1 OP--900 Communications Master Manual Number OP M
2 WARNING Thank you for purchasing automation equipment from PLCDirect. We want your new DirectLOGIC automation equipment to operate safely. Anyone who installs or uses this equipment should read this publication (and anyother relevant publications) before installing or operating the equipment. To minimize the risk of potential safety problems, you should follow all applicable local and national codes that regulate the installation and operation of your equipment. These codes vary from area to area and usually change with time. It is your responsibility to determine which codes should be followed, and to verify that the equipment, installation, and operation is in compliance with the latest revision of these codes. At a minimum, you should follow all applicable sections of the National Fire Code, National Electrical Code, and the codes of the National Electrical Manufacturer s Association (NEMA). There may be local regulatory or government offices that can also help determine which codes and standards are necessary for safe installation and operation. Equipment damage or serious injury to personnel can result from the failure to follow all applicable codes and standards. We do not guarantee the products described in this publication are suitable for your particular application, nor do we assume any responsibility for your product design, installation, or operation. If you have any questions concerning the installation or operation of this equipment, or if you need additional information, please call us at This publication is based on information that was available at the time it was printed. At PLCDirect we constantly strive to improve our products and services, so we reserve the right to make changes to the products and/or publications at any time without notice and without any obligation. This publication may also discuss features that may not be available in certain revisions of the product. Trademarks This publication may contain references to products produced and/or offered by other companies. The product and company names may be trademarked and are the sole property of their respective owners. PLCDirect disclaims any proprietary interest in the marks and names of others. Stage is a trademark of Koyo Electronics Industries Co., LTD. Think & Do Software is a trademark of Think & Do Software, Inc. Texas Instruments is a registered trademark of Texas Instruments, Inc. TI, TIWAY, Series 305, Series 405, TI305, and TI405 are trademarks of Texas Instruments, Inc. Siemens and SIMATIC are registered trademarks of Siemens, AG. GE is a registered trademark of General Electric Corporation. Series One is a registered trademark of GE Fanuc Automation North America, Inc. MODBUS is a registered trademark of Gould, Inc. IBM is a registered trademark of International Business Machines. MS-DOS and Microsoft are registered trademarks of Microsoft Corporation. Windows and Windows NT are trademarks of Microsoft Corporation. OPTOMUX and PAMUX are trademarks of OPTO. Copyright 998, PLCDirect Incorporated All Rights Reserved No part of this manual shall be copied, reproduced, or transmitted in any way without the prior, written consent of PLCDirect Incorporated. PLCDirect retains the exclusive rights to all information included in this document.
3 Manual Revisions If you contact us in reference to this manual, remember to include the revision number. Title: OP-900 Communications Master Manual Number: OP M Issue Date Effective Pages Description of Changes Original /96 Cover/Copyright Contents Manual Revisions 3 Index Original Issue Rev A 6/98 Downsize format Made minor corrections before reprinting
4 EU Information This product is manufactured in compliance with European Union (EU) Directives and carries the CE mark. The following information is provided to comply with EU documentation requirements. NOTE: Products with CE marks perform their required functions safely and adhere to relevant standards as specified by EC directives provided they are used according to their intended purpose and that the instructions in this manual are adhered to. The protection provided by the equipment may be impaired if this equipment is used in a manner not specified in this manual. Only replacement parts supplied by PLCDirect or its agents should be used. A listing of international affiliates is available at our Web site Technical Support If you need technical assistance, please call the technical support group at PLCDirect (3505 Hutchinson Rd., Cumming, GA 30040, U.S.A.) at They are available Monday through Friday from 9:00 A.M. to 6:00 P.M. Eastern Standard Time. Their Web Site address is SELV Circuits Environmental Specifications Preventative Maintenance and Cleaning All electrical circuits connected to the communications port receptacle are rated as Safety Extra Low Voltage (SELV). Operating Temperature Storage Temperature Operating Humidity Air Composition to 50 C --0 to 70 C 95% (non-condensing) No corrosive gases permitted No preventative maintenance is required. To clean the exterior of the panel disconnect the input power and carefully wipe the panel with a cloth moistened with plain water. External Fuse Protection for Input Power There are no internal fuses for the input power circuits, so external circuit protection is needed to ensure the safety of service personnel and the safe operation of the equipment itself. To comply with EU specifications, the input power must be fused. Use a fuse rated at twice the input current rating of the panel. For example, if the panel has an input current rating of 0.5 amperes, use a fuse rated for ampere.
