1 I/A Series HARDWARE Product Specifications G50 Server Enclosure PSS 21H-2X50 B4 Note: Shown without Cable Base (Included) The I/A Series G50 Server Enclosure with front and rear access provides environmental protection and housing for compatible I/A Series workstations, servers and The MESH Control Network switches. FEATURES The I/A Series G50 server enclosure with front and rear access offers the following features: 600w x 1000d x 2000mm high enclosure, available as vented only Front and rear accessible 19-inch system rails, with 42 U of available vertical mounting space (1U = 44mm (1.75 in)) Enclosure front access with left- or right-side mounted door - rear access with half-width doors Main power entry includes 16 A, Type D, double pole circuit breakers for 120/240 V ac systems. Enclosure selection for use in indoor NEMA 1 rated (not IP rated) temperature-controlled environments Enclosure can accommodate: Up to two sliding shelves per enclosure for Model H90 and P90 servers, H91 and P91 servers or Model H92 and P92 workstations; each shelf with up to two pairs of power strips (16A max/10a per socket)
2 Page 2 Rack-mounted equipment secured directly to the 19-inch rails, such as The MESH control network switches, depending on sizing, power, cabling and ventilation requirements Compact design to minimize use of floor space with both front and rear access that allow maximum density of enclosures in a control room environment Bottom or top cable entry for power wiring, but can be customer configured for simultaneous top and bottom cable entry Up to four redundant power strips (four primary and four secondary) per enclosure (eight total) Conveniently placed eyebolts for transporting and lifting the enclosures A 100 mm (3.9 in) plinth - total enclosure height of 2160 mm (85.0 in) Comfort handles with push-button/keylocks Standard safety earthing (grounding) studs INTRODUCTION The G50 server enclosure is a general purpose unit designed for housing compatible servers, switches and related equipment on shelves or on its 19-inch racks. The G50 enclosure is available as a vented enclosure only. The enclosure s rails provide 42 U of available vertical mounting space for rack-mounted or other equipment. The upper and lower halves of the enclosure are customizable, and may be either left empty or populated with various equipment configurations: Up to two sliding shelves; shelves can support the Windows or Solaris -based tower workstations and servers, such as the Model H91 and P91 server, depending on the size and ventilation requirements of the equipment. NOTE It is recommended that when using sliding shelves, only one shelf is pulled out at a time to prevent the enclosure from becoming unbalanced. Equipment secured directly to the rails, such as The MESH control network switches - depending on the sizing, power, cabling and ventilation requirements of the equipment NOTE Typically, workstations and servers are installed for access from the enclosure front, while switches are installed for access from the enclosure rear. The G50 enclosure is a free-standing, floor mounted unit with an NEMA 1 (1) rating for location in protected indoor environmental areas. No fans are provided with this enclosure as all enclosed equipment (servers, switches, and so forth) are assumed to have their own fans. SAMPLE CONFIGURATIONS The G50 enclosure can fit a variety of servers, switches and their associated power supplies and support equipment. The following examples are provided as viable examples for configurations in this enclosure. Figure 1 illustrates configurations for The MESH control network switches in the G50 enclosure. NOTE All switches must be installed in the G50 enclosure with the site requirements listed in their documentation. Refer to SITE PLANNING FOR SWITCHES on page 17 to locate the appropriate documentation. Figure 2 and Figure 3 illustrate configurations for the servers or workstations in the G50 enclosure. (1) The G50 enclosure does not have an IP rating as air flow is allowed through ceiling, floor and all walls.
