1 SunPower Module 40-year Useful Life Executive Summary: SunPower expects its modules (panels) have a useful life of more than 40 years, defined as 99% of modules producing at least 70% of their power. This is made possible through fundamental design differences which provide robust protection against real-world stresses. These differences are discussed in the context of comparative experimental data. In addition, SunPower s physics-based model, PVLife, provides the expected change in performance over time from major degradation and failure modes. This model matches well with field data. Collectively, these data suggest that a 40 year life is realistic useful life for SunPower modules. Introduction Due to the relative immaturity of large scale solar, the market generally assumes that modules have a useful life equal to the warranty period and leave no residual value afterwards. However, in most other industries this is not the case. For instance, consumer electronic products have warranties of one to three years; yet, are used for five to seven years. SunPower warrants its modules with a linear power warranty, leaving an asset producing at least 87% of warranted power at the end of 25 years 1. Further, SunPower offers the industry s first combined 25 year product and power warranty. The reason SunPower can confidently offer this high level of guarantee is due to the fundamental design differences of SunPower modules. Briefly, these design differences include the use of n-type silicon prevents early degradation due to LID. The thickly plated, tin coated copper foundation of the Maxeon cell is highly resistant against the forces of moisture and oxidation. This metal foundation allows for thinner, more flexible silicon, resulting in a cell which can withstand repeated snow and wind loading and can crack without significant power loss. Electroplating the metal directly onto the cell ensures a strong and uniform bond with low residual stresses. Cells are connected via an interconnect and three solder pads on the edges of each side of a cell, which provide relief for thermal expansion and a redundant electrical connection. Conventional Modules 2 connect the cells through a process intensive ribbon attachment. This difference gives the Maxeon cell extreme robustness against thermal cycling. Additionally, Maxeon cells have a low breakdown voltage which occurs uniformly across the cell. In a reverse-bias condition (shaded), thermal runaway is mitigated, regardless of whether or not bypass diodes are present. SunPower s X series modules, which make up an increasing portion of the product mix, has even better reverse bias characteristics, resulting in an even more shade tolerant module. 1 See for current warranty terms. 2 Definitions used throughout: Conventional Module or Conventional Panel is a 240W panel, 15% efficient, approximately 1.6 m2, made with Conventional Cells. Conventional Cells are silicon cells that have many thin metal lines on the front and 2 or 3 interconnect ribbons soldered along the front and back.
2 Finally, SunPower modules are highly resistant to potential induced degradation (PID), as shown through independent third party testing. The purpose of this paper is to define the criteria for a 40 year useful life and to share the experimental and analytical support underlying SunPower s expectation that the panels should have a useful life exceeding 40 years. Useful Life Defined SunPower defines the end of the useful life of a solar system installation as the time when 1% of the panels have dropped to below 70% power output. Said another way, 99% of modules are producing more than 70% of original rated power. This concept is similar to that used in equipment depreciation, where the useful life is the end of the period during which an asset will be used to generate revenues. There is no standard industry definition for useful life; however, this definition ensures that a site will continue to produce useful energy without incurring significant maintenance or large module current mismatch that will have a serious impact on the output of the solar field. In order to ensure this definition permeates into the product design cycle, SunPower has set this definition in requirements documents for module design and qualification. Experimental Data SunPower regularly tests its modules in various stresses meant to accelerate the degradation in the real world as part of its extensive qualification and reliability testing programs . Some summary test results are discussed below. Heat and Humidity The certification standard (IEC61215) test for the effects of moisture and humidity effects is the Damp Heat 1000 (DH1000) test, which places the product in an environmental chamber at 85⁰C and 85% relative humidity (RH) for 1000 hours. As with other certification requirements, this test is not designed to indicate reliability at 25 years; rather, it is intended to indicate a nominal level of safety in the field. Kempe more recently suggested  that hours may be more appropriate simulating 20 years in a hot and humid climate, such as Miami, Florida or Bangkok, Thailand. Assuming the conservative case that a module is in such a climate, 6000 hours would represent 40 years. Figure 1 shows data a Fraunhöfer Institute study, performed by TÜV and Fraunhöfer Institute, and published by Köhl , for a group of modules from seven unnamed Conventional Module manufacturers with at least 100MW of production per year in The plot shows performance after increasing hours of exposure to damp heat well beyond basic industry certifications. While well-built Conventional Modules fare well up to DH2000, shortly thereafter their power output (normalized by initial output) degrades significantly. SunPower performed testing in the same standard DH conditions (note SunPower s Reliability lab is certified by UL to carry out its own testing to UL standards). The black line shows that SunPower s current generation of modules degrade less than 3% after DH7500. SunPower s linear degradation indicates that the stress causes a slow and steady wear-out, as opposed to abrupt catastrophic failure.
