1 Installation and maintenance instructions Indirect fired domestic hot water tank Logalux ST50/ ST300/ For heating contractors Please read carefully prior to installation and maintenance /006 US
2 Contents General information About these instructions Standards and guidelines Tools, materials and accessories Safety Correct use Layout of the instructions Please observe these instructions Disposal Product description Specifications Dimensions and connections Safety limits DHW tank handling DHW tank installation Positioning the DHW tank Installing the DHW piping Checking the magnesium anode connection Installing the DHW temperature sensor (Logamatic Control) Installing Aquastat Start-up and shutdown Filling the DHW tank Operating tips Shutdown tips Maintenance Preparing the DHW tank for cleaning Cleaning the DHW tank Checking the magnesium anode Replacing the magnesium anode Starting the DHW tank up again after cleaning Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice.
3 General information General information. About these instructions These installation and maintenance instructions contain important information for the safe and proper installation, initial start-up and maintenance of Logalux ST50/ ST300/ domestic hot water tanks. These installation and maintenance instructions are designed for specialists, who through their vocational training and experience are knowledgeable in handling heating systems and DHW installations. The Logalux ST50/ ST300/ domestic hot water tank is referred to as the "DHW tank" in this document. Inform the user about the operation of the DHW tank, placing particular emphasis on safety aspects. Hand the installation and maintenance instructions to the user and recommend that they are kept in the vicinity of the heating system for reference purposes.. Standards and guidelines Observe all applicable standards, codes and guidelines! In Massachusetts, this DHW tank must be installed by a licensed plumber!.3 Tools, materials and accessories For the installation and maintenance of the DHW tank, you need the standard tools used in DHW installation. The following may also prove useful: Hand truck with strap Wet/dry vacuum cleaner Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice. 3
4 Safety Safety Logalux ST50/ ST300/ DHW tanks have been developed and built employing the latest technologies and they meet all applicable safety regulations. Please observe the safety instructions and the Installation and maintenance instructions to ensure optimum safe, economical and environmentally-friendly use of your DHW tank.. Correct use.3 Please observe these instructions WARNING! RISK TO HEALTH Improper installation and maintenance work can contaminate the potable water. Install and clean the DHW tank hygienically and thoroughly and in accordance with current standards. Logalux ST50/ ST300/ DHW tanks are designed for heating and storing potable water. Potable water regulations apply. Only heat these DHW tanks with heating water in closed loop systems.. Layout of the instructions There are two different levels of danger, identified by the following terms: WARNING! RISK TO LIFE Identifies possible risks emanating from a product that might lead to serious injury or death if appropriate care is not taken. TANK DAMAGE due to unsatisfactory cleaning and maintenance. Carry out cleaning and maintenance at least every two years. Immediately remedy all faults to prevent system damage. Only use original Buderus spare parts. Losses caused by the use of parts not supplied by Buderus are excluded from the Buderus warranty. RISK OF INJURY/ SYSTEM DAMAGE Indicates a potentially dangerous situation that could lead to minor or moderately serious injuries or to damage to property. User tips for the optimum utilization and setting of the device, plus other useful information..4 Disposal Dispose of the DHW tank packaging in an environmentally responsible manner. Dispose of old DHW tanks in an environmentally responsible manner. 4 Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice.
5 Product description 3 3 Product description Logalux ST50/ 300/ DHW tanks are fully factory-assembled and ready for connection. The main components of the DHW tank are: Storage tank (Fig., Item 5) with corrosion protection The cathodic corrosion protection comprises DUO- CLEAN MKT thermo-glazing from Buderus and a magnesium anode rod mounted on the access port (Fig., Item 3). Casing The removable parts of the casing are the casing lid (Fig., Item ) and the cable channel (Fig., Item 7). Insulation (Fig., Item 4) The insulation made from CFC-free hard polyurethane foam is directly applied to the DHW tank. A foam insulating element (Fig., Item ) minimizes heat loss through the access port cover. Access port cover with magnesium anode rod (Fig., Item 3) The access port cover provides access for maintenance and cleaning purposes Sensor well for installation of the DHW temperature sensor (Fig., page 6, M) The boiler's DHW thermostat regulates the set DHW temperature using this DHW temperature sensor (called the tank sensor). Heat exchanger coil Heat exchanger coil (Fig., page 6) transfers the energy from the heating water to the DHW inside the tank. The tank content is evenly heated throughout. Fig. Logalux ST50/ ST300/ DHW tank Item : Casing lid Item : Insulation element Item 3: Access port with magnesium anode rod Item 4: Insulation Item 5: DHW tank Item 6: Adjustable feet Item 7: Cable channel Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice. 5
6 4 Specifications 4 Specifications 4. Dimensions and connections Ø 7¼ RS Fig. Dimensions and connections (dim. in inches) Item : Magnesium anode rod Item : Heat exchanger coil M: DHW sensor well (DHW temperature sensor) EZ: DHW recirculation inlet AW: Domestic hot water outlet EK: Cold water inlet VS: DHW tank supply EL: Drain RS: DHW tank return Type ST50/ 40 Capacity Height (H) Weight AW VS/RS EK/EL EZ Gal. in. Lbs. 34¾" 45 ST00/ 53 NPT " NPT " NPT ¼" NPT ¾" 4¼" 86 ST300/ 79 57¾" 37 Tab. Dimensions and connections Dry weight (empty tank, excluding packaging). 4. Safety limits TANK DAMAGE by exceeding limits. For reasons of safety, do not exceed the listed limits. Approved maximum values Temperature Operating pressure On-site test pressure C ( F) bar (psi) bar (psi) Boiler water 00 () 6 (3) N/A DHW 95 (03) 0 (45 3 ) 0 (45 3 ) Tab. DHW tank safety limits Depending on the connection to the heating system, a separate safety device may be required (relief valve, diaphragm expansion vessel). Operating pressure and test pressure are overpressure. 3 Maximum 00 psi in Massachussetts. 6 Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice.
