NEUROFUZZY NETWORK MODELING OF DATA CENTRE ENERGY PERFORMANCE


 Theodora Lorraine Powell
 2 years ago
 Views:
Transcription
1 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance CHAPTER 6 NEUROFUZZY NETWORK MODELING OF DATA CENTRE ENERGY PERFORMANCE 6.1 Introduction An exploratory study of the wholesystem based neurofuzzy network modeling for data centre energy performance is conducted as part of the efforts to understand an empirical energy use pattern of data centres in Singapore. The models developed integrates energy consuming constituents contributing to the energy consumptions of data centres, and analyzes various factors such as physical parameters of space and environment control facilities, design and operation strategies of HVAC, UPS, IT equipment and lighting systems. Neurofuzzy network presents itself a desired and applicable candidate of modeling energy performance of complex systems by taking advantages of mimicking human decision and selftraining by existing data sets. A well structured and trained neurofuzzy model can serve as evaluation tool kits at both design and postdiagnostic stages of data centres. Energy saving potential can also be estimated quantitatively. FuzzyTech 5.5 is employed as the modeling software in this study. In this study, the neurofuzzy network models are established based on the energy performance benchmarking of the six data centres studied. Due to the small data base, these models cannot provide highly accurate evaluation of data centre energy performance and prediction of data centres energy saving potential. However, they can serve as efficient and effective tools, prior to the further and detailed measurement and verification (M&V) or energy simulation for the evaluation of data centre energy 146
2 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance performance and estimation of energy saving potential. 6.2 Application of neurofuzzy network in modeling data centre energy performance Fuzzy logic is a technology that enhances modelbased system design by using both intuition and engineering heuristics. This provides an efficient way of designing, optimizing, and maintaining highly complex systems and results in robust and fault tolerant systems. The use of linguistic modeling, instead of mathematical modeling, greatly enhances system transparency and modification potential. It leads to quick development cycles, easy programming and accurate control. Fuzzy logic principle is especially advantageous for problems that cannot be easily represented by mathematical modeling because data is either unavailable, incomplete, or the process is too complex to use a traditional approach [FuzzyTech, 2001]. There are a number of reasons for neurofuzzy network to be employed as modeling approach in this study. Firstly, data centres energy consumption is a complex system. A typical data centre contains various energy consuming systems including IT equipment, UPS, HVAC system, lighting, office equipment, building control system, fire suppression system, current transformer and standby power generator. The interactions among energy consuming systems also make this system more complex. Energy performance of data centres is also affected significantly by physical variables such as space usage, indoor temperature, humidity, as well as the design and operation strategies. While it is possible to develop a deterministicnamely precise mathematical or empiricalmodel, the complexity of the data centre energy performance makes it 147
3 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance difficult to be modeled using conventional modeling approach such as multiple regression. Energy simulation, the popular tool of modeling building system and predicting energy consumption, is another possible solution for modeling data centre. However, simulation is highly time and cost consuming. By comparison, neurofuzzy network with the capability of modeling complex system can be a suitable solution in this study. Secondly, the term energy performance is by nature a fuzzy concept. It not only associates with the energy consumption and power demand, but also the operational energy efficiencies of various systems and total data centre. A precise definition of energy performance does not exist. Traditional indicators such as annual energy consumption (kwh/m 2 /year) and power demand density (W/m 2 ) per unit gross floor area are not sufficient for describing data centres energy performance. For example, the total data centre power demand densities of data centre 4 and data centre 6 are 348 W/m 2 and 231 W/m 2 respectively. This does not mean that data centre 6 is more energy efficient than data centre 4, as data centre 6 may have a sparse equipment distribution over a large area, and also resulting in significant amount of energy spent on space cooling. Besides, it is found that the UPS system in data centre 6 is the least efficient among all the data centres studied. It is evident that energy efficiencies of HVAC and UPS systems, area occupancy, overdesigning of the supporting systems, designed power demands, and environmental setting put significant impact on data centres energy performance. For the reasons above, fuzzy logic which mimics human logic by combining various parameters or rules for making description or decision is suitable for the application of modeling data centre energy performance. 148
4 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance Thirdly, classification of energy performance involves the usage of fuzzy concept. For example, assuming the actual total data centre power density is categorized into 3 classes, which are less than 300 /m 2, 300 W/m 2 to 410 W/m 2 and higher than 410 W/m 2 respectively, a data centre of 301 W/m 2 will be classified under Class 2, and a data centre of 299 W/m 2 will be classified under Class 1. This could be an unreasonable classification since the difference of power demand between these two data centres is very slight. This reflects the fact that the defined power demand range of each class should not be a crisp range. There should be a buffer area between each class. In this case, fuzzy logic is particularly suited for addressing this issue. 6.3 Knowledge background of neurofuzzy network Structure of fuzzy logic model A typical fuzzy logic based approach involves three modules: a fuzzifier, a fuzzy interference engine, and a defuzzifier as illustrated in Figure 6.1. Input linguistic variables Fuzzy inference Output linguistic variables Linguistic Level Technical Level Fuzzification Input real variables Defuzzification Output real variables Figure 6.1 Typical structure of rulebased fuzzy logic model (Source: FuzzyTech, 2001; Gouda et al., 2001; Krarti, 2003) A fuzzifier is used to map input vectors into fuzzy sets defined by linguistic variables 149
5 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance such as Bad, Average and Good and membership functions. The inference engine associates fuzzy sets to other fuzzy sets using a rule library of IFTHEN fuzzy rules that highly intuitive and easily understood by human users. Finally the defuzzifier is used to map fuzzy sets to output vectors. Further information of fuzzy logic is provided following in section Principles of neural network For the purpose of enhancing fuzzy logic systems with learning capacities, neural network (NN) is introduced. The objective of a neural net is to process information in a manner that has been previously trained into the net. Training uses either sample data sets of inputs and corresponding outputs, or an expert who rates the performance of the neural net. A neural network can be any model in which the output variables are computed from the input variables by compositions of basic function or connections. However, one of the most commonly used neural network models is the multilayer perception [Krarti, 1998]. Figure 6.2 shows a schematic diagram of the structure of a neural network. Figure 6.2 Neural network schematic diagram (Source: Krarti, 2003) 150