3 NOTE In the following figures, the power strips are shown on the sides of the switches/servers to represent their association with the switches/servers on their half of the enclosure. In the field, power strips are mounted on front or rear side of the enclosure based on the configuration. PSS 21H-2X50 B4 Page 3
4 Page 4 N7 Chassis Managed Switch (P0972YE) Rack-Mounted Redundant Primary and Secondary Power 15A Wire Management Area N7 Switch requires 2U space above equipment Pri. Pwr. Strip N3 Chassis Managed Switch (P0973AS) Rack-Mounted Power 15A N3 Chassis Managed Switch (P0973AS) Rack-Mounted Power 15A Sec. Pwr. Strip Upper Half* N7 Chassis Managed Switch (P0972YE) Rack-Mounted Redundant Primary and Secondary Power 15A Power Terminals N1 Chassis Managed Switches (P0973AR) Rack-Mounted Power 5A Pri. Pwr. Strip Pri. Pwr. Strip P0973AR P0973AR P0973AR P0973AR P0973AR P0973AR Sec. Pwr. Strip Sec. Pwr. Strip Lower Half* Upper Half* Lower Half* Pri. Pwr. Strip Pri. Pwr. Strip P0973HA P0973HA P0973BJ P0973BJ P0973BH P0973BH P0973BK P0973BK 8-Slot Redundant Power Supply Chassis 2.5A P0973HA P0973HA P0973BN P0973BJ P0973BJ P0973BN P0973BH P0973BH P0973BN Sec. Pwr. Sec. Pwr. Strip 24-Gigabit (SFP) Port Managed Switch (P0973HA) Wire Management Area 24-Port Fiber Managed Switch (P0973BJ) 24-Port Copper Managed Switch (P0973BH) 8-Port Copper/ 8-Port Fiber Managed Switch (P0973BK) 24-Gigabit (SFP) Port Managed Switch (P0973HA) 2-Slot Redundant Power Supply 2.5A (P0973BN) 24-Port Fiber Managed Switch (P0973BJ) 24-Port Copper Managed Switch (P0973BH) N7 Switch requires 2U space above equipment Power Terminals P0973HA P0973HA P0973BN N1 Switch (P0973AR) N3 Chassis Managed Switch (P0973AS) Rack-Mounted Power 15A N7 Chassis Managed Switch (P0972YE) Rack-Mounted Redundant Primary and Secondary Power 15A Upper Half Lower Half * Upper and lower half equipment configurations are interchangeable where specified (*). NOTE: You must follow the installation guidelines provided in the switches documentation on page 16. All part numbers are subject to change. Other equipment may be installed, per its specifications. For this enclosure configuration, top entry only. Figure 1. Example Configurations for The MESH Control Network Switches in G50 Enclosure (Part 1)
5 Page 5 Upper Half* Model H91/P91/H92/P92 (Tower) Rack-Mounted Power 10A Model H91/P91/H92/P92 (Tower) Rack-Mounted Power 10A Model H91/P91/H92/P92 (Tower) Rack-Mounted Power 10A Pri. Pwr. Sec. Pwr. Lower Half* Pri.Pwr. Pri.Pwr. Pri.Pwr. Pri.Pwr. Model H90 and P90 Servers Model H90 and P90 Servers Model H90 and P90 Servers Model H90 and P90 Servers Model H90 and P90 Servers Model H90 and P90 Servers Model H90 and P90 Servers Model H90 and P90 Servers Model H90 and P90 Servers Sc.Pwr. Sc.Pwr. Sc.Pwr. Sc.Pwr. Model H90 and P90 Servers Rack-Mounted Power 8A * Upper and lower half equipment configurations are interchangeable where specified (*). Be aware that a G50 enclosure can have no more than four primary and four secondary power strips. NOTE: All part numbers are subject to change. Other equipment may be installed, per its specifications. Figure 2. Example Configurations for I/A Series Workstations and Servers in G50 Enclosure (Part 1)
6 Page 6 Pri. Pwr. Strip Model H91/P91/H92/P92 (Tower) Shelf-Mounted Power 10A Shelf (H91/P91/H92/P92 Only) Sec. Pwr. Strip Upper Half* Wire Management Area P0973BK P0973BK 8-Slot Redundant Power Supply Chassis 2.5A 8-Port Copper/ 8-Port Fiber Managed Switch (P0973BK) Upper Half Model H90 and P90 Servers Rack-Mounted Power 8A Model H90 and P90 Servers Model H91/P91/H92/P92 (Tower) Rack-Mounted Power 10A Lower Half Model H91/P91/H92/P92 (Tower) Shelf-Mounted Power 10A * Upper and lower half equipment configurations are interchangeable where specified (*). Shelf (For H91 and P91Only) Power Terminals For this enclosure configuration, bottom entry only. NOTE: You must follow the installation guidelines provided in the switches documentation on page 16. All part numbers are subject to change. Other equipment may be installed, per its specifications. Figure 3. Example Configurations for I/A Series Workstations and Servers in G50 Enclosure (Part 2)
