1 INSPECTION AND TESTING OF EMERGENCY GENERATORS Certification requirements NFPA 101(00), Sec requires that emergency generators be installed, tested and maintained in accordance with NFPA 110, Standard for Emergency and Standby Power Systems. Chapter 2 of NFPA 101 references the 1999 edition of NFPA 110. Buildings that fall under Chapter 18 of NFPA 101(00) and are equipped with or in which patients require the use of life-support systems (e.g. hospitals, nursing homes with residents on ventilators) must also meet the maintenance and testing provisions of the 1999 edition of NFPA 99, Standard for Health Care Facilities [see NFPA 101(00), Sections , , and ]. Provisions dealing with maintenance and testing of emergency generators can be found in NFPA 99(99), Sec This section starts out by referencing NFPA 110, but also deals with such issues as: Testing intervals Test conditions Personnel qualifications Maintenance and testing of circuitry Maintenance of batteries Each facility should have a copy of these standards. They can be ordered from NFPA at or Generator classifications In order to follow the requirements in NFPA 99 and NFPA 110, you need to know the classification systems used by those standards: 1. Let s take a look at NFPA 99 first: a. NFPA 99 treats emergency generators as part of an essential electrical system (EES), which is defined as, A system comprised of alternate sources of power and all connected distribution systems and ancillary equipment, designed to ensure continuity of electrical power to designated areas and functions of a health care facility during disruption of normal power sources, and also to minimize disruption within the internal wiring system. [see NFPA 99(99), Chapter 2, Definitions]. b. NFPA 99 breaks essential electrical systems down into three categories Type 1, Type 2 and Type 3. Basically, the services provided by a facility determine the type of EES required as follows: NFPA 99(99), Sec requires essential electrical systems in hospitals to conform to Type 1 system requirements. NFPA 99(99), Sec requires essential electrical systems in nursing homes to conform to Type 2 system requirements. By exception, however, Type 3 systems are allowed in nursing homes that do not provide life support (e.g. ventilators). c. For a more detailed description of these three types of systems, see Chapter 3 of NFPA 99(99). If you re unsure about which type of system describes your generator, the vendor that installed and/or maintains your generator should be able to provide you with that information.
2 Page 2 of 7 2. NFPA 110, on the other hand, treats emergency generators as part of an emergency power supply system (EPSS). a. There are two important definitions to keep in mind [see NFPA 110(99), Chapter 2]: Emergency Power Supply (EPS): The source of electric power of the required capacity and quality for an emergency power supply system (EPSS), including all the related electrical and mechanical components of the proper size and/or capacity required for the generation of the required electrical power at the EPS output terminals. A further explanation can be found in the Appendix [see NFPA 110(99), Sec. A-2-1]: For rotary energy converters, components of an EPS include the following: prime mover, cooling system, generator, excitation system, starting system, control system, fuel system, and lube system, if required. Emergency Power Supply System (EPSS): A complete functioning system of an EPS coupled to a system that can consist of conductors, disconnecting means, and overcurrent protective devices, transfer switches, and all control, supervisory, and support devices up to and including the load terminals of the transfer equipment needed for the system to operate as a safe and reliable source of electrical power. b. NFPA 110 breaks emergency power supply systems down into two categories Level 1 and Level 2. Once you know the NFPA 99 classification of your emergency generator (i.e. Type 1, Type 2 or Type 3), that standard tells you where your generator fits into NFPA 110. NFPA 99(99), Sec specifies that: Type 1 and Type 2 essential electrical system power sources shall be classified as Level 1 generator sets per NFPA 110. Type 3 essential electrical system power sources shall be classified as Level 2 generator sets per NFPA 110. State licensure requirements MSFC(07), Sec requires that emergency generators be maintained in accordance with the 2002 edition of NFPA 110. Fortunately, the provisions in this edition of the standard applicable to inspection and testing are very similar to those found in the 1999 edition of the standard. Maintenance and testing Applicable standards Requirements for routine maintenance and operational testing of emergency generators can be found in: Chapter 6 of the 1999 edition of NFPA 110 Chapter 8 of the 2002 edition of NFPA 110 Sections 3-4.4, and of NFPA 99(99) Maintenance and testing General 1. Maintenance and testing is critical to the continued reliability of your emergency generator and must be performed in accordance with manufacturer s recommendations, instruction manuals, and the minimum requirements of NFPA 110 and the authority having jurisdiction (AHJ) [see: NFPA 110(99), Section 6-1.1; NFPA 110(02), Sec ].
