1 Tracer-1206RN / 1210RN / 1215RN Maximum Power Point Tracking Solar Charge Controller INSTRUCTION MANUAL Thank you very much for selecting our product! This manual offers important information and suggestions with respect to installation, use and troubleshooting, etc. Please read this manual carefully before using the product and pay attention to the safety recommendations in it.
2 Tracer-1206RN / 1210RN / 1215RN Maximum Power Point Tracking Solar Charge Controller Specification Summary System Voltage Rated Battery Current Rated Load Current Max. PV Input Voltage** Tracer-1206RN Tracer-1210RN Tracer-1215RN Max. PV Input Power 12V System 24V System 12 / 24VDC 10A 10A 60VDC 100VDC 150VDC 130W 260W **Array voltage should never exceed maximum PV input voltage. Refer to the solar module documentation to determine the highest expected array Voc (open circuit voltage) as defined by the lowest expected ambient temperature for the system location.
3 Contents 1 Important Safety Information General Information Overview Optional Accessories Installation Instructions General Installation Notes Mounting Wiring Operation MPPT Technology Battery Charging Information LED Indications Setting Operation Protections, Troubleshooting and Maintenance Protection Troubleshooting Maintenance Warranty Technical Specifications... 22
4 1 Important Safety Information Save These Instructions This manual contains important safety, installation and operating instructions for Tracer. The following symbols are used throughout this manual to indicate potentially dangerous conditions or mark important safety instructions,please take care when meeting these symbols. WARNING: Indicates a potentially dangerous condition. Use extreme caution when performing this task. CAUTION: Indicates a critical procedure for safe and proper operation of the controller. NOTE: Indicates a procedure or function that is important for the safe and proper operation of the controller. General Safety Information Read all of the instructions and cautions in the manual before beginning installation. There are no user serviceable parts inside the Tracer. Do not disassemble or attempt to repair the controller. Disconnect the solar module and fuse/breakers near to battery before installing or adjusting the Tracer. Install external fuses/breakers as required. Do not allow water to enter the controller. Confirm that power connections are tightened to avoid excessive heating from loose connection.
5 2 General Information 2.1 Overview Thank you for selecting the Tracer controller which represents advanced technology of our company. The features are listed below: 12V / 24V auto recognition. Advanced maximum power point tracking technology to optimize using the solar system. Peak conversion efficiency of 97 %, high Tracking efficiency of 99%. Very fast sweeping of the entire I-V curve, several seconds tracking speed. Widely used, automatic recognize day/night. Timer function with 1-15 hours option for street light. Unique dual timer function, enhance the flexibility of street light system. Sealed, Gel and Flooded battery option. Adopting temperature compensation and correcting the charging and discharging parameters automatically, improving the battery lifetime. Electronic protection: over charging, over discharging, overload, short circuit. Reverse protection: any combination of solar module and battery, without causing damage to any component. Excellent thermal design and nature air cooling. RJ45 interface with remote meter MT-5, convenient to check operating parameters of controllers. The Tracer series controller is for off-grid solar system and control the charging and discharging of the battery, especially suitable for the street light system. The controller features a smart tracking algorithm inside that maximizes the energy from the solar PV module(s) and charge the battery. At the same time, the low voltage disconnect function (LVD) will prevent the battery from over discharging. The Tracer controller charging process has been optimized for long battery life and improved system performance. The comprehensive self-diagnostics and electronic protection functions can prevent damage from installation mistakes or system faults. In addition, the Tracer controller has a RJ45 interface to allow communication with a meter for remote monitoring. Although the Tracer controller is very simple to configure and use, please take your time to read the operator's manual and become familiar with the controller. This will help you make full use of all the functions and improve your solar PV system.
6 The features of Tracer controller: Figure 2-1 Tracer Characteristics 1 Temperature Sensor Measure ambient temperature and make temperature compensation for charging and discharging. 2 Charging Status LED Indicator An LED indicator that shows charging status and overvoltage of battery. 3 Battery Status LED Indicator An LED indicator that shows battery status or system errors. 4 Setting Indicator Corresponding indicator will be on when set timer1, timer2 and battery type. 5 LED Digital Display Display the load work mode and status. 6 Setting Button (in manual mode used for load ON/OFF) Set load work mode and select battery type. 7 Solar Module Terminals Connect solar modules. 8 Battery Terminals Connect batteries. 9 Load Terminals Connect loads. 10 RJ45 Communication Interface Communicate with remote meter MT-5.
7 2.2 Optional Accessories Remote Meter (Model:MT-5) The digital remote meter displays system operating information, error indications, and self-diagnostics read-out. Information is displayed on a backlit LCD display. The large numerical display and icons are easy to read and large buttons make navigating the meter menus easy. The meter can be flush mounted in a wall or surface mounted using the mounting frame (included). The MT-5 is supplied with 2m of cable and a mounting frame. The MT-5 connects to the RJ45 port on the Tracer. 3 Installation Instructions 3.1 General Installation Notes Read through the entire installation section first before beginning installation. Be very careful when working with batteries. Wear eye protection. Have fresh water available to wash and clean any contact with battery acid. Uses insulated tools and avoid placing metal objects near the batteries. Explosive battery gasses may be present during charging. Be certain there is sufficient ventilation to release the gasses. Avoid direct sunlight and do not install in locations where water can enter the controller. Loose power connections and/or corroded wires may result in resistive connections that melt wire insulation, burn surrounding materials, or even cause fire. Ensure tight connections and use cable clamps to secure cables and prevent them from swaying in mobile applications. Use with Gel, Sealed or Flooded batteries only. Battery connection may be wired to one battery or a bank of batteries. The following instructions refer to a singular battery, but it is implied that the battery connection can be made to either one battery or a group of batteries in a battery bank. Select the system cables according to 3A/mm 2 current density. 3.2 Mounting NOTE: When mounting the Tracer, ensure free air through the controller heat sink fins. There should be at least 150mm of clearance above and below the controller to allow for cooling. If mounted in an enclosure, ventilation is highly recommended. WARNING: Risk of explosion! Never install the Tracer in a sealed enclose with flooded batteries! Do not install in a confined area where battery gas can accumulate.