6 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance The first and last layers of neurons are called input and output layers; between them are one or more hidden layers. The neuron depicted by the small circles is the fundamental building block of a network. Each element of the input set, INPUT i, is multiplied by a weight, W ij, and the products are summed to provide the output at the neuron, OUTPUT j : OUTPUT j = Σ i INPUT i W ij +B j Eqn (6.1) where, B j is the bias at the neuron j. The bias is the activation threshold for the neuron j. This bias avoids the tendency of an activation function to get stuck in the saturated, limiting value area of the activation function described below. After each OUTPUT j is calculated, an activation function is applied to modify it. The activation function is typically a bounded monotonic function. Sigmoid function is the most common one. ƒ(x)= 1/ (1+exp(x)) Eqn (6.2) The weights W ij of the neural network are adjusted iteratively so that application of a set of inputs produces the desired set of outputs. If the computed outputs do not match the known values during network training, the NN model is in error. The error, E, is typically calculated as the sum of squared differences between computed and target values: E= Σ j (OUTPUT j TARGET j ) 2 Eqn (6.3) 151
7 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance If the error E is large, then the neural network weights, W ij are adjusted to reduce this error. The most commonly used approach to adjust the weights is the gradient descent method. Using this approach, the weights is changed from W ij to (W ij a de/dw ij ), where parameter a is called the learning rate. This procedure of weight adjustment is called backpropagation. A simplified procedure for the learning process of neural network is summarized below: Provide the network with training data consisting of patterns of input variables and target outputs. Assess how closely the network output matches the target outputs. Adapt the connection strengths (i.e., weights) between the neurons so the network produces better approximations of the desired target outputs. Continue the process of adjusting the weights until some desired accuracy level is achieved. Analyse the results to assess the validity of the parametric relationships Neurofuzzy network [FuzzyTech, 2001] The key benefit of fuzzy logic is that it allows design consultant to describe desired system behaviour with simple IFTHEN relations. However, this is at the same time its major limitation. In many applications, knowledge that describes desired system behaviour is contained in data sets. The design consultant must derive the IFTHEN rules from the data sets manually. In this case, a neural network presents a solution since it can train the model itself from the data, while the fuzzy logic model provides 152
8 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance the rules which governs the paradigm relationships. On the other hand, neural network itself is limited by a number of reasons. Firstly, neural network solution stands as a black box. Design consultant can neither interpret what derive a certain behaviour, nor modify a neural network manually to influence a certain behaviour. Secondly, neural network require prohibitive computational effort, and numbers of sample data during the modeling process. Thirdly, selection of the appropriate net model and setting the parameters of the learning algorithm is still a tough job which requires extensive experience. Among the mentioned reasons, inadequacy of data base and experience, as well as the lack of an easy way to verify and optimize a neural network solution are probably the major limitations of neuro network. For this application, combined use of neural network and fuzzy logic might provide a powerful technique which compensates individual method s weakness. Neural network can learn from data sets, while fuzzy logic solutions are easy to verify and optimize. Neurofuzzy network combines the advantages of fuzzy systems, the explicit knowledge representation of knowledge, and the ability to cope with uncertainties with the learning power of neural network Method of neurofuzzy network modeling using FuzzyTech 5.5 FuzzyTech 5.5 is powerful software using neurofuzzy technology, with which models describing complex systems can be established easily and clearly. As shown in Figure 6.3, the basic neurofuzzy network model typically consists of input variables, rule blocks and output variables. 153
9 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance Fuzzification Fuzzy Inference Defuzzification Figure 6.3 Basic structure of fuzzy logic model Fuzzification The fuzzification interface consists of the following operations [Gouda et al., 2001]: 1) Perform a scale mapping that transfers the input variable ranges into a corresponding universe of discourse (quantization/ normalization). 2) Performs the fuzzification strategy that converts crisp input data into suitable linguistic variables, which may be viewed as labels of fuzzy sets. Firstly, in the fuzzification interface, real values are transformed into linguistic variables. In this study all the input and output variables are defined correspondingly to three classes within the full range of observed values. For example, Total data centre energy consumption is converted into fuzzy sets such as low, medium and high. 154
10 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance The degree to which the crisp value belongs to a set is represented by a value between 0 and 1, called the degree of membership µ. Fuzzy logic describes degree of membership by a function known as a membership function (MBF). Standard membership functions are used in most practical applications with types of Z, Lambda, Pi and S, as shown in Figure 6.4. Figure 6.4 Standard membership function types Figure 6.5 below shows the fuzzification of term total data centre energy consumption. Based on the data collected during the measurements in the 6 data centre studied, the details of the ranges of defined input and output variables are given in Appendix H. Degree of Membership Range of real value 4100 kwh/m 2 /year Figure 6.5 Fuzzification of variable 155
11 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance For example, energy consumption at 4100 kwh/m 2 /year is a member of the fuzzy sets for the terms: Low to the degree of 0.00 Medium to the degree of 0.30 High to the degree of Fuzzy inference Once all input variable values are translated into the respective linguistic variable values, the socalled fuzzy inference step evaluates the set of IFTHEN rules that define system behaviour. IFTHEN rules always describe the reaction to a certain situation as: IF <situation> THEN <action>. The inference is a calculus consisting of the steps: aggregation, composition and, if necessary, result aggregation. First, aggregation determines the degree to which the complete IF part of the rule is fulfilled. Special fuzzy operators are used to aggregate the degrees of support of the various preconditions. There are in Min operator, which corresponds with the linguistic AND, is most common and has been employed for the study. Equation below shows the principle of this method. Figure 6.6 shows the dialog of input fuzzy operator. AND: µ (A^B)=min {µ(a), µ(b)} Eqn (6.4) 156
12 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance Figure 6.6 Operator of input aggregation Each rule defines an action to be taken in the THEN part. The degree to which the action is valid is given by the adequacy of the rule to the current situation. This adequacy is computed by the aggregation as the degree of truth of the IF part. In the composition step, the degree of truth of the IF part of the rule is multiplied by a weighting factor, named Degree of Support (DoS). This factor represents the individual significance of the rule. By this way, rules themselves can be fuzzy, with a support between 0 and 1. The support of a consequence is calculated by linking the support of the entire condition with the DoS by composition operator. See the equation below. µ THEN =µ IF * DoS Eqn (6.5) 157