3 Page 3 of 7 2. Your facility should have at least two sets of instruction manuals for all major generator components. One set should be kept in a secure, convenient location near the equipment. The other set should be kept in a different secure location [see: NFPA 110(99), Section 6-2.1; NFPA 110(02), Sec ]. These manuals must, at a minimum, contain the following: A detailed explanation of the operation of the emergency power supply system Instructions for routine maintenance Detailed repair instructions An illustrated parts list and part numbers Illustrated and schematic drawings of electrical wiring systems, including operating and safety devices, control panels, instrumentation and annunciators 3. Special tools and testing devices necessary for routine maintenance must be available for use when needed [see: NFPA 110(99), Section 6-2.3; NFPA 110(02), Sec ]. 4. Routine maintenance, inspection and operational testing of the emergency generator and associated components must be overseen by a properly trained person [see MSFC(07), Sec ; NFPA 99(99), Sec (b)3; NFPA 110(99), Sec ; NFPA 110(02), Sec ]. Evidence of such training should be kept in the designated employees personnel file. In the absence of a properly trained person on-site, an outside vendor may need to be contracted to oversee the performance of all or part of these services. 5. The standards do not establish a specific date and time of day for required testing. Those are to be determined by management and are typically scheduled so as to provide minimum disruption of facility operations. Weekly inspections To meet federal certification and state licensure requirements, healthcare facilities must inspect their emergency generators weekly [see NFPA 110(99), Sec ; NFPA 110(02), Sec ]. At a minimum, this weekly inspection should include a check of the following: 1. Fuel (check main and day tank fuel supply levels; day tank float switch; piping, hoses and connectors; operating fuel pressure; and for any obstructions to tank vents and overflow piping 2. Oil (check for proper oil level and oil operating pressure; lube oil heater) Engine oil level can be checked with the unit stopped or running on many engines; otherwise, it should be checked with the unit stopped Oil operating pressure should normally be above 40 psi 3. Cooling system (check coolant level, water pump(s), jacket water heater, belts, hoses, fan) 4. Exhaust system (check drain condensate trap and for possible leakage) 5. Battery system [look for possible corrosion; check specific gravity, electrolyte level (a level between 1250 and 1275 is acceptable) and battery charger] 6. Electrical (conduct a general inspection of wiring and connections; check circuit breakers/fuses) 7. Prime Mover/Generator (Check for debris, foreign objects, loose or broken fittings; check guards and components; look for any unusual condition of vibration, leakage, noise, temperature or deterioration NOTE: This is not an all-inclusive list. The equipment manufacturer may have additional maintenance requirements that will likely include monthly, quarterly, semi-annual and annual inspections and checks.