7 DHW tank handling 5 5 DHW tank handling RISK OF INJURY from carrying heavy loads. The transported item should always be lifted and carried by at least two people. RISK OF INJURY by not securing the tank adequately during transport. Use only suitable means for transportation, e.g. a hand truck with strap. Secure the load against falling. Where possible, transport the DHW tank fully packed to the installation room. This ensures protection during handling. You can order hand trucks from one of our dealers. Moving the DHW tank on its pallet Position the hand truck (Fig. 3, Item. ) at the back of the packed DHW tank (Fig. 3, Item. ). Secure the DHW tank to the truck using a strap. Move the DHW tank to its installation location. Remove the wrapping plastic, wooden boards and the polystyrene lid protectors. Fig. 3 Moving DHW tank with hand truck (general layout) Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice. 7
8 6 DHW tank installation 6 DHW tank installation 6. Positioning the DHW tank The DHW tank is designed for vertical installation and can be installed beside the boiler. The clearances shown in Figure 4 are strongly recommended for cleaning purposes. The floor has to be level and able to support a full tank. TANK DAMAGE from frost. The boiler room needs to be dry and protected from freezing. TANK DAMAGE from corrosion. Use the tank in closed loop systems only. Fig. 4 Positioning the DHW tank (general layout) Do not use open expansion vessels. Ensure adequate clearance above the DHW tank for the replacement of the magnesium anode (maintenance). Ensure that the boiler room has a minimum height in accordance with Table, page 6. Fitting adjustable feet Place the lid protector (Fig. 5, Item ) on the floor. Carefully lay the DHW tank down flat onto the lid protector. Screw in the three adjustable feet supplied (Fig. 5, Item ) up to ¾" ". Return the DHW tank to its upright position and level horizontally by turning the adjustable feet as appropriate until tank is plumb. Fig. 5 Leveling the DHW tank vertically Item : Lid protector Item : Adjustable foot 8 Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice.
9 DHW tank installation 6 6. Installing the DHW piping Please observe the following instructions for connecting the DHW tank to the piping. These instructions are important for fault-free operation. RISK TO HEALTH WARNING! Improper installation work can contaminate potable water. Install the DHW tank hygienically in accordance with current standards and codes. Rinse the DHW tank and piping thoroughly with potable water. SYSTEM DAMAGE due to incorrect installation. Observe all local, state and national codes, standards and guidelines applicable to the installation and operation of this DHW tank. If the capacity of the boiler exceeds 00,000 Btu/hr, the safety mechanisms on the DHW tank need to be adjusted accordingly. SYSTEM DAMAGE from leaking connections. Connect all connection pipes free from stress. Fig. 6 Installation diagram (general layout) Item : DHW tank Item : Shutoff valve Item 3: Pressure relief valve Item 4: Check valve Item 5: DHW tank pump Item 6: DHW recirculation pump (optional) Item 7: Air eliminator Item 8: Drain valve Item 9: Non-return valve Item 0: Diaphragm expansion vessel (MAG-W) AW: Domestic hot water outlet EZ: DHW recirculation inlet VS DHW tank supply RS DHW tank return EK/EL: Cold water inlet/drain M: Test port Attach the included brass tees to the AW and EK/EL connections. Install the included relief valve on the NPT ¾" connection of the brass tee on the AW connection. Install the included drain valve on the NPT¾" connection of the brass tee on the EK/EL connection. If a Logamatic control is being used, see installation instructions in section 6.4, page 0. If a Honeywell Aquastat is being used for DHW control, see installation instructions in section 6.5, page. Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice. 9
10 6 DHW tank installation 6.3 Checking the magnesium anode connection Check that the ground wire (Fig. 7, Item ) of the magnesium anode (Fig. 7, Item ) is connected properly. Fig. 7 Checking the magnesium anode connection Item : Magnesium anode Item : Ground wire 6.4 Installing the DHW temperature sensor (Logamatic Control) If a Buderus Logamatic control or Goldline SP34D control is being used, install the DHW temperature sensor supplied in the tank connection set (accessory) as follows: Insert the sensor pack (Fig. 8, Item to 4) until it bottoms out inside the sensor well (Fig. 8, Item 5). During insertion, the plastic spiral (Fig. 8, Item 3) holding the sensor pack together slides back automatically. The compensating spring (Fig. 8, Item 4) ensures contact between the sensor well and the sensor surfaces, thereby ensuring a reliable temperature measurement Fig. 8 Installing the DHW temperature sensor Item : Spacer Item : Temperature sensor Item 3: Plastic spiral Item 4: Compensating spring Item 5: Sensor well 0 Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice.