3 Figure 1: Damp heat testing of seven Conventional and SunPower modules. The Conventional Modules in Köhl s study show a sharp power drop starting after 2000 hours, while SunPower modules remain relatively unaffected beyond 7000 hours. Equivalent years in a hot and humid environment (e.g. Bangkok)  are shown on bottom axis. Sensitivity analysis gives ±30% on 20 year equivalent time. The difference in performance under damp-heat stress is due to the design differences of the cells. Conventional Cells have thin metal lines on the sunny side to conduct current through the module, and those lines are susceptible to corrosion due to their necessarily small size (so as not to block the incoming photons), and their composition (silver paste). SunPower has no metal on the front of the cell, and the entire back of the cell is covered with a tin-plated copper foundation. The tin-plated copper is very resistant to corrosion, and the volume of metal is so large that even substantial corrosion stress causes very little change in the resistance of the circuit, providing high robustness against the effects of moisture. Temperature Cycling The industry-standard certification test for reliability against moisture and humidity effects is thermal cycling for 200 cycles (TC200), which places the product in an environmental chamber which swings from -40⁰C to 85⁰C 200 times. There is no consensus on the acceleration factor of this test due to the dependency on environmental factors, so it is difficult to relate number of cycles to years in the field. SunPower conducted a comparison using internal test data and data from Köhl s publication  (Figure 2). The results for the Conventional Module manufacturers vary substantially. While some manufacturers perform well for the period of testing; only degrading a few percent even at TC800, one product is down 10% by TC400, and down >25% by TC500; two other products are down 8%-9% by TC800. Note that all of these products pass the standard IEC certification standard of TC200. In contrast, SunPower s modules well in the test, exhibiting only 2% degradation at TC2000, ten times the duration of the IEC certification standard.
4 Figure 2: Thermal cycle testing of seven Conventional and SunPower Modules. The Conventional Modules in Köhl s study start to degrade steadily after 200 cycles, while SunPower remains practically unaffected at 2500 cycles. The primary reason that SunPower cells are more robust has to do with cell interconnection. The cell interconnect on a Conventional Cell is performed by soldering two or three metal ribbons at multiple points across the entire cell. Due to the difference in the amount of thermal expansion between the ribbon and the cell, stress can build up on the solder joints, which can act as initiation points for cracks and power loss . Further, a difficult to perform strain-relief bend should be applied between cells to extend the lifetime . In contrast, SunPower cells are connected with a strain-relieved copper bar and six solder pads per cell. Solder joints are small, so the mismatch from thermal expansion results in less stress in the joint. Further, multiple solder joints provide redundancy in case a single joint fails. Dynamic Loading SunPower s design qualification includes a dynamic load test (DLT), where a force of 2400Pa is repeatedly applied to the front and back of the module, deflecting it back and forth cyclically. This is equivalent to 50 lb/ft² (244 kg/m²) load or a sustained wind speed of 90mph (145kph) equivalent to a category one hurricane. This test is designed to ensure that a product can withstand a lifetime of shipping, installation, and environmental stresses. A side-by-side comparison of a Conventional Module and a SunPower module in this dynamic load test is shown in Figure 3. After 1000 cycles, the standard efficiency module shows several broken cells in the center, and a power loss of nearly 4%. The shunt resistance, an indication of module integrity, has dropped 25%. The SunPower module, on the other hand, shows no broken cells and no measurable power loss; the shunt resistance appears to have risen slightly but this is within the tolerance of flash testing accuracy.
5 Figure 3: Electroluminescent images flash test data after 1000 cycles of dynamic loading to 2400Pa (equivalent to 130mph (209kph) wind), conducted at SunPower. The Conventional Module (left) suffered from power loss while the SunPower module (right) was not significantly affected. Reverse Bias and Bypass Diodes When cells are put into reverse bias, instead of converting photons to electricity, they convert electricity to heat. This happens any time the current generated by the rest of the cells in the string of modules exceeds the current that a cell can support. Common causes of reverse bias are shading from leaves, chimneys, or the buildup of soiling along the bottom of a module. If too much heat is dissipated from a reverse bias cell, particularly if that heat is concentrated to a small defect region on the solar cell, the heating can cause failure of the other components within the module, such as the backsheet, glass, or encapsulant. Conventional Modules rely on bypass diodes to deactivate the portion(s) of the module where one or more cells are shaded, typically resulting in a 33% power drop. While this has a negative effect on energy output, it mitigates the heating issue. One tradeoff of this design is that the reliability of the module is tied to the bypass diode. Diode life depends on several factors such as diode quality, junction box handling, and module installation; but, all diodes will eventually fail with use. This is because an activated diode runs at an elevated temperature, reducing the remaining life of the diode , . Depending on how a diode fails, it can permanently remove a substring from the module or allow a shaded cell to run unmitigated in reverse bias, leading to module failure. SunPower s cells run in reverse bias at much lower temperatures, so bypass diodes are not required to ensure long term reliability (Table 1). However, when enough cells are in reverse bias, the cumulative power loss from the shaded cells can exceed the power produced from the cells in forward bias, so SunPower includes diode protection to enhance energy yield.