4 Page 4 of 7 Monthly testing 1. To meet federal certification and state licensure requirements, healthcare facilities must exercise their emergency generators under load at least monthly [see NFPA 110(99), Sec ; NFPA 110(02), Sec ]. There are a number of ways to comply with this requirement: a. The base requirement is that generators be exercised for a minimum of 30 minutes* using one of the following methods [see NFPA 110(99), Sec ; NFPA 110(02), Sec ]: i. Under operating temperature conditions and at not less than 30 percent of the generator s nameplate kw rating. A 100 kw generator, for example, would need to be exercised under a load of at least 30 kw to meet this requirement. Normal operating temperatures are set by the manufacturer. Something to consider when scheduling your monthly tests is that your particular generator may not reach operating temperature in 30 minutes* and that running the generator for short periods of time may be harmful to the engine. You also want to make sure that the generator runs long enough to ensure that all engine parts are properly lubricated. ii. Loading that maintains the minimum exhaust gas temperatures recommended by the manufacturer (it is unlikely that minimum exhaust gas temperatures will be reached if the generator isn t carrying a load equivalent to at least 30 percent of the generator s nameplate kw rating). *Note: Warm-up and cool-down times do not count toward the required 30 minutes. b. An alternate method is provided for diesel-powered generators that do not meet the testing requirements outlined in 1.a above. This could occur when, for example, a large generator in relation to the load is installed (e.g. either to account for the largest motor connected to the generator or to accommodate future expansion of the facility). Such generators can be exercised monthly with the available load and exercised annually with supplemental loads at 25 percent of nameplate rating for 30 minutes, followed by 50 percent of nameplate rating for 30 minutes, followed by 75 percent of nameplate rating for 60 minutes, for a total of 2 continuous hours [see NFPA 110(99), Sec ; NFPA 110(02), Sec ]. c. For gasoline-powered, natural gas-powered or propane-powered generators that do not meet the testing requirements outlined in 1.a above, it will likely be necessary to add more load to the generator or conduct a load bank test to comply with testing requirements (a load bank is, typically, a mobile piece of equipment that simulates the actual electrical load the generator is intended to power). Where equivalent loads are used for testing, it s important to note that such loads are required to be automatically replaced with the emergency loads in case of failure of the normal power [see NFPA 110(99), Sec ; NFPA 110(02), Sec ]. d. Where a generator set is used for peak load shaving or operated during a power outage, such use is allowed to be substituted for a routine monthly test, provided the generator is operated in accordance with the standards and the appropriate data are recorded. Another thing to keep in mind, however, is that NFPA 99(99), Sec (b)1 requires a minimum 20-day and maximum 40-day interval between tests [see also NFPA 99(99), Sections (b) and (b)].
5 Page 5 of 7 2. Load tests must include complete cold starts [see NFPA 99(99), Sec (b)2; NFPA 110(99), Sec ; NFPA 110(02), Sec ]. 3. Time delays must be set as follows [see NFPA 110(99), Sec ; NFPA 110(02), Sec ]: a. Time delay on start: 1 second minimum.* Exception: Gas turbine cycle: 0.5 second minimum. *Note: NFPA 101(00), Sec requires that emergency loads be picked up within 10 seconds. b. Time delay on transfer to emergency: none. c. Time delay on restoration to normal power: 5 minutes minimum (to give the primary source sufficient time to stabilize before retransfer of the load, a delay of between 15 and 30 minutes is recommended). d. Time delay on shutdown: 5 minutes minimum. It s important to be prepared in case something goes wrong during testing. It is strongly recommended that your facility have a policy in place that makes provisions for a portable generator or other alternate power source for situations in which the emergency generator malfunctions or, worse yet, is out of service. Transfer switches 1. Transfer switches are required to be operated monthly [see MSFC(07), Sec ; NFPA 110(99), Sec ; NFPA 110(02), Sec ]. 2. This monthly test must consist of electrically operating the transfer switch from the normal/standard position to the alternate position and then a return to the normal/standard position [see MSFC(07), Sec ; NFPA 110(99), Sec ; NFPA 110(02), Sec ]. In many cases, a Transfer Test switch or button is provided and can be used to perform this test. Where this feature does not exist, it may be necessary to manually disconnect normal power in some fashion to the transfer switch (see some words of caution on testing below). 3. Transfer switches must also be inspected monthly to ensure that they are maintained free from accumulated dust and dirt and to check for deterioration of the transfer switch contacts [see MSFC(07), Sec ; NFPA 110(99), Sec ; NFPA 110(02), Sec ]. 4. Because they are such a key component in the successful operation of your emergency generator, it is recommended that you consider having infrared testing of your transfer switch(es) conducted annually to check for loose connections. Some words of caution on testing 1. Shutting off power, especially shutting off the main breaker, can expose a person to possible shock, electrocution and/or arc flash hazards. It is important, therefore, that anyone performing a test in this fashion be adequately trained and take proper safety precautions, including the wearing of proper personal protective equipment (PPE). To reduce the safety risks, it is strongly recommended that facilities not already so equipped consider adding a switch for testing of their transfer switches.