5 Table of Contents Introduction Is this Manual Right for You? Additional Manuals How the OP-900 Communicates Using the Communications Master...5 Easy Steps Step : Plan Your System of Panels (Pages 4--7) Step : Install the Panels and the OP-900 (Pages 8--6) Step 3: Configure the System and the Individual Panels (Pages 7--) Step 4: Download the Configurations to Each Panel (Page ) Step 5: Download the System to the OP-900 Master (Page ) Planning Your Memory Mapping Memory Consumption for Mapping Process Using a Memory Planner Installing the Panel Panel Specifications: Physical Specifications CPUs Supported Environmental Specifications Operating Specifications Dimensions Power and Cabling Requirements Assessing Your Application Needs? Connecting a Power Supply to the OP Power Supply Connections Pinout Diagrams for Cabling Choosing Your Connecting Cables Custom Cables for Connecting Panels to the OP Setting the Panel DIP Switches and OP-900 Jumper Assigning Addresses to the Panels Connected to the OP How to Set the Operator Panel Addresses Communication LED Indicators
6 ii Table of Contents Configuring Multiple Panels with the OPEditor System Requirements How to Install Step-by-Step Procedure Step : Load the OPEditor and Complete the Editor Setup Step : Select the LPT and COM ports Step 3: Select Multi-Panel Configuration Step 4: Select the Source for your Configuration Step 5: Enter the Correct PLC Brand and Type Step 6A: Select Configure Protocol and the PLC Subtype Step 6B: Set the Baud Rate, Parity and Stop Bits Step 6C: Set the Timeout Step 6D: Set the PLC Address for the Port Used Step 7: Add the Panel to the System Step 8: Select Panel to be Configured or Upload Existing Panel Configuration Step : Repeat Steps 8-0 for each OP-panel Step : Download the System Configuration to the OP Troubleshooting Observing the LEDs on the OP Requesting Data from PLC But No Response OP-900 Not Communicating Properly with the Panels Trouble Communicating with Computer During Configuration
7 Introduction Sections This table provides an overall description of the topics covered within this manual. Introduction Introduces the physical and functional characteristics. Also provides introduction to planning your system. 3 Memory Mapping Installation and Specifications Explains memory mapping in a multi-panel configuration. Shows how to prepare for system installation, including specifications and mounting instructions. Includes connecting cables part numbers and specifications. 4 Configuring Your Panels Shows how to configure the panel. The OP--WINEDIT for windows contains Help windows which will assist with configuring the panels. 5 Trouble Shooting Shows you how to diagnose and correct common problems. Introduction Is this Manual Right for You? The OP-900 Communications Master provides an intelligent interface between your programmable controller (PLC) and two or more OptiMatet panels. This manual shows you how to install, configure and operate your OP-900 Communications Master. It includes wiring diagrams and power requirements, as well as the information you need for selecting the proper connecting cables. OP -900 OP -900 Power Source DL405 CPU Base J J Power Supply (8 to 30 VDC) OptiMate Panels Additional Manuals There are several other manuals you will find helpful or necessary: D Respective PLC User Manuals--Shows you the memory conventions, programming instruction sets, data or file types, communications protocol, etc. D Respective OptiMate operator panel User Manuals--Shows you the memory mapping requirements, modes of operation, ladder logic needed for operation of the respective panel, initial setup requirements, and much more.
8 Introduction How the OP-900 Communicates The OP-900 communicates with your OptiMate panels via two RS4 ports at a baud rate of 900. It communicates with your PLC at the rate you indicate during configuration. Depending on brand and model of PLC, this will be some rate between 00 and 900 baud. Later on in this manual, we will show you how to select the communcation baud rate between your OP-900 and PLC. This is done with the same OPEditor software that you use to configure the individual OptiMate panels. The OP-900 knows which OptiMate panel is sending information to it, because each OP panel has a unique address assigned via its respective DIP switch. You can have up to 3 panels connected to a single OP-900. Addresses 0 thru 30 are available for this purpose. See the diagram below for more about DIP switch settings. Shown below is a sample configuration using a PLCDirect programmable controller, a pushbutton panel (OP-4), a lamp annunciator panel (OP-4) and a menu-driven operator panel (OP-50). Notice that each panel has a unique address, and that each panel has been assigned specific memory inside the PLC for the purpose of mapping your configurations. I/O of machinery and processes PLCDirect DL05 or DL405 family 00 to 900 baud (RS3 or RS4) OP-900 DIP Switch for setting addresses ON T OP-4 Power Supply 900 baud (RS4) OP-4 J J 900 baud (RS4) OP-50 T=termination resistor. Numbers with ON positions are added together. Above example shows Address = 5 Power Supply DIP switch is set to Address 0. Base Addr=V40600 Consumes: V V40603 (64 bits) Power Supply DIP switch is set DIP switch is set to Address 0. to Address 03. Base Addr=V000 Base Addr=V00 Consumes: Consumes: V000--V007 V00--V07 (8 bits) (8 bits) Power Supply
9 Introduction 33 Using the Communications Master...5 Easy Steps Step : Plan Your System of Panels (Pages 4-7) In the next section, we provide you with a template for planning your multi-panel OptiMate system. It s main purpose is to have you plan in advance what base register addresses you want to use for each panel, and to make sure that the consecutive bits consumed by each panel during the mapping process do not overwrite each other. You need to know this information when you do the configuration in Step 3. Step : Install the Panels and the OP-900 (Pages 8-6) Preparing for installation, you will want to check the individual specifications. These include dimensions, power requirements, cabling requirements, and NEMA ratings. We include information you will need formounting; i.e. cutout dimensions, cabling requirements, components needed, etc. This manual includes only the specifications for the OP-900. Review the individual OptiMate User Manuals for each respecitive panel used. Cables External Power Step 3: Configure the System and the Individual Panels (Pages 7 -) You need the OptiMatet OPEditor software in order to configure the system and all the individual panels. At the time of publication, we have a DOS version with the introduction of a Windows version due in early 996. This software is the same regardless of whether you are connecting to a PLCDirect or Allen-Bradley product. Your PC OptiMate OptiMate Configuration Editor Version. /95 OMCFG0 Step 4: Download the Configurations to Each Panel (Page ) As you configure the OP-900 for a multi-panel system, you will be configuring each panel as a part of the overall configuration process. After each panel is configured, you will then download the configuration to the individual panel. Step 5: Download the System to the OP-900 Master (Page ) After all the panels have been downloaded with their respective configurations, you then download the overall scheme to the OP-900 itself. This requires that you set a jumper on the OP-900. Set the Jumper for Downloading J J
