1 ME AGS Auto Gen Start Stand-alone System for Coach Generators Operator s Manual
3 ME AGS Operator s Manual Auto Gen Start Stand-alone System for Coach Generators Table of Contents Section Page 1. Overview 2 2. Configuration 3 3. Installation 5 4. Operation Specifications Troubleshooting Warranty 16 ENABLE OFF TEST SAVE THESE INSTRUCTIONS This manual contains important safety instructions Magnum Energy, Inc. 1
4 1. Overview IMPORTANT SAFETY INFORMATION This product must be installed by a qualified technician in accordance with all applicable electrical codes Always disconnect the coach s batteries before installing this product Remove the generator s spark plug (or disconnect the battery on diesel generators) to prevent accidental starting during installation of this product Use insulated tools The Auto Gen Start System for Coach Generators Congratulations on purchasing your new Auto Gen Start (AGS) for coach generators. The AGS is designed to automatically start your coach generator, based on the inside temperature of the coach or a low battery condition. These features allow you to leave pets and precious items in your coach while you enjoy a day away golfing, touring or just sight seeing - all the while knowing your coach will stay cool and comfortable. Even if you don t have pets, there s nothing better than returning a nice cool coach while dry camping in hot weather. Plus, you will always have charged batteries - no more worrying about dead batteries. The AGS also includes settings for "Quiet Time" so you can comply with park and rally rules. The AGS does not interfere with your air conditioner controls or the manual generator start/stop switches in your coach. Installing the AGS is a simple process and requires the following tools: Pencil Electrical Tape Level Drill Phillips Screw Driver 7/64 & 1/8 Drill Bits Utility Knife or Hole Saw Magnum Energy, Inc.
5 2. Configuration 1. Configuring the AGS Controller The Magnum AGS Controller can be configured for 12 or 24 VDC operation. It can also be configured for various diesel or gas generator brands and models. The controller s default settings are set for "12 VDC" and "Diesel" operation. If necessary, refer to Table 1 (next page) to determine which setting is correct for your system. To access the jumpers, remove the controller s four cover screws. For Onan Quiet Diesel generators, the controller is configured with the "Diesel/Gas" jumper positioned over the two left-hand pins as shown below (factory default). For most "gas" as well as other diesel generators you must configure the controller with the "Diesel/Gas" jumper positioned over the two right-hand pins as shown below For 12 Volt DC operation, the controller is configured with the "12/24 V" jumper positioned over the two left-hand pins as shown below (factory default). For 24 Volt DC operation, you must configure the controller with the "12/24 V" jumper positioned over the two right-hand pins as shown below. Remove the four cover screws 12/24 V Jumper Onan Quiet Diesel (default) Other Diesel and Gas Not Used Controller and Internal Board DIESEL/GAS Jumper 12 VDC Operation (default) 24 VDC Operation Figure 1 - AGS Controller Configuration (DIESEL/GAS and 12/24 V DC Operation) Magnum Energy, Inc. 3
6 2. Configuration VERSION V 2.0 V 2.1 DATE March 1, 2004 March 1, 2004 START TYPE 3-wire start 3-wire start GEN TYPES Onan Quiet Diesel Most gas and other diesels: Emerald, Marquis, MicroLite, MicroQuiet, Onan, and PowerTech FEATURES Temp & low voltage start Temp & low voltage start Quiet time, & net enabled Quiet time & net enabled 12 or 24 volt DC operation 12 or 24 volt DC operation (jumper select) (jumper select) Software version Software version (jumper select) (jumper select) Temp start (connects 3 ways) Temp start (connects 3 ways) Directly to a/c thermostat Directly to a/c thermostat Uses a sensor only Uses a sensor only Wall switch Wall switch (stand alone operation only) (stand alone operation only) NETWORK Connects to ME inverter Connects to ME inverter PORT (uses ME-RC remote with (uses ME-RC remote with version 0.5 or higher) version 0.5 or higher) REMOTE Stand alone switch, Stand alone switch, PORT pigtail direct to a/c thermostat, pigtail direct to a/c thermostat, or sensor only or sensor only START RELAY closes for 20 seconds closes for 10 seconds (pin 5&6) STOP RELAY closes for 10 seconds closes for 10 seconds (pin 6&7) AUX RELAY N/A N/A (pin 1&8) RELAY SEQ Stop 10 sec, Delay 4 sec, Stop 10 sec, Delay 4 sec, Start 20 sec Start 10 sec B+ Voltage 10 VDC 10 VDC (min at pin 2) B+ GEN RUN checks for B+ 2 sec checks for B+ 2 sec (pin 2) after crank time after crank time TEST MODE Ignores B+ for test Ignores B+ for test (runs 30 sec then off) (runs 30 sec then off) GEN START Yes, ignores auto start Yes, ignores auto start (MANUAL) (if B+ present) (if B+ present) Allows manual start Allows manual start within quiet time within quiet time LED, GREEN Blinks on start, solid on run Blinks on start, solid on run LED, RED Red after 4 tries Red after 4 tries (Time between tries = 2 min) (Time between tries = 2 min) Table 1 - Magnum AGS Software Revs (4/2/04) Magnum Energy, Inc.