7 Page 7 BAYING G50 ENCLOSURES Multiple G50 enclosures can be installed connected to one another to maximize the use of floor space and ease of cabling. The enclosures can be bayed together using kit P0931VV, discussed in the Enclosures and Mounting Structures Site Planning and Installation User s Guide (B0700AS). NATIONAL ELECTRICAL MANUFACTURERS ASSOCIATION RATING The metal enclosures provide the outer layer of protection for the equipment contained within to support a NEMA 1 rating. When the equipment includes covers or layers built into the equipment itself, a minimum of contaminants in the plant environment reaches the equipment, thus greatly extending its life. The enclosures support convenient top or bottom cable entry for power wiring. EQUIPMENT MOUNTING All equipment installed in this enclosure must be attached to the 19-inch rails directly or indirectly via a sliding shelf. As well, all equipment must be able to fit within the physical constraints of the enclosure with sufficient space for air flow and associated cabling, including cable routes, sufficient bend radius and dressing. All servers, switches and similar equipment which require air intake must be installed to maintain a consistent air flow in a single direction in the enclosure. The air intakes for these equipment must face the same direction, and their exhausts must face the same direction to ensure that no hot exhaust from one piece of equipment enters in the air intake of another. NOTE Ensure that the front and rear doors on the enclosure allow for unrestricted air flow, and are not obstructed by objects such as print pockets. INPUT POWER CABLING The enclosures can be configured for bottom cable entry or top cable entry or modified by the customer for simultaneous top and bottom cable entry. For the top cable entry version, customer power feeds enter through customer-configured cable glands. For the bottom entry version, the power cables enter through removable gland plates, located at the bottom (inside) of the enclosure, which can be removed, drilled, or punched for cable routing. POWER AND EARTHING (GROUNDING) Power wiring to the enclosure is routed through the bottom (through removable gland plates) or top of the enclosure. Customer-supplied dual power input feeds terminate at circuit breaker assemblies. All enclosure structural elements are integrally earthed by the enclosure design to meet the appropriate industry regulations and standards. Earthing (Grounding) Two M8 studs (one for each enclosure side) provide a central earth (ground) point and dedicated earthing points when baying enclosures together. Power Distribution Each enclosure is available with a dedicated assembly for customer redundant main power. Power distribution is provided by 16 A, Type D, double pole circuit breakers for 120/240 V ac systems. The enclosure may be ordered without these power distribution circuit breakers when the customer has requirements for power distribution specific to regional electrical codes.
8 Page 8 A [63.4mm] 2.5 in. FRONT and REAR Z BRACKET ORIENTATION Z FOUR PLACES [116mm] 4.6 in. [750mm] 29.5 in. [67.5mm] 2.66 in. DETAIL A SCALE 1 : 2 Top View Figure 4. G50 Server Enclosure - Top View - Rails
9 Page 9 Redundant AC Power Strip Outlets (IEC) 25mm x 75mm (1.0in x 3.0in) Wire Duct for ac Power Distribution (Representative) Invensys-Provided Switch Form Factor (Not Supplied) (Representative) Tower PC Server/Workstation Form Factor Secured to Rails (Not Supplied) (Representative) Tower PC Server/Workstation Form Factor (Not Supplied) Lower Single Sliding Shelf Option Redundant AC Power Strip Outlets (IEC) Protective Earth (PE) Studs Figure 5. G50 Server Enclosure With Server, Bottom Entry, Front View
10 Page 10 Redundant AC Power Strip Outlets (IEC) (Representative) Invensys-Provided Switch Form Factor (Not Supplied) (Representative) Tower PC Server/Workstation Form Factor Secured to Rails (Not Supplied) (Representative) Tower PC Server/Workstation Form Factor (Not Supplied) Lower Single Sliding Shelf Option Power Circuit Breaker Assemblies Figure 6. G50 Server Enclosure With Server, Bottom Entry, Rear View
11 Page 11 Redundant AC Power Strip Outlets (IEC) 25mm x 75mm (1.0in x 3.0in) Wire Duct for ac Power Distribution Upper Sliding Shelf Option Redundant AC Power Strip Outlets (IEC) Lower Single Sliding Shelf Option Redundant AC Power Strip Outlets (IEC) Redundant AC Power Strip Outlets (IEC) Protective Earth (PE) Studs Figure 7. G50 Server Enclosure, Empty, Bottom Entry, Front View
12 Page 12 Redundant AC Power Strip Outlets (IEC) Redundant AC Power Strip Outlets (IEC) Power Circuit Breaker Assemblies Figure 8. G50 Server Enclosure, Empty, Bottom Entry, Rear View
13 Page 13 Power Circuit Breaker Assemblies Redundant AC Power Strip Outlets (IEC) 25mm x 75mm (1.0in x 3.0in) Wire Duct for ac Power Distribution Redundant AC Power Strip Outlets (IEC) (Representative) Invensys-Provided Switch Form Factor (Not Supplied) (Representative) Tower PC Server/Workstation Form Factor Secured to Rails (Not Supplied) (Representative) Invensys-Provided Switch Form Factor (Not Supplied) Protective Earth (PE) Studs Figure 9. G50 Server Enclosure With Server, Top Entry, Front View