8 Step 1: Choose Mounting Location Locate the Tracer on a vertical surface protected from direct sun, high temperature, and water. Step 2: Check for Clearance Place the Tracer in the location where it will be mounted. Verify that there is sufficient room to run wires and that there is sufficient room above and below the controller for air flow. 150mm Warm air 150mm Cool air Figure 3-1 Mounting and cooling Step 3: Mark Holes Use a pencil or pen to mark the four (4) mounting hole locations on the mounting surface. Step 4: Drill Holes Remove the controller and drill four sizeable holes in the marked locations. Step 5: Secure Controller Place the controller on the surface and align the mounting holes with the drilled holes in step 4. Secure the controller in place using the mounting screws. 3.3 Wiring NOTE: A recommended connection order has been provided for maximum safety during installation. NOTE: The Tracer is a negative ground controller. Any negative connection of solar module, battery or load can be earth grounded as required. Grounding is recommended.
9 CAUTION: Don t connect the loads with surge power exceeding the ratings of the controller. CAUTION: For mobile applications, be sure to secure all wiring. Use cable clamps to prevent cables from swaying when the vehicle is in motion. Unsecured cables create loose and resistive connections which may lead to excessive heating and/or fire. Step 1: Battery Wiring WARNING: Risk of explosion or fire! Never short circuit battery positive (+) and negative (-) or cables Figure 3-2 Battery wiring Before connecting the battery, measure the battery voltage. It must be over 9V to power the controller. For 24V, the voltage must be greater than 18V to properly detect a 24V battery. The 12/24V battery detection is automatic and the check is only performed at start-up. Wire an in-line fuse holder no more than 150mm from the battery positive terminal. Do not insert a fuse at this time. Confirm the connection correct and then turn on the power.
10 Step 2: Load Wiring The Tracer load output can connect DC electronic devices of which rated voltage is same as battery s. Tracer will provide battery voltage to the loads. See Section 4.4 Setting Operation for more details about the load control. Fuse Load Figure 3-3 Load wiring Connect load positive (+) and negative (-) to the Tracer load output as shown in figure 3-3. The load terminals may exist voltage, connect carefully to avoid short circuit. An in-line fuse holder should be wired in series in the load positive (+) or negative (-) wire as shown. Do not insert a fuse at this time. Confirm the connection correct and then turn on the power. If wiring the load connection to a load distribution panel, each load circuit should be fused separately. The total load draw should not exceed the 10A load rating. Step 3:Solar Module Wiring WARNING: Risk of electric shock! Exercise caution when handling solar wiring. The solar module(s) high voltage output can cause severe shock or injury. Cover the solar module(s) from the sun before installing solar wiring. The Tracer can accept 12V, 24V nominal off-grid solar module arrays. Grid tie solar module(s) may be used if the open circuit voltage does not exceed the maximum solar input rating. The solar module(s) nominal voltage must be equal to or greater than the nominal battery voltage.
11 Solar Module Figure3-4 Solar Module wiring Step 4: Accessories (option) Install Remote Meter (purchased separately) if required. Refer to the instructions provided for detailed installation procedures. Step 5: Confirm Wiring Double-check the wiring in step1 through 4. Confirm correct polarity at each connection. Verify that all six power terminals are tightened. Solar Module Fuse Fuse Battery Load Figure3-5 System Wiring review
12 Step 6: Confirm Power-up When battery power is applied and the Tracer powers up, the battery led indicator will be green. If the Tracer does not power up or battery status LEDs error exists, refer to Section 5 Troubleshooting 4 Operation 4.1 MPPT Technology The Tracer utilizes Maximum Power Point Tracking technology to extract maximum power from the solar module (s). The tracking algorithm is fully automatic and does not require user adjustment, Tracer technology will track the array maximum power point voltage (Vmp) as it varies with weather conditions, ensuring that maximum power is harvested from the array through the course of the day. Current Boost In many cases, Tracer MPPT technology will boost the solar charge current. For example, a system may have 8 Amps of solar current flowing into the Tracer and 10 Amps of charge current flowing out to the battery. The Tracer does not create current! Rest assured that the power into the Tracer is the same as the power out of the Tracer. Since power is the product of voltage and current (Volts Amps), the following is true*: (1) Power Into the Tracer =Power Out of the Tracer (2) Volts In Amps In=Volts Out Amps Out * Assuming 100% efficiency. Actually, the losses in wiring and conversion exist. If the solar module s Vmp is greater than the battery voltage, it follows that the battery current must be proportionally greater than the solar input current so that input and output power are balanced. The greater the difference between the maximum power voltage and battery voltage, the greater the current boost. Current boost can be substantial in systems where the solar array is of a higher nominal voltage than the battery.
