2 Ex Protection Concepts Electrical Electrical Symbol Typical Typical Zones IEC Standard Basic concept of protection IEC EPL Increased safety e Gb 1,2 IEC No arcs, sparks or hot surfaces. Type n (non-sparking) na Gc 2 IEC Enclosure IP54 or better Flameproof d Gb 1,2 IEC Contain the explosion, quench Type n (enclosed break) nc Gc 2 IEC the flame Quartz/sand filled q Gb 1,2 IEC Quench the flame Intrinsic safety ia Ga 0,1,2 IEC Intrinsic safety ib Gb 1,2 IEC Limit the energy of sparks and Intrinsic safety ic Gc 2 IEC surface temperatures Type n (energy nl Gc 2 IEC limitation) Pressurised (up to 2007) p Gb 1,2 IEC Pressurised px Gb 1,2 IEC Pressurised py Gb 1,2 IEC Pressurised pz Gc 2 IEC Type n (sealing & nc Gc 2 IEC hermetic sealing) Type n (restricted nr Gc 2 IEC Keep the flammable gas out breathing) Type n (simple nz Gc 2 IEC pressurised) Encapsulation ma Ga 0,1,2 IEC Encapsulation mb Gb 1,2 IEC Oil immersion o Gb 1,2 IEC
3 Ex Protection Concepts Non-Electrical Non-electrical Symbol Typical Possible EN Standard Basic concept of protection IEC EPL Zone(s) Flow restricted enclosure fr - 2 EN Relies on tight seals, closely Flameproof enclosure d - 1,2 EN matched joints and tough enclosures to restrict the breathing of the enclosure Inherent safety g - 0,1,2 pren Low potential energy (draft standard) Constructional safety c - 0,1,2 EN Ignition hazards eliminated by good engineering methods Control of ignition sources b - 0,1,2 EN Control equipment fitted to detect malfunctions Pressurisation p - 1,2 EN Enclosure is purged and pressurised to prevent ignition sources from arising Liquid immersion k - 0,1,2 EN Enclosure uses liquid to prevent contact with explosive atmospheres
4 Ex Protection Concepts Dust Protection Electrical Dust Protection (Electrical) Symbol Typical IEC EPL Typical Zone(s) IEC Standard Basic concept of protection Enclosure t Da, Db, Dc 20 IEC Standard protection for dusts, rugged tight enclosure Intrinsic safety i 21 IEC Similar to t, but with some relaxations if circuit inside is intrinsically safe Encapsulation m 22 IEC Protection by encapsulation of incendive parts Pressurised p Db,Dc 21,22 IEC Protection by pressurisation of enclosure
5 Ex d Flameproof AS/NZS/EN/IEC Zone 1 & 2 Suitable
6 Ex d Flameproof Concept Lamps, circuits and sparking devices are contained within flameproof enclosure. Wiring enters enclosure via flameproof cable gland or flameproof barrier. Joints on covers or openings are protected by the flamepath. Does not prevent explosion occurring but contains the explosion and prevents ignition of surrounding atmosphere.
7 Ex d Flameproof Barrier Cable Gland Body Poured Seal/Compound Enclosure Wall
8 Ex d Flame Path Flanged Design Flame path Flame path Enclosure wall
9 Flameproof vs. Explosion Proof Difference between Flameproof & Explosion proof boxes Enclosure must have recessed screws or bolts for access 1.5 safety factor vs. 4 times Typically must be machined and fabricated at the factory vs. the field Most Ex d enclosures individually tested
10 Flameproof Testing
11 Ex d Flameproof 3 types of joints Flanged Joint Threaded Joint Spigot Joint
12 Field Modification of Ex d Equipment Flameproof enclosures are normally supplied complete with all internal components fitted and certified as a single entity by a recognized test authority. The testing procedure will take into consideration the free internal volume after all the components have been fitted, the temperature rise, creepage and clearance distances and the rise in pressure as a result of an internal explosion using a gas/air mixture in its most explosive proportions. Replacement components should be the same as the original components. For example, a component larger or smaller than the original will affect the internal geometry of the enclosure. Pressure piling is a possibility if a larger component is fitted and increased volume will result if a smaller component is fitted. Drilling and tapping of the entries should only be carried out by the manufacturer of the enclosure or his approved agent. The threads of the entries are required to be compatible with those of the cable glands or conduit in terms of type of thread, thread pitch and clearance tolerance since flamepaths exist at these points. Gaskets can only be replaced, they must not be added retrospectively if not included as part of the original design.
13 Obstruction of Flamepath A solid obstruction such as a wall, steelwork, conduit, brackets or weatherguards or other electrical equipment in close proximity to the opening of the joint can, in the event of an internal explosion, reduce the efficiency of the flamepath to the extent that ignition of the external gas or vapor could occur. Minimum distances between the flamepath opening and an obstruction as specified in IEC Group IIA IIB IIC Distance 10mm 30mm 40mm
14 Ex d IIB vs. Ex d IIC Construction Can you spot the difference in construction?... Flanged designed enclosures are not designed for IIC applications. However, you can find certain flanged enclosures suitable for IIB+H2
15 Ex d Flameproof Conduit Systems Although, conduit is not widely used in Northern Europe, this technique is included in the CENELEC standard and the IEC standards as one of the entry methods into flameproof enclosures. The design and testing requirements are contained in the CENELEC and IEC Standard IEC Either tapered (NPT) or parallel (straight or metric) threads are acceptable. The conditions are: The Ex d enclosure must be certified. Only the manufacturer can make the drilled and tapped entries into the Ex d enclosure. All conduits or cable glands entering the enclosure must be sealed by an approved method. From the area beyond the enclosure seal, all of the wiring methods and fittings are considered installation materials and not subject to any certificate or approval. Thus, getting fittings certified to the ATEX directive would not be a common practice. The correct use of conduit installation is spelled out in the installation standards EN and IEC
16 Weatherproofing Ex d Equipment In general, the use of Ex d flameproof equipment without the use of gaskets or seals will only provide protection up to IP54. For applications requiring higher levels of IP protection, the use of gaskets integrated within the flamepath is a common option to consider. Other weatherproofing materials considered and commonly used are nonhardening grease bearing textile tape in the UK and non-setting grease or compounds. The use of non-setting grease on machined surfaces of flamepaths has two advantages since in addition to providing an additional level of ingress protection, it also inhibits the formation of rust on these surfaces. Silicone based greases require careful consideration in order to avoid possible damage to the elements of gas detectors. In general, consult with the manufacturer of Ex d equipment for recommendations involving lubricants and tapes to be sure.