7 3. Installation Installing the AGS Controller 1. Determine a suitable location to mount the Auto Gen Start (AGS) controller. It must be located in a clean, dry and protected place. Use the template at the rear of the manual to prepare the selected mounting area. The controller can be mounted in any direction; however, allow ample room to access the adjustment dials and to view the LEDs for troubleshooting. Wiring is much easier if the controller is mounted within easy access to the generator s remote switch wiring. Predrill the four 1/8 holes if necessary. 2. Remove the 8 pin connector from the controller by pulling it straight out. Wire the controller according to Figures 4 and Use the four 8x3/4 screws (provided) to mount the controller to the coach s wall. 4. When all of the wiring is complete, plug the 8 pin connector into the AGS controller. ENABLE OFF TEST Controller Switch Figure 2 - AGS Controller and Remote Switch Magnum Energy, Inc. 5
8 3. Installation ENABLE OFF Figure 3 - AGS Switch and Controller Magnum Energy, Inc.
9 3. Installation Installing the AGS Switch WARNING: Always check for hidden wires, pipes and cables before drilling or cutting into the coach s walls and cabinets. 1. Locate a convenient spot to mount the AGS Switch. The side wall of the coach s refrigerator enclosure is the most common (and recommended). The switch should be mounted midway up the wall for best results. NOTE: The thermistor that is used to sense the coach s interior temperature is located on the back of the AGS Switch. It is vital that the switch be placed where interior room temperatures can be accurately sensed by the thermistor. Keep the switch away from heating and air conditioning ducts, window drafts and avoid mounting it on the coach s exterior walls. Interior walls and cabinets provide much more stable temperatures and also make it easier to route the switch s cable to the AGS Controller. 2. Use the template at the rear of the manual to cut a hole for the AGS Switch. Feed the 6 wire phone cable through the opening and route it to the AGS Controller. Use care in routing the cable to insure the cable does not become pinched or cut by rough or sharp edges. Leave enough slack to allow movement of the cable once the installation is complete. 3. Make sure the switch is the "OFF" position and then plug the cable into the RJ-11 phone connector on the back of the AGS Switch. Mount the switch to the wall using the two 6x1 screws provided. 4. Plug the other end of the 6 wire phone cable into the AGS Controller s RJ-11 connector marked Remote. 5. If all wiring is correct, the unit performs a "self test" when power is applied. The "STATUS" LED blinks green. At the same time, the "READY" LED turns on solid green. With the remote connected, the "READY" LED comes on solid green. If the remote is not connected, the "READY" LED blinks green. Installation is now complete. Reconnect the generator s spark plug (or reconnect the battery for diesel generators) Magnum Energy, Inc. 7
10 3. Installation 6 Wire Phone Cable AGS Controller AGS Controller ENABLE OFF TEST AGS Switch Aux Aux GEN Hour Meter Start Comm Stop GEN Start/Stop Switch Amp Ground Fuse VDC Battery Ground Figure 4 - AGS Wiring Diagram Magnum Energy, Inc.