13 An Advantage Over Traditional Controllers Traditional controllers connect the solar module directly to the battery when recharging. This requires that the solar module operate in a voltage range that is below the module s Vmp. In a 12V system for example, the battery voltage may range from 11-15Vdc but the module s Vmp is typically around 16 or 17V. Figure 4-1 shows a typical current VS. voltage output curve for a nominal 12V off-grid module. Current VS. Voltage in 12V system Typical Battery Voltage Range Maximum Power Point Output power in 12V system Traditional Controller Operating Range Tracer Maximum Power Point Figure 4-1 Nominal 12V Solar Module I-V curve and output power graph The array Vmp is the voltage where the product of current and voltage (Amps Volts) is greatest, which falls on the knee of the solar module I-V curve as shown in Figure4-1. Because Traditional controllers do not operate at the Vmp of the solar modules(s), energy is wasted that could otherwise be used to charge the battery and power system loads. The greater the difference between battery voltage and the Vmp of the module, the more energy is wasted. Tracer MPPT technology will always operate at the Vmp resulting in less wasted energy compared to traditional controllers. Conditions That Limits the Effectiveness of MPPT The Vmp of a solar module decreases as the temperature of the module increases. In very hot weather, the Vmp may be close or even less than battery voltage. In this situation, there will be very little or no MPPT gain compared to traditional controllers. However, systems with modules of higher nominal voltage than the battery bank will always have an array Vmp greater than battery voltage. Additionally, the savings in wiring due to reduced solar current make MPPT worthwhile even in hot climates.
14 4.2 Battery Charging Information Four Charging Stage The Tracer has a 4-stage battery charging algorithm for rapid, efficient, and safe battery charging. Figure 4-2 Tracer MPPT charging algorithm Bulk Charge In this stage, the battery voltage has not yet reached boost voltage and 100% of available solar power is used to recharge the battery. Boost Charge When the battery has recharged to the Boost voltage setpoint, constant-voltage regulation is used to prevent heating and excessive battery gassing. The Boost stage remains 120 minutes and then goes to Float Charge. Every time when the controller is powered on, if it detects neither over discharged nor overvoltage, the charging will enter into boost charging stage. Float Charge After the Boost voltage stage, Tracer will reduce the battery voltage to Float voltage setpoint. When the battery is fully recharged, there will be no more chemical reactions and all the charge current transmits into heat and gas at this time. Then the Tracer reduces the voltage to the floating stage, charging with a smaller voltage and current. It will reduce the temperature of battery and prevent the gassing, also charging the battery slightly at the same time. The purpose of Float stage is to offset the power consumption caused by self consumption and small loads in the whole system, while
15 maintaining full battery storage capacity. In Float stage, loads can continue to draw power from the battery. In the event that the system load(s) exceed the solar charge current, the controller will no longer be able to maintain the battery at the Float setpoint. Should the battery voltage remains below the boost reconnect charging voltage, the controller will exit Float stage and return to Bulk charging. Equalize WARNING: Risk of explosion! Equalizing flooded battery can produce explosive gases, so well ventilation of battery box is necessary NOTE: Equipment damage! Equalization may increase battery voltage to the level damaging to sensitive DC loads. Ensure that all load allowable input voltages are greater than the equalizing charging set point voltage. NOTE: Equipment damage! Over-charging and excessive gas precipitation may damage the battery plates and activate material shedding on them. Too high an equalizing charge or for too long may cause damage. Please carefully review the specific requirements of the battery used in the system. Certain types of batteries benefit from periodic equalizing charge, which can stir the electrolyte, balance battery voltage and complete chemical reaction. Equalizing charge increases the battery voltage, higher than the standard complement voltage, which gasifies the battery electrolyte. If it detects that the battery is being over discharged, the solar controller will automatically turn the battery to equalization charging stage, and the equalization charging will be 120mins. Equalizing charge and boost charge are not carried out constantly in a full charge process to avoid too much gas precipitation or overheating of battery.
16 4.3 LED Indications Charging Indicator Battery Indicator LED Digital Tube Figure 4-3 LED Indicators Charging Indicator The green LED indicator will light whenever sunlight is available for battery charging, the green charging LED will stay on in normal charging. The charging LED indicator flashes when battery over voltage. Please refer to Chapter 5 for troubleshooting. Charging LED indicator Table4-1 Color Indication Operating State Green On Solid Charging Green Flashing Battery over-voltage Battery Indicator GREEN ON when battery voltage in normal range GREEN FLASHING when battery full ORANGE ON when battery under voltage RED ON when battery over discharged Please refer to Chapter 5 for troubleshooting. Battery LED indicator Table 4-2 Color Indication Operating State Green On solid Normal (battery) Green Flashing Full (battery) Orange On solid Under voltage (battery) Red On solid Over discharged (battery)
17 PV Overvoltage indicators If the solar input open circuit voltage (Voc) exceeds the maximum rating, the array will remain disconnected until the Voc falls safely below the maximum rating. PV Overvoltage LED indicators Table 4-3 Color Indications Operating State Red LED digital tube displays P PV Overvoltage Load indicator When the load amp is 1.25times of rated current for 60 seconds, or the load amp is 1.5 times of rated current for 5 seconds (overload); or load short circuit, the Battery Indicator RED FLASHING. Please refer to section 5 for troubleshooting. Load LED indicator Table 4-4 Color Indication Load status Red battery indicator red flashing Overload or Short circuit 4.4 Setting Operation Dual Timer Function Light ON Light OFF Timer1 Number of hours Midnight Timer2 Number of hours Sunset Sunrise The default night length is 10 hours. The controller can learn the night length referring to the previous night so as to adapt to the different seasons. However, it will take some time to learn it. Notes: when the OFF time set at timer 2 is later than local sunrise time, the controller will turn off the load output at the sunrise time, which shows light control first!