17 Flameproof Ex d Quiz Components which arc or spark in normal operation are permitted with Ex d enclosures True Gaps at flamepaths are not necessary True An enclosure marked Ex d IIA is suitable for all subgroups False It is acceptable for one fixing screw to be left our of a flameproof enclosure cover False It is not acceptable to remove an unused component from within a flameproof enclosure True
18 Ex e Increased Safety (AS/NZS/EN/IEC ) Junction boxes and terminal enclosures for use in hazardous areas mainly contain non incendive devices i.e. terminals. For Ex e certified apparatus there are two main criteria when specifying the apparatus. 1. Are the components acceptable for use in the enclosure i.e. non sparking, and 2. Will any components or wiring be hotter than the temperature classification of the apparatus allows. By knowing the total current through the enclosure and the total resistance of the terminals and wiring, using Ohms Law it is possible to calculate the dissipation power of the circuit Zone 1 & 2 Suitable
19 Ex e Increased Safety (AS/NZS/EN/IEC ) Cage Type Post Type Screw Type All are suitable and have various advantages and disadvantages Post terminals are easy to use but provide a safety hazard as they are potentially exposed during maintenance. Wire terminals have been widely used and are the most common form of terminal rated EEx e
20 Ex e Increased Safety the principle.. General requirements for increased safety, Ex-e, enclosures are: ingress protection to at least IP 54 and additional tests for nonmetallic parts including thermal endurance, resistance to solvents, ultraviolet light, surface conductivity and mechanical resistance to impact of either 4 or 7 joules depending on the size of the enclosure. Ex certified electrical components (with electrical connections that cannot loosen by themselves) General requirements for terminals are: They must be designed to allow the conductor to be easily inserted and clamped, so that contact pressure is maintained without reducing the cross sectional area of the conductor and shall incorporate a positive locking device to prevent conductors working loose by vibration. Specified creepage distances as detailed EN/IEC for the grade of insulation material (CTI) and subsequent maximum voltage rating. Temperature limitation Current de-rating of the terminals (and conductors) of 50%
21 Ex e Increased Safety How the calculation of number/size terminals is done.. The equipment of Ex terminal boxes with terminals and cable screw-connections is subject to defined limits. It depends on the minimum gaps between the current carrying metal components of the terminals and the enclosure walls, and, in addition, on the heat generated at the terminal points. The maximum equipment for the individual enclosure size can be taken from the manufacturer documentation. Green: The maximum number, as physically indicated, can be used; rising temperature does not lead to the limit temperature or the maximum permissible surface temperature in the temperature class being exceeded. Red: Excessive heat generation; the limit temperature or the maximum permitted surface temperature will be exceeded. Remedy: Reduction of current, or Selection of a larger conductor Selection of a larger enclosure
22 Ex e Increased Safety How the calculation of number/size terminals is done.. White field with numbers: Here the limit values are shown. The numbers in the fields result in the maximum number of terminal points to be used! A standard terminal block, e.g. UK5N, has 2 connections; i.e. the values have to be divided by 2. A standard double stack, e.g. DK4, has 4 connections; i.e. the values have to be divided by 4.
23 Ex e Increased Safety Example based upon design limits.. Example #1 Enclosure with Qty mm² terminals: The max. number of terminals for the equipment (physical dimensions) results from the maximum equipment length of 252 mm. The width of the terminal blocks for 10mm² is 10.2mm. This allows the equipment with 24 terminals (252 : 10.2 = 24 terminals ) Equipment according to heat computation: 1) Full use of all 10mm² conductors with 16 A: max. equipment is possible, as the values are within the green fields 2) Full use of the conductors with 50 A: 9 conductors are permissible (10mm²)
24 Ex e Increased Safety Example based upon design limits.. Example #2 Enclosure with Qty mm² terminals with 10 A Qty. 3-4mm² terminals with 20A Qty. 3-16mm² terminals with 50A Cross section/mm² Current/amps Number / utilisation A 8 / (of 31) = 25 % 4 20A 3 / (of 12) = 25 % 16 50A 3 / (of 9) = 33 % Sum = 83% < 100 %, therefore, this means, that on technical heat grounds this equipment is permitted.
25 Ex e Increased Safety Installation Details Certified Ex-e terminal boxes must be provided with an internal or external ground connection of an adequate size for the wiring configuration. (Ex-e terminal boxes are not designed to carry earth fault currents.) The main internal/external ground connection must be connected to the main system earth with the correct coded wire of adequate size but not less than 4mm². All exposed metal parts must be grounded together and to the main ground terminal. IEC (Installations), subclause states In hazardous areas each unused core in multi-core cables shall either be connected to earth or be adequately insulated by means of suitable terminations. Insulation by tape alone is not recommended. Terminating the spare conductor onto an Ex-e terminal is recommended since the conductor could be used later as an active terminal.