11 DHW tank installation 6 Push the sensor holder clip (Fig. 9, Item ) onto the sensor well (Fig. 9, Item ) from the side. Route the sensor lead to the boiler or control panel (Logamatic control), ensuring the lead is not strained. Ensure this lead cannot come in contact with any hot boiler parts. See the wiring diagram supplied for the electrical connection of the temperature sensor. Fig. 9 Installing the sensor holder clip Item : Sensor holder clip Item : Sensor well 6.5 Installing Aquastat Remove cover from Aquastat (Fig. 0, Item ). To do so, undo the hex screw on the top. Screw on the holder (Fig. 0, Item 6) onto the Aquastat with self tapping screws (if there is already a holder or bracket in place, remove it). Insert temperature sensor and spring (Fig. 0, Item 4 and 5) into the sensor well (M) (Fig. 0, Item 3). Screw the Aquastat (Fig. 0, Item ) onto the DHW tank using self tapping screws (Fig. 0, Item ). Predrill two holes next to the M connection in the casing with a diameter to match the self tapping screws. RISK TO LIFE 3 WARNING! from electric shock. Before working on the electrical system: disconnect all power to the system by shutting off the emergency shutoff switch, or disengaging the heating system circuit breaker. Fig. 0 Installing Aquastat Item : Self tapping screws /8" /" Item : Aquastat Item 3: Sensor well (M connection) Connect the electrical power and set the temperature as shown in the manual supplied with the Aquastat. Item 4: Temperature sensor Item 5: Spring Item 6: Holder Replace the cover of the Aquastat. Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice.
12 7 Start-up and shutdown 7 Start-up and shutdown 7. Filling the DHW tank Before putting the DHW tank into operation, check for leaks. Carry out the leak test with potable water only. The on-site test pressure on the secondary side must not exceed 0 bar (45 psi). Vent the DHW tank by opening the vent/bleed valve (Fig., Item ) or the highest faucet of the house. Open the supply valve (Fig., Item ) to fill the DHW tank. Before heating up, check that the boiler, DHW tank and piping are completely filled with water. To bleed the air, open the vent/bleed valve (Fig., Item ). Check all connections, piping and the access port for leaks. Fig. Installation diagram (general layout) Item : Shutoff valve for cold water inlet Item : Blow-off line of the relief valve AW: EZ: EK: M Domestic hot water outlet DHW recirculation inlet Cold water inlet Sensor well Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice.
13 Start-up and shutdown 7 7. Operating tips 7.3 Shutdown tips TANK DAMAGE The DHW tank can be permanently damaged by excessive pressure if the relief valve is malfunctioning or blocked. Always keep the blow-off line of the relief valve (Fig., page ) open. Inform the user that the relief valve blow-off line (Fig., page ) always needs to be kept clear. the proper functioning of the relief valve should be checked annually by manually opening it. the local heating contractor should be notified if the thermal safety cut-out on the boiler is triggered frequently. TANK DAMAGE If the DHW tank ever has to remain empty for several days, residual moisture can cause corrosion damage. Thoroughly dry the inside of the DHW tank (e.g. with hot air) and keep the access port cover open. In the case of long periods away from home (e.g. vacation) we recommend the following: Keep the DHW tank in operation. Activate the vacation function on the control panel or select the lowest possible DHW temperature. If you ever need to shut down the DHW tank, observe the hygiene requirements for DHW systems (regarding flushing of piping) applicable in your state or jurisdiction. For operating information (e.g. how to set the DHW temperature), see the operating instructions for the control panel. Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice. 3
14 8 Maintenance 8 Maintenance Buderus recommends checking and cleaning the DHW tank by an expert contractor at least every two years. Please inform the user accordingly. Shorter cleaning intervals should be chosen under unfavorable operating conditions, such as hard water and/or high operating temperatures. TANK DAMAGE due to insufficient cleaning and maintenance. Carry out cleaning and maintenance at least every two years. Immediately remedy all faults to prevent possible damage. 8. Preparing the DHW tank for cleaning Disconnect all electrical power to your heating system. Empty the DHW tank by closing the fresh water supply valve and opening the drain valve. To vent the system, open the vent/bleed valve or the highest faucet. Remove the casing lid (Fig., Item ). To do so, remove the four screws on the side. Remove the thermal insulating element (Fig., Item ) on top of the access port cover. Fig. Removing the casing lid Item : Casing lid Item : Insulation element 4 Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice.