14 Page 14 Power Circuit Breaker Assemblies (Representative) Invensys-Provided Switch Form Factor (Not Supplied) (Representative) Tower PC Server/Workstation Form Factor Secured to Rails (Not Supplied) (Representative) Invensys-Provided Switch Form Factor (Not Supplied) Figure 10. G50 Server Enclosure With Server, Top Entry, Rear View
15 Page 15 Redundant AC Power Strip Outlets (IEC) 25mm x 75mm (1.0in x 3.0in) Wire Duct for ac Power Distribution Upper Sliding Shelf Option Redundant AC Power Strip Outlets (IEC) Redundant AC Power Strip Outlets (IEC) Lower Single Sliding Shelf Option Redundant AC Power Strip Outlets (IEC) Protective Earth (PE) Studs Figure 11. G50 Server Enclosure, Empty, Top Entry, Front View
16 Page 16 Power Circuit Breaker Assemblies Redundant AC Power Strip Outlets (IEC) Redundant AC Power Strip Outlets (IEC) Figure 12. G50 Server Enclosure, Empty, Top Entry, Rear View
17 Page 17 SITE PLANNING FOR SWITCHES When planning a G50 enclosure with switches installed, you must ensure that the site requirements for the switches are maintained within the enclosures. These site requirements are in the documentation provided by Invensys. Table 1 lists the Invensys documentation for the switches currently offered (2). Refer to The MESH Control Network Ethernet Equipment (PSS 21H-7C3 B4) for the complete list of switches and their associated Invensys documentation. Table 1. Invensys Switches Currently Offered for G50 Enclosure Description A-Series 24-Port Copper Managed Switch (P0973BH) A-Series 24-Port Fiber Managed Switch (P0973BJ) A-Series 8-Port Copper/ 8-Port Fiber Managed Switch (P0973BK) C-Series 24-Gigabit (SFP) Port Managed Switch (P0973HA) N-Series N1 Chassis Managed Switch (P0973AR) N-Series N3 Chassis Managed Switch (P0973AS) N-Series N7 Chassis Managed Switch (P0972YE) Invensys Manual B0700CH B0700CH B0700CH B0700CJ B0700CK B0700CK B0700CK (2) This list is subject to change. Refer to The MESH Control Network Ethernet Equipment (PSS 21H-7C3 B4) for the most up-to-date list of switches offered.
18 Page 18 ENCLOSURE FEATURES AND OPTIONS The G50 enclosure is provided with the following features, some of which are optional. Table 2. G50 Enclosure Features and Options Feature Base Enclosure Enclosure Access Front Door Front Door Mounting Rear Door Mounting Cable Entry Sidewalls Door Handle Equipment Supported (In Upper or Lower Half of Enclosure) Power Cord Sets (In Upper or Lower Half of Enclosure) Enclosure Lighting Earthing (Grounding) Main Power Availability Vented NEMA 1 rated (not IP rated) enclosure (no fans) Front and rear access Solid front door with inlet vents Universal mounting for left and right-hand door swing (left-hand is default) Half-width door with inlet vents Bottom cable entry or top cable entry Options configurable based on baying requirements Comfort handle with push-button/keylock Rack-mounted equipment secured directly to the rails (no support provided) Up to two sliding shelves for Model H91 and P91 Servers (tower form) Two, four, six or eight IEC-320 male/female cord sets None Two protective earth (ground) studs V ac, 50-60Hz input redundant power with 16 A, Type D, double pole circuit breakers, located in either the top or bottom of the enclosure Additionally, customer configured power entry (no provision for powering devices)
19 Page 19 Enclosure The enclosures are free-standing, floor mounted, steel industrial enclosures containing DIN rail mounted compatible servers, The MESH control network switches and related equipment, as discussed in this document. FUNCTIONAL SPECIFICATIONS ENVIRONMENTAL SPECIFICATIONS National Electrical Manufacturers Association Ratings Not IP rated/nema 1 Operating Temperatures Dependent on equipment loaded in the enclosure. Refer to the specifications listed in the equipment s Product Specification Sheet or other documentation. THERMAL WATTAGE LIMITS (FOR NON- ADJOINED ENCLOSURES) (3) Dissipation of 1000 W generates a +5 C (9 F) heat rise Storage Temperature -40 to 70 C (-40 to 158 F) Relative Humidity 5 to 95% (noncondensing) Acoustic Noise Level Ambient / Ambient Agency Certification Empty enclosure is UL and UL-C approved. Enclosure meets all applicable European Union directives and is CE compliant. Final installed enclosures populated with your equipment should be inspected by your local UL/CSA committee, or other local safety governing organization if required. A complete listing of certifications is available from enclosure vendor. For installed I/A Series equipment, refer to PSS 21H-2W2 B3. Area Designation Vented for general purpose areas. (3) The effective heat rise should be added to the planned ambient temperature and the result should be lower than the rated maximum ambient temperature of the equipment to be installed.