26 Ex e Increased Safety Installation Details Important considerations for use of EX Terminals Use conductors of the appropriate size as designated by the terminal. E.g. for a 2.5mm² terminal, the maximum conductor size is 2.5mm². Normally, the manufacturers also advise the AWG size of the conductor that is AWG for 2.5mm². If a larger conductor is used, the creepage & clearance distances could be reduced. The conductor insulation must be carried right up to the terminal throat within 1 mm of the clamp. Normal industrial ratings of the terminal and conductor are de-rated. Unless otherwise specified, only one conductor per terminal clamp is permitted. If flexible, fine stranded conductors are sued, care must be taken to avoid whiskering of the strands that can reduce the creepage and clearance distances. The use of ferrules is recommended to avoid this problem.
27 Increased Safety Ex e Quiz Ex e designed apparatus is suitable for use in Zone 0 False Increased safety enclosures must always withstand the pressure caused by an internal explosion Ex e equipment is mechanically strong to withstand damage from impact False True Ex e terminals are de-rated from their standard industrial rating True Ex e terminal boxes can be used in conjunction with Ex d equipment True
28 Ex ia, ib Intrinsic Safety (AS/NZS/EN/IEC ) Zone 0, 1 & 2 Suitable Circuit is controlled to reduce potential spark energy to below that which would ignite any flammable gas present. I.S. barriers are used to protect the field circuit from non protected circuits This includes the occurrence of:- ia - 2 fault conditions (Equal to NA Division 1 barrier (Zone 0) ib - 1 fault condition
29 Ex ia, ib Intrinsic Safety (EN/IEC ) Where the problem comes from During a potential fault, excess energy could be transmitted to the hazardous area and if a spark occurs could create an explosion. IS zener barriers drive excess energy to ground or by other means protect the device in the hazardous area from ever creating an explosion. Limited to about 1 watt or less in most instances. Typical Ignition Curves for I.S.
30 Ex ia, ib Intrinsic Safety Loop Concept
31 Enclosure Hazardous Location Zener Barriers - Concept Current limiting resistor Zener Protecting Fuse Fault Voltage Source + I.S. Circuit Voltage limiting Zeners Fault Current - Good Isolation from Ground required (500V min.) Non Hazardous Location Good Ground Connection 1 Ω Max.
32 Galvanic Isolated Barriers - Concept Hazardous Location Current limiting resistor Fault Voltage Transformer Source Protecting Fuse + I.S. Circuit Voltage limiting Zeners = Fault Current = - Isolation not needed Non Hazardous Location Safety Transformer No need of Safety Ground
33 Enclosure Hazardous Location Protection Under Fault Condition Zener Barriers Non Hazardous Location Current limiting resistor Zener Protecting Fuse Fault Voltage Source + I.S. Circuit Voltage limiting Zeners Fault Current Poor Isolation or short to Ground Fault Current to ground in Hazardous Location! 250V 250A Fault Current to ground in Non Hazardous Location! - Good Ground Connection 1 Ω Max.
34 Protection Under Fault Condition Isolated Barriers Enclosure Hazardous Location Current limiting resistor Fault Voltage Transformer Source Protecting Fuse + I.S. Circuit Voltage limiting Zeners = = Fault Current remains in Non Hazardou s Location - Isolation not needed Non Hazardous Location Safety Transformer No need of Safety Ground
35 Zener Barriers Advantages Lower parts cost Elementary three components device Disadvantages Dedicated Safety Ground Cost Safety Depends on Good Safety Ground Good Lines Isolation Voltage Drop across Resistor Zeners leakage Infl. accuracy Isolation of lines Infl. Accuracy Requires routine Checks. Grounded non linear semi-conductor (Zener) reduces immunity to interferences (common mode rejection) Applicable only with sensors that are well isolated from ground (500 V)
36 Galvanically Isolated Barriers Advantages No Safety Ground requirement (No cost / No maintenance) Safety not impaired by a fault to ground. Full voltage availability. Better overall accuracy Zener Leakage does not affect accuracy Isolation of lines does not affect accuracy Higher common mode rejection and immunity to interferences Allows the use of grounded or poorly isolated sensors Disadvantages Higher part cost
37 Intrinsic Safety Wiring Methods Intrinsically safe circuits may be wired in the same manner as comparable circuits installed for unclassified locations with two exceptions summarized as separation and identification. These wiring practices are simple and clear; however, they often are overlooked and are the source of potential problems. The intrinsically safe conductors must be separated from all other wiring by placing them in separate conduits or by a separation of 2 inches of air space. Within an enclosure the conductors can be separated by a grounded metal or insulated partition.
38 Combining wiring for IS and non-is circuits can also be combined in single enclosures as long as proper segregation and identification methods are employed. Intrinsic Safety Wiring Methods
39 Remember.. The requirements for 50mm segregation applies not just to the terminals but also all of the interior wiring. Keep this in mind when installation of I.S. and non-i.s. circuits within the same enclosure.