6 Page 6 of 7 2. The explanatory information in NFPA s 1999 Health Care Facilities Handbook to Sec (b)2, which addresses test conditions (including cold starts and appropriate automatic and manual transfer of essential electrical system loads), provides more food for thought: Testing procedures might range from manually disconnecting power to the power sensors on transfer switches to manually opening the main incoming feeder breakers. It is very important that each test method be fully understood by all staff through appropriate notification and that the consequences of each method (if something fails to function) be weighed carefully. A procedure for returning to the normal power source should also be established in the event a failure occurred during testing. There is a false assumption that disconnecting a facility s mains is the best method of testing the standby generator(s) and essential electrical system. One has to always consider the possibility that failure of the disconnecting means or some other unexpected contingency might make it difficult or impossible to restore normal power. It is probably better to initiate engine start by interrupting power just ahead of the transfer switch(es) on an alternating or rotating basis in order to make sure each transfer switch has an intact engine start circuit. DOCUMENT your inspections and tests NFPA 110(99), Sec requires the establishment of a written schedule for routine generator maintenance and testing [see also: MSFC(07), Sec ]. A sample schedule can be found in Appendix A of the standard [see Figure A-6-3.1(a)]** or may even be available from the equipment manufacturer [see also: NFPA 110(02), Sec and Figure A.8.3.1(a); 1999 Health Care Facilities Handbook Appendix C-3.2]. ** Because there is a lot riding on the successful operation of a facility s emergency generator, it is strongly recommended that the schedule for Level 1 emergency power supply systems be followed when establishing your maintenance schedule. A written record of generator inspections, tests, exercising, operation and repairs must be maintained on the premises and be available for review by the fire inspector on request. This record must, at a minimum, include: the date of the report, name(s) of the person(s) providing the service, identification of unsatisfactory conditions and corrective action taken (including parts replaced), and any testing of repairs recommended by the manufacturer [see MSFC(07), Sec ; NFPA 99(99), Sec ; NFPA 110(99), Sec ; NFPA 110(02), Sections and ]. A sample inspection log can be found in Appendix A of NFPA 110(99) [see Figure A-6-3.1(b)] or may even be available from the equipment manufacturer [see also: NFPA 110(02), Figure A.8.3.1(b)]. A sample testing log can be found in NFPA 110(02), Figure A.8.4.1(a) or may even be available from the equipment manufacturer. As an alternate, sample inspection and testing logs have been developed to serve as a guide that you can use in creating your own logs. Completed logs are provided to serve as examples of how the logs are expected to be filled out.
7 Page 7 of 7 It s important that at least two people in your facility know where your logs are kept to increase the likelihood that they can be readily provided if requested during an inspection. It is recommended that these logs be maintained for at least three years. Click Here for the Emergency Generator Weekly Inspection Checklist Click Here for the Emergency Generator Monthly Test Log
Generator Testing in Nursing Facilities Introduction Recent emergencies and natural disasters have emphasized the need to ensure that nursing facilities have an adequate EPSS in place should the loss of
Prime Power Services, Inc. Georgia, Carolinas 800 741 0128 NFPA 110 Standards for Emergency & Stand by Generators June 1, 2010 NFPA Disclaimer The views and opinions expressed in this seminar are purely
CITY OF SPRING LAKE PARK Code Enforcement Department 1301 81 st Avenue NE Spring Lake Park MN 55432 Business Phone 763-784-6491 Fax 763-792-7257 INSPECTION, TESTING AND MAINTENANCE OF FIRE PROTECTION SYSTEMS
Oil and Coolant Circulating Heating System Model - OCSM Installation & Operation Manual 216280-000 REV 2 Identifying Your System The HOTSTART heating system is designed to heat fluids for use in marine
ELECTRICAL EMERGENCY SYSTEM PLAN REVIEW What to Look for during Plan Review OVERVIEW OF CODE REQUIREMENTS First determine the type of emergency power system; is the system designed for Emergency or Legally
Page 1 January 2, 2009 INSPECTION AND TESTING OF FIRE ALARM SYSTEMS Introduction Early warning plays a key role in a healthcare facility s ability to safely evacuate its residents during a fire emergency.