10 4 Planning Your Memory Mapping Planning Your Memory Mapping When using more than one OP-panel in a system, it is important that you plan ahead to make sure the memory mapping for one panel does not overwrite the memory mapping for another panel. Let s take a look again at a typical system. Notice that each panel shown consumes a fixed amount of memory for its mapping. For example, The OP-4 needs 64 consecutive bits; the OP-4 needs 8 consecutive bits; and the OP-50 needs 8 consecutive bits. When you are planning your system, you have to make sure that your panels don t compete for the same memory space. To help you with this process, we have given you a memory assignment template on Page 7. We have also included a chart on Page 6 that shows you the memory requirements for each of the currently available OP-panels. I/O of machinery and processes PLCDirect DL05 or DL405 family 00 to 900 baud (RS3 or RS4) OP-900 Power Supply J J 900 baud (RS4) 900 baud (RS4) OP-4 OP-4 OP-50 Power Supply DIP switch is set to Address 0. Base Addr=V40600 Consumes: V V40603 (64 bits) Power Supply DIP switch is set DIP switch is set to Address 0. to Address 03. Base Addr=V000 Base Addr=V00 Consumes: Consumes: V000--V007 V00--V07 (8 bits) (8 bits) Power Supply
11 Planning Your Memory Mapping 55 Memory Consumption for Mapping Process NOTE: For PLCDirect and compatibles, remember that the V-Memory and R-Memory addresses are numbered in octal -not decimal. For example, V007 and V00 are consecutive registers -V008 and V009 do not exist. OP-4 Data Registers DL05/DL405 DL305 A-B Function Consumes 64 consecutive bits: 4 sixteen bit registers (DL05/DL405 and A-B) 8 eight bit registers (DL305 only) OP-4 Consumes 8 consecutive bits: 8 sixteen bit registers (DL05/DL405 and A-B) 6 eight bit registers (DL305 only) m m+ m+ m+3 n n+ n+ n+3 n+4 n+5 n+6 n+7 Data Registers DL05/DL405 DL305 A-B Lamps -6 ON/OFF Lamps 7-4 ON/OFF Lamps -6 flash Lamps 7-4 flash Function Pushbuttons -6 ON/OFF Pushbuttons 7-4 ON/OFF LEDs -6 flash LEDs 7-4 flash LEDs -6 ON/OFF LEDs 7-4 ON/OFF Force Function Data (-6) Force Function Mode/Data (7-4) Data Registers DL05/DL405 DL305 A-B Function OP-3 Consumes 4 consecutive bits: 4 sixteen bit registers (DL05/DL405 and A-B) 8 eight bit registers (DL305 only) OP-500 p p+ p+ p+3 p+4 p+5 p+6 p+7 p+8 p+9 p+0 p+ p+ p+3 Data Registers Location data Location data Location 3 data Location 4 data Location 5 data Location 6 data Location 7 data Location 8 data Location 9 data Location 0 data Location data Location data Force data flags Data to be forced DL05/DL405 DL305 A-B Function Consumes 8 consecutive bits: 8 sixteen bit registers (DL05/DL405 and A-B) 6 eight bit registers (DL305 only) OP-50 q q+ q+ n+3 q+4 q+5 q+6 q+7 Top line message selection Bottom line message selection Top line data/menu function* Decimal point, top line Bottom line data Decimal point, bottom line Status register Control register *q+ holds Function Number for the OP-50 only. See OP-50--M manual.
12 6 Planning Your Memory Mapping Using a Memory Planner DL405 On Page 7, we have included a template for planning your memory mapping in a multi-panel configuration. The following example shows the memory requirements and assignments for three OP-panels connected to a DL405 programmable controller. Refer to the chart on Page 5 to find out how many registers of consecutive memory are required for each panel. Memory does not have to be consecutive between the various panels. OP-900 J J OP-4 OP-4 OP-50 Notice that we have remapped some addresses to take advantage of select features that require individual bit manipulation.we have kept things simple here to make the example easy to understand. For the OP-4, for example, we have only remapped the pushbuttons, and have elected not to use some other features that would require remapping, i.e. LED separation, force function, etc. On the other hand, we have remapped the status and control registers of the OP-50. By thinking out memory allocation for the original mapping and remapping, we can prevent possible memory overlap in either area. Refer to your respective OP-panel User Manuals to determine what features need to make use of remapping. Remapping is never an issue with the DL450 or Allen-Bradley PLCs because of bit-of-word capability. For these PLCs ignore this part of the template.
13 Planning Your Memory Mapping 77 I. OP-Panel Memory Planner PLC Address for OP-900 Panel Panel Registers Original Mapping Remapping Number Name Needed Base Final Word ( ) Relationship Function Address Address
14 8 Installing the Panel Installing the Panel Panel Specifications: In this section, you will be given all of the information you need to install the panel. Before actually installing the OP-900 panel, it may be helpful to examine the specifications and make sure that the requirements of your application are met. Physical Specifications Weight Panel Fasteners ounces NEMA Rating NEMA Four holes to accept four 6x3 machine screws CPUs Supported CPUs DL05, DL05, DL305, DL405, PLCDirect Compatibles SLC 5/03, SLC5/04 Environmental Specifications Operating Temperature Storage Temperature Operating Humidity Air Composition to 50 C --0 to 80 C 5 to 95% (non-condensing) No corrosive gases permitted Operating Specifications Power Budget Requirement Power Connector Absolute Maximum Voltage Diagnostics Communication Link VDC 30 VDC 55 4 VDC Removable Terminal Block position 3 VDC Power On, CPU RS3 or RS4 4800, 9600 and 900 baud 5 pin female D type connector *Only 4800 and 9600 baud will work with Allen-Bradley PLCs.