6 Table 1: Illustrative comparison of estimated cell power dissipation with one cell in reverse bias SunPower X21 SunPower E20 Conventional Module Module Power Number of cells I mp (STC, amps) V mp (STC, volts) V Rb (reverse bias, volts) Heat (W) % Module power remaining: with diode 96% 90% 67% 3 without diode 96% 90% 42% 1 V RB value from literature . 2 Power Rb = V Rb x I mp, all of this power is dissipated as heat. 3 % Power = Dissipated Watts / Module Power. Assumes diode shorts 1/3 of the Conventional Module when present. If diode does not activate, assumes power dissipates as heat. Estimate for comparison purposes only. The average power dissipation indicates the impact on module power, but it does not indicate the lifetime challenge when a cell is in reverse bias. For a SunPower cell, the heat dissipation is uniform over the surface area of the cell and the temperature rise is moderate. This is because the cell architecture places a heavily doped positive region immediately adjacent to a heavily doped negative region evenly across the back of the cell, resulting in a lower voltage potential for a cell in reverse bias. The design of the Conventional Cell places a heavily doped region at the top and bottom, with a lightly doped region in between. When the cell is forced into reverse-bias, the current finds the weakest point in the cell to get from the positive side to the negative side often at a small region along the edge of the cell creating a focused hotspot. For example, using the values in Table 1, and assuming a hotspot region of 9 cm², the Conventional Module has a heat flux of more than 15 W/cm². Higher heat flux causes results in higher temperatures, as shown in a recent study, where a Conventional Cell in reverse bias ran more than 70 C (159 F) hotter than an equivalently shaded Maxeon cell, causing irreversible damage to the Conventional Module. Summary of experimental data SunPower modules show significantly less degradation than Conventional Modules in the industry standard reliability stresses meant to simulate hot and humid environments and constant thermal cycling. Testing for the dynamic loading affects from shipping, installation, and field exposure also show less degradation. Finally, SunPower modules do not require a diode for safe operation in shaded conditions, removing the potential for a single point of failure.
7 Analytical Data In addition to reliability testing, SunPower engages in fundamental research, supported by both accelerated testing and field data. Years of research on all key degradation modes are integrated into a cell-by-cell, hour-by-hour performance model called PVLife which has been validated and published in scientific conference proceedings , , , . PVLife primarily models the physics of each failure mode it is not a statistical or reliability blockdiagram model. Instead, the intent is to solve for a specific system/array s degradation rate, given the module used, its electrical and physical configuration, its mounting, and the weather and irradiance expected. PVLife solves the coupled electro-thermal equations that predict module performance for a given set of weather conditions in order to obtain cell temperature and electrical parameters; at each hour of the day for every day of the system s life. It computes the incident spectrum, electrical operating point, and temperature of each individual cell. PVLife uses this electrical and thermal solution as input to physical models for the key degradation and failure modes and computes incremental degradation and chance for failure during each time-step in the simulation. Also, different modes are coupled via the electro-thermal solver. In order to determine the effects of different degradation modes, SunPower invested in years of fundamental research. Through experimentation and corroboration with field data, the underlying physics of failure for each mode were identified and quantified. The degradation modes modeled for SunPower modules are: Cell damage induced by ultraviolet (UV) radiation Photo-thermal encapsulant browning Polarization High-voltage degradation Soiling Other effects An example of a PVLife analysis for a SunPower module installed on a T0/Oasis tracker in a harsh desert location indicates less than 10% power degradation at fifty years (black line, Figure 4). The lower 90% confidence level, reflecting model uncertainties, shows less than 20% power degradation.
8 Figure 4: PVLife output for the current generation of Maxeon cells (solid line) in a utility installation and a desert climate. Lower 90% confidence level (dashed line) reflects the combined uncertainties from degradation modes. Module starting point is offset to match mean module power distribution above nameplate rating. Failure Modes Unlike degradation modes, failure modes do not cause appreciable degradation in performance until catastrophic failure. Two key failure modes govern the life of SunPower modules: Backsheet cracking due to relative humidity and hydrolysis Solder-joint failure due to temperature cycling Backsheet Failure PVLife conservatively defines the onset of an abrupt reduction of strength, as documented by McMahon , to a 100% chance of failure. McMahon showed that, as polymer chains break down due to humidity and heat, the entire polymer network slowly weakens to a critical point at which the tensile strength starts to decrease at an accelerated rate. This is conservative because at the critical point, the backsheet material still maintains at least 60-65% of its initial strength. Based on these criteria, the analysis indicates that SunPower backsheet materials are robust against this failure mode for well over 70 years (Figure 5) even in harsh desert climates.
9 Figure 5: Backsheet degradation, based on experimental data fit to McMahon s model, suggests sufficient backsheet strength for more than 40 years Solder Joint Failure SunPower conducted thermal cycling experiments with different temperature profiles. Using the failure time in these accelerated tests and an acceleration factor calculator, the lifetime distribution of solder joints in any given environment can be determined. Solder joint failure is expected to be the dominant end of life failure mode for SunPower modules. SunPower cells have three solder connections on each side of a cell. In the event that one solder joint fails, the power can travel through the other two, resulting in redundant cell interconnection. Failure for a module is considered to occur when the probability of all three solder joints on one side of a cell breaking is above 1%. Because current cannot pass through the substring, running instead through the bypass diode, the module power will fall below the 70% criteria.