20 Page 20 PHYSICAL SPECIFICATIONS Mass The mass of the enclosure is dependent upon the particular configuration and equipment selected. Consult with an Invensys representative if precise mass figures are required. ENCLOSURE (MAX. CONFIGURATION) 600 mm wide x 1000 mm deep kg (516 lb) SIDE PANEL 2000 mm high x 1000 mm deep - 6 kg (14 lb) Mounting Floor CAUTION To prevent injury, this enclosure must be bolted down. Refer to the installation guide. Construction MATERIAL Doors Sheet steel, 2.0 mm (14 ga) Frame, Roof, Side Panels, Gland Plates Sheet steel, 1.5 mm (16 ga) Base/Plinth Sheet steel and plastic FINISH Frame Dipcoat-primed, RAL 7044 smooth Doors, Roof, Side Panels Dipcoat-primed, powder-coated, RAL 7035 (light gray) textured Base/Plinth Dipcoat-primed, RAL 7022 (umbra gray) smooth, plastic cover caps RAL 9005 (jet black) Gland Plates and Internal Hardware Zinc-plated, passivated Cable Entry Bottom through gland plate(s) Top through customer cutouts in enclosure top Earthing (Grounding) ROOF, SIDEWALLS, GLAND PLATES Automatic potential equalization built in FRONT AND REAR DOORS Dedicated 4 mm 2 (11 ga) ground strap to enclosure frame ENCLOSURE Two protective earth (ground) M8 studs (one for each enclosure side) Power Input Terminals CIRCUIT BREAKERS Type Compression Wire Size Solid: Up to 6 mm 2 (3 AWG) Stranded: Up to 4 mm 2 (8 AWG) Enclosure Equipment Cabling Universal mounting straps are supplied for securing, routing and strain relieving of enclosure equipment cables. Each strap supports up to a 75 mm (3 in) diameter cable bundle.
21 Page 21 FOR MORE INFORMATION For additional information describing I/A Series enclosures with DIN rail mounted equipment, refer to the following documentation: Document Number Description PSS 21H-2X8 B3 G-Series Enclosures Overview PSS 21H-4U6 B4 Model H91 and P91 Workstation Servers for Windows Server 2003 Operating System PSS 21H-4U12 B4 Model H90 and P90 Workstation Servers for Windows Server 2003 Operating System PSS 21H-4D13 B4 PSS 21H-7C3 B4 B0700CH B0700CJ B0700CK ISA-S (not Invensys-supplied) Model H92 and P92 Workstations for Windows XP Professional Operating System The MESH Control Network Ethernet Equipment A-Series (P0973BH/P0973BJ/P0973BK) Switches, Hardware and Software Configuration Instructions The MESH Control Network Hardware Instructions for C-Series Switches (P0973BL/HA) The MESH Control Network Hardware Instructions for N-Series Switches (P0973AR/P0973AS/P0972YE) Environmental Conditions for Process Measurement and Control Systems: Airborne Contaminants
22 Page 22 DIMENSIONS - NOMINAL *Roof- Inlet Vent Lifting Eyebolts (4 Places) G50 Server Enclosure *Rear Half-Width Door (Fully Opened) Perforated Front Door Base Plinth *Roof Inlet Vent Front Front **Front Door (Fully Opened) Front * VENTED ENCLOSURES ONLY - DOORS AND ROOFS ARE PERFORATED TO ALLOW AIR FLOW. ** FRONT DOORS ARE FACTORY-CONFIGURED FOR LEFT-HAND SWING, BUT CAN BE RECONFIGURED AT SITE FOR RIGHT-HAND SWING.
23 Page 23
24 Page 24 Invensys Operations Management 5601 Granite Parkway Suite 1000 Plano, TX United States of America Global Customer Support Inside U.S.: Outside U.S.: or contact your local Invensys representative. Website: Invensys, Foxboro, I/A Series, InFusion, and the Invensys logo are trademarks of Invensys plc, its subsidiaries, and affiliates. All other brands and product names may be the trademarks of their respective owners. Copyright Invensys Systems, Inc. All rights reserved. Unauthorized duplication or distribution is strictly prohibited. MB 21A 0811
Cabinets 101: Configuring A Network Or Server Cabinet North, South and Central America White Paper May 2012 www.commscope.com Contents Background Information 3 What is a network or server cabinet? 3 What
Rittal s Comprehensive Family Of... NETWORK RACK SOLUTIONS STANDARD & ECONOMICAL BasicRack A complete low-cost, high-quality basic equipment management system. Design Six web channel holes per side allow
LIEBERT VNSA Installation Sheet Description The Liebert vnsa network switch is designed for connecting multiple Ethernet-ready devices and comes in various models. The unit may have: A Liebert icom display
CompactRack Features Ample space for components and cabling provided in an efficient, compact design. The innovative frame concept with triangular extrusions ensures low weight while maintaining high stability.