13 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance Figure 6.7 shows an example of the defined rules. Input variables Degree of support (DOS) Output variables Figure 6.7 Definition of fuzzy rules A result aggregation step determines the maximum degree of support for each consequence which is used for all further processing. Also shown in Figure 6.6, there are two methods of result aggregation, the maximum method (MAX) and the bounded sum method. If more than one rule produces the same consequence, an operation must aggregate the results of these rules. MAX operator takes the maximum of the Dos values as final result. The BSUM method takes the bounded sum. In this study, MAX method is employed to aggregate the results of these rules, as presented by the equation below. MAX result aggregation: µ RESULT = max i (µ THEN, RULEi ) Eqn (6.6) With the application of neurofuzzy network in this study, all the fuzzy rules were formulated automatically from the training data. Firstly, a full range of possible rules is generated. For example, say, there are two input variables and one output variable; and each variable has three classes low, medium, high. The total number of possible 158
14 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance rules is 3x3x3=27. After the neural network training, weight of each fuzzy rule is determined through Dos. The insignificant rules will be removed from the rule block. Further discussion of neurofuzzy training is provided in Section Defuzzification The result produced from the fuzzy rules are linguistic values, namely fuzzy, for the output variables. The defuzzification step translates the linguistic results into real values. There are several methods of defuzzification. CentreofArea (CoA), sometime also called CentreofGravity (CoG) is the most frequently used defuzzification method. This method is based on taking the aggregate of the fuzzy outputs from each rule, weighted by their grades of fuzzy input set membership, see Figure 6.8. Figure 6.8 Deffuzification with CentreofArea The CentreofMaximum (CoM) is another commonly used method of defuzzification. It computes a crisp output as a weighted average of the term membership maxima, weighted by the inference results (Figure 6.9). The locations of the individual term membership maxima are indicated by the gray arrows and the inference result is shown 159
15 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance by the height of the black bar in the arrows. Figure 6.9 Deffuzification with CentreofMaximum Most CoA implementations are only approximations since they neglect overlapping and can be represented with methods such as CoM. Note that, since the quality of approximation has proved to be fair enough for the vast majority of applications, and CoA defuzzification is significantly slower than the approximated CoA methods, most hardware and software implementations of fuzzy logic algorithm only support CoM and others rather than the real CoA [FuzzyTech, 2001]. For this reason, CoM is employed in this study Neurofuzzy training i) Training of fuzzy rules The basic idea of neurofuzzy approach is to set up a complete fuzzy rule base, not by entering the rules, but by presenting a set of training samples and selecting the set of rules that represent the samples [FuzzyTech, 2001]. In the neurofuzzy model, neural network training function is used to evaluate the significances or weights of the 160
16 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance predefined fuzzy rules. Unlike early neurofuzzy network approaches, this study employs restricted training, which requires a given rule base, to restrict the number of rules used and save apriori knowledge that was entered into the system before training. This is due to the fact that if a huge unrestricted rule base does not provide a good match to the given sample distribution, the training may not converge. Configuration of neural training is shown in Figure The definitions of the terms in this dialog are shown in Appendix I. Figure 6.10 Configuration of neural training (Source: FuzzyTech, 2001) ii) Training of fuzzification and defuzzification In a fuzzy system, membership function of these parameters found in the fuzzification (input variables) and defuzzification (output variables) can also be trained. The manner in which neurofuzzy model treats the parameters of the membership functions of variables is similar to the training of fuzzy rules. Figure 6.11 shows an example of the 161
17 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance variable after training. Figure 6.11 Training of output variable Summary of settings of neurofuzzy network modeling Fuzzyification Membership function (MBF) Standard membership function Fuzzy inference Input aggregator Min operator (linguistic AND) Result aggregator Max operator (maximum of the degree of support (DoS) value) Defuzzification Method of defuzzification Centre of Maximum (CoM) Neurofuzzy training Learning method Batch Random 162
18 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance Winner neurons 1 Step Width (DoS) 0.1 Step Width (Term) 1% Stop criteria Max. Steps from 4000 to Max. Deviation from 50% to 1%, factor 0.75 Avg. Deviation 0.1% 6.4 Objectives of neurofuzzy network modeling of data centre energy performance Data centre energy performance involves a complex system of energy consuming components and elements. It comprises various energy consuming components and environmental and design variables. Neurofuzzy network combining the advantages of fuzzy systems, the explicit knowledge representation of knowledge, and the ability to cope with uncertainties with the learning power of neural network is a powerful technique for developing desired solution of integrating all these systems and variables into a whole system. The objectives of neurofuzzy network modeling in this study are as follows: a. To develop wholesystem based models for data centre energy performance. b. To provide efficient and effective evaluation of data centre energy performance, and accurate estimation of energysaving potential of data centres based on the models developed. 163
19 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance 6.5 Modeling methodology In this study, neurofuzzy network modeling consists of four steps. Figure 6.12 shows the systematic diagram of the modeling procedure. Parameter analysis Establish fuzzy logic model Neural network training Model verification Figure 6.12 Systematic diagram of modeling procedure Parameter analysis & establishment of fuzzy logic model Based on parameter analysis conducted in Chapter 5, variables that affect overall data centre energy performance are determined; linking those (input variables) to the key indicators (output variables) of data centre energy performance by fuzzy rule blocks, the structure of the model is determined. The results of parameter analysis are summarized as follows. The key indicators of total data centre energy performance are the total data centre energy consumption per unit gross floor area in term of kwh/m 2 /year and the energy consumption of IT equipment as a percentage of total data centre energy consumption. The significant energy consuming system of data centres are HVAC system and IT equipment. Physical variables gross floor area (m 2 ), IT footprint as a percentage of gross floor area, and total overdesigning of data centre power demand plus energy consumptions of HVAC and IT equipment in terms of kwh/m 2 /year are set as the 164
20 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance significant variables of total data centre energy consumption. On the other hand, relative energy effectiveness of HVAC system which is denoted by the ratio of HVAC energy consumption to IT equipment energy consumption seems to be positively correlating to IT equipment energy consumption as a percentage of total data centre energy consumption. Based on the results of parameter analysis, model of total data centre energy performance is shown in Figure Figure 6.13 Model of overall data centre energy performance where, Grss_area is gross floor area of data centre (m 2 ) HVAC_energy is HVAC energy consumption per unit gross floor area (kwh/m 2 /year) IT_energy is IT equipment energy consumption per unit gross floor area (kwh/m 2 /year) ITfootprint is IT equipment footprint area as percentage of gross floor area (%) Total_overdesign is overdesigning of total data centre power demand () Total_energy is total data centre energy consumption per unit gross floor area (kwh/m 2 /year) HVAC_Vs_IT is the ratio of HVAC energy consumption to IT equipment energy consumption () IT_Vs_Total is the IT equipment energy consumption as percentage of total data centre energy consumption (%) 165