40 Intrinsic Safety Ex i Quiz The minimum required protection for intrinsically safe equipment is IP55 Terminals for intrinsically safe circuits must be at least 50mm from terminals or un-insulated conductors of any non-intrinsically safe circuits Ex n cannot be designed for apparatus gas grouping IIC False True False Intrinsically safe equipment marked (Ex ia) IIC is designed to be installed in a hazardous area False Equipment marked Ex ib IIC T4 is suitable for installation in a Zone 0 area False
41 Intrinsic Safety Ex i Quiz It is permissible to work on an intrinsically safe circuit without a gas free certificate The insulation resistance between an intrinsically safe and nonintrinsically safe circuit must be capable of with standing a minimum of 500VDC Intrinsically safe and non-intrinsically safe cables may be run in the same cable tray if the cables are armoured True True True You cannot use any terminal color but blue for terminals containing only intrinsically safe circuits False
42 Ex na Non-Sparking (AS/NZS/EN/IEC ) Ex na Non-Sparking is a lesser degree of protection than EEx e, where as standard industrial equipment that under normal operation will not produce arcs, sparks or surface temperature high enough to cause ignition of the surrounding gas vapor mixture. Typical products include Zone 2 lighting fixtures and certain enclosures Zone 2 Suitable Electric motors (Squirrel cage motors), terminal boxes, fuses, LEDs, transformers, apparatus requiring low energy, plug connectors, cells, batteries, etc.
43 This provides the customer the ability to use arcing components in a Zone 2 environment w/o the need for flameproof equipment Ex nr Restricted Breathing (AS/NZS/EN/IEC ) Zone 2 Suitable Enclosures, Glands & Cable must be suitable. In this, the product is subject to temperature rise tests and ingress tests to determine the amount of breathing can take place. If during the operation, the product through tight gasketing or sealing has been found to restrict the air flow both in and out of the product, it is determined to be restrictive breathing.
44 Restricted Breathing Better gasketing restricts fixture's breathing Cable entries must be sealed maintains Integrity of fixture Only Exterior Temperatures Considered Big difference In T-Codes Permits Use of Higher Wattages Ex nr Restricted Breathing (EN/IEC ) Allows Flexibility in Lighting Design Temperature based upon external hot spot Enclosed and gasketed fixtures based upon lamp surface temperature, significant difference
45 EX nr vs. Division 2 Lighting Example (NEC) Wattage 400 Watt 250 Watt 150 Watt 100 Watt 70 Watt High Pressure Sodium (SON) Div. 2 Unit T-Code T-2A T-2A T-2B T-3 T-3 Ex nr Unit T- Code T-3C T-3C T-3C T-4A T-4A Change 120 o C 120 o C 100 o C 80 o C 80 o C Implication for lighting design is the use of higher wattage fixtures and using fewer of them for particular areas most notably for floodlights and wellglass applications In the IEC world, it means that more Zone 2 HID can be used since the T-Ratings are comparable to Zone 1 lights, i.e. with no intermediate T Identification numbers, HID for Zone 2 almost always needed a Zone 1 type construction.
46 Ex nr Restricted Breathing (EN/IEC ) Cable Gland Issues. Per SIRA, a Notified Body in the UK "Ex nr glands are a recent creation and no such thing existed until recently. If the glands have been tested and certified as Ex cable glands then they are equipment and don t, in their own right, need to be re-assessed in order to fit. However, the interface does need re-assessing, just like Ex e glands. This is because the gland to enclosure interface needs to maintain the sealing for the restricted breathing. Whilst we could test the sealing, say an O ring or flat seal on an example enclosure, we can t be sure that the actual enclosure to which it is fitted will affect the same sealing. For example it may be a round enclosure and therefore wouldn t seal. For this reason, a condition of certification is imposed related to the interface having to be re-assessed, but this is really the only assessment required (other than temperature limits perhaps). Per , all glands to be used in conjunction with Ex nr equipment must be suitable and certified Ex nr
47 Ex nl Energy Limitation (AS/NZS/EN/IEC ) Zone 2 Suitable Ex nl is a lower form of protection than I.S. and is typical used in circuits in individual components based upon spacing of circuits and other protection concepts. Ex np Pressurized (AS/NZS/IEC ) Zone 2 Suitable Pressurized enclosure, not subject to purging, in which faults are indicated by a drop in the pressure. However, the system need not be switched off immediately. A good example of this is a Zone 2 purge indicator that does not control the equipment being protected, but merely provides indication that the equipment is being protected. Ex P requires de engergization of the panel being protected.
48 Ex nc Enclosed Break (AS/NZS/EN/IEC ) Basic "Encapsulation" - enclosed device - non-ignitable component Contact mechanism or housing designed such that ignition is avoided. - hermetically sealed device Sealing by means of a fusing process such as soft soldering or brazing, welding or fusing of glass in metal - sealed device so constructed, that it cannot be opened during normal operation. - encapsulated device completely enclosed in an encapsulating compound.