15 Maintenance 8 Remove the hex screws (Fig. 3, Item ) from the access port cover (Fig. 3, Item 3). Remove the access port cover, transport handle (Fig. 3, Item ) and access port cover gasket (Fig. 3, Item 4) from the DHW tank. 8. Cleaning the DHW tank Check the DHW tank interior for scale deposits. SYSTEM DAMAGE from damaged surface finish. Never use hard objects or objects with sharp edges to clean the interior walls of the DHW tank. Fig. 3 Removing the access port cover Item : Hex screws Item : Transport handle Item 3: Access port cover Item 4: Access port cover gasket Item 5: Magnesium anode rod If there are scale deposits inside the DHW tank, proceed as follows: Hose down the interior of the DHW tank with a cold water jet (approx psi pressure) (Fig. 4). You can increase the cleaning effect of the jet by heating up the DHW tank before cleaning. The thermo-shock effect releases scale deposits more easily from the heat exchanger coil. Remove the residues with a wet & dry vacuum cleaner with plastic suction tube. Fig. 4 Hosing down the inside of the DHW tank Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice. 5
16 8 Maintenance 8.3 Checking the magnesium anode The magnesium anode is a sacrificial anode, which is consumed during the operation of the DHW tank. The magnesium anode should be checked annually. The tank warranty is rendered void if the anode rod is not properly maintained Visual inspection of the anode rod Check magnesium anode rod (Fig. 5, Item ) for decay. Replace the magnesium anode rod if its diameter has been reduced to about /" to 3/4" Never bring the magnesium anode surface into contact with oil or grease. Keep everything clean Checking the anode rod without emptying the tank Conduct the measurement as follows: Measure the protective current only when the tank is filled with water. Values between 0.3 ma and 30 ma are good. Disconnect the anode ground wire (Fig. 5, Item 5) at one of the two connection points. Set the multimeter (MM)(Fig. 5, Item ) to ma DC (milliamps). Connect the black cable (Fig. 5, Item 7) on the MM to a hex screw (Fig. 5, Item 8) on the access port cover. Connect the red cable (Fig. 5, Item 6) on the MM to the anode. Connect terminals to shiny metal surfaces only. Enter the values measured and your signature in the table below (Tab. 3). Fig. 5 Checking anode with multimeter Item : Digital multimeter Item : Magnesium anode Item 3: Access port cover Item 4: M8 thread Item 5: Ground wire Item 6: Red multimeter cable Item 7: Black multimeter cable Item 8: Hex screw Date Measured value [ma] Contractor company/signature Tab. 3 Values measured in anode testing After every test, reconnect the ground wire to its proper connection point. 6 Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice.
17 Maintenance Replacing the magnesium anode Remove M8 nut (Fig. 6, Item 0) to release the ground wire eyelet (Fig. 6, Item 8). Remove M8 nut (Fig. 6, Item 7). Remove the access port cover (Fig. 6, Item 3) from the magnesium anode (Fig. 6, Item ). Replace the magnesium anode. Fit the new magnesium anode together with all small parts supplied with it, as shown in Fig NOTICE: An improperly installed anode rod may not protect the tank. 3 Fig. 6 Replacing the magnesium anode Item : Magnesium anode Item : Gasket Item 3: Access port cover Item 4: Insulating sleeve Item 5: Washer Item 6: Lock washer Item 7: M8 nut Item 8: Ground wire eyelet Item 9: Lock washer Item 0: M8 nut Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice. 7
18 8 Maintenance 8.5 Starting the DHW tank up again after cleaning SYSTEM DAMAGE from faulty gaskets. After cleaning, we recommend you use a new access port cover gasket (Fig. 7, Item 4) to prevent the DHW tank from leaking. Put the access port cover (Fig. 7, Item 3) back in place with gasket (Fig. 7, Item 4). Screw the hex screws (Fig. 7, Item ) hand tight on the access port cover, screwing on the transport handle (Fig. 7, Item ) at the same time. Then use a torque wrench to tighten the hex screws (Fig. 7, Item ) to 8- ft lbs. Fill the DHW tank and restart the heating system. Check all connections and the access port cover for leaks. Insert the insulating element (Fig. 8, Item ) on top of the access cover. Place casing lid (Fig. 8, Item ) onto the DHW tank and screw it down with four screws on the sides. 3 4 Fig. 7 Installing access port cover Item : Hex screws Item : Transport handle Item 3: Access port cover Item 4: Access port cover gasket Item 5: Anode rod 5 Fig. 8 Fitting the casing Item : Casing lid Item : Insulation element 8 Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice.