18 Load Control Settings 1. Dusk to Dawn (Light ON + Light OFF) When solar module voltage goes below the point of NTTV (Night Time Threshold Voltage) at sunset, the solar controller will recognize the starting voltage and turn on the load after 10 minutes delay; When solar module voltage goes above point of DTTV (Day Time Threshold Voltage), the solar controller will recognize the starting voltage and turn off the load after 10 minutes delay. 2. Light ON + Timer (1-15h on) When solar module voltage goes below the point of NTTV (Night Time Threshold Voltage) at sunset; the solar controller will recognize the starting voltage and turn on the load after 10 minutes delay for several hours which users set on the timer. The timer setting operation is referred to as Load Work Mode Setting. 3. Test Mode It is used to test the system and the same as Dusk to Dawn. But there is no 10 minutes delay when controller recognizes the starting voltage. When below the starting voltage, the controller will turn on the load, if higher, it will turn off load. The test mode makes it easy to check the system installation. 4. Manual Mode This mode is to turn on/off the load by Setting Switch. Load Work Mode Setting Timer1 Setting indicator Figure 4-4 Instruction figure on setting Work mode LED digital tube Timer2 Setting indicator Battery type Setting Indicator Setting button Press the setting button once and setting indicators will be changed once among timer
19 1, timer2 and battery type. When timer 1 setting indicator is on, press the setting button for more than 5 seconds till the LED digital tube flashes. Then press the setting button till the desired number appears according to the following table. The setting is finished when the digital tube stop flashing. Timer 2 setting is the same as timer 1 when the setting indicator is on timer2. Load work mode Table 4-5 LED Timer1 Digital No. Disable n Dusk to Dawn, Load will be on all night 0 Load will be on for 1 hour after ten minutes delay since sunset 1 Load will be on for 2 hours after ten minutes delay since sunset 2 Load will be on for 3 hours after ten minutes delay since sunset 3 Load will be on for 4 hours after ten minutes delay since sunset 4 Load will be on for 5 hours after ten minutes delay since sunset 5 Load will be on for 6 hours after ten minutes delay since sunset 6 Load will be on for 7 hours after ten minutes delay since sunset 7 Load will be on for 8 hours after ten minutes delay since sunset 8 Load will be on for 9 hours after ten minutes delay since sunset 9 Load will be on for 10 hours after ten minutes delay since sunset 10 Load will be on for 11 hours after ten minutes delay since sunset 11 Load will be on for 12 hours after ten minutes delay since sunset 12 Load will be on for 13hours after ten minutes delay since sunset 13 Load will be on for 14 hours after ten minutes delay since sunset 14 Load will be on for 15 hours after ten minutes delay since sunset 15 Test mode 16 ON/OFF mode 17
20 Load work mode Table 4-6 Timer2 LED Digital No. Disable n Load will be on for 1 hour before sunrise 1 Load will be on for 2 hours before sunrise 2 Load will be on for 3 hours before sunrise 3 Load will be on for 4 hours before sunrise 4 Load will be on for 5 hours before sunrise 5 Load will be on for 6 hours before sunrise 6 Load will be on for 7 hours before sunrise 7 Load will be on for 8 hours before sunrise 8 Load will be on for 9 hours before sunrise 9 Load will be on for 10 hours before sunrise 10 Load will be on for 11 hours before sunrise 11 Load will be on for 12 hours before sunrise 12 Load will be on for 13hours before sunrise 13 Load will be on for 14 hours before sunrise 14 Load will be on for 15 hours before sunrise 15 Notes: If timer 1 is Dusk to Dawn( 0), Test mode (16) or ON/OFF mode (17), the timer 2 will be disabled(n). Battery Type Setting Press Setting Button and hold on 5 seconds when the LED is on battery type setting mode. The led will be flashing. Continue to press and the number will repeat from 1 to 3, and stop pressing until the desired number appears according to the following setting table: Battery type setting Table 4-7 Battery type Digital tube display Sealed lead acid battery 1 Gel battery 2 Flooded battery 3
21 5 Protections, Troubleshooting and Maintenance 5.1 Protection PV Array Short Circuit If PV array short circuit occurs, clear it to resume normal operation. PV Overvoltage If PV Overvoltage occurs, the array will remain disconnected until the voltage falls safely below the maximum rating. Load Overload If the load current exceeds the maximum load current rating, the controller will disconnect the load. Overloading must be cleared up through reapply power or pressing the setting button. Load Short Circuit Fully protected against load wiring short-circuit. After one automatic load reconnect attempt, the fault must be cleared by reapply power or pressing the setting button. PV Reverse Polarity Fully protection against PV reverse polarity, no damage to the controller will result. Correct the miswire to resume normal operation. Battery Reverse Polarity Fully protection against battery reverse polarity, no damage to the controller will result. Correct the miswire to resume normal operation. Damaged Local Temperature Sensor If the temperature sensor short-circuited or damaged, the controller will be charging or discharging at the default temperature 25 to prevent the battery damaged from overcharging or over discharged. High Voltage Transients PV is protected against high voltage transients. In lightning prone areas, additional external suppression is recommended.