49 Non-Incendive Ex n Quiz A certified gland must always be used for an Ex n application True For Ex n standards, hermetic sealing of enclosure can be satifactory achieved by the use of O rings and/or gaskets Ex n cannot be designed for apparatus gas grouping IIC True False The Temperature classification for an Ex n standard must always take into consideration the external and internal surface temperature True Live working is not permitted on Ex n type equipment True
50 Entire rooms or buildings can be pressurized as well as enclosures. The requirements of IEC must meet the following: Ex p Pressurized (AS/NZS/EN/IEC ) Positive pressure must have sufficient capacity to maintain pressure of at least 25 Pa (2.5mm water gauge) in the room and the room must have either air locks for the doors or the outward velocity must be at least m/s with all doors and any openings simultaneously opened. Pressurizing gas must be air (containing at least 19.5% Oxygen by volume When the pressurizing system fails, any equipment such as lights that cannot be switched off must be protected by other means suitable for the location. One note: the NFPA requires 25 Pa internal pressure for enclosures, while the IEC requires 50 Pa for enclosures in Zone 1 and 25 Pa for pressurized rooms. Zone 1 & 2 Suitable
51 Ex q Powder Filled (AS/NZS/EN/IEC ) Powder filling originated in France where it has been used for many years. IEC Standard 79 5 introduced in 1967 established this concept as an international method of protection. Zone 1 & 2 Suitable This protection concept is normally suitable up to and including Group IIC gases and The original IEC standard referred to sand filled but has been changed to powder filled. the T6 temperature classification, in Zone 1 or 2 hazardous area locations. The enclosure construction requirements are a pressure test of 0.5 bar (1 bar = 14.5 psi) over pressure for 1 minute and, if not protected by another enclosure, a minimum Ingress Protection of IP 54, the same requirement for Ex e enclosures. If the component is protected by another enclosure (e.g. a capacitor in the type of protection q built into a light enclosure) then no specific requirements for the type of IP protection is required. When the enclosure is filled with the q medium (quartz sand, powder or glass beads) there must be no voids in the enclosure. The maximum distance from live parts of electrical components to earth fitted inside the metal enclosure or metal screen is specified and, depending on the applied voltage, can vary from 10 mm at 250 volts to 50 mm at 6,600 volts. If the enclosure is permanently factory sealed and the voltage does not exceed 500 volts, the minimum distance between live parts or live parts to earth can be reduced by 5 mm.
52 Ex m Encapsulation (AS/NZS/EN/IEC ) Zone 1 & 2 Suitable Encapsulation is a type of protection whereby parts that are capable of igniting an explosive atmosphere, by either sparking or heating, are enclosed in a compound is such a way that the explosive atmosphere cannot be ignited under operating or installation conditions. The selected compound must be in line with the requirements given in IEC and may be any thermosetting, thermoplastic, epoxy, resin (cold curing) or elastomeric material with or without fillers and/or additives, in their solid state. The temperature p range must satisfy the requirements of an appropriate standard for this type of protection. (Thermal stability at maximum operating temperature.) When considering the safety aspects of Ex m encapsulation, the design must account for: Resistors, capacitors, optoisolators, diodes etc., must not operate at more than 2/3 of their rated voltage. The temperature rise of components and wiring must be limited. Voids and air pockets other than those for relays or other devices must be avoided. The effect of a component s short circuit during fault conditions. The Ex m encapsulation protects electronic circuit relays, timers, lamp test devices and components in Zones 1 or 2 hazardous areas. Encapsulation is finding increased usage for printed circuit boards that are assembled in small rail mounted housings similar to terminals.
53 Ex o Oil Immersion (AS/NZS/EN/IEC ) Zone 1 & 2 Suitable In 1968, IEC subcommittee 31E wrote IEC Standard 79 6 which was recognized by many countries for use in Zone 1 locations. The Oil Immersion Ex o concept has historically been used for heavy duty switchgear, motor starters and transformers. The basic principle as shown above is to immerse the electrical parts in mineral oil, which will prevent any exposure of the arcing or sparking to the an explosive atmosphere. It will also quench arcs and limit the temperature rise on electrical q p parts. Standards for oil immersion protection, Ex o, require that all parts capable of producing arcs or sparks must be immersed in the oil at a depth not be than 25 mm. A method to check the oil level must be provided, e.g., by a sight glass or by some other reliable method. Some mineral oils used in switchgear apparatus produce acetylene and hydrogen gas when arcing occurs. Because of the risk of fire or an explosion with oil immersion, this application for apparatus in hazardous areas has been generally restricted. In the Petro Chemical industries there are very few examples of Ex o certified products installed in hazardous areas even though the standards permit its use in Zones 1 and 2.
54 Hybrid Ex Protection Techniques It is very common to use a variety of protection concepts in a single product Shown below are two examples. The light fitting is rated Ex dem using Ex e Increased safety for the housing & terminal, Ex d flameproof for the disconnect switch and lamp holders and Ex m for encapsulation of the ballast.. Final product rated Ex edm The control panel below is using Ex e increased safety for the housing and terminals and Ex d for flameproof operators Final product rated Ex de
55 Hybrid Ex Protection Techniques 316SS Ex d & Ex e Enclosures
56 Examples of Ex components potentially inside Ex e enclosures Question: ATEX U or X designation. Assembly, Component Certification
57 Hybrid Protection Techniques These products also use hybrid technologies to reach the same effect but in different ways The enclosures below are rated either Ex d flameproof or Ex e increased safety with the arcing components housed in the d chamber, while the e terminals are in the attached e enclosure separated with the use of line bushings that provide an flameproof barrier between the two enclosures. While previously, the order of the protection letters was deemed to indicate the primary means of protection first with secondary protection second and so on, the latest version of states that the protection concepts should be in alphabetical order. Arcing/Sparking Non Arcing/Sparking
58 Hybrid Ex Protection Techniques How many protection techniques can you find in this picture? Hint: Total of five methods Ex m Ex e Ex ia Ex d Ex nr What Zone is this enclosure suitable for??? Zone 2
59 Hybrid Ex d & e Protection e & d electrical components: the contacts make and break in a flameproof d chamber Ex e enclosure Ex de component d switch or contacts e enclosure e enclosure d switch In general, many of the latest developments of products for hazardous locations involve the combining of various protection techniques. As long as combination of protection techniques are all suitable for the same Zone or Category of hazard, the product is suitable for that hazard. Example, both e & d protection techniques are suitable for Category 2 (22) or Zone 1 hazardous areas.