10 Figure 6: results of solder joint sub-model show that the probability of module failure exceeds the 1% threshold after 70 years. Module failure is defined as all three joints on one side of a side of a cell within a module failing. PVLife Validation SunPower has deployed over 3GW of modules globally and manages two fleets of Conventional Modules from acquisitions, 240MW from twenty manufacturers and 500MW from a high quality European manufacturer. Recently, SunPower conducted a system level degradation study of 445 utility systems within the SunPower operating fleet . The study included 266 systems (86MW) using SunPower modules as old as 5.5 years, and 179 systems (42MW) using non-sunpower modules as old as 11.5 years. Data spanning back to the site commissioning date were used to determine fleet-wide degradation rates, representing 3.2 million module-years of monitored data. Black and Veatch, an independent engineering firm, audited the methods and results for the SunPower fleet . The annual system power degradation rate (AC side of the inverter) for SunPower systems using the previous generation of modules, was -0.32±0.05% (95% confidence) per year, and for non-sunpower Conventional Module systems was -1.25±0.05% (95% confidence) per year, and in both cases was shown to be constant with time. SunPower is currently collecting field data on its current generation of modules in order to conduct a similar analysis; however, these modules have not been fielded in significant quantities for enough time. PVLife estimates for the previous generation SunPower module compare well with laboratory accelerated testing data as well as field data obtained from various SunPower product monitoring efforts. These
11 results serve to validate the electro-thermal model, degradation sub-models, and increase the understanding of the coupled effects of degradation. The analyzed field data of the previous generation of SunPower modules compares very well with the PVLife simulations (Figure 7). Figure 7: Comparison of PVLife and analyzed field data from the previous generation of SunPower modules (yellow). PVLife compares well with field data. For reference, the degradation of Conventional Modules is included (grey). Summary of Analytic Data The physical model of degradation and catastrophic failure, which is backed up by field data and stress tests, suggests that SunPower modules should have a total degradation well under 30% over 40 years due to the primary degradation modes. Further, catastrophic module failure from backsheet delamination or solder joint failure should be well below 1% even after 40 years. SunPower continues to actively pursue design changes to reduce the impact of degradation and failure modes to further extend module lifetime.
12 Conclusion SunPower has invested heavily in module design, qualification, and analysis to design panels with an expected useful life exceeding 40 years. SunPower defines the end of the useful life of a solar system installation as the time when 1% of the panels have dropped to below 70% power output. Experimental data which emulate stresses seen in the real world show that SunPower modules are robust against a variety of stresses. Further, PVLife, a model which simulates hour-by-hour degradation in a particular climate and is based on years of fundamental research, was used to estimate degradation and failure rate for SunPower modules. PVLife has been validated through various comparisons against measured field data. These data suggest that it is reasonable to expect SunPower modules to have a useful life exceeding 40 years.
13 Bibliography  D. Degraaff, S. Caldwell, R. Lacerda, G. Buena, A. Terao, and D. Rose, Qualification, Manufacturing, and Reliability Testing Methodologies for Deploying High-Reliability Solar Modules, in European Photovoltaic Solar Energy Conference and Exhibition, 25th,  M. Kempe, J. Wohlgemuth, D. Miller, M. Reese, and A. Dameron, Modeling the Ranges of Stresses for Different Climates / Applications, in International PV Module QA Forum,  M. Köhl, K. Weiss, M. Heck, and D. Philipp, PV reliability : Results of a German four-year joint project Part I : accelerated ageing tests and modelling of degradation, in European Photovoltaic Solar Energy Conference and Exhibition, 24th,  J. Wendt, M. Träger, M. Mette, A. Pfennig, and B. Jaeckel, The Link Between Mechanical Stress Induced By Soldering And Micro Damages In Silicon Solar Cells, in European Photovoltaic Solar Energy Conference and Exhibition, 24th, 2009, pp  N. Bosco, Modeling Metal Fatigue As a Key Step in PV Module Life Time Prediction outline Modeling metal fatigue, in PV Module Reliability Workshop,  E. Maset, E. Sanchis-kilders, J. B. Ejea, A. Ferreres, J. Jordán, V. Esteve, P. Brosselard, X. Jordà, M. Vellvehi, and P. Godignon, Accelerated Life Test for SiC Schottky Blocking Diodes in High-Temperature Environment, IEEE Transactions on Device and Materials Reliability, vol. 9, no. 4, pp ,  S. Somisetty, P. Ersland, X. Yang, and J. Barrett, Reliability investigation and characterization of failure modes in Schottky diodes, Microelectronics Reliability, vol. 46, no. 8, pp , Aug  K. Bothe, K. Ramspeck, D. Hinken, C. Schinke, J. Schmidt, S. Herlufsen, R. Brendel, J. Bauer, J.-M. Wagner, N. Zakharov, and O. Breitenstein, Luminescence emission from forward- and reverse-biased multicrystalline silicon solar cells, Journal of Applied Physics, vol. 106, no. 10, p ,  M. Mikofski, M. Anderson, S. Caldwell, D. Degraaff, E. Hasselbrink, D. Kavulak, R. Lacerda, D. Okawa, Y. Shen, A. Tedjasaputra, A. Terao, and Z. Xie, A Dynamic Cell-by-Cell PV System Model to Predict Lifetime Performance and Reliability, in European Photovoltaic Solar Energy Conference and Exhibition, 26th, 2011.