11 3. Installation Note: Pin #1 is located on the LEFT side facing the terminal block 6 Wire Connector from AGS Remote Switch Aux Contact Generator Stop / Preheat Common from Generator Start / Stop Switch (Ground) Generator Start - 12 VDC (Negative) from Battery + 12 VDC (Positive) from Battery Generator B+ (+ 12 VDC) from Generator Hour Meter Aux Contact Figure 5 - AGS Connector Pin Legend (from left to right) Magnum Energy, Inc. 9
12 3. Installation The AGS comes preset for voltage, temperature and generator run time directly from the factory. Quiet Time is factory preset to "OFF" (defeated). For the majority of customers, no adjustments are necessary. If you need to make changes to the factory adjustments, you can do so by rotating the knobs on the front panel of the AGS Controller. See diagram below: 1. The "START TEMP F" factory setting is set at 75 F (25 C). When the inside coach temperature reaches this point, the generator will automatically start to power the air conditioner. NOTE: To change this setting, slowly rotate the knob marked "START TEMP F" clockwise to increase temperature or counterclockwise to decrease temperature. The temperature range is adjustable from 65 F to 85 F (18 C to 29 C). 2. The "START VOLTS" factory setting is set at 11 VDC. When the battery voltage drops to this setting, the generator will automatically start and recharge the batteries. There is a 2 minute delay once the voltage setting is reached. NOTE: To change this setting, slowly rotate the knob marked "START VOLTS" clockwise to increase the voltage or counterclockwise to decrease voltage. The range is 10 VDC to 12 VDC. NOTE: This system is capable of both 12 VDC and 24 VDC operation. For 24 VDC applications, the value indicated on the cover is automatically doubled (i.e., 11 VDC equals 22 VDC). 3. The "RUN TIME HOURS" factory setting is set at 2 hours. This is the length of time the generator will run once the "START TEMP F" or "START VOLTS DC" setting has been reached and the generator starts. NOTE: To change this setting, slowly rotate the knob marked "RUN TIME HRS" clockwise to increase generator run time and counterclockwise to decrease generator run time. Generator run time can be set from 1 to 5 hours. NOTE: To defeat the Temperature or Voltage Start feature, turn the adjustment knob fully counter-clockwise (OFF) Magnum Energy, Inc.
13 3. Installation 4. The "CLOCK" (used only on the stand-alone version of the AGS system) is a 24 hour internal clock. The clock can only be set between the hours of 8 AM and 4 PM. To set the clock, turn the dial either counter-clockwise or clockwise to the approximate time of day. Once set the clock will continue to keep time. In the event the control module loses power, the clock must be reset. NOTE: When using the Network Port on the inverter, the Clock dial is defeated. For network operation, set the clock using the remote control (see the AGS Network System manual). 5. "QUIET TIME" is a program that prevents the generator from starting during specific hours of the evening and early morning. It is adjustable for five pre-selected time ranges. To set quiet time, turn the dial either counter-clockwise or clockwise to the hours required: 9-7 (9 PM to 7 AM), 9-8 (9 PM to 8 AM), 9-9 (9 PM to 9 AM), 10-8 (10 PM to 8 AM), 11-8 (11 PM to 8 AM). The program only needs to be set once. NOTE: To defeat the Quiet Time feature, turn the dial fully counter-clockwise ("OFF" position). RUN TIME HOURS Adjustment START TEMP F Adjustment START VOLTS DC Adjustment CLOCK AM/PM Adjustment QUIET TIME PM/AM Adjustment NOTE: In the event the control module loses power the CLOCK must be reset. Figure 6 - AGS Controller Adjustments Magnum Energy, Inc. 11
14 4. Operation WARNING: Set the AGS Switch to the "OFF" position before servicing the electrical or generator system. NOTE: It is recommended that the AGS Switch be set in the "OFF" position while storing the coach or leaving the coach unattended for extended lengths of time. It is also recommended that the AGS Switch be set in the "OFF" position while the coach is plugged into shore power. 1. Set the air conditioner thermostat to match the AGS "START TEMP F" setting. If two air conditioners, it is suggested that the second air conditioner thermostat be set 2 to 5 higher than the first air conditioner. This staggered setting allows the first air conditioner to keep the coach cool. The second air conditioner will only switch on if the coach temperature continues to rise, thus conserving power. 2. Set the "START VOLTS DC" to 11 VDC. 3. Activate the system by pressing the AGS Switch to the "ENABLE" position. This is the normal operating position. When the coach s inside temperature reaches the "START TEMP F" or the "START VOLTS DC" setting, the LED will blink green and the AGS will initiate the start sequence. The AGS will attempt 4 times to start the generator. If the generator fails to start, the LED will turn red indicating a fault. When the generator starts, the LED turns solid green. It will continue to run until the "RUN TIME HRS" setting is reached at which time a stop signal is sent to the generator. To manually stop the generator anytime during the run time cycle, simply press the "Enable" switch to the "OFF" position. NOTE: Once the generator has completed the "RUN TIME HRS" the AGS will immediately monitor the "TEMP START F" and "START VOLTS DC" for the next auto start cycle. If a fault occurs, press the AGS Switch to "OFF" and then back to the "ENABLE" or "TEST" position. If the problem persists, check the troubleshooting chart at the back of the manual Magnum Energy, Inc.