19 Notes Logalux ST50/ ST300/ DHW tank - Technical specifications are subject to change without prior notice. 9
20 BBT North America Corporation 50 Wentworth Avenue Londonderry, NH Tel Fax Products manufactured by BBT Thermotechnik GmbH D Wetzlar BBT North America Corporation reserves the right to make changes without notice due to continuing engineering and technological advances.
BUILT-IN DISHWASHER INSTALLATION INSTRUCTIONS PLEASE READ COMPLETE INSTRUCTIONS BEFORE YOU BEGIN LEAVE INSTALLATION INSTRUCTIONS AND USER'S GUIDE WITH OWNER ALL ELECTRIC WIRING AND PLUMBING MUST BE DONE
Indirect-Fired Storage Water Heater Models WH-30 through WH-80 INSTALLATION AND OPERATING INSTRUCTIONS Contents Page Ratings and Specifications..................... 2 Installation Requirements......................
Electric Water Heater OWNER S MANUAL FORCE 10 MARINE COMPANY 23080 HAMILTON ROAD RICHMOND, BC CANADA V6V 1C9 TEL: (604) 522-0233 FAX: (604) 522-9608 If your water Heater is Damaged or you have questions
INSTALLATION INSTRUCTIONS & HOME OWNERS MANUAL EEMAX ELECTRIC TANKLESS WATER HEATERS IMPORTANT SAFETY INFORMATION When installing or using any high voltage electrical appliance, basic safety precautions
Model Number: Serial Number: Information Manual Installation and Troubleshooting Instructions for Electric Tankless Residential Water Heaters. ATTENTION: IF YOU ARE NOT A LICENSED PLUMBER OR A LICENSED
Speedflow Undersink Unvented Water Heater Models SF10K and SF15K Instruction Manual Version 2.0 May 2009 Hyco SpeedFLOW UnVENTED WATER HEATER Models SF10K (10 Litres) and SF15K (15 Litres) 1. Introduction
NATURAL GAS TO PROPANE CONVERSION KIT 090 INSTALLATION INSTRUCTIONS FOR ALTITUDES 0 -,00 FT. ONLY PROPANE CONVERSION KIT SAFETY... INSTALLATION REQUIREMENTS... Tools and Parts... LP Gas Requirements...
Installation Instructions Built-In Dishwasher If you have questions, call 1-800-4-MY-HOME (1-800-469-4663) or visit our website at: www.sears.com BEFORE YOU BEGIN Read these instructions completely and
SunMaxx Solar Filling Operating Instructions Content 1. Declaration of conformity... 2 2. Introduction... 2 3. Transportation and unpacking... 4 4. Mounting and commissioning... 5 5. End of operation...
STATFlow Direct-to-Drain System For use with STATIM 2000 and STATIM 5000 Autoclaves Installation Guide and Operator s Manual STATFlow Installation Guide and Operator s Manual 95-113193 Rev 2.0. Copyright
Installation and User Instructions Unvented Electric Storage Water Heater Models: S10UNV, S15UNV. MULTIPOINT Please read and understand these instructions before starting work. Please leave this leaflet
Page 1 of 34 19-1 Cooling system components, removing and installing WARNING! The cooling system is pressurized when the engine is warm. When opening the expansion tank, wear gloves and other appropriate
SYMPHONY Spread Lavatory Faucet with Speed Connect Drain Congratulations on purchasing your American Standard faucet with Speed Connect drain, a feature found only on American Standard faucets. Speed Connect
Operator: Save these instructions for future use! FAILURE TO READ AND FOLLOW ALL INSTRUCTIONS CAREFULLY BEFORE INSTALLING OR OPERATING THIS CONTROL COULD CAUSE PERSONAL INJURY AND/OR PROPERTY DAMAGE. DESCRIPTION
I N S T A L L A T I O N I N S T R U C T I O N S F O R T H E H i l k o i l Energy S aving Hot Water Kit IMPORTANT: These installation instructions are meant to be used as a guide for woodstove owners and
VITOCELL-V 00 Indirect-fired domestic hot water storage tank 4 to 0 / 60 to Technical Data Manual Model Nos. and pricing: see Price List Vitocell-V 00 4 to / 60 to Vitocell-V 00 0 / Vitocell-V 00 CVA Series
6302 6959 02/2006 GB For the user Operating instructions Logano G215 WS Oil and gas-fired boilers Please read thoroughly before use. Overview Regulations and directives Installation: 90/396/EEC gas appliance
NITROUS TRANSFER PUMP INSTRUCTIONS SAFETY TIPS Never directly inhale nitrous oxide. When inhaled in large quantities, nitrous oxide can cause respiratory ailments or in extreme cases, death by suffocation.