14  M. A. Mikofski, D. F. J. Kavulak, D. Okawa, Y. Shen, A. Terao, M. Anderson, S. Caldwell, D. Kim, N. Boitnott, J. Castro, L. Ann, L. Smith, R. Lacerda, D. Benjamin, and E. Hasselbrink, PVLife : An Integrated Model for Predicting PV Performance Degradation over 25 + Years, in IEEE Photovoltaic Specialists Conference, 38th, 2012, no. 3, pp  E. Hasselbrink, M. Anderson, Z. Defreitas, M. Mikofski, Y.-C. Shen, S. Caldwell, A. Terao, D. Kavulak, Z. Campeau, and D. DeGraaff, Validation of the PVLife Model Against 3 Million Module-Years of Live Site Data, in IEEE Photovoltaic Specialists Conference, 39th,  E. F. C. Hasselbrink, D. Ph, C. Mark, D. F. J. Kavulak, D. Okawa, Y. Shen, A. Terao, M. Anderson, W. Caldwell, D. Kim, N. Boitnott, L. Ann, L. Smith, and R. Lacerda, Module Lifetime Prediction through Integrated Modeling of Known Failure Modes, in PV Module Reliability Workshop, 2012, pp  W. McMahon, H. A. Birdsall, G. R. Johnson, and C. T. Camilli, Degradation Studies of Polyethylene Terephthalate, Journal of Chemical Engineering Data, vol. 4, pp ,  M. Anderson and Z. Defreitas, A SunPower Fleet-Wide System Degradation Study using Year-over-Year Performance Index Analysis,  R. Romero, Review of SunPower Fleet-Wide System Degradation Study using Year-over- Year Performance Index Analysis SunPower Corporation. All rights reserved. SUNPOWER, the SUNPOWER logo, and MAXEON are trademarks or registered trademarks of SunPower Corporation in the U.S. and other Countries.
SunPower Module Degradation Rate Summary Section I provides a detailed design comparison showing that the integrated back contact design of SunPower Maxeon solar cells makes them inherently more robust
MECHANICAL STABILITY OF SOLAR CELLS WITHIN SOLAR PANELS S. Pingel, Y. Zemen, O. Frank, T. Geipel and J. Berghold SOLON SE, Am Studio 16, 12489 Berlin, Germany Tel.: +49 30 81879-0, Fax: +49 30 81879-9999,
SHARP SOLAR Frequently Asked Questions for PV Integrators Revised 05/04/2010 How do I determine the PTC rating of a module? PTC refers to PVUSA Test Conditions, which were developed to test and compare
2 nd Atlas/NIST PV Materials Durability Workshop November 13 14 Acetic acid production rate in EVA encapsulant and its influence on performance of PV modules Tsuyoshi Shioda Mitsui Chemicals, Inc. Outline
Product or Process Modifications Requiring Limited CBTL Retesting to Maintain Certification This document sets forth a uniform approach to maintain the certification of products that have, or will, undergo
Materials Matter For Higher Returns Innovating Photovoltaics: the Way Ahead Solar Europe Industry Initiative Milan, May 7th, 2013 Stephan Padlewski, PhD Marketing Manager, EMEA DuPont Photovoltaic Solutions
Dynamic mechanical load testing Solar Power International Workshops on Bankability Chicago, IL October 21, 2013 Geoffrey S. Kinsey, Ph.D. Director of PV Technologies Fraunhofer Center for Sustainable Energy
Technology Advantage 2 FIRST SOLAR TECHNOLOGY ADVANTAGE 3 The Technology Advantage Cadmium Telluride (CdTe) photovoltaic (PV) technology continues to set performance records in both research and real-world
VISHAY GENERAL SEMICONDUCTOR www.vishay.com Rectifiers IMPORTANT CHARACTERISTICS OF BYPASS DIODES FOR PHOTOVOLTAIC SOLAR CELLS 1. Forward Voltage Drop (V F ) at Bypass The basic function of bypass diodes
1 Long-term performance of photovoltaic modules Artur Skoczek 2 The European Solar Test Installation (ESTI) has the primary objective of providing the scientific and technological basis for a sound and
Preserve the sun s energy. BP Solar warranties Safeguarding your investment in solar BP Solar s energy solutions are a great investment in forward looking and environmentally responsible technology. Now
predictive energy modeling with solarworld and pvsyst America s Authority on Solar SolarWorld PVsyst Results 1 introduction As one of the largest and most established vertically integrated photovoltaics
Solar Cell Optimization: Cutting Costs and Driving Performance 1 Executive Summary Over the past several years, DC optimizers have become an important technological ingredient in many residential, commercial
International PV QA Task Force (PVQAT) Sarah Kurtz representing many people SOPHIA Workshop Freiburg, Germany June 3 4, 2014 NREL/PR-5J00-62136 NREL is a national laboratory of the U.S. Department of Energy,