15 4. Operation 4. When the AGS Switch is placed in the "OFF" position, all AGS generator start functions are disabled. The LED will also be off when the switch is in this position. 5. When necessary, hold (and release) the switch in the "TEST" position (on the remote AGS Switch) or press down the "PUSH TO TEST" switch (on the AGS Controller) to test the system. The generator will start and run for approximately 30 seconds before shutting off. NOTE: If the generator is running when the switch is held in the "TEST" position, the generator will stop and then start again. The generator will start and run for approximately 30 seconds before shutting off. ENABLE Switch STATUS LED ENABLE OFF TEST Figure 7 - AGS Remote Switch Operation TEST Switch STATUS LED READY LED Figure 8 - AGS Controller Operation Magnum Energy, Inc. 13
16 5. Specifications Weight (Controller) Weight (Switch) 1 lb (0.5 kg) 0.25 lb (0.1 kg) Dimensions (Controller) Dimensions (Switch) 3.0 H x 5.2 W x 1.33 D (7.6 cm H x 13.2 cm W x 3.3 cm D) 2.25 H x 3.25 W x 1.5 D (5.7 cm H x 8.3 cm W x 3.8 cm D) Electrical Requirements Controls LED Indicator Temp Sense Range Voltage Start Range Quiet Time Range Clock Generator Run Range Connections Electrical Connections 12 VDC or 24 VDC Enable, Off, Test On, Off, Fault Condition 65 F to 85 F (18 C to 29 C) 75 F (25 C) - factory setting 10 VDC to 12 VDC (or) 20 VDC to 24 VDC 9PM to 7AM, 9PM to 8AM, 9PM to 9AM, 10PM to 8AM, 11PM to 8AM 24 hour 1 to 5 hours 2 hours - factory setting Screw Terminals (rear mounted) Gen B+ (from Gen Hour Meter) +12 VDC +12 VDC or +24 VDC Pos (from Battery) -12 VDC or -24 VDC Neg (from Battery) Generator Start Common (from Gen Start/Stop Switch) Generator Stop/Preheat Specifications at 25 C Subject to change without notice Magnum Energy, Inc.
17 6. Troubleshooting To test the system for proper operation, hold the AGS Switch in the "TEST" position and release. The generator should start and run for 30 seconds and then shut off. If the generator does not start and stop as expected, refer to the troubleshooting chart below. If the problem persists, contact your dealer. LED INDICATION SYMPTOM OPERATION/SOLUTION RED Gen won't start. Check Gen start wiring, = GEN FAULT Turn "off" then "enable" to reset. RED Gen won't stay Check Gen B+ wiring, = GEN FAULT on. check gen, turn "off" then "enable" to reset. GREEN BLINK Gen start initiated. No problem. = GEN START GREEN SOLID Gen started ok. No problem. = GEN START READY OFF No 12 or 24 volt Check fuse, check = POWER OFF DC power to control 12 or 24 volt DC wiring, box. Turn "off" then "enable" to reset. READY BLINK No remote control Check remote = NO REMOTE sensed or plugged connections, in. Turn "off" then "enable" to reset. READY SOLID Normal operation. No problem. = POWER ON Magnum Energy, Inc. 15
18 7. Warranty 36 Month Limited Warranty Magnum Energy, Inc., warrants the ME Series Auto Gen Start to be free from defects in material and workmanship that result in product failure during normal usage, according to the following terms and conditions: 1. The limited warranty for the product extends for 36 months beginning from the product's original date of purchase. 2. The limited warranty extends to the original purchaser of the product and is not assignable or transferable to any subsequent purchaser. 3. During the limited warranty period, Magnum Energy will repair, or replace at Magnum Energy's option, any defective parts, or any parts that will not properly operate for their intended use with factory new or rebuilt replacement items if such repair or replacement is needed because of product malfunction or failure during normal usage. The limited warranty does not cover defects in appearance, cosmetic, decorative or structural parts or any non-operative parts. Magnum Energy's limit of liability under the limited warranty shall be the actual cash value of the product at the time the original purchaser returns the product for repair, determined by the price paid by the original purchaser. Magnum Energy shall not be liable for any other losses or damages. 4. Upon request from Magnum Energy, the original purchaser must prove the product's original date of purchase by a dated bill of sale, itemized receipt. 5. The original purchaser shall return the product prepaid to Magnum Energy in Everett, WA. Magnum Energy will return the product prepaid to the original purchaser after the completion of service under this limited warranty. 6. This limited warranty is voided if: the product has been modified without authorization the serial number has been altered or removed the product has been damaged through abuse, neglect, accident, high voltage or corrosion. the product was not installed and operated according to the owner's manual. IN CASE OF WARRANTY FAILURE, CONTACT MAGNUM ENERGY INC. FOR A RETURN AUTHORIZATION (RA) NUMBER BEFORE RETURNING THE UNIT FOR REPAIR. Magnum Energy, Inc th Street SW - Suite 250 Everett, WA p: f: Magnum Energy, Inc.