15 Installing the Panel 99 Dimensions (All dimensions are given in inches) 8. Power Connector RS3/RS4 Port (To PLC) J J RS4 Ports (To Single or Multiple Drop panels) 8.
16 0 Installing the Panel Power and Cabling Requirements What Are Your Application Needs? By using an OptiMate OP--900 Communications Master, you can connect multiple Optimate units up to a single CPU. Up to 3 individual units can be connected in a daisy-chain fashion to the OP Communications are via RS4 between the OP--900 and the operator interfaces. If you use a good quality shielded cable, you can have a total distance of up to 4000 feet between the OP--900 and the last operator interface unit in the chain. If you only have a short distance (up to 30 feet), you can use ribbon cable and easy-to-install crimp-on ribbon connectors. OP-900 Power Source DL405 CPU Base Power Supply OP-panels
17 Installing the Panel Connecting a Power Supply to the OP-900 Power Supply Connections The OP-900 panel can operate on DC voltages between 8 and 30 VDC rated at 3.75 watts. Connect the panel to a power supply (within the required voltage range and wattage) using the terminal block connector supplied. The connector is polarized to prevent reversing the connections. The male receptacle on the rear of the panel will only connect in one way with the female connector that is supplied with your OP-900 panel. Pin is the positive connection, while Pin is the negative, or ground, connection. You must use an external power supply that can deliver voltages in the 8 to 30 VDC range, and can supply 3.75 watts of power. A two-prong male connector is on the side of the unit. Your OP-panel is shipped with the female connector. GND + Install the connector to a cable for attachment to your power supply. The power supply is not sold by PLCDirect. Model Current Consumed at VDC OP A Current Consumed at 4VDC 0.6A
18 Installing the Panel Pinout Diagrams for Cabling Connecting Cable RJ (PLC) DB pin (PLC) DB RJ (PLC) DB DB5 (PLC) DB DB5 (PLC) DB Pin Mini DIN DB The connecting cable may vary depending on the CPU used. Refer to the following page to confirm the proper cable is chosen for connecting your PLC. PLC OP--CBL = 0V = not used 3= Din 4= Dout 5= not used 6= not used 8= not used 7= 0V 6= not used 5= CTS 4= RTS 3= RXD = TXD = not used = Din = Dout 3= not used 4= 0V 8= YOM 7= CTS 6= not used 5= not used 4= On-line 3= Din = Dout = YOP 3= not used = not used = not used 0= not used 9= not used 8= not used 7= 0V 6= not used 5= CTS 4= RTS 3= Din = Dout = not used RJ RJ = tied (0V) 4= tied (0V) 3= tied (0V) = not used = not used 0= not used 9= not used 5 5= not used 4= not used 3= not used = not used = not used 0= not used 9= not used 5= not used 4= not used 3= not used = not used = not used 0= not used 9= not used 8= not used 7= not used 6= not used 5= not used 4= not used 3= Din = Dout 5 =0V RJ (6P6C) 5-pin RJ (4P4C) DB5 DB5 Mini--DIN OP--CBL-- OP--3CBL OP--4CBL-- OP--4CBL-- OP--ACBL-- DB5 DB5 DB5 DB5 DB5 DB5 RS-4 Pinout PLC Panel Din + = Dout+ Din -- = Dout -- Dout + 9 = Din + Dout -- 0 = Din-- 0V 5 =0V RTS+ CTS+ RTS-- CTS-- 9= not used 0= not used = not used = not used 3= not used 4= not used 5= not used Panel 5 = not used = Dout 3= Din 4= not used 5= 0V 6= not used 7= not used 8= not used
19 Installing the Panel 3 Choosing Your Connecting Cables Depending on which PLC you are using, you may require as manyas two cables. Here are the requirements: D OP-ACBL-: all units require this cable for configuration. This is a 9-pin female to 5-pin male cable that connects your personal computer to the OP-panel. This cable is also used to connect an OP-panel to the Allen-Bradley SLC 500 CPUs listed. D CPU Cables: You will also need the appropriate cable to connect your CPU to the OP-panel. Use the chart shown to the right to choose the correct communications cable. A-B MicroLogix Only port OP-ACBL-- * requires RS3 Data Communications Unit (D3--3--DCU) **-- also DC versions Family DirectLOGICt DL05 DirectLOGICt DL05 DirectLOGICt DL305 DirectLOGICt DL405 CPU (or other device) OptiMate Cables Port Cable DL30 Only port OP--CBL DL30 Only port OP--CBL DL40 Top port OP--CBL Bottom port OP--CBL DL50 Top port OP--CBL Bottom port OP--CBL-- D--DCM (module) Only port OP-4CBL-- DL330 Requires DCU* OP--4CBL-- DL330P Requires DCU* OP-4CBL-- DL340 Top port OP-3CBL Bottom port OP-3CBL DL350 Top port OP-CBL Bottom port OP-4CBL- DL430 Top port (5-pin) OP-4CBL-- Bottom port (5-pin) OP-4CBL-- DL440** Top port OP-4CBL-- Bottom port OP-4CBL-- DL450 Phone Jack OP-CBL Top port (5-pin) Bottom port (5-pin) OP-4CBL-- OP-4CBL-- D4--DCM (module) Only port OP-4CBL-- Slice I/O panels Only port OP-4CBL-- GE Series IC60CPU05/06 Requires DCU* OP-4CBL-- GE Seriest 90/30 All Models (3--35) RS3, RS4 Serial Port GE Fanuct Series 90 Micro All Models RS3, RS4 Serial Port OP-GCBL-- OP-GCBL-- MODICON ModBus RJ45 port OP-MCBL-- TI305t / SIMATIC TI305t TI405t / SIMATIC TI405t , PPX: Requires DCU* OP-4CBL , PPX: Requires DCU* OP-4CBL-- 35S--07 (or 35 w/ Stage Kt) Requires DCU* OP-4CBL-- 330S--37, PPX:330S--37 Requires DCU* OP-4CBL , PPX: Phone Jacks OP-3CBL If DCU is used* OP-4CBL CPU, PPX:45--CPU ** Only port OP-4CBL-- PPX:430--CPU Top port (5-pin) OP-4CBL-- Bottom port (5-pin) OP-4CBL CPU, PPX:435--CPU ** Top port (5-pin) OP-4CBL-- Bottom port (5-pin) OP-4CBL-- Smart Slicet I/O panels Only port OP-4CBL-- A--B SLC 500 5/03, 5/04 Bottom port OP-ACBL--