Colocation Rack Secure, Separate Server Hosting and Housing in Data Centers Colocation Rack Secure, Separate Server Hosting and Housing in Data Centers An intelligent physical infrastructure is required
MCR1900 Media Converter 19-Slot Chassis Installation Guide Part #5500304-11 Copyright Statement This document must not be reproduced in any way whatsoever, either printed or electronically, without the
19 standard cabinet for server Overview Material specification Corner verticals: 1.5 mm steel End frames: 1.5 mm steel Panel mounts: 2.0 mm steel Panel mount supports: 1.5 mm steel Side panels, door and
SERVER ROOM CABINET INSTALLATION CONCEPTS SERVER ROOM CABINET INSTALLATION CONCEPTS SERVER ROOM CABINET INSTALLATION CONCEPTS ZPAS 169 EXAMPLES OF SERVER ROOMS PROJECTS WITH ZPAS CABINETS Data Box in the
Powerware Enclosure Solutions Product Focus Powerware Enclosures IT availability and reliability are critical corporate issues in today s demanding, mission-critical environments. For this reason, it is
IT infrastructure Efficiency-boosting solutions nextlevel for data centre 2 Rittal IT infrastructure The whole is more than the sum of its parts. The same is true of Rittal The System. With this in mind,
I/A Series HARDWARE Product Specifications PSS 21H-4U14 B4 V90 (Virtualization Server Host Hardware) The I/A Series Model V90 Server Virtualization Host is a Hewlett-Packard ProLiant DL380 rack mount server
Rack Installation Instructions Guidelines This publication provides information about how to install your server into a standard rack cabinet using the rail kit shipped with your server. If you no longer
Access Server Rack Cabinet Compatibility Guide A Guide to the Selection and Evaluation of Access Server Rack Cabinets for Compatibility and Use with Third Party Server Chassis Kalkenstraat 91-93 B-8800
SYSTIMAX Solutions InstaPATCH ZERO Solution Guide Rapid Server Deployment and Change Management North, South and Central Americas 1 As data centers face ever-increasing IT demands, growth demands and evolving
Outdoor 33.6W Dual Port Passive Power-over-Ethernet Midspan For External Security Cameras and Wireless Access Points Features SELV Compliant No Detection Passive Injector Gigabit Compatible Full Protection
Secure your IT equipment with confidence... secure with NetClosure SERVER CABINETS NetClosure s REM Series Server Cabinet is the ultimate solution designed and engineered for demanding data center environments.
TrueAlarm Systems UL, ULC, CSFM Listed; FM Approved* Network Annunciators; es Features Provides a dedicated local area network (LAN) for connection of a TrueSite workstation server to remote clients: es
IT-SOLUTIONS Well conceived Haewa Group has gained a strong profile as an innovative and competent supplier for the machinery, systems, electrical and electronic industries, well beyond European geographic
Express5800/120Ed Rack Mount Kit Installation Procedures PN: 455-01607-001 Proprietary Notice and Liability Disclaimer The information disclosed in this document, including all designs and related materials,
19 Compact Rack 19 Server Compact Rack 1.76 to 1.90 1.75 Network and Server Compact Rack Strong points 1.78 19 Compact Rack 1.80 19 Server Compact Rack 1.81 19 Compact Rack Without Door 1.82 Accessories
Foxboro Evo Process Automation System Product Specifications PSS 31H-2Z32 FBM232 Field Device System Integrator Module, 10/100 Mbps Ethernet, Single The FBM232 Field Device System Integrator (FDSI) module
Issue 6 Data Centre Solutions RACKS POWER COOLING MONITORING SECURITY SERVICE & SUPPORT The simple route to the perfect data centre Data centres are complex systems. Software, hardware and IT infrastructure
1 Compaq 10000 Series Racks The 10000 series racks are a family of 1000mm deep racks which are available in 22U, 36U, 42U and 47U 600mm widths. Compaq 10000 Series Racks provides a common, integrated platform
CABINETS: ENCLOSED THERMAL MOUNTING MANAGEMENT SYSTEMS WHITE PAPER Supporting Cisco Switches In Hot Aisle/Cold Aisle Data Centers 800-834-4969 email@example.com www.chatsworth.com All products
Quick Installation Guide 24-port PoE switch with 2 copper Gigabit ports and 2 Gigabit SFP ports (af Version 15.4W) Table of Contents Introduction.. Power Over Ethernet (PoE) & Features.... Unpacking and