Hoffman Specialty Installation & Maintenance Instructions HS-(E) and Thermostatic Traps Series H, C and X Series C & NPT Series C NPT Series X NPT Series C NPT Series H Ratings Maximum Max. Operating NPT
SMD Rework Station Thank you for purchasing the Hakko 50B SMD Rework Station. The Hakko 50B is designed to solder and desolder surface mounted devices with hot air. Please read this manual before operating
CDS TROUBLESHOOTING SECTION I. VACUUM 1.0. Weak vacuum at wand. Gauge reads normal (10hg to 14hg) 1.1. Clogged hoses or wand tube. Disconnect hoses and carefully check for an obstruction. 1.2. Excessive
Product Instruction Manual Speedflow SF05K, SF10K & SF15K SF05KSS, SF10KSS & SF15KSS Undersink unvented water heater V15.6/6 Version 3.2 Jan 2015 Thank you for purchasing a Hyco Speedflow unvented water
CAST IRON THE BASICS 1. DO NOT LIFT ON YOUR OWN. 2. ONLY LIFT THE RADIATOR VERTICALLY. 3. DO NOT LIFT MORE THAN 8/10 SECTIONS AT ANY ONE TIME. 4. POSITION THE RADIATOR BEFORE FINAL ASSEMBLY. 5. THIS PRODUCT
Engine BHW Cooling system components, removing and installing Page 1 / 24 19-1 Cooling system components, removing and installing Warning! When doing any repair work, especially in the engine compartment,
Mini Tank water heater Electric undersink Water heaters GL 2.5 - GL 4 - GL 6+ IMPORTANT SAFETY INSTRUCTIONS WARNING When using electrical appliances, safety precautions to reduce the risk of fire, electric
Back Pack Sprayer Operator's Manual MODELS MS - 40 MS - 50 WARNING DANGER Read rules for safe operation and all instructions carefully. ECHO provides this Operator's Manual which must be read and understood
ITE Indirect calorifier ITE - 400/500/600/750/1000 0310 117 Installation, User and Service Manual Innovation has a name. Read this manual carefully Warning Read this manual carefully before starting the
Operators manual Basic water heater Isotemp Basic water heater has been designed and produced to ensure that your water heater will give long and trouble free operation for many years. It is important,
Overview READ ENTIRE INSTRUCTIONS BEFORE STARTING INSTALLATION PARTS LIST A. Flush valve B. Lever mounting base C. Flush handle assembly D. Grey/Blue float stop E. Grey float (Full Flush) F. Flush valve
Non-Metallic Electric Water Heater USE & CARE MANUAL WITH INSTALLATION INSTRUCTIONS FOR THE INSTALLER Residential Electric Models 30-05 Gallon Capacity TM The purpose of this manual is twofold: one, for
Watts Pure Water Systems WM-120-PT Installation and Operation Manual Premier Water Systems Do not use with water that is microbiologically unsafe or of unknown quality without adequate disinfection before
CHRONOMITE INSTANT-FLOW MICRO WATER HEATER INSTALLATION AND OPERATION INSTRUCTIONS - (LOW FLOW MODELS) (Before installation, compare electrical needed for the model of heater selected) TABLE 1 Model No.