20 4 Installing the Panel Custom Cables for Connecting Panels to the OP-900 You must build your own cables for connecting the multiple panels to your OP-900. Since the proper cable choice really depends on your application, we offer the following connectors. For electrically noisy environments, we recommend a good shielded cable, such as Belden 979 or equivalent. This type of cable will require the solder-type connectors. If you re going 30 feet or less, you can use ribbon cable. For ribbon cable, we recommend Belden 9L805 or 3M 3365/5. See the chart below for more details concerning the Belden cable. D OP -CMCON - pack of 4 ribbon cable connectors. D OP -CMCON - pack of 4 solder-type connectors. Ribbon cable with DB5 male connectors attached. Panels can be connected directly to the OP-900 ports or be daisy-chained to other OP-panels. OP-900 Power Source PLC Belden 979 Specifications No. twisted pairs Power Supply Nom. Impedance (ohms) 00 Nom. Capacitance (pf/m) 4 Wire Gauge (AWG) 4 OP-panels Note: Panels can be located as far away as 4000 feet from the OP-900 when using shielded cable (Belden 979 or equivalent). Flat ribbon connections can be used for a distance of 30 feet maximum. For ribbon cable, we recommend Belden 9L805 or 3M 3365/5. Notice in the diagram below that the receive and transmit lines are wired straight through for each of the panels connected to the OP-900. For example, pin 9 of the OP-900 is the Tx+ line and pin 9 of the panel is the Rx+ line. This keeps you from having to twist cable wires. The matchup between Tx and Rx is handled internally by the OP =Tx+ 0=Tx - =Rx+ =Rx - OP-900 Ribbon or Shielded Cable 5 9=Rx+ 0=Rx - =Tx+ =Tx =Rx+ 5 0=Rx - =Tx+ Panel # =Tx - Panel # 9 9=Rx+ 0=Rx - =Tx+ =Tx - 5 Panel #3 0 9
21 Installing the Panel 5 Setting the Panel DIP Switches and OP-900 Jumper Assigning Addresses to the Panels Connected to the OP-900 A 6-position DIP switch on the rear of each individual panel allows you to assign a hardware address to your panel. Each panel must have a unique address. You can use any address between 0 and 30 when communicating between a panel and the OP-900 Master Communications panel. Address 3, however, is reserved. See the note that follows. NOTE: You must use Address No. 3 when you are using the OPEditor software to download or upload your panel configurations to each individual panel. Switch On SW Position Address Value T ON = ENABLE OFF = DISABLE How to Set the Operator Panel Addresses To set the address on any of the individual panels so that they can communicate with the OP-900, simply set the apppropriate switches on the dip switch to the desired address. The figure below shows the binary weighting of each switch position. Notice that it is in decimal format. To select address 4 for example, you would press switches, 3 and 4 down to the right, and switches, 3 and 5 to the left ( = 4). Remember that you must use address 3 only when communicating with a computer for uploading or downloading. The letter T in position 6 stands for terminal resistor. The final panel in a multi-drop panel configuration should have this position turned ON. NOTE: Each time you change the DIP switch setting, you must power cycle the panel. Setting the Jumper of the OP-900 There is a jumper terminal on the edge of the OP-900 (located between the cable connector and the power supply connector). This jumper must be in place in order for the OP-900 to communicate with your computer for downloading or uploading configurations. You must remove this jumper when you want the OP-900 to communicate with your PLC. To communicate with your computer (jumper in place) To communicate with your PLC (jumper removed)
OP--613 Operator Panel Manual Number OP--613--M WARNING Thank you for purchasing automation equipment from PLCDirect. We want your new DirectLOGIC automation equipment to operate safely. Anyone who installs
PLC Master / Slave Example A 2 PLC The Example This chapter provides an example of a PLC master / slave network and is designed for the experienced user. This chapter does not provide detailed descriptions
ENET-710 ENET-710 - Ethernet Module JAN / 06 ENET-710 FOUNDATION E N E T 7 1 0 ME smar www.smar.com Specifications and information are subject to change without notice. Up-to-date address information is
Application Note Last reviewed: 03/17/2008 AN-KEP-003.doc Page 1 of 23 Introduction... 1 Recommended s and ports to use... 1 Cable Wiring... 2 MDM-TEL Configuration ( Wizard)... 3 Direct Logic Communications
MDM192 MULTI-DROPS DIGITAL MODEM FOR PRIVATE LINE USER GUIDE Document reference : 9010709-03 If you have questions about the MDM192 or desire assistance, contact ETIC TELECOMMUNICATIONS at the following
2-Port RS232/422/485 Combo Serial to USB2.0 Adapter (w/ Metal Case and Screw Lock Mechanism) Installation Guide 1. Introduction Thank you for purchasing this 2-Port RS232/422/485 Combo Serial to USB Adapter.