We're with you... FOR THE LIFE OF THE SYSTEM 25 YEAR WARRANTY * Electricity prices are predicted to continue to rise in the future. If you're serious about installing energy in your home, look no further
What are the basic electrical safety issues and remedies in solar photovoltaic installations? Presented by: Behzad Eghtesady City of Los Angeles Department of Building and Safety Topics Covered Photovoltaic
SUNPOWERCORP.COM US HEADQUARTERS SunPower Corporation 3939 N. 1st Street San Jose, California 95134 USA 1-800-SUNPOWER sunpowercorp.com MORE POWER. A BETTER INVESTMENT. Established Incorporated in 1985
INTERNATIONAL STANDARD IEC 61215 Second edition 2005-04 Crystalline silicon terrestrial photovoltaic (PV) modules Design qualification and type approval This English-language version is derived from the
Design qualification and type approval of PV modules acc. to IEC 61215:2005 / IEC 61646:2008 TÜV Rheinland Immissionsschutz und Energiesysteme GmbH Renewable Energies 2009-01-22 January 2009 Design qualification
Exercise 2 The Solar Panel (Photovoltaic Panel) EXERCISE OBJECTIVE When you have completed this exercise, you will be familiar with the operation of the silicon photovoltaic (PV) cell. You will be introduced
Polymer Termination An alternative termination material specifically designed to absorb greater levels of mechanical stress thereby reducing capacitor failures associated with mechanical cracking Mechanical
EVALUATING SOLAR ENERGY PLANTS TO SUPPORT INVESTMENT DECISIONS Author Marie Schnitzer Director of Solar Services Published for AWS Truewind October 2009 Republished for AWS Truepower: AWS Truepower, LLC
Design qualification and type approval of PV modules TÜV Immissionsschutz und Energiesysteme GmbH Test Centre for Energy technologies May 2003 Design qualification and type approval of PV-modules in accordance
Photovoltaic Panel Bypass Diode Protection Sweetman (Soo Man) Kim - Vishay Diodes Market Development Introduction Most solar panels are assembled as photovoltaic (PV) panels attached to glass or poly-carbonate,
t DARK CURRENT-VOLTAGE MEASUREMENTS ON PHOTOVOLTAC MODULES AS A DAGNOSTC OR MANUFACTURNG TOOL D. L. King, 6. R. Hansen, J. A. Kratochvil, and M. A. Quintana Sandia National Laboratories, Albuquerque, NM
Application Note, V1.0, May 2005 Automotive MOSFETs in Linear Applications: Thermal Instability by Peter H. Wilson Automotive Power N e v e r s t o p t h i n k i n g. - 1 - Table of Content 1. Introduction...
EMERGENCY POWER SOLAR CELLS Solar panels require no fuel other than sunlight. They produce no emissions, no fumes and have no rotating parts. Other than an occasional wipe down to remove dust, they are
Solar Photovoltaic (PV) Cells A supplement topic to: Mi ti l S Micro-optical Sensors - A MEMS for electric power generation Science of Silicon PV Cells Scientific base for solar PV electric power generation
Module information for arpa-e ADEPT workshop, Washington, D.C. 2-8-2011 Doug Rose SunPower Corporation 2011 SunPower Corporation Common solar module construction Glass Low iron AR/Non-AR (environmental
PV module safety qualification according to IEC 61730:2004 EN 61730:2007 TÜV Rheinland Immissionsschutz und Energiesysteme GmbH Renewable Energies January 2009 Version 2009-01-22 Overview The long term
Materials Matter Better long-term PV system performance and higher financial returns As Lifetimes Improve, Investment Returns Improve. DuPont PV Materials Stand the Test of Time. The world s demand for
REC QUALITY: BEYOND EXPECTATIONS Ensuring industry-leading standards of solar panel quality Contents Introduction to REC A look at who we are and our facilities Exceeding International Standards How REC
PARTIALLY SHADED OPERATION OF A GRIDTIED PV SYSTEM Chris Deline National Renewable Energy Laboratory, Golden, CO ABSTRACT Partial shading of a PV installation has a disproportionate impact on its power
POTENTIAL INDUCED DEGRADATION OF SOLAR CELLS AND PANELS S. Pingel, O. Frank, M. Winkler, S. Daryan, T. Geipel, H. Hoehne and J. Berghold SOLON SE, Am Studio 16, 12489 Berlin, Germany ABSTRACT Since solar
Everline Module Application Note: Round LED Module Thermal Management PURPOSE: Use of proper thermal management is a critical element of Light Emitting Diode (LED) system design. The LED temperature directly