19 1/8 Drill Bit Template Controller 5 2 Remote Switch 7/64 Drill Bit 1-5/8 Cutout 1-1/4 2-1/8
20 Magnum Energy, Inc th Street SW - Suite 250 Everett, WA p: f: p/n rev. 3 6/04
ME AGS Auto Gen Start Network System with Inverter and Remote for Coach Generators Operator s Manual ME AGS Operator s Manual Auto Gen Start Network System with Inverter and Remote for Coach Generators
AGS Owner's Manual Xantrex Automatic Generator Start Control System TABLE OF CONTENTS INTRODUCTION...3 Main Features...3 Safety Summary...3 THINGS YOU SHOULD KNOW...4 THEORY OF OPERATION...5 System...5
FEATURES & APPLICATIONS Inexpensive 2 wire to 3 wire start controller for electric start high speed gas generators. Optimized for use with Outback Invertors. Supports three types of 3 wire generator control
INSTALLATION AND TROUBLE SHOOTING MANUAL for all Models of Nova Kool AC/DC and DC only Refrigerators and Freezers. Thank you for choosing Nova Kool for your refrigeration needs. For over 20 years we have
INSTALLATION & SERVICE MANUAL Display Panel The PowerLine EMS TM is a specialized power distribution and energy management system intended to be used in recreational vehicles. The Control Module is housed
REMOTE METER TM Installation and Operation Manual. Digital Remote Meter for Monitoring System Performance. Version: RM-1 1098 Washington Crossing Road Washington Crossing, PA 18977 USA www.morningstarcorp.com
8400 Series Thermostats Safety & Installation Instructions READ AND SAVE THESE INSTRUCTIONS 61000652D 8400 Tstat Install.indd 1 Table of contents Installation Installation location recommendations... 3
Builder MODEL 1010 Series Non-Programmable Single Stage Heat/Cool Thermostat USER MANUAL Compatible with low voltage single stage gas, oil or electric heating or cooling systems, including single stage
Rev. D PRODUCTIVITY THROUGH INNOVATION 600 CONTROL DIRECT DRIVE TECHNICAL/OPERATION MANUAL 10 BORIGHT AVENUE, KENILWORTH NEW JERSEY 07033 TELEPHONE: 800-524-0273 FAX: 908-686-9317 TABLE OF CONTENTS Page
DIGITAL 9415 NON-PROGRAMMABLE THERMOSTAT NeW G E O GAS ELECTRIC OIL 2 Heat / 2 Cool User's Manual Quick Start Installation 110-1043B Application The Robertshaw 9415 is a multi-stage thermostat designed
Progressive Industries, Inc. EMS Electrical Management System Complete Installation Guide and Operating Instructions for: Model EMS-HW50C Rated at 240V/50A Manufactured by: Progressive Industries, Inc.
PAC-2000 REV A ELECTRIC COOLING FAN CONTOLLER 4510 W. 61 ST St. N, Sioux Falls, SD. 57107 Phone: (605) 332-6513 FAX: (605) 339-4106 www.dakotadigital.com Operation The electric cooling fan controller provides
PAC-2700 ELECTRIC COOLING FAN CONTOLLER PAC-2700 FAN CONTROLLER IMPORTANT NOTE: The +12V for the controller should NOT be taken from the same circuit as the Power 12V as this can cause the fan to cycle
TM Automatic Humidifier Control SEH-7100-000 by Skuttle Indoor Air Quality Products Safety and Installation Instructions* INSTALLER: READ COMPLETE INSTALLATION INSTRUCTIONS BEFORE BEGINNING INSTALLATION.