60 Which EX protection method is the most cost effective solution? Generalities If Zone 1 locations Ex e Increased Safety is typically the way to go if at all possible due to weight, cost and ease of maintenance Ex d used when e protection is not practical, i.e. Motor Starters, Circuit Breakers, etc. Hybrid e & d usually the best concept where you take the best of both and combine the two. Lighting Zone 1 HID lighting is going to always be Ex d construction, where fluorescents are more likely to be Ex e plastics. LED s have have been designed using both protection concepts. For low mounting applications, fluorescents are usually a most cost effective solution. To minimize fixture count, higher wattage HID s in Zone 2 or non-hazardous locations with intermixed Fluorescents has been the trend. Instrumentation circuits for Zone 1 are typically I.S. Generalities If Zone 2 locations. More protection concepts are available such as Ex nr lighting, Ex na lighting, Ex nc non-sparking, etc. The major area of potential savings is Zone 2 lighting HID, restricted breathing vs. Flameproof Ex d construction. The component issues with glands and enclosures for the most part will not change from Zone 1 construction, i.e. brass glands, fiberglass enclosures, etc. In general, look at Ex e construction wherever possible, minimize the Ex d wherever possible
David O Brien, CMP Products (David.OBrien@cmp-products.com) 1) Main Function of Cable Glands 2) Common Issues with Cable Glands 3) Compliance / Standards, changing times 4) How do we select Cable Glands?
This document is the Exd Flame Detector Installation Guide/010/Issue 3 Flameproof (Ex d) IR² and IR³ Flame Detector Installation Guide General This Installation Guide gives information on the Flameproof
1 of 7 Explosion proof enclosures DE8 C 2 of 7 The Ex d enclosures are rugged and designed for harsh environment like: Oil and gas industry Chemical industry Pharmaceutical industry Agribusiness Without
> Latest LED technology with a high luminous efficacy and a long service life > As pendant light fitting or side entry lamp > Central locking > All-pole disconnection by means of an N/C switch when the
Informational Note No. 2: In unclassified locations, identification is necessary to ensure that nonintrinsically safe wire will not be inadvertently added to existing raceways at a later date (C) Color
> As pendant light fitting or side entry lamp > Version with 1 or 2 lamps: 18 W, 36 W and 58 W > Central locking > All-pole disconnection by means of an N/C switch when the lamp is opened > End of life
Terminal box The /TNCC range comprises many standard sizes of enclosures manufactured in stainless steel 316L for maximum environmental protection. The main body is manufactured from minimum 1,5 mm sheet
2.12 page 223 2.12 Products for Explosion hazardous Environment Non-electric valves for explosion 2.12.1 page 224 hazardous environment The following manually and mechanically actuated valves are available
Electrical Equipment in Hazardous Areas: Field Inspections Bill Rankin Electrical Engineer / Senior Electrical Inspector Abstract Electrical equipment and installations that fall within explosive gas atmospheres
Important information: These instructions contain safety information, read and follow them carefully. Dialight will not accept any responsibility for injury, damage or loss which may occur due to incorrect
Instructions for Safe Use (Certification N:o VTT 08 ATEX 029) Thank you for choosing Slam Trans portable transformer for your job site. Purpose of this manual is to provide you all the necessary safety
Making sense of Intrinsic Safety and Intrinsically Safe Tools What is Intrinsically Safe? Intrinsic safety is a protection standard employed in potentially explosive atmospheres. Devices that are certified
www.stahl.de > Clear assignment safe technology easy installation > Intelligent structure only one rotary actuator for frequency-controlled drives ) 20 ms leading auxiliary contact for safe motor disconnection
IEC 61892-7 INTERNATIONAL STANDARD Edition 2.0 2007-11 Mobile and fixed offshore units Electrical installations Part 7: Hazardous areas INTERNATIONAL ELECTROTECHNICAL COMMISSION PRICE CODE XA ICS 47.020.60
Series Features: Color coding and pin configuration makes it physically impossible to mate plugs and receptacles of different voltages and current ratings (per IEC 60 309-2). Interlocked switch mechanism
FieldBarrier Features Assembly 8... 12 outputs Ex ia IIC, FISCO and Entity Advanced fault isolation and diagnostics at the spur FieldBarrier in Zone 1/Div. 2 Instruments in Zone 0...1/Div. 1 For FOUNDATION
Two Documents are used for the Classification of Combustible Dusts and Hazardous Locations: NFPA 499-Recommended Practices for the Classification of Combustible Dusts and Hazardous Locations for Electrical
0102 Model Number Features 15 mm quasi flush Usable up to SIL2 acc. to IEC 61508 Accessories BF 30 Mounting flange, 30 mm V1-G-N-2M-PUR Female cordset, M12, 2-pin, NAMUR, PUR cable V1-W-N-2M-PUR Female
distributing & controlling system solutions your safety our reality Users > Oil and gas industry production storage transport > Petrochemical industry > Chemical industry > Pharmaceutical industry > Food
Operating Instructions Cable Glands Ex d and Ex e with Compound > Contents 1 Contents 1 Contents...2 2 General Information...2 3 General Safety Information...3 4 Designated Use...4 5 Technical Data...4
> Saltwaterresistant enclosure, aluminium alloy, optionally with painting > Maintenancefree operation and long service life with induction lamp or LED > Mounting with ring bolts or tiltable mounting bracket
SPARTAN Floodlight Range Installation Guide CML13ATEX3007 IEC Ex CML14.0001 This installation guide provides instructions for installing the Infra-Red and White-Light SPARTAN SPX series of explosion protected
Safety instructions VEGAFLEX FX8*(*).FC/ O****A/H***** FM 3046039 Class I Div 1, Groups A, B, C and D Class II Div 1, Groups E, F and G; Class III Class I, Zone 0, AEx ia IIC Ga, Ga/Gb, Gb Document ID:
www.allsafetyproducts.com Page 1 of Introduction to Handiwash system Hot and cold water at any location is now an affordable reality. All Safety Products Inc are proud to announce what is undoubtedly the
Technical data sheet TDS0070 ATEX Certified II 2 G Ex d IIC T4 Gb IECEx Certified Ex d IIC T4 Gb Ta = -20ºC to +60ºC FEATURES INCLUDE: - ATEX and IECEx Certified explosion proof Exd housing for Premier
SDN-P DIN Rail Series The SDN DIN Rail power supplies provide industry leading performance. Sag Immunity, transient suppression and noise tolerant, the SDN series ensures compatibility in demanding applications.