CHECK, TEST, INSPECT REQUIREMENTS OF THE ONTARIO FIRE CODE CHECK - Means visual observation to ensure the device or system is in place and is not obviously damaged or obstructed. TEST - Means operation
Hartford Steam Boiler One State Street P.O. Box 5024 Hartford, CT 06102-5024 Tel: (800) 472-1866 www.hsb.com July 2014 Safety should only be inspected, tested and maintained by qualified trained personnel.
Last Update: December 8, 2014 A. Description of System Consultant s Handbook Page 1 of 6 1. Provide a diesel engine driven electric generating unit, factory assembled, tested and certified to operate at
Standard Operating Procedures IN OPERATING DEEP WELL PUMP BEFORE YOU START Make sure that you are properly oriented and knowledgeable to the location, functions and how to operate/manipulate the following:
LOAD BANK TESTING PROCEDURE APPENDIX G SPS-G-1 of 9 I. General GENERATOR LOAD BANK TESTING AND ENGINE TESTING A. Provide all equipment, labor, materials and supervision necessary to test the stand-by diesel
Safe Use of Emergency Generators IEC Fact Sheet No. 21 Paul W. Benson, University of Illinois and LaVerne E. Stetson, USDA-ARS Introduction Electric power suppliers cannot guarantee continuity of electrical
Model: 400E-2M BERMAD Electrically Controlled Deluge Valve with Easy Lock Manual Reset Installation Operation Maintenance Safety First BERMAD believes that the safety of personnel working with and around
Fire Alarm System Monitoring - CAN/ULC-S561-03 Brian McBain ULC Regulatory Services May 4, 2011 Copyright 1995-2007 Underwriters' Laboratories of Canada. All rights reserved. No portion of this material
NFPA 20 2016 and Beyond Gayle Pennel, P.E. - Aon Fire Protection Engineering Aon Fire Protection Engineering Corporation NFPA 20-2016 Major Changes Automatic Supervision of Pressure Transducers Connectivity
Applies to: All Facilities Management Employees GUIDELINES: Issued: April 22, 2014 Revised: February 24, 2015 Author: Communications Coordinator PURPOSE: The purpose of these guidelines is to define roles
Winnipeg Fire Department Fire Prevention Branch Manitoba Fire Code Life-Safety Equipment Maintenance Requirements The Fire Prevention Branch of the Winnipeg Fire Department has prepared this document of
Thermo Top - Troubleshooting Tree 07-15-2002 CAUTION Troubleshooting requires comprehensive knowledge about the structure and theory of operation of the Thermo Top heater. Troubleshooting and repairs may
INSTRUCTIONS FOR BUILDINGS WITH FIRE PROTECTION EQUIPMENT FIRE EXTINGUISHERS,SPRINKLER SYSTEMS AND FIRE ALARMS Attachment #1 Inspection of Fire Extinguishers Fire Extinguishers must be tested according
National Competency Based Skill Training Refrigeration and Air-conditioning Mechanic Logbook Trainee:... Training Provider:... Year:... Trainee Contact no:... Competency Based Skill Training Logbook Introduction
The following information must be fully completed and forwarded to your local Liebert sales office to establish your equipment warranty. Installer Address Owner Address Owner e-mail address Installation
FIRE SAFETY REGISTER Premises Name: Premises Address: Fire Safety Manager: Contact No. Kerry County Fire Service www.kerrycoco.ie 1 CONTENTS Section Title Page 1.0 Introduction 3 2.0 Guidance for the completion
SECTION 26 32 13.13 EMERGENCY GENERATOR PART 1: GENERAL 1.01 SCOPE OF WORK A. Provide complete factory assembled generator set equipment with digital (microprocessor-based) electronic generator set controls,
Instruction Sheet 07-2013 Installation Instructions for Alarm Module Kit A043F059 1 Introduction The information contained within is based on information available at the time of going to print. In line
Federal Wage System Job Grading Standards for Air Conditioning Equipment Operating, 5415 Table of Contents WORK COVERED... 2 WORK NOT COVERED...2 TITLES... 2 GRADE LEVELS... 2 HELPER AND INTERMEDIATE JOBS...