Digital HDTV Over-the-Air Antenna w/built-in KING SureLock Digital TV Signal Meter Owner s Manual OA8200 WHITE OA8201 BLACK 11200 Hampshire Avenue South, Bloomington, MN 55438 PH 952.922.6889 FAX 952.922.8424
148 OLD CONCORD TURNPIKE, BARRINGTON NH 03825 USA TEL (603) 868-5720 FAX (603) 868-1040 1-800-435-6708 E-Mail:email@example.com www.seafrost.com ELECTRONIC THERMOSTAT AND THERMOMETER With SPEED CONTROL
Automatic Generator Start Owner s Guide Automatic Generator Start Owner s Guide About Xantrex Xantrex Technology Inc. is a world-leading supplier of advanced power electronics and controls with products
ADI 9510-B Advantium 2 Plus Alarm INSTALLATION AND OPERATING INSTRUCTIONS Carefully Read These Instructions Before Operating Carefully Read These Controls Corporation of America 1501 Harpers Road Virginia
OPERATING INSTRUCTIONS MODEL 810 HIGH VOLTAGE POWER SUPPLY Introduction The Model 810 High Voltage Power Supply is a self-contained unit that produces a variable high voltage output at low current levels.
Go Power! Manual GP TS-30 Go Power! Electric Inc. PO Box 6033 Victoria, BC V8P 5L4 Tel: 866-247-6527 Fax: 866-607-6527 Email: firstname.lastname@example.org Table of Contents 1. INTRODUCTION... 3 2. INSTALLATION...
Model 201 Wiegand Touchpad Reader Installation Guide P/N 460353001C 15AUG11 2011 UTC Fire & Security. All rights reserved. This document may not be copied in whole or in part or otherwise reproduced without
SERVICE INSTRUCTION SPLIT TYPE ROOM AIR CONDITIONER WALL MOUNTEDtype INVERTER Models Indoor unit Outdoor unit ASYG07LECA ASYG09LECA ASYG12LECA ASYG14LECA AOYG07LEC AOYG09LEC AOYG12LEC AOYG14LEC R410A CONTENTS
OWNER'S MANUAL Model 20-1050CUL AC Power Inverter/Charger System OM/A96283 REV. A Table of Contents Section 1 Introduction... 1 Section 2 Installing the 20-1050CUL... 4 Section 3 Installing the IFM1 Interface
SERVICE MANUAL 12VDC WALL THERMOSTAT AIR CONDITIONING SYSTEMS ROOFTOP UNITS ONLY! WARNING - SHOCK HAZARD! TO PREVENT THE POSSIBILITY OF SEVERE PERSONAL INJURY, DEATH, OR EQUIPMENT DAMAGE DUE TO ELECTRICAL
Extended warranties are available for purchase at www.progressivedyn.com Installation and Operation Guide for PD4000 Series Power Control Center Member Thank you for selecting Progressive Dynamics as your
350 WATT HYBRID INVERTER (SOLAR / INVERTER / AC MAINS) Users Manual Page 1 1. Introduction Thank you for purchasing the 350 Watt Hybrid Inverter. Connected to the 12 volt battery, the 350W Hybrid Inverter
68 Flexible, high specification system Choice of 1, 2, 4 or 8 zones Simple one-shot auto-reset user test facility Approved to EN54 Maintenance free poly switch circuit protection, with auto reset Class
Pub. 988-0064-351 LST-3800 In-Dash Digital Sonar Gauge Installation & Operation Instructions The LST-3800 is a depth and temperature gauge that comes with a 200 khz transducer, features deep and shallow
RV Products Division SERVICE MANUAL FOR 12 VDC WALL THERMOSTAT AIR CONDITIONING SYSTEMS ROOF TOP UNITS ONLY Airxcel, Inc. RV Products Division P.O. Box 4020 Wichita, KS 67204 1976A376 (1-11) TABLE OF CONTENTS
IR Repeater Operation Manual P8620 Congratulations on your purchase of the P8620 IR Repeater. This operating manual will provide a guide to installation and operation of the product. Please read thoroughly
INTRODUCTION CMD-8000 rev. A COMMANDER SERIES REMOTE CONTROL ENTRY SYSTEM Thank you for purchasing the CMD-8000 Commander from Dakota Digital. This, along with many other products that Dakota Digital has