PV Module Electroluminescence: Enlightening Defects Michael Reuter a, Liviu Stoicescu b, Jürgen H. Werner a,b a Steinbeiszentrum Photovoltaik, Stuttgart, Germany b Insitute for Photovoltaics, University
PVWATTS DERATING FACTORS FOR SOLARBRIDGE PANTHEON MICROINVERTERS AND ACPV SYSTEMS AUTHOR Vincent Bartlett Senior Member of Technical Staff Version 1.5 March 22, 2013 SolarBridge Technologies 1 INTRODUCTION
Blocking Diodes and Fuses in Low-Voltage PV Systems John C. Wiles, Southwest Technology Development Institute, and David L. King, Sandia National Laboratories Presented at the 26th IEEE Photovoltaic Specialists
SolarCity Photovoltaic Modules with 35 Year Useful Life Andreas Meisel 1, Alex Mayer 1, Sam Beyene 1, Jon Hewlett 1, Karen Natoli Maxwell 1, Nate Coleman 1, Frederic Dross 2, Chris Bordonaro 3, Jenya Meydbray
GENERAL INSTALLATION MANUAL FOR EGING PV MODULES PLEASE READ THIS MANUAL CAREFULLY BEFORE INSTALLING OR USING THE MODULES. PLEASE PASS ALONG THE ATTACHED USER MANUAL TO YOUR CUSTOMER. 1. INTRODUCTION This
Exercise 5 Effect of Shading on Solar Panel Operation EXERCISE OBJECTIVE When you have completed this exercise, you will be familiar with the effect of shading on solar panel operation. DISCUSSION OUTLINE
403 Hitachi Review Vol. 63 (2014), No. 7 Featured Articles O&M Service for Megasolar Power Plants and Precise Monitoring Techniques for PV Modules Tohru Kohno Tetsuharu Ohya Tomoharu Nakamura OVERVIEW:
High Resolution Spatial Electroluminescence Imaging of Photovoltaic Modules Abstract J.L. Crozier, E.E. van Dyk, F.J. Vorster Nelson Mandela Metropolitan University Electroluminescence (EL) is a useful
Figure at left Ut alissen dignibh esse dipsumsan velisse tem zzriliquis alit lore facidui etum zzrillan hendignit, ver irit augait luptat faccum iliquatue facilit aliquis molore. Photovoltaic String Inverters
Systems Operating at High DC:AC Ratios WHITE PAPER Abstract Recent trends in the PV industry have been towards an increasing DC:AC ratio, where the AC conversion capacity attached to a PV system is significantly
Why a Qualification Test Can NOT be used for Lifetime Assessment and Proposal for Pathway to Standard for Lifetime Assessment Sarah Kurtz (NREL) Solar Power International Anaheim, CA Sept 14, 2015 NREL/PR-5J00-65080
Mater. Res. Soc. Symp. Proc. Vol. 1493 2013 Materials Research Society DOI: 10.1557/opl.2013. 221 Comparison of multi-crystalline silicon PV modules performance under augmented solar irradiation Yang Hu
Changing the way our world is powered. TRUSTED SOLAR SOLUTIONS FOR YOUR HOME. Since 1985 SunPower has been leading global solar innovation. SunPower solar panels consistently deliver more energy and long-term
ANALYSIS 2: Photovoltaic Glass Replacement Problem Identification Bridgeside II is designed to accommodate 80 percent lab space and 20 percent office space. Laboratory equipment can consume a considerable
Application Note PVA-600-1 Guide To Interpreting I-V Curve Measurements of PV Arrays March 1, 2011 Copyright Solmetric Corporation, 2010 http://www.solmetric.com All Rights Reserved. Reproduction, adaptation,
43 rd IEEE Photovoltaic Specialists Conference, June 5-10, 2016, Portl, USA 1 MWT CELLS FOR SHADE-LINEAR, DIODE-FREE MODULES B.K. Newman, E. Bende, J. Loffler, J. Wang, J. Zhai, D. Liu, Z. Wang, Y. Chen,
: String sizing Conext CL Series 965-0066-01-01 Rev A DANGER RISK OF FIRE, ELECTRIC SHOCK, EXPLOSION, AND ARC FLASH This Application Note is in addition to, and incorporates by reference, the installation
Solar Fundamentals Solar power investment decision making Chilean Solar Resource Assessment Antofagasta and Santiago December 2010 Edward C. Kern, Jr., Ph.D., Inc. Global Solar Radiation Solar Power is
Silicone Compounds for High-Voltage Insulators: HPS Testing of Silicone Compounds Part 2 of a 2-Part Series by Hubbell Power Systems R. ALLEN BERNSTORF, PRINCIPAL ENGINEER, INSULATORS DAVID RYAN, POLYMER
Solar energy......solar technology in endurance testing Solar & Photovoltaic systems - Environmental testing...... we are your partner Energy generated by the sun (solar energy) is considered forward looking
FEATURES High pulse loading capability Small size. APPLICATIONS Where high resistance, high stability and high reliability at high voltage are required High humidity environment White goods Power supplies.