14. Guide 14.1 Refrigeration Cycle System In order to diagnose malfunctions, ensure the air conditioner is free from electrical problems before inspecting the refrigeration cycle. Such problems include
Coolant Circulating Heating System TCR Controlled Installation & Operation Manual 216261-000 REV 5 Identifying Your System The HOTSTART heating system is designed for use in marine propulsion, diesel-powered
CASE STUDY 1 COMMISSIONING A GAS FIRED STEAM BOILER A steam boiler has been built and installed at a factory for the provision of process steam. The following lists the requirements used in the commissioning
SECTION IV MAINTENANCE PROCEDURES FOR FIRE PROTECTION SYSTEMS SECTION IV SECTION IV MAINTENANCE PROCEDURES FOR FIRE SAFETY EQUIPMENT TABLE OF CONTENTS... Page Preface... 1 Maintenance and Inspection Schedules...
FACILITY FIRE PREVENTION AND EMERGENCY PREPAREDNESS INSPECTION CHECKLIST Date of Inspection: Conducted by: Location: Reviewed by: Date of Review: Comments or additional corrective action taken as a result
Website: www.andico.com.au Service manual CAUTION - BEFORE SERVICING THE UNIT, READ THE SAFETY - PRECAUTIONS IN THIS MANUAL. - ONLY FOR AUTHORISED SERVICE PERSONNEL. MODELS: MPK1-09CR-QB8 MPK1-12ER-QB6
GENERAL The Chemetron skid mount scroll medical air system is designed to provide medical breathing air for hospital and medical institutions. This system meets NFPA 99 requirements for Level 1 breathing
GENERATOR POLARIZATION INDEX (PI) TEST 1 AUTOMATED GENERATOR NAMEPLATE DATA: GENERATOR MFR. KVA KW VOLTS (KV) AMPS PHASE FREQUENCY RPM GENERATOR CONTROL MFR. GOVERNOR MFR. YEAR MANUF. TYPE CHOOSE VOLTAGE
Evaluate, Clean, and Tune Guidance The Evaluate, Clean and Tune (ECT) process serves three essential purposes in the Weatherization Assistance Program (WAP). The first is to evaluate the existing system
School District Lock-out / Tag-out Program Lock-out / Tag-out Program Table of Contents: I. Scope/Application II. III. IV. Employer Responsibilities Employee Responsibilities Disciplinary Action V. Protective
Table of Contents (MEC 6)... 1 Function: Operate Vessel Machinery and Systems... 1 Diesel engines.... 1 Operational procedures.... 3 Operate and monitor a vessel s engines and auxiliary equipment.... 4
SDX Submersible Depth Transmitter User Manual January 2011 USER INFORMATION Stevens makes no warranty as to the information furnished in these instructions and the reader assumes all risk in the use thereof.