21 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance As shown in section 5.2, affecting variable IT equipment energy consumption in terms of kwh/m 2 /year is affected by the overdesigning of IT equipment power demand and IT equipment footprint area as percentage of gross floor area. These relationships are described in the model of IT equipment energy performance (Figure 6.14). Figure 6.14 Model of IT equipment energy performance where, IT_overdesign is the overdesigning rate of IT equipment power demand Based on the results of parameter analysis in Section 5.4, variables such as energy consumptions of HVAC and the ratio of HVAC energy consumption to IT equipment energy consumption, which indicate energy performance of HVAC system, are also affected by other variables. Figure 6.15 depicts that HVAC energy consumption (kwh/m 2 /year) is affected by IT equipment energy consumption (kwh/m 2 /year), gross floor area (m 2 ), IT equipment footprint area as percentage of gross floor area and the overdesigning of HVAC system. The ratio of HVAC energy consumption to IT equipment energy consumption is determined by the overdesigning of HVAC system. 166
22 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance Figure 6.15 Model of HVAC system energy performance Moreover, as shown in Figure 5.12 and Figure 5.21, overdesigning of HVAC system power demand and total data centre power demand are both affected by the overdesigning of IT equipment power demand. Figure 6.16 Integrated model of total data centre energy performance 167
23 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance As stated earlier, neurofuzzy network is suitable for the purpose of modeling complex systems. Based on the models above, it is practical to integrate all the affecting variables and systems to a wholesystem based model of total data centre energy performance (Figure 6.16). In this model, the preliminary input variables are gross floor area (m 2 ), overdesigning of IT equipment power demand, and IT equipment footprint as a percentage of gross floor area. Rule block level 1 acts as the intermediate level collecting the information from input variables and transmit it to the next level defined as rule block level 2. On this step, the information that overdesigning of IT equipment power demand determines the overdesigning of HVAC cooling capacity and the overdesigning of total data centre power demand is input to the model and passed to the next level of rule block. Rule block level 2 also acts as the intermediate level collecting the information from input variables and transmitting it to the next level defined as rule block level 3. Rule blocks 2and 4 (RB2 & 4) together illustrate the structure of HVAC system energy performance. Rule block 3 describes the significant variables that affect IT equipment energy consumption. Rule block level 3 is defined as the same as that in the previous model of total data centre energy performance (Figure 6.13). It receives the information transmitted from rule block level 2 and other independent significant variables including gross area, IT equipment footprint as percentage of gross floor area. Based on the information 168
24 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance received, the values of the output variables can be determined Neural network training Data obtained from investigations conducted in the data centres studied are then used to train the model. This training data consist of both the observed values of input variables and output variables. Based on the correlationship analysis conducted in Chapter four, data centre 6 seems often the disturbing point of the analysis. This can be explained by its significantly larger area than other facilities and the low occupancy rate of the floor area. For this reason, the data of data centre 6 is excluded from the training. However, this data centre will be used to as a new data to test the validity of the trained model and evaluate the energy saving potential. Appendix J shows the training data of the model Model verification After the training, the information of the data is learned and stored into the model, and the significance levels of the various fuzzy rules are determined. Those rules have minor influences on output variables that are removed from the rule blocks. The trained model can then be used to predict the energy performance of a data centre. Moreover, by changing one or more values of the input variables, the influences of that or those variables can be examined. 169
25 Chapter 6: Neurofuzzy Network Modeling of Data Centre Energy Performance However, sometime the neural training may not converge, which may lead to inaccurate prediction and analysis. This is due to many reasons. The main reason is the constraint of sample size. In this study, only 6 sets of data obtained from the selected data centres are available for the training and testing of the model. Moreover, there are significant variations among data centres in terms of energy consumption, power demand and systems efficiencies. These can lead to a poor convergence of the model developed. Improper model structure and unrestricted and great number of fuzzy rules can also result in improper model. In this case, further reexamination of model structure and more sample data are needed. Figure 6.17 Training result in 3D plot Figure 6.17 depicts the trained model of total data centre energy performance in a 3Dimensional plot. Relationships between HVAC energy consumption (vertical axis) and Gross area and Overdesigning of IT equipment power demand (horizontal axes) are depicted graphically. 170
About the NeuroFuzzy Module of the FuzzyTECH5.5 Software
About the NeuroFuzzy Module of the FuzzyTECH5.5 Software Ágnes B. Simon, Dániel Biró College of Nyíregyháza, Sóstói út 31, simona@nyf.hu, bibby@freemail.hu Abstract: Our online edition of the software
More informationENERGY PERFORMANCE OF DATA CENTRES IN SINGAPORE SUN HANSONG. (B.Eng.) A THESIS SUBMITTED FOR THE DEGREE OF MASTER OF SCIENCE (BUILDING)
ENERGY PERFORMANCE OF DATA CENTRES IN SINGAPORE SUN HANSONG (B.Eng.) A THESIS SUBMITTED FOR THE DEGREE OF MASTER OF SCIENCE (BUILDING) DEPARTMENT OF BUILDING SCHOOL OF DESIGN AND ENVIRONMENT NATIONAL UNIVERSITY
More informationFirst steps in using of FuzzyTech5.5 Online Edition at College of Nyíregyháza
First steps in using of FuzzyTech5.5 Online Edition at College of Nyíregyháza András Botos, Ágnes B. Simon College of Nyiregyháza, Rákóczi út 69., Nyíregyháza Abstract:9 In this paper you can read about
More informationA FUZZY LOGIC APPROACH FOR SALES FORECASTING
A FUZZY LOGIC APPROACH FOR SALES FORECASTING ABSTRACT Sales forecasting proved to be very important in marketing where managers need to learn from historical data. Many methods have become available for
More informationCHAPTER 5 FUZZY LOGIC CONTROLLER FOR THE CONICAL TANK PROCESS
99 CHAPTER 5 FUZZY LOGIC CONTROLLER FOR THE CONICAL TANK PROCESS 5.1 INTRODUCTION Fuzzy Logic Controllers are normally preferred for control applications, due to their fault tolerance, knowledge representation,
More informationIntroduction to Fuzzy Control
Introduction to Fuzzy Control Marcelo Godoy Simoes Colorado School of Mines Engineering Division 1610 Illinois Street Golden, Colorado 804011887 USA Abstract In the last few years the applications of
More informationNTC Project: S01PH10 (formerly I01P10) 1 Forecasting Women s Apparel Sales Using Mathematical Modeling
1 Forecasting Women s Apparel Sales Using Mathematical Modeling Celia Frank* 1, Balaji Vemulapalli 1, Les M. Sztandera 2, Amar Raheja 3 1 School of Textiles and Materials Technology 2 Computer Information
More informationINTELLIGENT ENERGY MANAGEMENT OF ELECTRICAL POWER SYSTEMS WITH DISTRIBUTED FEEDING ON THE BASIS OF FORECASTS OF DEMAND AND GENERATION Chr.