F M -W RayClic Connection System Installation Instructions RayClic WARNING: Shock Hazard 718K Pipe Heating Cable with HWAT, IceStop, also Listed De-icing and and XL-Trace heating Snow Melting Equipment
Art.S001-S002 SOLAR MODULE WITH DELIVERY AND RETURN CONNECTIONS Technical Information sheet 0001/07/Rev01 ENG FUNCTION Series S001 and S002 circulation units are applied to the primary circuit of solar
Fan Coil Replacement Coil Kit EBX & EBXX These instructions must be read and understood completely before attempting installation. These instructions covers the installation of replacement coil kit into
SHC 2.5, SHC 4 MINI-TANK ELECTRIC WATER HEATERS INSTALLATION INSTRUCTIONS FOR THE LICENSED PLUMBER The SHC series is tested and certified by WQA against NSF/ANSI 372 for lead free compliance. SHC 2.5 Table
Replacement parts DO NOT SERVICE THE BOILER WITHOUT A WM97+ MAINTENANCE KIT AVAILABLE Failure to adhere to these guidelines can result in severe personal injury, death or substantial property damage. The
Air Conditioner Water Heater Model ACWH18 Installation Guide IMPORTANT! READ THIS FIRST! Commissioning of this unit must be done by a licensed HVAC technician. Commissioning includes making the electrical
Product Manual CVS Type 67AFR Filter Regulator Introduction This CVS Controls product manual includes instructions for the installation, adjustment, maintenance and parts ordering of the CVS Type 67AFR
To the Installer: Please attach these instructions next to the water heater. To the Consumer: Please read these and all component instructions and keep for future reference. Techtanium Solar Indirect Water
ATS Overhead Table Shelf System INSTRUCTION MANUAL ATS Overhead Table Shelf System Instruction Manual Warranty Newport Corporation warrants this product to be free of defects in material and workmanship
Use & Care Manual With Installation Instructions for the Installer Electric Tankless Water Heaters The purpose of this manual is twofold: one, to provide the installer with the basic directions and recommendations
Oil and Coolant Circulating Heating System Model - OCSM Installation & Operation Manual 216280-000 REV 2 Identifying Your System The HOTSTART heating system is designed to heat fluids for use in marine
Installation Manual DIAPHRAGM WELL TANK IN-LINE SERIES: 2-5 & 7 GALLON VERTICAL SERIES: 14-20-25-32-36-52-65-86-96-119 GALLON HORIZONTAL SERIES: 7-14 & 20 GALLON NO LEAD NO LEAD: The weighted average of
OTF Oil Fired Pool Heater Installation Operation Maintenance Manual Service Policy 722010 Congratulations on the purchase of your new pool heater. In order to maintain peak performance of your pool heater
123 Industrial Loop Road Paynesville, MN 56362 Phone: 1-800-864-1649 www.master-mfg.com MASTER MANUFACTURING MASTER GARDNER Part Number PCD E3 009B MM Rev 1 Nov. 2010 INTRODUCTION The purpose of this manual
Remote Faucet Pump System USE &CARE GUIDE See Important Safeguards on page 2 An exclamation point within an equilateral triangle is intended to alert user to the presence of important operating and maintenance
R O A D M A S T E R, I N C. ROADMASTER, Inc. 6110 NE 127th Ave. Vancouver, WA 98682 6 13 11 MOUNTING BRACKET KIT Cable Tab 14 12 7 15 9 Cable Tab 360-896-0407 fax 360-735-9300 www.roadmasterinc.com ITEM
6302 2766 03/2003 US For installers Boiler Installation and Maintenance Manual Condensing Gas Boiler SB615 Series Please read these instructions carefully! Impressum This equipment conforms to the following
STABITHERM INSTALLATION & SERVICE BOOKLET TABLE OF CONTENTS Introduction...3 Warranty...3 Product Range and Physical Description...4 Method of Operation...5 Recommended Pressures and Temperatures...6 Flow
Installer / Service Provider details USER MANUAL INSTALLATION INSTRUCTION WARRANTY REGISTER Free Hot Water Solar Storage Tank (SST) with Single/Double coil heat exchanger Customer / User Congratulations
Seaward Products WATER HEATERS OWNER S MANUAL Serial Number: IMPORTANT SAFETY INSTRUCTIONS WARNING When using electrical appliances, basic safety precautions to reduce the risk of fire, electrical shock,
INSTALLATION INSTRUCTIONS & HOME OWNERS MANUAL ECO 18 ECO 24 ECO 27 IMPORTANT SAFETY INFORMATION As when installing or using any high voltage electrical appliance, basic safety precautions should always
INSTR3010 0406 Installation and Operating Instructions Installation Instructions for SS EPE-316L Series Congratulations on your purchase of this Aqua-Pure high flow, single housing filtration system. This
Part No. 130009 Iss. 12 August 2004 Elson www.elsonhotwater.co.uk Open Vented Thermal Store providing mains pressure hot water heated by electricity Installation, Servicing and User's Instructions Read
OPERATING AND MAINTENANCE MANUAL FOR COMMERCIAL ELECTRIC WATER HEATER ELECTRIC HEATER COMPANY BASE MODEL SE HUBBELL ELECTRIC HEATER COMPANY P.O. BOX 288 STRATFORD, CT 06615 PHONE: (203) 378-2659 FAX: (203)