Air Conditioner Water Heater - A Product of HotSpot Energy LLC PLEASE READ THIS BEFORE YOU INSTALL THE UNIT 1. This air conditioner must be installed and/or repaired by a qualified technician. If you perform
Mike Holt s Illustrated Guide to NEC Requirements for Generators and Standby Power Systems Rule 220.87, Articles 445, 700, 701, and 702 Based on the 2011 NEC Extracted from Mike Holt s Illustrated Guides
INDUSTRY WIDE LABOR-MANAGEMENT SAFETY COMMITTEE SAFETY BULLETIN #23 GUIDELINES FOR WORKING WITH PORTABLE POWER DISTRIBUTION SYSTEMS AND OTHER ELECTRICAL EQUIPMENT "ADDENDUM C" WORKING WITH 480 VOLT SYSTEMS
Course Firefighter I Unit IX Salvage and Overhaul Power Supply, Lighting Equipment, And Emergency Scene Safety Rationale Because firefighting and other fire service emergency operations can happen anytime
Power topic #7016 Part 3 of 3 Technical information from Cummins Power Generation Transfer switch set up for reliability and efficiency, part 3: ATS settings for best operation > White paper By Gary Olson,
INSTRUCTIONS FOR BUILDINGS WITH FIRE PROTECTION EQUIPMENT FIRE EXTINGUISHERS,SPRINKLER SYSTEMS AND FIRE ALARMS Attachment #1 Inspection of Fire Extinguishers Fire Extinguishers must be tested according
Unpackaging & Handling Be sure to carefully inspect the unit before accepting the shipment. If any damage has occurred document it with the trucking company immediately. Contact your Kellogg Distributor
Environment of Care Utility Systems Management Plan 2014 Updated 4.18.2014 PURPOSE The objectives of the Utility Systems Management plan is to establish, maintain, and continually provide a reliable utility
ASCO SERIES 165 Power Transfer Switches An Automatic Transfer Switch helps prevent... Your business or home from losing power during bad weather or utility power equipment failures The loss of valuable
. RFP: Attachment J-C18.1 HVAC Work Instructions NNC13ZFD017J SOW Item No. Title Page C18-02 Control Air Systems Annual PM 2 C18-03 Split System AC Indoor Section Annual PM 3 C18-04 Condensing Unit Semi-Annual
BRAVER UPS (Uninterruptible Power System) User s Manual Safety CAUTION! This UPS utilizes voltages that may be hazardous. Do not attempt to disassemble the unit. The unit contains no user replaceable parts.
Pellet Heater Owner's Manual Installation and Operating Instructions Please read this entire manual before installation. Save these instructions. SAFETY NOTICE HEATER MUST BE PROPERLY INSTALLED AND MAINTAINED
Important New Code Requirements for SCCR Labeling of Data Center Equipment Michael P. Murphy D V L G r o u p 1 1 5 S i n c l a i r R o a d B r i s t o l, P A 1 8 9 6 3 Short Circuit Current Ratings (SCCR)
2008 Scheduled Maintenance Guide OWNERS FIND IT ONLINE 2008 Scheduled Maintenance Guide For your convenience, scheduled maintenance information for your vehicle is also available at www.toyotaownersonline.com
LOAD BANK PART NUMBER 2004297/2004298 OPERATIONS AND MAINTENANCE MANUAL Prepared by: 5455 N River RD W Geneva, OH 44041 Phone: 1-800-969-8527 TechSupport@get-psi.com HDT 1 TM-2004297/2004298 TABLE OF CONTENTS
FOR NEW OR REPLACEMENT SEWAGE PUMPS RECOMMENDED INSTALLATION & MAINTENANCE AB SUMP & SEWAGE PUMP MANUFACTURERS ASSOCIATION P.O. BOX 647 NORTHBROOK, IL 60065-0647 The materials contained in this document
SECTION 263235 STANDBY GENERATOR TESTING AND COMMISSIONING PART 1 - GENERAL 1.1 SUMMARY A. Section Includes: 1. Standby generators. 2. Automatic Transfer Switches (ATS). 3. System start-up services. 4.