22 5.2 Troubleshooting Trouble Shooting Table 5-1 Faults Possible reasons Troubleshooting PV array disconnection Charging LED indicator off during daytime when sunshine falls on PV modules properly. Green charging LED indicator flashing Battery LED indicator are orange Battery LED indicator RED color LED digital tube displays P Battery Indicator red flashing Battery voltage higher than over voltage disconnect voltage(ovd) Battery under voltage Battery over discharged PV Overvoltage Over load or short circuit Check that PV and battery wire connections are correct and tight. Check if battery voltage over high. Disconnect the solar module Load output is normal,, charging LED indicator will return to green automatically when fully charged. The controller cut off the output automatically, LED indicator will return to green automatically when fully charged. Check whether the PV parameters match with the controller s; It will be reconnected automatically until the voltage falls safely below the maximum rating. Overload: Please reduce the load and press the button once, the controller will resume to work after 3s; Short circuit: when the first short-circuit occurs, the controller will automatically resume to work after 10s; when a second short-circuit occurs, press the button, the controller will resume to work after 3s.
23 5.3 Maintenance The following inspections and maintenance tasks are recommended at least two times per year for best controller performance. Check that the controller is securely mounted in a clean and dry environment. Check that the air flow and ventilation around the controller is not blocked. Clear all dirt or fragments on the heat sink. Check all the naked wires to make sure insulation is not damaged for serious solarization, frictional wear, dryness, insects or rats etc. Maintain or replace the wires if necessary. Tighten all the terminals. Inspect for loose, broken, or burnt wire connections. Check and confirm that LED digital tube is consistent with required. Pay attention to any troubleshooting or error indication.take necessary corrective action. Confirm that all the system components are ground connected tightly and correctly. Confirm that all the terminals have no corrosion, insulation damaged, high temperature or burnt/discolored sign, tighten terminal screws to the suggested torque. Inspect for dirt, insects and corrosion, and clear up. Check and confirm that lightning arrester is in good condition. Replace a new one in time to avoid damaging of the controller and even other equipments. Warning:Risk of electric shock! Make sure all the power is turned off before above operations, and then follow the corresponding inspections and operations.
24 6 Warranty The Tracer charge controller is warranted to be free from defects for a period of TWO (2) years from the date of shipment to the original end user. We will, at its option, repair or replace any such defective products. Claim procedure: Before requesting warranty service, check the Operation Manual to be certain that there is a problem with the controller. Return the defective product to us with shipping charges prepaid if problem cannot be solved. Provide proof of date and place of purchase. To obtain rapid service under this warranty, the returned products must include the model, serial number and detailed reason for the failure, the module type and size, type of batteries and system loads. This information is critical to a rapid disposition of your warranty claim. This warranty does not apply under the following conditions: 1. Damage by accident, negligence, abuse or improper use. 2. PV or load current exceeding the ratings of product. 3. Unauthorized product modification or attempted repair 4. Damaged occurring during shipment. 5. Damage results from acts of nature such as lightning, weather extremes 6. Irreclaimable mechanical damage.
25 7 Technical Specifications Electrical Parameters Description Nominal System Voltage Rated Battery Current Maximum Battery Voltage Max. Solar Input Voltage Max. PV input power Self-consumption* Charge Circuit Voltage Drop Discharge Circuit Voltage Drop Parameter 12VDC / 24VDC Auto work 10A 32V Tracer-1206RN 60VDC Tracer-1210RN 100VDC Tracer-1215RN 150VDC 12V/ 130W 24V /260W <10mA(24V) 0.26V 0.15V Communication TTL232 / 8pin RJ45 * Charging & discharging circuit closed, LED digital tube OFF, remote meter MT-5 disconnected. Battery Parameters (Tem:25 ) Control Parameter Battery charging setting Gel Sealed Flooded High Volt Disconnect 16V; x2/24v 16V; x2/24v 16V; x2/24v Charging limit voltage 15.5V; x2/24v 15.5V; x2/24v 15.5V; x2/24v Over Voltage Reconnect 15V; x2/24v 15V; x2/24v 15V; x2/24v Equalization voltage 14.6V; x2/24v 14.8V; x2/24v Boost voltage 14.2V; x2/24v 14.4V; x2/24v 14.6V; x2/24v Float voltage 13.8V; x2/24v 13.8V; x2/24v 13.8V; x2/24v Boost return voltage 13.2V; x2/24v 13.2V; x2/24v 13.2V; x2/24v Low voltage reconnect 12.6V; x2/24v 12.6V; x2/24v 12.6V; x2/24v Under voltage recover 12.2V; x2/24v 12.2V; x2/24v 12.2V; x2/24v Under voltage warning 12V; x2/24v 12V; x2/24v 12V; x2/24v