Approved by APPROVED Fire Alarm System Accessories FM Approved* Intrinsically Safe Devices Single and Dual Channel Isolated Barrier Modules Features Single or dual channel intrinsically safe, transformer
Mechatronic pressure measurement Compact pressure switch Flameproof enclosure Ex d Model PCA WIKA data sheet PV 33.31 for further approvals see page 4 Process Compact Series Applications Pressure monitoring
www.stahl.de > Switch socket / plug 63 A > Large switch handle with clear switch position indication padlockable in 0- and I-position > Low insertion and withdrawal forces through individually encapsulated
Highest level of safety under the most difficult conditions Fire protection for potentially explosive areas Fire detection technology The Ex Products Nuclear power Logical: The avoidance of flammable materials
330450 High Temperature Acceleration System Bently Nevada* Asset Condition Monitoring Description The standard 330400 Accelerometer has a limited temperature range it can be exposed to, due to its signal
SEISMIC VELOCITY TRANSDUCER T1-40 Measurement of Omnidirectional Absolute Vibrations Certified according to ATEX 94/9/CE directive OPERATION Transducer T1-40 serves for seismic measurement of the absolute
Capacitive Prox Threaded, Cylindrical Sensor Detects Metallic and Non-metallic Objects Permits non-contact detection of metallic and non-metallic objects such as glass, wood, water, oil and plastic Allows
Legislation, Standards and Technology Lightning and surge protection for intrinsically safe circuits by Manfred Kienlein Special explosion protection measures must be taken in all industrial sectors where
Table of Contents Introduction............................................................. 3 Basic Requirements for an Explosion.......................................3 What is an explosion?...................................................3
PTX Resistance Thermometer Measurement of temperatures in gases, vapors, liquids and dust Technical short manual 05.16 Main features Process temperature from -200 C to 600 C Wide variety of process connections,
What are the basic electrical safety issues and remedies in solar photovoltaic installations? Presented by: Behzad Eghtesady City of Los Angeles Department of Building and Safety Topics Covered Photovoltaic
The basics of explosion protection preface It is a fact that gases, vapours and mists escape during the production, processing, transportation and storage of flammable substances in the chemical and petrochemical
ATEX Directive 94/9/EC - EUROPEAN DIRECTIVES GENERAL The accidental ignition of an atmosphere containing a large quantity of gas, vapour, mists and/or dust may cause an explosion. Specific measures have
Basics of Explosion Protection INTRODUCTION Understanding Global Explosion Protection Class and Division System Class-Zone System CENELEC Zone System IEC A INTRODUCTION Basics of Explosion Protection Basics
Modular Integration of Process Equipment Packages for Oil and Gas Facilities Copyright Material PCIC Europe Paper No. PCIC Europe XXXX Allan Bozek EngWorks, Inc. 1620 49 th Avenue, SW Calgary, AB T2T 2T7
Outdoor 33.6W Dual Port Passive Power-over-Ethernet Midspan For External Security Cameras and Wireless Access Points Features SELV Compliant No Detection Passive Injector Gigabit Compatible Full Protection
Mechatronic pressure measurement Mini pressure switch Stainless steel switch enclosure Model PXS WIKA data sheet PV 34.36 Process Mini Series Applications Pressure monitoring and control of processes Safety-critical
Product guide Enclosed NEMA starters usa.siemens.com/nema-controls The right choice for applications that demand the best Siemens NEMA combination and non-combination starters for industrial and construction
425 CONTROLS DATA MANAGEMENT PROCESS AUTOMATION EUROCUBE General purpose single phase thyristors and solid state relays Product data abc 425 EUROCUBE A complete range of low cost solid state relays and
Overview d Immersion Heaters consist of hairpin bent tubular elements welded or brazed into a flange and provided with wiring boxes for electrical connections. heaters are installed by bolting to a matching
Connectors - up to 280 Amps 2 Pole Wires sizes from #12 (3.3 mm²) to 1/0 (50 mm²) fit in the second to largest connector in the SB series. The 3 pole adds an additional position for power or grounding.