USB to RS-422/485 Serial Adapter User Manual Ver. 2.00 All brand names and trademarks are properties of their respective owners. Contents: Chapter 1: Introduction... 3 1.1 Product Introduction... 3 1.2
User Manual IC-485AI Note: This equipment has been tested and found to comply ith the limits for a Class A digital device pursuant to Part 15 of the FCC Rules. These limits are designed to provide reasonable
Programming and Using the Courier V.Everything Modem for Remote Operation of DDF6000 1.0 Introduction A Technical Application Note from Doppler System July 5, 1999 Version 3.x of the DDF6000, running version
to RS422/RS485 Isolated Universal Converter 1. Introduction The converts serial data from the standard to either RS422 or RS485. Features: Universal converter can be used with both and other manufacturer
DX4010V2 EN Installation Instructions RS-232/USB Serial Interface Module DX4010V2 Installation Instructions Trademarks Trademarks BlackBox is either a registered trademark or a trademark of BlackBox Corporation
User Guide Modbus Communications for PanelView Terminals Introduction This document describes how to connect and configure communications for the Modbus versions of the PanelView terminals. This document
User manual Compact Web PLC WP240 series IEC-line update: 09-01-2014 IEC-line by OVERDIGIT overdigit.com 1. General description The WP240 device is a PLC, programmable in IEC61131-3 language using CoDeSys
ADAM-4561 1-port Isolated USB to RS-232/422/485 Converter User s Manual Part No. 2000456100 Printed in Taiwan Feb. 2001 1.1 Introduction Advantech s ADAM-4561 allows PC users to connect their serial devices
Orbit PCI Mk 2 Network Card User Manual Part No. 502566 Issue 4 Information in this document is subject to change without notice. Companies, names and data used in examples herein are fictitious unless
and Troubleshooting 7 2 and Troubleshooting Starting the Network PLC as Master Networks If you re using a PLC as the master station, you must put the CPU in Run mode before the communications program can
Installation Instructions Universal Serial Bus (USB) to DH-485 Interface Converter Catalog Number 1747-UIC Contents Overview..................................................3 Computer and Operating System
ALL-USB-RS422/485 USB to Serial Converter RS422/485 User Manual ALL-USB-RS422/485 USB to RS-422/485 Plugin Adapter This mini ALL-USB-RS422/485 is a surge and static protected USB to RS-422/485 Plugin Adapter.
ISHIDA BC-3000 Scale to Scale Communications Setup Procedure & Operating Instructions March 2006 PN 94561 Revision History Date Page Description March 2006 Initial publication August 2006 2 Added RS-232
Artisan Technology Group is your source for quality new and certified-used/pre-owned equipment FAST SHIPPING AND DELIVERY TENS OF THOUSANDS OF IN-STOCK ITEMS EQUIPMENT DEMOS HUNDREDS OF MANUFACTURERS SUPPORTED
Serial Device Server - RS232/RS485 to Ethernet converter USR-TCP232-300 Hard version: V2.0 File version: V1.1 2011-8-17 Serial Device Server - RS232/RS485 to Ethernet converter is an Equipment for convert
RN-XV-RD2 Evaluation Board 2012 Roving Networks. All rights reserved. -1.01Version 1.0 9/28/2012 USER MANUAL OVERVIEW This document describes the hardware and software setup for Roving Networks RN-XV-RD2
Quick Installation A Series of Intelligent Bar Code Reader with NeuroFuzzy Decoding This chapter intends to get your new FuzzyScan scanner working with your existing system within minutes. General instructions
Hardware Installation and Configuration Guide Trademark Notices Comtrol, DeviceMaster, and PortVision are registered trademarks of Comtrol Corporation. Ethernet is a registered trademark of Digital Equipment
POS 208 / 808 DISTRIBUTED BY INTELLIGENT CASH DRAWER WEDGES MADE IN CANADA USER S MANUAL 2 Table of Contents Introduction............................................... 3 POS 208 Installation........................................
User Manual 10/10 MN0500005Z-EN replaces 07/04 AWB74-1490GB Teleservice via RS interface XC100/XC00 All brand and product names are trademarks or registered trademarks of the owner concerned. Emergency
Introduction: Implementation of the MVI56-MCM module for modbus communications: Initial configuration of the module should be done using the sample ladder file for the mvi56mcm module. This can be obtained
This Quick Start Guide is designed to familiarize the user with the connection and configuration of the DTS-305 DIN rail mounted single / 3 phase power & energy meter with RS-485 or TCP communications.