R22. K Control. Indoor Unit. Nomenclature. PL H 3 G K H B Compatibility Unit style Heat Pump Horse Power Control Boost Heaters R22. K Control. Outdoor Unit. Nomenclature. PU H 3 Y K A Compatibility Outdoor
ADA COMPLIANT BOX STYLE TELEPHONE INSTALLATION, PROGRAMMING AND OPERATING INSTRUCTIONS FOR MODEL PBX INSTALLATION INSTRUCTIONS Step 1. Determine the position for the Hands-free phone in the elevator phone
LMU-5000 Hardware and Installation Guide Plan The Installation Verify Power, Ground and Ignition. Be sure to check each source (power, ground and ignition) to ensure that the proper signaling exists. This
IMR-4 I/O Interface Module 1 IMR-4 Auxiliary Input / Output Interface Module Introduction: The IMR-4 is designed to interface to the Audio Expansion Port of the Poly- Planar line of Audio Centers. It provides
325C AIR COMPRESSOR KIT PART NO. 32530-32533 - 32534-32538 350C AIR COMPRESSOR KIT PART NO. 35030-35033 400C AIR COMPRESSOR KIT PART NO. 40040 450C AIR COMPRESSOR KIT PART NO. 45040 325C 350C 400C 450C
Portable Air Conditioner OWNER S MANUAL Read these instructions before use 8 Model: MN12CES / MN10CESWW Voltage rating: 120V~60Hz Power rating : 1100W (MN12CES) Power rating : 900W (MN10CESWW) Customer
GL-235 Solar Pool Controller Installation & Operation Manual for models GL-235-LV GL-235-LV-HV G LDLINE CONTROLS INC. North Kingstown, RI USA www.goldlinecontrols.com 888-921-7665 Description The GL-235-LV
FITTING AND OPERATING INSTRUCTIONS FOR DIGISTAT OPTIMISER PROGRAMMABLE 7 DAY ROOM THERMOSTAT SYSTEM General information is given in the users instruction leaflet despatched with the appliance and/or on
543-0032-00, 943-0032-00 User s Manual 1 Comfort Alert Diagnostics Faster Service And Improved Accuracy The Comfort Alert diagnostics module is a breakthrough innovation for troubleshooting heat pump and
User's Guide Model 382260 80W 3-in-1 Switching DC Power Supply Introduction Congratulations on your purchase of the Extech 80W 3-in-1 Switching DC Power Supply. The Model 382260 has three output ranges
Portable Air Conditioner OWNER S MANUAL Read these instructions before use Model: MM14CCS Customer Support : 1-800-474-2147 Voltage rating: 115V~60Hz Power rating : 1400W For product inquiries or support
6.4 LCD Color Monitor OWNER S MANUAL INTRODUCTION OHM642 The Clarion OHM642 is a full-featured 6.4" LCD Color Monitor that can be used as a stand alone monitor, or can be integrated into a mobile multimedia
SERVICE MANUAL FOR 6535 SERIES TWO TON HIGH EFFICIENCY PACKAGED HEAT PUMPS TABLE OF CONTENTS 1. Warnings...2 2. Accessibility Of Appliance...3 3. Unit Dimensions And Specifications...3 4. Unit Specifications
Wireless TV Speaker Item No. 204094 OPERATING GUIDE Thank you for purchasing the Sharper Image Wireless TV Speaker. Please read this operating guide carefully before use and keep it for future reference.
PAC2750 ELECTRIC COOLING FAN CONTOLLER IMPORTANT NOTE: The 12V for the controller should NOT be taken from the same circuit as the Fan Power 12V as this can cause the fan to cycle on and off. www.dakotadigital.com
PART 8: FIELD WIRING A. INSTALLATION MUST COMPLY WITH: 1. National Electrical Code and any other national, state, provincial or local codes or regulations. 2. In Canada, CSA C22.1 Canadian Electrical Code
INSTRUCTION BOOK FOR Multi-Media Lectern Set-Up Power Connect power supply to 110/120 VAC 3-wire outlet (220/240 VAC models to 220/240 VAC source). Reading Light Depress light switch to activate light.