INTELLIGENT ENERGY MANAGEMENT OF ELECTRICAL POWER SYSTEMS WITH DISTRIBUTED FEEDING ON THE BASIS OF FORECASTS OF DEMAND AND GENERATION Chr. Meisenbach M. Hable G. Winkler P. Meier Technology, Laboratory
More informationBuilding Energy Management: Using Data as a Tool
Building Energy Management: Using Data as a Tool Issue Brief Melissa Donnelly Program Analyst, Institute for Building Efficiency, Johnson Controls October 2012 1 http://www.energystar. gov/index.cfm?c=comm_
More informationBank Customers (Credit) Rating System Based On Expert System and ANN
Bank Customers (Credit) Rating System Based On Expert System and ANN Project Review Yingzhen Li Abstract The precise rating of customers has a decisive impact on loan business. We constructed the BP network,
More informationNTC Project: S01PH10 (formerly I01P10) 1 Forecasting Women s Apparel Sales Using Mathematical Modeling
1 Forecasting Women s Apparel Sales Using Mathematical Modeling Celia Frank* 1, Balaji Vemulapalli 1, Les M. Sztandera 2, Amar Raheja 3 1 School of Textiles and Materials Technology 2 Computer Information
More informationINTRODUCTION TO NEURAL NETWORKS
INTRODUCTION TO NEURAL NETWORKS Pictures are taken from http://www.cs.cmu.edu/~tom/mlbookchapterslides.html http://research.microsoft.com/~cmbishop/prml/index.htm By Nobel Khandaker Neural Networks An
More informationSoftComputing Models for Building Applications  A Feasibility Study (EPSRC Ref: GR/L84513)
SoftComputing Models for Building Applications  A Feasibility Study (EPSRC Ref: GR/L84513) G S Virk, D Azzi, K I Alkadhimi and B P Haynes Department of Electrical and Electronic Engineering, University
More informationHOW TO CONDUCT ENERGY SAVINGS ANALYSIS IN A FACILITY VALUE ENGINEERING STUDY
HOW TO CONDUCT ENERGY SAVINGS ANALYSIS IN A FACILITY VALUE ENGINEERING STUDY Benson Kwong, CVS, PE, CEM, LEED AP, CCE envergie consulting, LLC Biography Benson Kwong is an independent consultant providing
More informationAdaptive model for thermal demand forecast in residential buildings
Adaptive model for thermal demand forecast in residential buildings Harb, Hassan 1 ; Schütz, Thomas 2 ; Streblow, Rita 3 ; Müller, Dirk 4 1 RWTH Aachen University, E.ON Energy Research Center, Institute
More informationPrediction of DDoS Attack Scheme
Chapter 5 Prediction of DDoS Attack Scheme Distributed denial of service attack can be launched by malicious nodes participating in the attack, exploit the lack of entry point in a wireless network, and
More informationDeferring Elimination of Design Alternatives in Object Oriented Methods
Deferring Elimination of Design Alternatives in Object Oriented Methods Mehmet Aksit and Francesco Marcelloni TRESE project, Department of Computer Science, University of Twente, P.O. Box 217, 7500 AE
More informationApproach to Energy Management for Companies
Approach to Energy Management for Companies Tomiyasu Ichimura Masahiro Maeeda Kunio Fukumoto Ken Kuroda Ryuzou Fukunaga Most companies in Japan are taking energysaving actions in an effort to cope with
More informationBenchmarking Residential Energy Use
Benchmarking Residential Energy Use Michael MacDonald, Oak Ridge National Laboratory Sherry Livengood, Oak Ridge National Laboratory ABSTRACT Interest in rating the reallife energy performance of buildings
More informationKnowledge Incorporation into Neural Networks From Fuzzy Rules
published in: Neural Processing Letters (3), pages 23242, 999. Knowledge Incorporation into Neural Networks From Fuzzy Rules Yaochu Jin (yaochu.jin@alliedsignal.com) Dept. of Industrial Engineering The
More informationData center power use: a review of the historical data
Data center power use: a review of the historical data Jonathan G. Koomey, Ph.D. LBNL and Stanford University JGKoomey@lbl.gov, JGKoomey@stanford.edu http://datacenters.lbl.gov Presented at the IBM Austin
More informationCurrent Standard: Mathematical Concepts and Applications Shape, Space, and Measurement Primary
Shape, Space, and Measurement Primary A student shall apply concepts of shape, space, and measurement to solve problems involving two and threedimensional shapes by demonstrating an understanding of:
More informationDetection of DDoS Attack Scheme
Chapter 4 Detection of DDoS Attac Scheme In IEEE 802.15.4 low rate wireless personal area networ, a distributed denial of service attac can be launched by one of three adversary types, namely, jamming
More information6.2.8 Neural networks for data mining
6.2.8 Neural networks for data mining Walter Kosters 1 In many application areas neural networks are known to be valuable tools. This also holds for data mining. In this chapter we discuss the use of neural
More informationForecasting of Economic Quantities using Fuzzy Autoregressive Model and Fuzzy Neural Network
Forecasting of Economic Quantities using Fuzzy Autoregressive Model and Fuzzy Neural Network Dušan Marček 1 Abstract Most models for the time series of stock prices have centered on autoregressive (AR)
More informationFuzzy Logic Derivation and Simulation of a ThreeVariable Solar Water Heater Using Matlab Fuzzy Logic Toolbox
Fuzzy Logic Derivation and Simulation of a ThreeVariable Solar Water Heater Using Matlab Fuzzy Logic Toolbox Rionel Belen Caldo Faculty Member and Research Coordinator, College of Engineering and Computer
More informationData Center Power Requirements: Measurements From Silicon Valley
July 10, 2001 Data Center Power Requirements: Measurements From Silicon Valley Jennifer MitchellJackson a, Jonathan G. Koomey b*, Bruce Nordman b, Michele Blazek c a Energy and Resources Group, 310 Barrows
More informationInternational Journal of Scientific & Engineering Research, Volume 4, Issue 5, May ISSN
International Journal of Scientific & Engineering Research, Volume 4, Issue 5, May213 737 Letter Recognition Data Using Neural Network Hussein Salim Qasim Abstract The letters dataset from the UCI repository
More informationHow Does Your Data Center Measure Up? Energy Efficiency Metrics and Benchmarks for Data Center Infrastructure Systems
How Does Your Data Center Measure Up? Energy Efficiency Metrics and Benchmarks for Data Center Infrastructure Systems Paul Mathew, Ph.D., Staff Scientist Steve Greenberg, P.E., Energy Management Engineer
More informationPower Prediction Analysis using Artificial Neural Network in MS Excel
Power Prediction Analysis using Artificial Neural Network in MS Excel NURHASHINMAH MAHAMAD, MUHAMAD KAMAL B. MOHAMMED AMIN Electronic System Engineering Department Malaysia Japan International Institute
More informationRecommendations for Measuring and Reporting Overall Data Center Efficiency
Recommendations for Measuring and Reporting Overall Data Center Efficiency Version 1 Measuring PUE at Dedicated Data Centers 15 July 2010 Table of Contents 1 Introduction... 1 1.1 Purpose Recommendations
More informationFuzzy Candlestick Approach to Trade S&P CNX NIFTY 50 Index using Engulfing Patterns
Fuzzy Candlestick Approach to Trade S&P CNX NIFTY 50 Index using Engulfing Patterns Partha Roy 1, Sanjay Sharma 2 and M. K. Kowar 3 1 Department of Computer Sc. & Engineering 2 Department of Applied Mathematics
More informationSTATISTICA. Clustering Techniques. Case Study: Defining Clusters of Shopping Center Patrons. and
Clustering Techniques and STATISTICA Case Study: Defining Clusters of Shopping Center Patrons STATISTICA Solutions for Business Intelligence, Data Mining, Quality Control, and Webbased Analytics Table
More informationDAILY MULTIVARIATE FORECASTING OF WATER DEMAND IN A TOURISTIC ISLAND WITH THE USE OF ANN AND ANFIS
DAILY MULTIVARIATE FORECASTING OF WATER DEMAND IN A TOURISTIC ISLAND WITH THE USE OF ANN AND ANFIS D. Kofinas, E. Papageorgiou, C. Laspidou, N. Mellios, K. Kokkinos CONTEMPORARY APPROACHES ON WDS MANAGEMENT
More informationDesign of Prediction System for Key Performance Indicators in Balanced Scorecard
Design of Prediction System for Key Performance Indicators in Balanced Scorecard Ahmed Mohamed Abd ElMongy. Faculty of Systems and Computers Engineering, AlAzhar University Cairo, Egypt. Alaa eldeen
More informationIranian J Env Health Sci Eng, 2004, Vol.1, No.2, pp.5157. Application of Intelligent System for Water Treatment Plant Operation.