81471067 Electric Monitor Motor Control Panel For use with Model 8394059 SPIT-FIRE Monitor Installation, Operation, and Maintenance Instructions FOR ATEX APPLICATIONS 1302 WEST BEARDSLEY AVENUE P.O. BOX
Legislation, Standards and Technology Explosion Protected Electrical Apparatus in the Russian Federation Adaptations of National Standards to International Standards, deviations and peculiarities by Vitaly
Legislation associated with Hazardous Locations Pieter Coetzee ZONE 2 ZONE 0 ZONE 1 Be safe be Ex Contents History Introduction Occupational Health and Safety Act. (Act 85 of 1993) General Machinery Regulation
FL Series: Light Duty Nonmetallic Fluorescent Lighting Fixtures, Standard and Emergency Battery Back-Up 2 x 58 W 2 x18 W Compliance Data: ATEX IEC: Zone 2 22 ATEX IEC CE Ex nr II or na II T6 or T5 or T4
ELECTRICAL GUIDELINES FOR SINGLE-FAMILY HOME OWNERS: Chapter 12 of the Burlington Code of ordinances allows owner occupants of single family homes to do their own wiring if they choose. If you choose to
INSTALLATION OPERATION AND MAINTENANCE INSTRUCTIONS FOR EXHEAT INDUSTRIAL IMMERSION HEATERS (INCLUDING FLAMEPROOF) Please read these instructions thoroughly before installation and ensure they are passed
Hazardous Locations Training If you are involved with projects associated with hazardous locations, which involves the installation or inspection and maintenance of electrical or non-electrical e.g. mechanical;
Type: DILM115(RAC240) Article No.: 239548 Sales text Contactor,55kW/400V,AC operated Ordering information Connection technique Description Description Rated operational current Screw terminals 3 pole AC
Background When combustible products are loaded/off-loaded from a tanker truck there is a risk of an explosion occurring due to ignition caused by a static discharge from the truck itself. To prevent this
-5 Safety information The product was developed, manufactured and inspected according to the basic safety requirements of EC Guidelines and state-of-the-art technology. The instrument is designed for use
for harsh & hazardous (classfied) locations Construction Demolition Maintenance Turnarounds Shutdowns D-13 temporary / mobile power Temporary power products are used on industrial and construction sites
Type FX4 FX4 Explosion-Proof Electric Air Heaters FX4 heaters are UL listed and/or CSA certified for use in hazardous locations. They are designed for dry indoor industrial applications such as oil refineries,
READ THIS MANUAL BEFORE PROCEEDING WITH THE INSTALLATION. FAILURE TO FOLLOW THE INSTALLATION INSTRUCTIONS MAY VOID YOUR WARRANTY! The main power to any existing system must be disconnected prior to the
INTEK SPA VIA MAZZINI 75, REZZATO, BS 25086, ITALY has been assessed and found to be eligible to participate in the Third Party Test Data Program (TPTDP) DA File: DA928 Issued: 206-07-2 Jim Feth Expires:
0102 Model Number Features 2 mm flush Usable up to SIL 2 acc. to IEC 61508 Technical Data specifications Switching element function NAMUR, NC Rated operating distance s n 2 mm Installation flush Output
ES-3481 JUNE 27, 2005 PRESSURE AND TEMPERATURE SENSORS FOR THE E340 BOILER ROOM CONTROL DESCRIPTION The PS348 and TS348 Series of pressure and temperature sensors are designed for use with the E340 Boiler
Temperature Repeater Features Assembly 1-channel isolated barrier V DC supply (Power Rail) Resistance and RTD input (Pt100, Pt500, Pt1000) Resistance output Accuracy 0.1 % Line fault detection (LFD) for
2100 and 2100E Level Switches Product Bulletin Fisher 2100 Pneumatic and 2100E Electric Liquid Level Switches Fisher 2100 on-off pneumatic switch and 2100E electric switch sense (shown in figure 1) high
Safety Instructions CGR Zone 20/21 IECEx Centurion Guided Radar HAWK CGR SERIES IECEx Zone 20/21 Intrinsically Safe probe / Flameproof enclosure IECEx TSA 14.0037X Ex ia tb [ia Da] IIIC T85 C Da Db Tamb
33.6W Power over Ethernet Waterproof Adapter PoE Plus Single Port Injector for Outdoor Application Features Compliant with the IEEE802.3at Standard -40 to +60 C Temperature Range Diagnostic LEDs Full Protection
SPECIFICATION FOR LOW VOLTAGE SWITCHBOARD SEN I N D E X Description 10 STANDARD TECHNICAL REQUIREMENTS 11 Standards 12 General Operating Conditions 13 General Description Of Switchboard 131 Structure 132
8146/5 Series Breaker Panelboards DISTRIBUTION BREAKER PANELBOARDS FOR HAZARDOUS & CORROSIVE ENVIRONMENTS Breaker Panels Features: Wide variety of Flameproof branch circuit breakers for Zone 1 & Division
Specifications and Ordering Information 1701/06 FieldMonitor Isolator Terminal Base and 170190 Dual Galvanic Isolator for Hazardous Areas Description The 1701/06 Isolator Terminal Base (ITB) and 170190
Electrical Temperature Measurement Threaded Resistance Thermometers Model TR10-D, Miniature Design WIKA Data Sheet TE 60.04 Applications Machine building, plant and tank construction Power transmission
MAKING MODERN LIVING POSSIBLE Instruction ATEX instruction for PAHT G 2-90 in dust applications danfoss.high-pressurepumps.com Table of Contents 1. Common demands for Category 2 and 3 installations...3
Safety Requirements for Power Supplies Intended for Medical Applications Disclaimer: Emerson does not warrant the accuracy or completeness of this article, including but not limited to, the reliability
D46 Isolating Barriers for our sensors A5S1 in Ex-areas Series KEY FEATURES ATEX / IECEx certified, also approval for UL / CSA and EAC (Russia, Kazakhstan and Belarus Customs Union) Protection grade Ex
Your consent to our cookies if you continue to use this website.