Generator System Preventive Maintenance and Contingency Planning Agenda Types of power generation systems Benefits of a preventive maintenance program Power generation maintenance items Contingency Plans
Georgia State Amendments to the International Mechanical Code (2012 Edition) Georgia Department of Community Affairs Community Development Division 60 Executive Park South, N.E. Atlanta, Georgia 30329-2231
Service Requirements Fire protection equipment requires care and maintenance at scheduled intervals to assure it will operate properly and safely when needed. Only personnel who are trained and qualified
Electric Water Heater Operation and Installation Manual (LIMITED WARRANTY AND TANK REPLACEMENT POLICY) The following information should be noted at time of installation and retained for future reference.
COMPONENTS ILLUSTRATION ON-VEHICLE INSPECTION 1. INSPECT REFRIGERANT VOLUME (a) Check the sight glass on the air conditioning tube and accessory. (1) Prepare the vehicle according to the chart below. Item
Environmental Health & Safety Policy Manual Issue Date: 7/27/2015 Policy # EHS-400.16 Electrical Safety Policy 1.0 PURPOSE: This policy is intended to protect individuals working at the LSU Health Sciences
Federal Wage System Job Grading Standards for Electric Power Controlling, 5407 Table of Contents WORK COVERED... 2 WORK NOT COVERED...2 TITLES... 2 GRADE LEVELS... 2 SPECIAL ADDITIONAL RESPONSIBILITIES...
Page 1 of 6 The University inspects, tests, and maintains emergency power systems in accordance with the Joint Commission Environment of Care Standard EC.02.05.07 for the following facilities and equipment:
SUGGESTED SPECIFICATION for Series 300 Automatic Transfer Switches PART 1 GENERAL 1.01 Scope Furnish and install automatic transfer switches (ATS) with number of poles, amperage, voltage, and withstand
GUIDELINES FOR INSTALLATION OF TEMPORARY AND PERMANENT ABOVEGROUND DIESEL FUEL TANKS FOR EMERGENCY AND STANDBY POWER SYSTEMS LOCATED OUTSIDE OF BUILDINGS For Use by Unidocs Member Agencies or where approved
USER INSTRUCTIONS FOR GET PORTABLE 12k BTU AIR CONDITIONER MODEL No. GPACU12HR CONTENTS Introduction Safety Notes Identification of parts Installation instructions Operation instructions Maintenance Troubleshooting
A Guide to Trouble-Free Cooling Towers A basic understanding of cooling tower operation and maintenance will help keep a cooling water system running in top condition, year after year By David M. Suptic
IMPORTANT SAFETY NOTICE To: Our Valued Customers User safety is a major focus in the design of our products. Following the precautions outlined in this manual will minimize your risk of injury. ITT Goulds
1in. Clear Water Pump OWNER'S MANUAL WARNING: Read carefully and understand all INSTRUCTIONS before operating. Failure to follow the safety rules and other basic safety precautions may result in serious
Department of Environmental Health & Safety Energy Control and Power Lockout Program for Facilities Management January 2009 1 TABLE OF CONTENTS 1. Introduction 3 2. Objective 3 3. Scope 3 4. Definitions
Crawford Inspection Services C.C.B. # 76914 www.crawfordinspections.com Portland Area PO Box 665 West Linn, OR 97068 Ph: (503) 650-6957 Salem Area 5434 River Rd. N; #192 Keizer, OR 97303 Ph: (503) 362-5809
Scope This guideline defines the standard tests that all electrical systems and equipment must pass prior to final acceptance by the University. These tests are in addition to acceptance tests specified
SWIMMING POOL HEAT PUMP Installation & User Manual Model HP40B HP50B HP65B Hayward Pool Products Canada, Inc. T: 1-888-238-7665 www.haywardpool.ca CONTENT I. Application 4 II. Features 4 III. Technical