FOSTCDR pn 8684R1 FOSTCDR-0812ds page 1/5 Industrial Serial to Multimode Fiber Optic Converter Data Rates up to 115.2 kbps 2.5 Mile (4 km) Range 10 to 30 VDC Input Voltage Wide Operating Temperature 2000V
Sense Box VOICE RECORDING SYSTEM ISDN PRI / BRI / Analog SUB-SYSTEM ISDN2, ISDN30 Sense Box USER MANUAL TABLE OF CONTENTS 1. STATUTORY INFORMATION... 3 1.1 SAFETY WARNING... 3 1.2 SAFETY EXTRA LOW VOLTAGE
16-Port RS232 to USB2.0 High Speed Multi Serial Adapter (w/ Metal Case) Installation Guide 1. Introduction Thank you for purchasing this 16-Port RS232 to USB2.0 High Speed Multi Serial Adapter. It is an
GV-Data Capture V3 Series User's Manual Before attempting to connect or operate this product, please read these instructions carefully and save this manual for future use. 2006 GeoVision, Inc. All rights
Model 201 Wiegand Touchpad Reader Installation Guide P/N 460353001C 15AUG11 2011 UTC Fire & Security. All rights reserved. This document may not be copied in whole or in part or otherwise reproduced without
DirectSOFT Quick Start Manual Number QS--DSOFT-M WARNING Thank you for purchasing automation equipment from PLCDirect. We want your new DirectLOGIC automation equipment to operate safely. Anyone who installs
Universal I/O EDI Distributor Control Interface Wiring and Setup Instructions EDI UNIVERSAL I/O INTERFACE MODULE The only interface needed for EDI-V5 controls Network compatible with all older EDI controls
DIN Rail Mounted Leased Line Modem Users Manual 366-101 Rev. 2 Copyright 2008 Miille Applied Research Co., Inc. Houston, Texas This page is left blank intentionally Page i TABLE OF CONTENTS LIST OF FIGURES...
User Manual Web Operating Panel AP User Manual General Settings, Updating and Troubleshooting Copyright The documentation and the software included with this product are copyrighted 2010 by Advantech Co.,
How to read this guide The following shows the symbols used in this Quick start guide with descriptions and examples. Symbol Description Example P oint Reference Caution [ ] This symbol explains information
IP-COM-M IP-COMi-M IP-COM-M PoE IP-COMi-M PoE RS-232 RS-232/422/485 RS-232, Power over Ethernet RS-232/422/485, Power over Ethernet Edition: September 2012 The computer programs provided with the hardware
MS830 / MS833 Barcode Reader v1.0 9-December-2014 Publication Information 2014 Imagine Communications Corp. Proprietary and Confidential. Imagine Communications considers this document and its contents
Data Bulletin 1210DB0002R3/05 03/2005 LaVergne, TN, USA Communications Wiring for POWERLINK G3 Systems Class 1210 Retain for future use. ABOUT THIS BULLETIN This data bulletin describes the proper wiring
T3 Mux M13 Multiplexer User Manual [Type the abstract of the document here. The abstract is typically a short summary of the contents of the document. Type the abstract of the document here. The abstract
R Installation Guide APA-1460 SlimSCSI PCMCIA-to-SCSI Host Adapter Introduction This document explains how to install and use Adaptec s APA -1460 SlimSCSI PCMCIA-to-SCSI adapters. The SlimSCSI adapters
Dual Ports Serial PC Card User Manual FCC COMPLIANCE STATEMENTS This equipment has been tested and found to comply with the limits for a Class B digital device, pursuant to Part 15 of the FCC Rules. These
Technical Data WinPFT File Transfer Utility (Catalog No. 2711-ND7) Overview WINPFT is a stand-alone Windows utility which lets you transfer applications developed for standard PanelView terminals or Dataliner
2100 POS System 2100 User Guide Thank you for selecting UTC RETAIL s innovative Model 2100 Point of Sale solution! This guide is designed to acquaint you with the features and functionality of the 2100
One Port Serial Server Users Manual Model ESP901, ESP901E Documentation Number: ESP901-2303 International Headquarters B&B Electronics Mfg. Co. Inc. 707 Dayton Road -- P.O. Box 1040 -- Ottawa, IL 61350
Part Number 129777-01 Revision A, January 1996 3500 Monitoring System Rack Configuration and Utilities Guide Copyright 1995 Bently Nevada Corporation All Rights Reserved. No part of this publication may
1 de 7 1. Introduction This Technical Note explains how to configure the Modbus Gateway for Vantage Pro2. The Modbus Gateway allows the easy connection of a PLC (Programmable Logic Controller), RTU (Remote
Backup Scanner Module Catalog Number 1747-BSN Installation Instructions 2 Backup Scanner Module Important User Information Because of the variety of uses for the products described in this publication,
Series Six Plus Programmable Controller Gl?K-0147B June 1989 Central Processor Unit 8-Slot Rack 1l-Slot Rack General Description The Central Processor Unit (CPU) for the Series Six Plus Programmable Logic
BIT COMMANDER Serial RS232 / RS485 to Ethernet Converter (Part US2000A) Copyrights U.S. Converters 1 Contents Overview and Features... 3 Functions..5 TCP Server Mode... 5 Httpd Client Mode.5 TCP Auto mode....6
RSC232 Communication Converter Installation and Operation Manual LIMITED WARRANTY The manufacturer offers the customer a 24-month functional warranty on the instrument for faulty workmanship or parts from
Safety Precautions Read and understand this specifications, instruction manual, installation manual and catalog to make proper use of the product. WARNING If critical situations that could lead to user
GV-Keyboard User's Manual V2.0 Before attempting to connect or operate this product, please read these instructions carefully and save this manual for future use. 2007 GeoVision, Inc. All rights reserved.