Photovoltaic modules - current status, further trends and reliability issue Jörg Bagdahn Fraunhofer Center for Silicon Photovoltaics CSP Anhalt University of Applied Sciences Agenda Fraunhofer Center Silicon
Best Performance/Cost Ratio LED Flip Chip COB Module Brighter and Cooler Lower Thermal Resistance & Junction Temperature Apollo 600 Chip on Board is a high-performance LED module based on Flip Chip Opto
Originally published in the Canadian Welding Association Journal, Spring 2013, pp 30 39 Welding on In service Pipelines: Dispelling Popular Myths and Misconceptions Bill Amend Sr. Principal Engineer, Welding
PERFORMANCE OF MPPT CHARGE CONTROLLERS A STATE OF THE ART ANALYSIS Michael Müller 1, Roland Bründlinger 2, Ortwin Arz 1, Werner Miller 1, Joachim Schulz 2, Georg Lauss 2 1. STECA ELEKTRONIK GMBH, Mammostr.
H2Engineering, Inc. 114 East Fifth Avenue Tallahassee, FL 32303 Phone 850.224.7922 Fax 850.224.5876 ADDENDUM #1(BID PACKAGE # 3) To: Jeff Williams From: Peter Lindstrom Co: Leon County Date: October 04,
The Current status of Korean silicon photovoltaic industry and market 2011. 3.17 Sangwook Park LG Electronics Inc. contents 1.Introduction (World PV Market) 2.Korean PV market 3.Photovoltaics in LG Electronics
Review on the Thermographic analysis of PV panels/system using the infrared thermal cameras Prathmesh Mayekar 1, Mrs. N. J. Kotmire 2, Mahesh Wagh 3, Nilkanth Shinde 4 1 Research Scholar, Energy Technology,
INNOVATIVE SOLAR STRATEGIES The Importance of Energy Solutions Providers WHITE PAPER MORE ENERGY. FOR LIFE. INTRODUCTION Over the last several years, energy markets have dramatically changed, and the solar
ADVANCING SOLAR TECHNOLOGY u Enabling thin wafers for today s high efficiency silicon solar cells IL-RTS In-Line Rapid Thermal Shock ABSTRACT: Reducing consumption of silicon through the use of thin wafers
The Importance of Accurate Lifetime Assessment to PV Investors Jon Previtali Wells Fargo Environmental Finance Solar Power International September 2015 Wells Fargo s Investment in Solar $1,600 350 $1,400
WELCOME TO SUNPOWER Why Partner with SunPower? Worldwide footprint Over 500 systems on 4 continents Over 1 GW of solar manufactured Over 85 patents and 25 years of R&D Over a quarter century of experience
Integrated Technology, Inc. ESD CONSIDERATIONS IN HIGH SPEED CIRCUITS APPLICATION NOTE AN-123 By Stanley Hronik INTRODUCTION The primary cause of component failure in high speed logic circuits is electrostatic
ENERGÍA SOLAR TÉRMICA Y FOTOVOLTAICA: MÓDULOS, PANELES Y COMPONENTES PRINCIPALES The role of manufacturer s in the quality of PV products Aarón Sánchez Juárez ANES Vicepresidente Researcher at: Renewable
Cell-to-Module Gains and Losses in Crystalline Silicon PV Andrew Gabor Gabor Photovoltaics Consulting, LLC July 10, 2013 - Intersolar NA 1 Some material sourced from 2 Outline Background Loss/Gain Types
SECTION 13650 Photovoltaic (PV) Glass PART 1 GENERAL 1.01 WORK TO BE PERFORMED A. Provide all labor, materials, tools, and equipment to complete the installation of the PV Glass system. B. Install, equip,
SOLAR ELECTRIC MODULE ES-124 & ES-62T Owners Manual and Installation Guide circuit. Reverse connection will damage the module and may result in fire. CAUTIONS Solar electric modules produce DC electricity
Residential Solar Service Agreement (RSSA) Customer Sited Solar Photovoltaic Systems This Agreement is made and entered into this day of, 20, ( Effective Date ) by and between the Orlando Utilities Commission
Solar energy... Solar technology in endurance testing Weiss Umwelttechnik GmbH Simulationsanlagen Messtechnik Solar & Photovoltaic Systems Environmental Testing...... we are your partner Energy generated
12 SOLAR PHOTOVOLTAIC POWER by John Ware IT IS PLANNED for BS 7671:2008 to include a new Section 712 providing additional requirements for safety applicable to solar photovoltaic (pv) power supply systems.
Annexure-A 32/1/2013-14/PVSE(Part-II) Ministry of New and Renewable Energy SPV Off Grid Division Scheme: Installation of 10,000 nos. of solar photovoltaic water pumping systems for irrigation purpose implemented
Photo: TÜV Rheinland In the PV+Test mechanical loading tests, solar photovoltaic modules are first subjected to a load of 2,400 pascals and then to 5,400 pascals. A new entry in the list of the best modules
Your consent to our cookies if you continue to use this website.