525 Installation Instructions Thank you very much for purchasing PIAA product. Please read this entire manual before installation and use of this product. For Installers Please give this Installation Manual
Technical Information and Diagnostic Guide This guide will assist you in becoming more familiar with the working components of the NITE Plus System and the proper steps and procedures to completely diagnose
MODE ALARM Portable Air Conditioner OWNER S MANUAL Read these instructions before use 8 Model: MF08CESWW Voltage rating: 115V~60Hz Power rating : 800W Customer Support : 1-800-474-2147 For product inquiries
520 Installation Instructions Thank you very much for purchasing PIAA product. Please read this entire manual before installation and use of this product. For Installers Please give this Installation Manual
MANUAL 1.1 Nature Power 400 Watt Wind Turbine Instruction Manual dan kruger [Pick the date] Serial Number: 1. Introduction: This manual contains installation and safety information for the Nature Power
3RP / 5RP 4-BUTTON SERIES VEHICLE SECURITY SYSTEMS INSTALLATION MANUAL Before you begin the installation Read the INSTRUCTIONS! Always use a multi-meter when verifying vehicle wiring. Before mounting the
VLT Series 300 Watt True Sine Wave Inverter PURE SINE WAVE INVERTER I ON 0 OFF REMOTE CONTROL AC OUTPUT POWER STATUS Vout Vin Models VLT12-300 VLT24-300 300 Watt VLT Series Inverter - 1 - TABLE OF CONTENTS
ODYR-22-1 & SLX-22-1 TIRE AIR PRESSURE GAUGE Features: 4 tires displayed at one time. Provides both pressure and temperature readings. Can read 4 vehicle tires and 2 or 4 trailer tires. A warning feature
DUAL SENSING DIGITAL THERMOSTAT PRODUCT INSTRUCTIONS www.rehau.com Construction Automotive Industry SCOPE This guide gives instruction regarding REHAU Programmable Digital Thermostat installation and operation.
Owner s Manual & Safety Instructions Save This Manual Keep this manual for the safety warnings and precautions, assembly, operating, inspection, maintenance and cleaning procedures. Write the product s
RC-100 / RC-100B Heat Pump 2 Stage Heat / 1 Stage Cool Thermostat Installation Instructions DESCRIPTION The RC-100 is a precision digital thermostat designed for 24 VAC heat pump systems. It has the capability
Owner s Manual Slim Rack In Wall Slide Out System With Control Box 1510000236 or 1510000276 Content Copyright LCI/PowerGear Issued: December 2014 #3010002814, Rev. 0F Owner s Manual Dual Planetary Gearmotor
PagePac Issue 3 by PAGEPAL V-5335700 INTRODUCTION The PagePal unit interfaces most telephone systems (PBX, KTS, Centrex) to virtually any public address audio system. In addition, PagePal furnishes inputs
Model 53603 Owner s Manual Español - P. 19 Français - P. 39 Table of Contents I. Introduction............................ 1 Sample Watering Plan.......................... 1 II. Installation...........................
PCU Plus V-FORCE Plus Engineered For Power! INSTALLATION & USER GUIDE 2008 JET Performance Products Installation Instructions JET V-Force / Power Control Unit 1. Mounting the V-Force / PCU Using the supplied
Owner s Manual & Safety Instructions Save This Manual Keep this manual for the safety warnings and precautions, assembly, operating, inspection, maintenance and cleaning procedures. Write the product s
INSTALLATION MANUAL EKRTR EKRTETS 1 2 1 2 3 60 87 170 161 ±1.5 m >0.2 m 3 5 4 34 125 4 5 28 50 EKRTR EKRTETS Contents Read this manual attentively before starting up the unit. Do not throw it away. Keep
A102-05, Page 1 952-361-3026, INC. (Fax) 952-368-4129 327 LAKE HAZELTINE DRIVE, CHASKA, MN 55318 800-328-0738 MAXIGARD A1000 SPEED SWITCH Introduction The Maxigard A1000 speed switch is designed to monitor
280C AIR COMPRESSOR KIT PART NO. 28021 IMPORTANT: It is essential that you and any other operator of this product read and understand the contents of this manual before installing and using this product.
Universal Fan and Light Remote Control Hand-Held Remote and Wall Cradle Owner s Guide and Installation Manual English Form# 44092-01 20101215 2010 Hunter Fan Co. 1 Welcome Table of Contents 1 Welcome...2
4505 ADJUSTABLE TIMER INTRUCTIONS The 4505 processor controlled timer module may be used as a highly accurate 30 second fixed timer or by removing a jumper, may be adjusted to provide endlessly variable
ADI 5106G Certified ISO 9001:2000 Single Station Remote Alarm 529 5106-01-120 529 5106-01-220 INSTALLATION AND OPERATING INSTRUCTIONS Carefully Read These Instructions Before Operating Controls Corporation
OPERATING AND MAINTENANCE MANUAL FOR T1000 CONTROLLER 2014 Edition CONTROL BOARD AND DISPLAY The control board supplies all the necessary functions for heater operation. These include control temperature,