USBSPYDER08 Discovery Kit for Freescale MC9RS08KA, MC9S08QD and MC9S08QG Microcontrollers User s Manual Copyright 2007 SofTec Microsystems DC01197 We want your feedback! SofTec Microsystems is always on
USB-to-Serial RS-232 Hub USB-to-Serial RS-422/485 Hub USER MANUAL UC2322 / UC2324 / UC4852 / UC4854 FCC Information This equipment has been tested and found to comply with the limits for a Class B digital
TCP/IP MODULE CA-ETHR-A INSTALLATION MANUAL w w w. c d v g r o u p. c o m CA-ETHR-A: TCP/IP Module Installation Manual Page Table of Contents Introduction...5 Hardware Components... 6 Technical Specifications...
Somfy Digital Network (SDN) Installation and Programming SSoomffyy SSyysst teemss IInncc.. 1 Table of Contents 1 General Information and Features... 3 1.1 ILT2 Motor... 3 1.2 SDN Switches... 4 1.3 ILT2
User Manual UNICOM 2500 Installation Operation Programming Universal Communication Converter UNICOM 2500 Electro Industries/GaugeTech 1800 Shames Drive Westbury, New York 11590 Tel 516.334.0870 Fax 516.338.4741
RS232C < - > RS485 CONVERTER S MANUAL Model: LD15U INTRODUCTION Milestone s model LD-15U is a RS232 to RS 485 converter is designed for highspeed data transmission between computer system and or peripherals
EMBEDDED ACCESS CONTROL Hardware Installation Guide Lenel goentry Hardware Installation Guide, product version 1.00. This guide is item number DOC- ENHW-ENU, revision 1.003, April 2009 Copyright 2009 Lenel
CU-111 APRIL 11, 2013 Paragon Explorer Lite Communication Software For Fireye Paragon Scanners using Windows XP DESCRIPTION Paragon Explorer Lite, is the basic PC based configuration tool for Paragon model
Table of Contents Name Page Number PLC Connections 1 Cable Solutions for Omron PLCs 11 Cable Solutions for Multi-Vendor PLCs 15 i Reference Information PLC Connections The following pages illustrate the
Programming PC adapter V4 USB PC Adapter V4 Configuration PC adapter with USB cable Flat Ribbon Cable Power Supply Unit Device Driver General The USB PC adapter V4 is used for communication between a PC
SEC 4100 SYSTEM MONITOR Programmable Serial Interface Card Series 2 USER MANUAL Rev. P1.11 September 13, 2006 DeltaV is a trademark of Emerson Process Management, Inc Emerson Process Management, Inc. 1998,
LevelOne IFE-0500 4-Port PoE + 1-Port TP Industrial Fast Ethernet Switch User Manual Ver. 1.0.0-0711 1 FCC Warning This Equipment has been tested and found to comply with the limits for a Class-A digital
APPLICATION Note TELECOM SOLUTIONS FOR THE 21ST CENTURY Using the PB-100 for All-Call Dialing March 22, 2002 Features Compatible with Windows 95, 98, ME, NT 4.0, 2000 Male sub-d 9 pin cable provided 20
February 2015 February 2015 Application Note - Connecting an Electricity Meter to SolarEdge Devices (Europe and APAC) This document describes how to connect an electricity meter to a SolarEdge device (inverters,
Rev No.: 0 Page No.: 1 RS232/CMOS C US ON SD 1 2 3 4 No Switch Position ON OFF 1 RS485 TYPE 2 Wire 4 Wire 2 Direction CTRL Internal ON OFF 3 Direction CTRL External ON OFF 4 Termination ON OFF RS232/CMOS
Specifications subject to change OCT 2013; Rev. 1.3 HSG Engineering Tech Bulletin Recommended RS-485 Wiring for NetAXS-4/NetAXS-123 Loops Overview This document provides the recommended RS-485 wiring for
3DLevelScanner II Different Ways of Connecting to 3DLevelScanner II A.P.M Automation Solutions LTD. www.apm-solutions.com Version 3.0 2 Different Ways of Connecting to 3DLevelScanner II Version 3.0 Table
Wireless Router Setup Manual NETGEAR, Inc. 4500 Great America Parkway Santa Clara, CA 95054 USA 208-10082-02 2006-04 2006 by NETGEAR, Inc. All rights reserved. Trademarks NETGEAR is a trademark of Netgear,
DVPPF02-H2 PROFIBUS DP Slave Communication Module Application Manual Warning Please read this instruction carefully before use and follow this instruction to operate the device in order to prevent damages
IntesisBox ModBus Server - KNX Gateway for integration of KNX equipment into Modbus (RTU and TCP) control systems. Integrate KNX based lighting control into your SCADA, BMS, PLC "talking" Modbus. Master