-J05 REV. 0-0-0 XL PREMIUM OIL COOLER KIT GENERAL Kit Number 0008 Models For model fitment information, see the P&A Retail Catalog or the Parts and Accessories section of www.harley-davidson.com (English
One Year Warranty ELECTRIC Stock U.S. # of Volts Weight CONN. Height Dia. Watts # GAL. Elements INS. Inches Fused Ceramic Shield tank lining is corrosion-resistant for years of dependability. Adjustable
Fleck 4650 Service Manual TABLE OF CONTENTS JOB SPECIFICATION SHEET...1 INSTALLATION AND START-UP PROCEDURE...1 CONTROL VALVE DRIVE ASSEMBLY...2 CONTROL DRIVE ASSEMBLY FOR CLOCK...3 BYPASS VALVE ASSEMBLY...4
CHRONOMITE INSTANT-FLOW WATER HEATER INSTALLATION AND OPERATION INSTRUCTIONS - (LOW FLOW MODELS) (Before installation, compare electrical needed for the model of heater selected) TABLE 1 Model No. Wattage
Always place the pump as close to the liquid to be pumped as possible. Keep the suction line short and with few bends. Keep the pump and engine on a level foundation. A poor foundation and a heavy suction
Installation Operation Maintenance Troubleshooting Version 2.1, Apr/09 1607 DAYTONA Congratulations! All of us at Summit Dental Systems want you to know that your 1607 Daytona Cuspidor has been built with
Electric Mini Tank Water heaters GL 2.5 - GL 4 - GL 6+ IMPORTANT SAFETY INSTRUCTIONS WARNING When using electrical appliances, safety precautions to reduce the risk of fire, electric shock or injury to
DAZZLE Installation Instructions 08.80 Spread Lavatory Faucet with Speed Connect Drain* Congratulations on purchasing your American Standard faucet with Speed Connect drain, a feature found only on American
owners manual with installation instructions dynafact boost GAUGE this manual is for use with systems 64050-64054 GENERAL INSTALLATION PRACTICES This manual is an installation guide for all 1. Banks DynaFact
SHOWER WATER HEATER MODEL BS 35 / 45 / 60 BS 35 E / 45 E / 60 E OPERATION AND INSTALLATION INSTRUCTIONS 2 This water heater must be installed (water and electrical installation), commissioned and serviced
Utility Distribution Systems 6/2012 A0011037 1 WARRANTY This equipment is warranted to be free from defects in materials and workmanship, under normal use and service, for a period of 12 months from date
Assembly and instructions Franke Minerva 3-in-1 Kettle Tap Retain for reference NB: For use only with Franke Heating Tank INTRODUCTION The Kettle Tap is suitable for dispensing boiling water (100 C) and
Multi-Pure Whole House Water Treatment System Installation, Operation and Maintenance Manual Multi-Pure Model TO15000 Warning Please read manual carefully before proceeding with installation. It is recommended
INSTALLATION INSTRUCTIONS BL-8704 EXPOSED BLACK LEVER THERMOSTATIC MIXING VALVE WITH RISER KIT, HANDSET, LEVER DIVERTER, 8 ROSE AND ADJUSTABLE RISER PIPE BRACKET. Dimensions in Inches (& Millimetres) 1
Portable Air Conditioner Owner's Manual Model:3 in 1 12,000 Btu/h Series 3 Please read this owner s manual carefully before operation and retain it for future reference. CONTENTS 1. SUMMARY...1 2. PORTABLE
123 Industrial Loop Road Paynesville, MN 56362 Phone: 1-800-864-1649 www.master-mfg.com INTRODUCTION The purpose of this manual is to assist you in the assembly, operation and maintenance of your sprayer
SureSite Magnetic Liquid Level Indicator Instruction Bulletin No. 177664-1 (Rev. E) Section 1: Weldments Thank you for purchasing the GEMS SureSite Magnetic Level Indicator. Please read this document prior
Instruction Sheet P/N 160780 01 Stainless Steel Single and Dual Circulation Kits Introduction The single and dual high-pressure circulation kits allow you to vary and control the circulation rate of coating
Features Heavy Duty Construction Hydrastone cement lining provides longer tank life Copper-silicon tappings cannot rust or corrode High impact composite jacket eliminates damage during installation and
SECTION 15459 PART 1 - GENERAL 1.1 RELATED DOCUMENTS: A. Drawings and general provisions of Contract, including General and Supplementary Conditions and Division-1 Specification sections, apply to work
Technical Service Bulletin: Triac Printed Circuit Board Replacement TRONIC 5000C Pro Models: WH17, WH27, WH36 Introduction Fig. 1 ELECTRICITY IS EXTREMELY DANGEROUS. TAKE EXTRA PRECAUTIONS AND ENSURE ALL
INSTRUCTION MANUAL A-00-091-376 REVISION A Series E1 and E3 Instant Hot Water Recirculating Systems HOT WATER HEATER HOT WATER HEATER BS Models A. Return into Cold Water Line at Top of Water Heater fig.
2010 Residential Water Heater Replacement Check List The intent of this check list is to provide installers a general reference for the enforcement of code requirements in the Greater San Diego Area. This