26 Low voltage disconnect 11.1V; x2/24v 11.1V; x2/24v 11.1V; x2/24v Discharging limits voltage 10.8V; x2/24v 10.8V; x2/24v 10.8V; x2/24v Equalize duration 2hours 2hours Boost duration 2hours 2hours 2hours Threshold Voltage Description NTTV (Night Time Threshold Voltage) DTTV (Day Time Threshold Voltage) Parameter 5V; x2/24v 6V; x2/24v Temp compensation Description Parameter Temperature Compensation Coefficient(TEMPCO)* -30mV/ /12V(25 ref) * Compensation of equalize, boost, float and low voltage disconnect voltage. Environmental Parameters Environmental Parameter Ambient temperature range -35 to +55 Storage temperature range -35 to +80 Humidity range Enclosure Altitude 10%-90%(NC) IP m Mechanical Parameters Mechanical Dimension Parameter 156 x 97 x 68 / mm Mounting holes 147 x 60 / mm Mounting hole size Φ5 Terminal 4mm 2 Weight 0.55kg
27 PV Power Conversion Efficiency Curve Illumination Intensity: 1000W/m 2 Temperature: 25 C Tracer-1210RN: 1. Solar Module MPP Voltage(17V) / Nominal System Voltage(12V) 96,0% 95,5% 95,0% 94,5% 94,0% 93,5% 93,0% 92,5% 92,0% Solar Module MPP Voltage(34V) / Nominal System Voltage(12V) 95,0% 94,0% 93,0% 92,0% 91,0% 90,0%
28 3. Solar Module MPP Voltage(68V) / Nominal System Voltage(12V) 95,0% 93,0% 91,0% 89,0% 87,0% 85,0% 83,0% 81,0% Solar Module MPP Voltage(34V) / Nominal System Voltage(24V) 97,5% 97,0% 96,5% 96,0% 95,5% 95,0% 94,5% 94,0% 93,5%
29 5. Solar Module MPP Voltage(68V) / Nominal System Voltage(24V) 97,0% 96,0% 95,0% 94,0% 93,0% 92,0% 91,0% 90,0% 89,0% 88,0%
30 Tracer Dimensions (mm) Westech-Solar Energy GmbH Tel: Fax: Website:
EPSOLAR Utility model patent NO. 201120064092.1 Tracer-2210RN / 2215RN Maximum Power Point Tracking Solar Charge Controller INSTRUCTION MANUAL Thank you very much for selecting our product! This manual
S10I / S20I / S30I Solar Light Controller USER MANNUAL Thank you very much for selecting our product! This manual offers important information and suggestions with respect to installation, use and troubleshooting,
EPSOLAR LS1024B / LS2024B/ LS3024B Solar Charge Controller USER MANUAL Thank you very much for selecting our product! This manual offers important information and suggestions with respect to installation,
View Star series Solar Charge Controller INSTRUCTION MANUAL Thank you very much for selecting our product! This manual offers important information and suggestions with respect to installation, use and
Manual EN IMPORTANT Always connect the battery first, in order to allow the Controller to recognize system voltage Use a 12V (36 cells) solar array for a 12V system. Use a 24V (72 cells) solar array for
HQST 20A 30A 40A MPPT Solar Charge Controller User Manual Version 1.0 Important Safety Instructions Please reserve this manual for future review. This manual contains all instructions of safety, installation
MASSPOWER MPPT Solar charge controller Installation and Operation Manual Block 5, Lingyun Industrial Park, No.1177,Lingyun Road, Ningbo National Hi-Tech Zone Ningbo,zhejiang,China. Post:315000 TEL:+86-574-86699988
INSTRUCTION MANUAL ----------For solar charge controller, ----------EPRC-MF series IP67 RATINGS (12/24V auto work) EPRC10-MF,10A 12/24V auto-work, 10A NOTES: For use with solar panels only TECHNICAL INFORMATION
EPsolar itracer Series Maximum Power Point Tracking Solar Charge Controller OPERATION MANUAL Thank you very much for selecting our product! This manual offers important information and suggestion about
PWM10CC PWM30CC RENOGY Pulse Width Modulation Solar Charge Controller Manual 2775 RENOGY E Philadelphia is a trademark of St., RNG Ontario, Group Inc. CA 91761 2015 RNG Group 1-800-330-8678 Inc. All rights
EPsolar etracer series Network Maximum Power Point Tracking Solar Charge Controller OPERATION MANUAL Models: ET2415N ET3415N ET4415N ET6415N Thank you very much for selecting our product! This manual offers
Table 3: Charging voltage for 4 types of battery Battery Battery GS-MPPT-320W Type Type Code Bulk Voltage Floating Voltage Vented 01 14.3 V 13.2 V Sealed 02 14.3 V 13.4 V Gel 03 14.3 V 13.7 V NiCd 04 14.3
REMOTE METER TM Installation and Operation Manual. Digital Remote Meter for Monitoring System Performance. Version: RM-1 1098 Washington Crossing Road Washington Crossing, PA 18977 USA www.morningstarcorp.com
Manual EN Appendix IMPORTANT Always connect the batteries first. Use for 12V battery system only 12V (36 cells) solar panel array. Use for 24V battery system only 24V (72 cells) solar panel array. BlueSolar
12 Volt 30 Amp Digital Solar Charge Controller User s Manual WARNING Read carefully and understand all INSTRUCTIONS before operating. Failure to follow the safety rules and other basic safety precautions
MT-50 Remote Tracer Meter RENOGY Remote Tracer Meter for Commander Series and ViewStar Series Charge Controllers 2775 E. Philadelphia St., Ontario CA 91761 1-800-330-8678 1 Version 2.0 Table of Contents
Intelligent Solar Charge Controller User s Manual Please read this manual carefully before you use this product. Catalogue 1. Product Introduction 3 2. Installation 4 3. Operation 5 4. Common Fault and
Manual for Fire Suppression & Methane Detection System Fogmaker North America Post address: 150 Gordon Dr Exton, PA 19341 Delivery address: 150 Gordon Dr Exton, PA 19341 Tel: 610-265-3610 Fax: 610-265-8327
WITH TWO BATTERY CHARGING EPSOLAR s duo-battery charging solar controller, For RVs, Caravans,and boats. Adjust options: 1. Battery type selection. 2. Two battery charging priority(from 0-100%) 3. Charging
BRAVER UPS (Uninterruptible Power System) User s Manual Safety CAUTION! This UPS utilizes voltages that may be hazardous. Do not attempt to disassemble the unit. The unit contains no user replaceable parts.