Iranian J Env Health Sci Eng, 2004, Vol.1, No.2, pp.5157 Application of Intelligent System for Water Treatment Plant Operation *A Mirsepassi Dept. of Environmental Health Engineering, School of Public
More informationSelecting an IndustryStandard Metric for Data Center Efficiency
Selecting an IndustryStandard Metric for Data Center Efficiency By Neil Rasmussen White Paper #157 Executive Summary The development of standards for the measurement and specification of data center efficiency
More informationNeural Networks. CAP5610 Machine Learning Instructor: GuoJun Qi
Neural Networks CAP5610 Machine Learning Instructor: GuoJun Qi Recap: linear classifier Logistic regression Maximizing the posterior distribution of class Y conditional on the input vector X Support vector
More informationAnalecta Vol. 8, No. 2 ISSN 20647964
EXPERIMENTAL APPLICATIONS OF ARTIFICIAL NEURAL NETWORKS IN ENGINEERING PROCESSING SYSTEM S. Dadvandipour Institute of Information Engineering, University of Miskolc, Egyetemváros, 3515, Miskolc, Hungary,
More informationRecommendations for Measuring and Reporting Overall Data Center Efficiency
Recommendations for Measuring and Reporting Overall Data Center Efficiency Version 2 Measuring PUE for Data Centers 17 May 2011 Table of Contents 1 Introduction... 1 1.1 Purpose Recommendations for Measuring
More informationConception and Development of a Health Care Risk Management System
2011 International Conference on Biomedical Engineering and Technology IPCBEE vol.11 (2011) (2011) IACSIT Press, Singapore Conception and Development of a Health Care Risk Management System Nesrine Zoghlami,
More informationData Center Industry Leaders Reach Agreement on Guiding Principles for Energy Efficiency Metrics
On January 13, 2010, 7x24 Exchange Chairman Robert Cassiliano and Vice President David Schirmacher met in Washington, DC with representatives from the EPA, the DOE and 7 leading industry organizations
More informationA Comparative Study of the Pickup Method and its Variations Using a Simulated Hotel Reservation Data
A Comparative Study of the Pickup Method and its Variations Using a Simulated Hotel Reservation Data Athanasius Zakhary, Neamat El Gayar Faculty of Computers and Information Cairo University, Giza, Egypt
More informationCHAPTER 5 PREDICTIVE MODELING STUDIES TO DETERMINE THE CONVEYING VELOCITY OF PARTS ON VIBRATORY FEEDER
93 CHAPTER 5 PREDICTIVE MODELING STUDIES TO DETERMINE THE CONVEYING VELOCITY OF PARTS ON VIBRATORY FEEDER 5.1 INTRODUCTION The development of an active trap based feeder for handling brakeliners was discussed
More informationEMPLOYEE PERFORMANCE APPRAISAL SYSTEM USING FUZZY LOGIC
EMPLOYEE PERFORMANCE APPRAISAL SYSTEM USING FUZZY LOGIC ABSTRACT Adnan Shaout* and Mohamed Khalid Yousif** *The Department of Electrical and Computer Engineering The University of Michigan Dearborn, MI,
More informationAvoiding Costs from Oversizing Data Center and Network Room Infrastructure
Avoiding Costs from Oversizing Data Center and Network Room Infrastructure White Paper 37 Revision 6 by Neil Rasmussen > Executive summary The physical and power infrastructure of data centers and network
More informationBUILDING ENERGY DEMAND AGGREGATION AND SIMULATION TOOLS A DANISH CASE STUDY
BUILDING ENERGY DEMAND AGGREGATION AND SIMULATION TOOLS A DANISH CASE STUDY P. Gianniou; A. Heller; C. Rode Department of Civil Engineering, Technical University of Denmark, Kgs. Lyngby ABSTRACT Nowadays,
More informationReducing Data Center Energy Consumption
Reducing Data Center Energy Consumption By John Judge, Member ASHRAE; Jack Pouchet, Anand Ekbote, and Sachin Dixit Rising data center energy consumption and increasing energy costs have combined to elevate
More informationA New Approach For Estimating Software Effort Using RBFN Network
IJCSNS International Journal of Computer Science and Network Security, VOL.8 No.7, July 008 37 A New Approach For Estimating Software Using RBFN Network Ch. Satyananda Reddy, P. Sankara Rao, KVSVN Raju,
More informationThreat Modeling Using Fuzzy Logic Paradigm
Issues in Informing Science and Information Technology Volume 4, 2007 Threat Modeling Using Fuzzy Logic Paradigm A. S. Sodiya, S. A. Onashoga, and B. A. Oladunjoye Department of Computer Science, University
More informationModelBased Performance Monitoring: Review of Diagnostic Methods and Chiller Case Study
LBNL45949 CD425 ACEEE 2000 Summer Study on Energy Efficiency in Buildings, Efficiency and Sustainability, August 2025, 2000, Asilomar Conference Center, Pacific Grove, CA, and published in the Proceedings.
More informationA Fuzzy System Approach of Feed Rate Determination for CNC Milling
A Fuzzy System Approach of Determination for CNC Milling Zhibin Miao Department of Mechanical and Electrical Engineering Heilongjiang Institute of Technology Harbin, China email:miaozhibin99@yahoo.com.cn
More informationIntroduction to Machine Learning and Data Mining. Prof. Dr. Igor Trajkovski trajkovski@nyus.edu.mk
Introduction to Machine Learning and Data Mining Prof. Dr. Igor Trakovski trakovski@nyus.edu.mk Neural Networks 2 Neural Networks Analogy to biological neural systems, the most robust learning systems
More informationECE 533 Project Report Ashish Dhawan Aditi R. Ganesan
Handwritten Signature Verification ECE 533 Project Report by Ashish Dhawan Aditi R. Ganesan Contents 1. Abstract 3. 2. Introduction 4. 3. Approach 6. 4. Preprocessing 8. 5. Feature Extraction 9. 6. Verification
More informationInfrastructure & Cities Sector
Technical Article Infrastructure & Cities Sector Building Technologies Division Zug (Switzerland), October 18, 2011 Saving Energy in a Data Center A Leap of Faith? New guidelines from ASHRAE (American
More informationRisk Analysis and Quantification
Risk Analysis and Quantification 1 What is Risk Analysis? 2. Risk Analysis Methods 3. The Monte Carlo Method 4. Risk Model 5. What steps must be taken for the development of a Risk Model? 1.What is Risk
More informationLearning. Artificial Intelligence. Learning. Types of Learning. Inductive Learning Method. Inductive Learning. Learning.