7250 700w soundproof wall box Superior sound attenuation wall boxes With cooling ability up to 1.5kW Product overview and technical data O v e r v i e w 7250-SP 700 wide sound proof wall box As many office
THE NEXT GENERATION RACK FOR INFORMATION TECHNOLOGY THE RACK CABINET FOR INFORMATION TECHNOLOGY T7, THE HI-TECH HEART OF THE BLADESHELTER SYSTEM The real answer to the requirements of: Safety Versatility
42U/45U 28" Wide Rack Installation & Service Guide 96-00171-005 Rev B Important Information Information in this document is subject to change without notice and does not represent a commitment on the part
Full_IG.book Page 1 Monday, January 9, 2012 6:11 PM ProSafe 24 Port Gigabit Switch Installation Guide Full_IG.book Page 2 Monday, January 9, 2012 6:11 PM 2011 NETGEAR, Inc. All rights reserved. No part
NEW DESIGN CABLE MANAGEMENT PANEL WALL RACK CABINET 15 U VENTILATING FAN AC SOCKET STRIP (AC Power Distribution) BLANK PANELS x U OPEN RACK THERMOSTAD PANEL SET CABLE MANAGEMENT PANEL WITH COVER BAYING
Overview HP Managed and Unmanaged Notebook Charging Carts Models HP 20-Notebook Charging Cart HP 30-Notebook Charging Cart HP 20-Notebook Managed Charging Cart HP 30-Notebook Managed Charging Cart QL488AA#ABA
HPE 10000 G2 Series Rack Options Installation Guide Abstract This document is for the person who installs racks and rack products. This procedure is performed only by trained personnel. Hewlett Packard
PS6500 Storage Arrays Rack Mount Instructions Part Number: R724M Rev. A01 Copyright 2010 Dell, Inc. All rights reserved. Dell is a trademark of Dell, Inc. EqualLogic is a registered trademark. All trademarks
HP 2530 8-Port Switches Quick Setup Guide The switch drawings in this document are for illustration only and may not match your particular switch model. For more detailed instructions and information to
Rackmount Shelves Wallmount Shelves Keyboard/Mouse Trays Product Data Sheet Rackmount Shelves, Wallmount Shelves, Keyboard/Mouse Trays Overview Black Box offers a variety of 1U, 2U, and 3U high shelves
Rittal The System. Faster Better Worldwide. Rittal TS8 Specification Guide TS8 Freestanding Industrial Enclosures and Accessories Why Choose Rittal? The Rittal TS8 is the premier modular enclosure available
33.6W Power over Ethernet Waterproof Adapter PoE Plus Single Port Injector for Outdoor Application Features Compliant with the IEEE802.3at Standard -40 to +60 C Temperature Range Diagnostic LEDs Full Protection
RT freestanding accessories acrylic doors (600/800 cabinets) Flush finish Concealed hinge Doors must be unlocked for removal Can be hinged from right to left Quick release hinge Acrylic doors allow users
Rack Systems Solutions Designed to simplify cable management and improve power distribution Engineered by APC by Schneider Electric for Dell, NetShelter S is the next-generation rack enclosure solution
Savant Systems AMP-825 is a multi-room amplifier for distributed audio applications. The AMP-825 is an ultraefficient Class D amplifier delivering 8 channels of reliable amplification rated at 25 watts
Pull-out wire storage basket Finish: Chrome plated Load capacity: 30 kg Installation depth: 400 mm Version: Runners and baskets separated, designed for wardrobe interiors without doors Type of pull out:
This set of instructions applies to racking and rail kit installation for 6XX and above. The Rack Mounting Instructions section below provides information on installing the SC825 chassis into a rack unit
How to Set Up Your NSM4000 Appliance Juniper Networks NSM4000 is an appliance version of Network and Security Manager (NSM), a software application that centralizes control and management of your Juniper
GOING GREEN WITH CUSTOMIZABLE CABINETS AND RACKS Designed to provide industry leading airflow, CyrusOne s cabinets and rack solutions promote optimal cooling and contribute to reduced power consumption.
Site Readiness Guide September 2015 Copyright This document is provided "as-is." Information and views expressed in this document, including URL and other Internet website references, may change without
#112 Best Practices for Deploying the InfraStruXure InRow SC By David Roden Abstract The InfraStruXure InRow SC (ACSC100 and ACSC101) is a self-contained air conditioner for server rooms and wiring closets.