YSmart Technology Co.,Ltd GWV Series Grid Tie Microinverter User Manual The copyright of this user manual belong to YSmart TechnologyCompany Limited. Without the written permission of the copyright holder,
Wind/Solar Hybrid Street Light Controller User Manual Model: HY-WSC04-12AWM, HY-WSC04-12/24AWM, HY-WSC06-24AWM, HY-WSC06-48AWM 1. Product Introduction The wind/solar hybrid street light controller is an
Solar Home System User Manual AEHSHS0110W2L Solar Home System 2 Lamps All rights reserved Specifications subject to change without prior notice 2 Dear Customer, Thank you for purchasing Schneider Electric
Battery Power Inverters Renogy 500W 1000W 2000W Pure Sine Wave Inverter Manual 2775 E. Philadelphia St., Ontario, CA 91761 1-800-330-8678 1 Version 1.1 Important Safety Instructions Please save these instructions.
12 Volt 30 Amp Digital Solar Charge Controller Installation & Operation Manual This 30Amp charge controller is designed to protect your 12Volt Lead-acid or Gel-cell battery from being overcharge by solar
EN Manual Solar Fountain Mobile Phone Charger Copyrights 2008 Victron Energy B.V. All Rights Reserved This publication or parts thereof may not be reproduced in any form, by any method, for any purpose.
Solar Controller / Battery Charger User s Manual 1 Congratulations! You have made an excellent choice by purchasing this high quality KORR PWM solar controller which has been manufactured to the highest
SOLAR ELECTRIC MODULE ES-124 & ES-62T Owners Manual and Installation Guide circuit. Reverse connection will damage the module and may result in fire. CAUTIONS Solar electric modules produce DC electricity
DONGGUAN SHENGYANG INDUSTRIAL CO., LTD SY WMVC Smart Grid Tie Microinverter User Manual Dongguan Shengyang Industrial Co., Ltd. ADD: No. 1 Shangxin Road, New Village, Xin An Community, Chang An Town, Dongguan
Mobile Data Power Model: MDP-25 Topic Section Features... 2 Operational Features Summary... 2 Back-up Battery Power Internal Charger Voltage Spike Protection RF Noise Filtering Warning of Imminent Loss
User s Manual AURORA 1.2K/2.2K Uninterruptible Power System Safety CAUTION This UPS utilizes voltages that may be hazardous. Do not attempt to disassemble the unit. The unit contains no user serviceable
Digital echo-charge Owner s Manual Xantrex Digital echo-charge Battery Charger Thank you for purchasing a Xantrex Digital echo-charge. Xantrex Technology Inc. takes pride in manufacturing quality products
Charge Regulator SCR 12 Marine Manual Many thanks for purchasing a superwind product. The SCR 12 Marine is a charge regulator of highest quality and will perfectly and reliably charge your batteries for
30W SOLAR CHARGING STATION USER MANUAL & PRODUCT SPECIFICATIONS Model: SDP-Y-30W Thank you for choosing the Solarland Solar charging station. Please read this manual carefully before setting up and using
INSTALLATION MANUAL EKRTR EKRTETS 1 2 1 2 3 60 87 170 161 ±1.5 m >0.2 m 3 5 4 34 125 4 5 28 50 EKRTR EKRTETS Contents Read this manual attentively before starting up the unit. Do not throw it away. Keep
CC MPPT User s Manual Introduction Congratulations! You are the proud owner of one of the best MPPT charge controllers available in India. Please read this manual carefully before installing and operating
DIGITECH PRO 1000/1600/2200 VA UNINTERRUPTIBLE POWER SUPPLY UPS USER MANUAL ENGLISH Product Overview 1000 VA / 1600 VA / 2200 VA Front View Back View 1 Power Switch 1 USB Communication Port 2 LCD Display
Solar charger controller User s Manual Contents Important safety instructions... 6 1. Product description... 8 1.1 General description... 8 1.2 Features... 8 1.3 Maximum setpoint voltage limit... 8 1.4
RUTLAND HRDi CHARGE REGULATOR INSTALLATION AND OPERATION Introduction Congratulations and thank you for purchasing Marlec s HRDi Charge Regulator. This is the latest technology for charge regulation of
Industrial Single Phase On Line UPS LUV 50 / 60 / 80 / 100 / 150 / 200 User Manual Save This Manual Please read this manual carefully prior to storage, installation, wiring, operation and maintenance of
DC Inline Watt Meter RENOGY 150A High Precision Watt Meter and Power Analyzer 0 2775 E. Philadelphia St., Ontario CA 91761 1-800-330-8678 Important Safety Instructions Please save these instructions. This
450VA/650VA/850VA User s Manual Line Interactive UPS Uninterruptible Power System Table of Contents Safety Instructions Installation and Operation Specifications System Introduction Software Installation
AGS Owner's Manual Xantrex Automatic Generator Start Control System TABLE OF CONTENTS INTRODUCTION...3 Main Features...3 Safety Summary...3 THINGS YOU SHOULD KNOW...4 THEORY OF OPERATION...5 System...5
powered by Portable Solar Kits Owner s Manual Veuillez visiter gpelectric.com pour la version française de ce manuel de l utilisateur Visite gpelectric.com para la versión en español de este manual del
Traditional PWM vs Morningstar s TrakStar MPPT Technology Morningstar s MPPT charge controllers use the TrakStar advanced control MPPT algorithm to harvest maximum power from a Solar Array s peak power
MANUAL CONGRATULATIONS on the purchase of your new CTEK professional battery management unit. This unit is part of a range of professional battery chargers from CTEK SWEDEN AB. It represents the latest
280C AIR COMPRESSOR KIT PART NO. 28021 IMPORTANT: It is essential that you and any other operator of this product read and understand the contents of this manual before installing and using this product.
