time corresponding from 10 to 90 recovery time Minute Multiplied by 10Minute 8 A\h\L System voltage identification A:AUTO;h:Fixed 24V;L:Fixed 12V U. N. Relieve Wind manually brake Wind run Maintain N. C. Use Wind manually brake Wind brake Maintain H H Debug mode Manual Relieve of overload, short-circuit condition Common fault phenomena and processing methods: When the following phenomenon appeared, please according to the following method for inspection: phenomenon PV modules exposed to direct sunlight,the green charging light does not shine Under windy conditions,wind does not turn Load indicator flashes and no output Battery status indicator is red or flashing red,and no output Analysis Check the battery power of light across the wiring is correct,the connection is reliable; Please check whether the controller through the light manually or automatically brake; Output short circuit or overload,check the line and load for shorts;releasing a short circuit enters debug mode(hh),return to normal; Battery under voltage protection,forced off load output;the battery is fully charged automatically discharged after;
7 Technology index Model Double time model The system rated voltage AUTO 12V/24V Wind rated Power 12V300W/24V400W(A Model) 12V400W/24V600W(B Model) Wind speed setting range 0~999 Wind brake recovery time 10*N(1-9) Minute Wind speed setting method =((Wind rated speed/minute)*wind number of pole pairs)/(60/second) Solar rated charging Load output rated 10 Ampere current current 10 Ampere Over-load protection 1.25 rated current 30sec or 1.5 rated loads current 3 sec, overload protection 3 rated load current, short circuit protection No-load loss 25 ma Charging circuit voltage drop 0.15V Load circuit voltage drop 0.06V Work temperature Technical grade:-35 to +55 Over voltage protection 16.5V ; 2/24V;(keep working until drop to the point of Boost charge voltage action) Boost charge voltage 14.8V; 2/24V;(Immediately stop charge) (Only applied when over discharge appears) Full charge voltage 14.5V; 2/24V;(keep 10-min) Floating Charge voltage 14.2V; 2/24V; Charge return voltage 13.2V; 2/24V;(Interval time 10min) Over discharge return voltage 12.0V; x2/24v Lower voltage indicate 11.0V; x2/24v Over discharge voltage 10.5V; x2/24v Temperature compensation -4mV/ /2V Control mode The way of Buck MPPT Attention: If product instruction has the modification, Please forgive has not informed.
Protect B.PRO OPERATING INSTRUCTIONS Protect B. 750 PRO Protect B.1400 PRO Protect B.2300 PRO Protect B.1000 (BP) PRO Protect B.1800 (BP) PRO Protect B.3000 (BP) PRO 2 Thank you for purchasing the Protect
Automatic start of a generator General description This application note will help you to set your Xtender for an automatic start of a generator as per different parameters such as the output power, the
Instruction Manual 88 6//06 Veri-Flame Single Burner Monitoring System Model 5600 Version.2 Modulation Model No Purge Model Purge Model Copyright Disclaimer notice Copyright 2006 by Eclipse, Inc. All rights
AGS Owner's Manual Xantrex Automatic Generator Start Control System TABLE OF CONTENTS INTRODUCTION...3 Main Features...3 Safety Summary...3 THINGS YOU SHOULD KNOW...4 THEORY OF OPERATION...5 System...5
Instruction Manual 88 9/5/008 Eclipse Veri-Flame Single Burner Monitoring System Model 5600 Version Modulation Model No Purge Model Purge Model Co p y r i g h t Copyright 008 by Eclipse, Inc. All rights
BARNSTEAD THERMOLYNE CORPORATION Type F6000 Furnace OPERATION MANUAL AND PARTS LIST Series 1060 MODEL NUMBER VOLTAGE CONTROL DISPLAY ( C& F) RS232 COMM. F6010 220-240 Basic Automatic X ( C only) F6010-33
Installation and Operation Manual Environ TM Smart Thermostat 2 Copyright Enphase Energy Inc. 2010 141-00010 Rev 01 Contact Information Enphase Energy Inc. 201 1 St Street Petaluma, CA 94952 Phone: 707-763-4784
"Watt's Up" & "Doc Wattson" Watt Meter and Power Analyzer User's Manual Model WU100 v2 *** Please visit our website for the latest version of this manual *** Revision 1.7 9/1/2007 Notices Copyright Copyright
FILE. A10-022 Revised Sep. 2011 AIR CONDITIONER (MULTI TYPE) SERVICE MANUAL Air to Air Heat Exchanger with DX Coil Unit Model name: Model with a humidifier MMD-VNK502HEXE MMD-VNK802HEXE MMD-VNK1002HEXE
Electronic user s guide released subject to "Nokia User s Guides Terms and Conditions, 7th June, 1998" User s Guide NOKIA and the Arrows logo are registered trademark of Nokia Corporation, Finland. 1996
User Manual TABLE OF CONTENTS 1. BEFORE YOU BEGIN... 3 WHAT IS INCLUDED... 3 UNPACKING INSTRUCTIONS... 3 MANUAL CONVENTIONS... 3 ICONS... 3 SAFETY INSTRUCTIONS... 4 2. INTRODUCTION... 5 PRODUCT OVERVIEW...
AFG3000 Series Arbitrary/Function Generators Quick Start User Manual www.tektronix.com 07-63-0 Copyright Tektronix, Inc. All rights reserved. Tektronix products are covered by U.S. and foreign patents,
Model No. User Manual HD Visual Communication Unit KX-VC300/KX-VC600 Thank you for purchasing this Panasonic product. Please read this manual carefully before using this product and save this manual for
ComPar KIT 1 & 2 DMX LED light set with power outputs User manual Introduction Thank you for purchasing the Ayra ComPar Kit. You have either purchased the ComPar Kit 1 or ComPar Kit 2. This user manual
INDEX INTRODUCTION...1 CARE OF THE MANUAL...1 WARRANTY...1 GENERAL INFORMATION...2 END-OF-LIFE...2 SAFETY RULES...2 PRECAUTIONS FOR HANDLING AND USE OF REFRIGERANT FLUIDS...3 PRINCIPLES OF OPERATION...3
IP Power 9212 User Manual IP POWER 9212 USER MANUAL USER MANUAL IP POWER 9212 Version: V1.06 2006.02-1 - VER. X.X, Warning: any changes to this equipment without permission may cause damages to your equipment!
PROFESSIONAL WEATHER CENTER WS-1510-IT Instruction Manual Table of Contents Topic Page Features 2 Setting up 4 Function keys 7 LCD Screen 9 Manual Setting 10 Time alarm setting 13 Weather alarm operations