Learning Learning is essential for unknown environments, i.e., when designer lacks omniscience Artificial Intelligence Learning Chapter 8 Learning is useful as a system construction method, i.e., expose
More informationBuilding Energy Information Systems:
Building Energy Information Systems: State of the Technology and User Case Studies Jessica Granderson Lawrence Berkeley National Laboratory Sponsored by the California Energy Commission Public Interest
More informationOpen Access Research on Application of Neural Network in Computer Network Security Evaluation. Shujuan Jin *
Send Orders for Reprints to reprints@benthamscience.ae 766 The Open Electrical & Electronic Engineering Journal, 2014, 8, 766771 Open Access Research on Application of Neural Network in Computer Network
More informationNeural Networks for Sentiment Detection in Financial Text
Neural Networks for Sentiment Detection in Financial Text Caslav Bozic* and Detlef Seese* With a rise of algorithmic trading volume in recent years, the need for automatic analysis of financial news emerged.
More informationAPPENDIX A IEEE POWER QUALITY STANDARDS
113 APPENDIX A IEEE POWER QUALITY STANDARDS IEEE Standard 1411993, Recommended Practice for Electric Power Distribution for Industrial Plants, alias the Red Book. A thorough analysis of basic electricalsystem
More informationFollow links Class Use and other Permissions. For more information, send email to: permissions@pupress.princeton.edu
COPYRIGHT NOTICE: David A. Kendrick, P. Ruben Mercado, and Hans M. Amman: Computational Economics is published by Princeton University Press and copyrighted, 2006, by Princeton University Press. All rights
More informationAPPENDIX N. Data Validation Using Data Descriptors
APPENDIX N Data Validation Using Data Descriptors Data validation is often defined by six data descriptors: 1) reports to decision maker 2) documentation 3) data sources 4) analytical method and detection
More informationGreen IT Promotion Council, Japan
Concept of New Metrics for Data Center Energy Efficiency Introduction of Datacenter Performance per Energy [ DPPE ] Green IT Promotion Council, Japan February2010 Abstract Power Usage Effectiveness (PUE)
More informationLecture 6. Artificial Neural Networks
Lecture 6 Artificial Neural Networks 1 1 Artificial Neural Networks In this note we provide an overview of the key concepts that have led to the emergence of Artificial Neural Networks as a major paradigm
More informationProblems often have a certain amount of uncertainty, possibly due to: Incompleteness of information about the environment,
Uncertainty Problems often have a certain amount of uncertainty, possibly due to: Incompleteness of information about the environment, E.g., loss of sensory information such as vision Incorrectness in
More informationOptimising Energy Use in Cities through Smart Decision Support Systems
Optimising Energy Use in Cities through Smart Decision Support Systems Energy Management for Sustainable Action Plans, Brussels, 18 June 2015 Siegfried Zoellner, Coordinator, ICLEI European Secretariat
More informationMaking Sense of the Mayhem: Machine Learning and March Madness
Making Sense of the Mayhem: Machine Learning and March Madness Alex Tran and Adam Ginzberg Stanford University atran3@stanford.edu ginzberg@stanford.edu I. Introduction III. Model The goal of our research
More informationSoftware Engineering Prof. N.L. Sarda Computer Science & Engineering Indian Institute of Technology, Bombay Lecture4 Overview of Phases (Part  II)
Software Engineering Prof. N.L. Sarda Computer Science & Engineering Indian Institute of Technology, Bombay Lecture4 Overview of Phases (Part  II) We studied the problem definition phase, with which
More informationOPTIMIZATION OF VENTILATION SYSTEMS IN OFFICE ENVIRONMENT, PART II: RESULTS AND DISCUSSIONS
OPTIMIZATION OF VENTILATION SYSTEMS IN OFFICE ENVIRONMENT, PART II: RESULTS AND DISCUSSIONS Liang Zhou, and Fariborz Haghighat Department of Building, Civil and Environmental Engineering Concordia University,
More informationApplication of Neural Network in User Authentication for Smart Home System
Application of Neural Network in User Authentication for Smart Home System A. Joseph, D.B.L. Bong, D.A.A. Mat Abstract Security has been an important issue and concern in the smart home systems. Smart
More informationSoftware Development for Cooling Load Estimation by CLTD Method
IOSR Journal of Mechanical and Civil Engineering (IOSRJMCE) ISSN: 22781684Volume 3, Issue 6 (Nov.  Dec. 2012), PP 0106 Software Development for Cooling Load Estimation by CLTD Method Tousif Ahmed Department
More informationAn Introduction to Neural Networks
An Introduction to Vincent Cheung Kevin Cannons Signal & Data Compression Laboratory Electrical & Computer Engineering University of Manitoba Winnipeg, Manitoba, Canada Advisor: Dr. W. Kinsner May 27,
More informationSaumil Navalbhai Patel B.E., Gujarat University, India, 2007 PROJECT. Submitted in partial satisfaction of the requirements for the degree of
POWER LOAD BALANCING USING FUZZY LOGIC Saumil Navalbhai Patel B.E., Gujarat University, India, 2007 PROJECT Submitted in partial satisfaction of the requirements for the degree of MASTER OF SCIENCE in
More informationMULTIOBJECTIVE GENETIC OPTIMISATION FOR SELFORGANISING FUZZY LOGIC CONTROL
MULTIOBJECTIVE GENETIC OPTIMISATION FOR SELFORGANISING FUZZY LOGIC CONTROL M.F. Abbod, M. Mahfouf and D.A. Linkens University of Sheffield, Sheffield, UK A multiobjective genetic algorithm is developed
More informationCustomer Classification And Prediction Based On Data Mining Technique
Customer Classification And Prediction Based On Data Mining Technique Ms. Neethu Baby 1, Mrs. Priyanka L.T 2 1 M.E CSE, Sri Shakthi Institute of Engineering and Technology, Coimbatore 2 Assistant Professor
More informationD A T A M I N I N G C L A S S I F I C A T I O N
D A T A M I N I N G C L A S S I F I C A T I O N FABRICIO VOZNIKA LEO NARDO VIA NA INTRODUCTION Nowadays there is huge amount of data being collected and stored in databases everywhere across the globe.