powered by Portable Solar Kits Owner s Manual Veuillez visiter gpelectric.com pour la version française de ce manuel de l utilisateur Visite gpelectric.com para la versión en español de este manual del
350 WATT HYBRID INVERTER (SOLAR / INVERTER / AC MAINS) Users Manual Page 1 1. Introduction Thank you for purchasing the 350 Watt Hybrid Inverter. Connected to the 12 volt battery, the 350W Hybrid Inverter
HM-W536 Install Guide 9/13/2013 IMPORTANT SAFETY INSTRUCTIONS Warning - When using electrical devices, basic safety precautions should be followed to reduce the risk of fire, electrical shock or injury.
IMPORTANT! - YOU'RE SOLAR READY SOLAR POWER - THE NEW WAY TO RV! Your RV is PRE-WIRED for SOLAR POWER! Benefits of Solar Zamp Solar Portable Solar Kit Maximize Battery Life Electrical Independence Green,
MiniTec TM Series Manual Ranging Mini MultiMeter Model MN35 USER MANUAL Introduction Congratulations on your purchase of Extech s MN35 Manual Ranging Multimeter. This meter measures AC/DC Voltage, DC Current,
PSDC 08128 v.1.2 PSDC 12V/8A/8x1A Power supply for up to 8 analog cameras PTC/TOPIC. EN** Edition: 9 from 25.05.2015 Supersedes the edition: 8 from 12.12.2014 the 8x 1A/12V DC power output for powering
FILE: IM_091-120-12E-20 Rev A., 05-06-08 INSTRUCTION MANUAL AUTO CHARGE 3 STEP AUTOMATIC BATTERY CHARGER R MODEL #091-120-12E-20 for ODYSSEY AGM BATTERIES CAUTION This charger is calibrated to the ODYSSEY
USER S MANUAL MaxPower 400-600 UPS Uninterruptible Power System 28-2MAXPO0018 IMPORTANT SAFETY INSTRUCTIONS SAVE THESE INSTRUCTIONS This manual contains important instructions for models MaxPower 400 and
Oil and Coolant Circulating Heating System Model - OCSM Installation & Operation Manual 216280-000 REV 2 Identifying Your System The HOTSTART heating system is designed to heat fluids for use in marine
BB800 Off-Grid Solar System KEY PRODUCT FEATURES Control Box & Charge Controller 1000W of Solar Panels 4x200Ah of SLA Batteries in series 2KW Inverter Output Power Solar Panel & Battery Mounting Our entry
Builder MODEL 1010 Series Non-Programmable Single Stage Heat/Cool Thermostat USER MANUAL Compatible with low voltage single stage gas, oil or electric heating or cooling systems, including single stage
HP UPS R1500 Generation 3 Installation Instructions Part Number 650952-001 NOTE: The rating label on the device provides the class (A or B) of the equipment. Class B devices have a Federal Communications
200 PSI COMPRESSORS - MODEL NUMBERS 380C AIR COMPRESSOR KIT PART NO. 38033 480C AIR COMPRESSOR KIT PART NO. 48043 380C 480C IMPORTANT: It is essential that you and any other operator of this product read
INSTRUCTION MANUAL CM-600 CM-650 Clamp-on Meters Read and understand all of the instructions and safety information in this manual before operating or servicing this tool. 99945550 2008 Greenlee Textron
ADI 9510-B Advantium 2 Plus Alarm INSTALLATION AND OPERATING INSTRUCTIONS Carefully Read These Instructions Before Operating Carefully Read These Controls Corporation of America 1501 Harpers Road Virginia
Tracer- BN Series MPPT Solar Charge Controller User Manual Models: Tracer1215BN/Tracer2215BN Tracer3215BN/Tracer4215BN Important Safety Instructions Please reserve this manual for future review. This manual
325C AIR COMPRESSOR KIT PART NO. 32530-32533 - 32534-32538 350C AIR COMPRESSOR KIT PART NO. 35030-35033 400C AIR COMPRESSOR KIT PART NO. 40040 450C AIR COMPRESSOR KIT PART NO. 45040 325C 350C 400C 450C