Small form factor bay converter and hard drive installation HP xw6600 and HP xw8600 Workstations This document describes how to convert HP xw6600 and HP xw8600 Workstation 3.5-inch hard drive bays to hold
Distributing Power to Blade Servers Ten steps to selecting the optimal power distribution design With the growth in blade servers with dual or triple power supplies, a single rack of equipment can easily
Data Center Rack Systems Key to Business-Critical Continuity A White Paper from the Experts in Business-Critical Continuity TM Executive Summary At one time, data center rack enclosures and related equipment
RittalXpress Get the right rack. Right now. R Helping You Protect Your Business 2 RittalXpress IT Products and Accessories RittalXpress IT Products RimatriX5 Innovation Defined Rittal RimatriX5 An Innovative
Rack installation instructions Review the documentation that comes with the rack cabinet for safety and cabling information. Before you install the server in a rack cabinet, review the following guidelines:
SOHOline and SOHO Slimline The SOHOline and SOHO Slimline offer a modular, sturdy and compact design Ideal installation for; Offices Branch Offices Schools Computer Aided Classes Government Offices Hotels
1 Compaq Rack Options and Accessories Compaq offers a wide variety of rack options and accessories that help you to complete your 9000 and 10000 series racks. Monitors and Keyboards TFT5600RKM United States
Installation Smart-UPS VT MGE Galaxy 3500 Maintenance Bypass Panel 10-40 kva 400 V Contents Safety.................................................. 1 Save these instructions...................................
INSTALL INSTRUCTIONS KK-C-HVAC-1 HVAC UNIT 2003-2014 CHEVROLET/GMC VANS FOR (For NEW 2007 ALL WHITE KWIK-KITS ONLY) Warning do not attempt to install A/C units unless you are experienced with servicing
1 2 INTRODUCTION / TABLE OF CONTENTS Step One Offered in small and large sizes, the compact junction box is ideal for sensor wiring and conduit termination. The junction box is universally compatible with
Spec-00428 E763.422.2211 763.422.2600 PROLINE External Components PROLINE Tops and Bases PROLINE External Components PROLINE Tops and Bases Solid Tops Solid Tops are used to close the top opening on an
Server Chassis and Triplet Hardware v1.0 Author: Steve Furuta, Mechanical Designer 1 Scope This document describes the technical specifications for the custom chassis used in Open Compute Project servers
UB1 AIR CONDITIONING UNIT INSTALLATION INSTRUCTIONS INSTALLATION INSTRUCTIONS: Carefully read these instructions before installing your new air-conditioner. AUSTRALIAN AUTOMOTIVE AIR AL00500054E 1 Table
HP UPS R1500 Generation 3 Installation Instructions Part Number 650952-001 NOTE: The rating label on the device provides the class (A or B) of the equipment. Class B devices have a Federal Communications
Tyan Computer Transport PX22 Service Engineer s Manual 1 Precaution To read through the user manual, check all assembly and follow setup process before any operation on this server To keep paper clips,
Cisco Prisma II Platform In optical transmission systems, the network platform forms the foundation of the product family. The Cisco Prisma II platform provides network operators with the unique features
Page 1 of 12 Setting Up and Testing the MAX Hardware This chapter covers these topics: Planning the hardware installation Inserting an expansion card Setting up the hardware Connecting to input power Connecting
BF series 400 Incubators and cooling incubators Incubator with mechanical convection The BINDER incubator of the BF series with mechanical convection is suitable for all gentle incubation applications,
Connectors - up to 280 Amps 2 Pole Wires sizes from #12 (3.3 mm²) to 1/0 (50 mm²) fit in the second to largest connector in the SB series. The 3 pole adds an additional position for power or grounding.
6060 Spine Road Boulder, CO 80301 USA USA 1 800 255 6964 Europe 0161 864 6800 Worldwide 303 444 2009 Install NEMA 4X enclosure for the Sievers * InnovOx Online TOC Analyzer Introduction Purpose: To install
Placing network switches into rack enclosures can be convenient and can simplify network cabling. For any configuration, SwitchAir ensures your network switch is able to receive the required cool air from
CCTV Pole Cabinet The Cabinet assembly shall be listed by a National Recognized Testing Laboratory (NRTL) as defined by the U.S. Department of Labor. The testing laboratory must be listed by OSHA in its
Quick Start Guide Cisco Small Business Cisco Unmanaged Rackmount Switches Package Contents Cisco SF 100-16, SF 100-24, SF 102-24, SG 100-16, SG 100-24, or SG 102-24 Unmanaged Rackmount Switch Rackmount
Q. When should I use the Adjustable Quadra? A. Use the Adjustable Quadra with #12-24 threaded equipment mounting holes in network facilities to support patch panels, fiber enclosures and network switches.