More informationThe Quest for Energy Efficiency. A White Paper from the experts in BusinessCritical Continuity
The Quest for Energy Efficiency A White Paper from the experts in BusinessCritical Continuity Abstract One of the most widely discussed issues throughout the world today is the rapidly increasing price
More informationEFFICIENT DATA PREPROCESSING FOR DATA MINING
EFFICIENT DATA PREPROCESSING FOR DATA MINING USING NEURAL NETWORKS JothiKumar.R 1, Sivabalan.R.V 2 1 Research scholar, Noorul Islam University, Nagercoil, India Assistant Professor, Adhiparasakthi College
More informationdegrees of freedom and are able to adapt to the task they are supposed to do [Gupta].
1.3 Neural Networks 19 Neural Networks are large structured systems of equations. These systems have many degrees of freedom and are able to adapt to the task they are supposed to do [Gupta]. Two very
More informationDocumenting Performance Metrics in a Building Lifecycle Information System
LBNL41942 CBS379 To be presented at the Green Building Challenge Õ98 Conference, Vancouver, British Columbia, Canada, October 2628, 1998, and to be published in the proceedings. Documenting Performance
More informationRISK ASSESSMENT BASED UPON FUZZY SET THEORY
RISK ASSESSMENT BASED UPON FUZZY SET THEORY László POKORÁDI, professor, University of Debrecen pokoradi@mfk.unideb.hu KEYWORDS: risk management; risk assessment; fuzzy set theory; reliability. Abstract:
More informationData quality in Accounting Information Systems
Data quality in Accounting Information Systems Comparing Several Data Mining Techniques Erjon Zoto Department of Statistics and Applied Informatics Faculty of Economy, University of Tirana Tirana, Albania
More informationMBA 611 STATISTICS AND QUANTITATIVE METHODS
MBA 611 STATISTICS AND QUANTITATIVE METHODS Part I. Review of Basic Statistics (Chapters 111) A. Introduction (Chapter 1) Uncertainty: Decisions are often based on incomplete information from uncertain
More informationPERFORMANCE OF MPPT CHARGE CONTROLLERS A STATE OF THE ART ANALYSIS
PERFORMANCE OF MPPT CHARGE CONTROLLERS A STATE OF THE ART ANALYSIS Michael Müller 1, Roland Bründlinger 2, Ortwin Arz 1, Werner Miller 1, Joachim Schulz 2, Georg Lauss 2 1. STECA ELEKTRONIK GMBH, Mammostr.
More informationMIDLAND ISD ADVANCED PLACEMENT CURRICULUM STANDARDS AP ENVIRONMENTAL SCIENCE
Science Practices Standard SP.1: Scientific Questions and Predictions Asking scientific questions that can be tested empirically and structuring these questions in the form of testable predictions SP.1.1
More informationResidential Energy Services Demand: Lisbon case study towards Net Zero Energy House
Residential Energy Services Demand: Lisbon case study towards Net Zero Energy House Abstract Technically, reaching Net Zero Energy House (NZEH) is no longer a too ambitious goal as most of the technologies
More informationA Multilevel Artificial Neural Network for Residential and Commercial Energy Demand Forecast: Iran Case Study
211 3rd International Conference on Information and Financial Engineering IPEDR vol.12 (211) (211) IACSIT Press, Singapore A Multilevel Artificial Neural Network for Residential and Commercial Energy
More informationA Color Placement Support System for Visualization Designs Based on Subjective Color Balance
A Color Placement Support System for Visualization Designs Based on Subjective Color Balance Eric Cooper and Katsuari Kamei College of Information Science and Engineering Ritsumeikan University Abstract:
More informationVOLATILITY AND DEVIATION OF DISTRIBUTED SOLAR
VOLATILITY AND DEVIATION OF DISTRIBUTED SOLAR Andrew Goldstein Yale University 68 High Street New Haven, CT 06511 andrew.goldstein@yale.edu Alexander Thornton Shawn Kerrigan Locus Energy 657 Mission St.
More informationReview of some concepts in predictive modeling
Review of some concepts in predictive modeling Brigham and Women s Hospital HarvardMIT Division of Health Sciences and Technology HST.951J: Medical Decision Support A disjoint list of topics? Naïve Bayes
More informationEXPERIMENTAL ERROR AND DATA ANALYSIS
EXPERIMENTAL ERROR AND DATA ANALYSIS 1. INTRODUCTION: Laboratory experiments involve taking measurements of physical quantities. No measurement of any physical quantity is ever perfectly accurate, except
More informationChapter 14 Managing Operational Risks with Bayesian Networks
Chapter 14 Managing Operational Risks with Bayesian Networks Carol Alexander This chapter introduces Bayesian belief and decision networks as quantitative management tools for operational risks. Bayesian
More informationSan Jose State University Engineering 10 1
KY San Jose State University Engineering 10 1 Select Insert from the main menu Plotting in Excel Select All Chart Types San Jose State University Engineering 10 2 Definition: A chart that consists of multiple
More informationAbsolute and relative humidity Precise and comfort airconditioning
Absolute and relative humidity Precise and comfort airconditioning Trends and best practices in data centers Compiled by: CONTEG Date: 30. 3. 2010 Version: 1.11 EN 2013 CONTEG. All rights reserved. No
More informationScheduling of Flexible Manufacturing Systems Using Fuzzy Logic
Scheduling of Flexible Manufacturing Systems Using Fuzzy Logic by Pramot Srinoi A/Prof. Ebrahim Shayan Dr. Fatemeh Ghotb, School of Mathematical Sciences Abstract This paper presents a research project
More informationQuantitative Inventory Uncertainty
Quantitative Inventory Uncertainty It is a requirement in the Product Standard and a recommendation in the Value Chain (Scope 3) Standard that companies perform and report qualitative uncertainty. This
More informationCase Study: Opportunities to Improve Energy Efficiency in Three Federal Data Centers
Case Study: Opportunities to Improve Energy Efficiency in Three Federal Data Centers Prepared for the U.S. Department of Energy s Federal Energy Management Program Prepared By Lawrence Berkeley National
More information
Electrical Systems.
Review Root Causes of Energy Inefficiency Roadmap to Maximize Energy Efficiency Best Practices Alternative Energy Sources Controls Take Aways Seek Professional Help. ENERGY INEFFICIENCY OF
More informationCluster Analysis for Evaluating Trading Strategies 1
CONTRIBUTORS Jeff Bacidore Managing Director, Head of Algorithmic Trading, ITG, Inc. Jeff.Bacidore@itg.com +1.212.588.4327 Kathryn Berkow Quantitative Analyst, Algorithmic Trading, ITG, Inc. Kathryn.Berkow@itg.com
More information