1 2003 Emerson Process Management. All rights reserved. View this and other courses online at Operations & Maintenance 201 Using online monitoring and predictive diagnostics to reduce maintenance costs In this course: 1 Overview 2 Rotating Equipment Monitoring Technologies Online and Offline Monitoring 3 Field Instruments The Smart Instrument Advantage 4 Valves Diagnostics to Minimize Valve Maintenance Cost 5 Process Equipment 6 Now or Later 7 Operators and Maintenance Costs 8 Monitoring for Control Problems Overview Online monitoring, diagnostic tools, and intelligent digital field devices and plant equipment can help boost maintenance productivity. They deliver this advantage by enabling you to: See what s happening in your process and your equipment Detect and identify conditions that could lead to problems Deliver the right information to the right people at the right time As a result, you can take action to keep things running smoothly, efficiently, and profitably. With the ability to see what's actually happening and about to happen in your process and equipment, your operators and maintenance technicians no longer have to spend as much of their time reacting to unexpected events (caused by problems they didn't know about), or trying to find and fix problems that may not even exist.
2 Instead, they can focus on more productive tasks, like heading off problems they know are on the way, and finding new ways to reduce costs and improve performance. In fact, people who use online monitoring and diagnostic tools consistently report 40%+ reductions in maintenance cost, and 90%+ reductions in troubleshooting time. This course looks at some examples of how online monitoring, intelligent devices, and predictive diagnostics make this possible for rotating equipment, field instruments, valves, and process equipment. Hint As you go through the topics in this course, watch for answers to these questions: How can you use online monitoring and predictive diagnostics to help reduce maintenance costs? What tools are available to improve operator productivity so that they do not spend much of their time and talent reacting to unexpected maintenance situations? Rotating Equipment In most process plants, rotating equipment tends to be the least reliable component. Half of equipment failures that cause downtime typically involve mechanical equipment such as pumps, motors, compressors, and turbines. Rotating equipment maintenance cost can be significantly reduced by monitoring all candidate assets continuously with technologies such as vibration monitoring. Monitoring them periodically with technologies such as walk-around vibration monitoring, lube oil analysis, and thermography can also help. Benchmark studies show that companies monitoring 90% of candidate rotating equipment assets have maintenance costs up to two-thirds lower than companies that monitor only 60% of candidate assets.
3 Rotating Equipment >> Monitoring Technologies An effective monitoring program for rotating equipment uses multiple technologies. No single monitoring technique gives a comprehensive picture of rotating equipment health. By using multiple, complementary monitoring technologies, a clear picture of rotating equipment health and performance can be obtained. Vibration monitoring is a commonly used monitoring technology. However, other techniques are complementary to vibration monitoring and they should be implemented as a part of a comprehensive monitoring program. Lube oil analysis is the key to detecting conditions that cause deterioration before it starts. Key conditions to be monitored are oil contamination and oil chemistry. If contamination and oil chemistry issues are caught at an early stage, deterioration can be avoided. The cost of lube oil analysis and lubrication replacement is very small compared to the cost of failure downstream. Wear particle analysis can be combined with online vibration monitoring to reduce cost by locating internal damage and estimating the extent of the damage. For example, vibration monitoring that can detect an increase in high frequency noise alerts you to early bearing failure. However, wear particle analysis can show bearing wear at an earlier stage when less damage has occurred. In addition, the size and shape of wear particles can show the cause and severity of the damage, and the composition of the wear particles can isolate the location of the damage to specific components. Thermography can detect many problems ranging from steam leaking and insulation breakdown to electrical, wiring, and excess friction problems. For example, thermography can detect local hot spots that can indicate potential problems in motor windings. Motor current analysis can detect power problems that reduce motor life through excess loads or power imbalance that stresses parts of the motor.
4 Rotating Equipment >> Online and Offline Monitoring Online monitoring provides the most comprehensive early warning because it is able to provide a continuous flow of real-time information about what's happening in the equipment. It has the potential to detect conditions leading to deterioration before it actually starts. Assets that are critical to production, or have a high repair cost if failure occurs, should be monitored online. Continuous monitoring by permanent sensors, but with walk-around data collection, is the next best choice. This can detect and record transient events that can cause damage even if they are not reported immediately. Walk-around monitoring with temporary sensors is the third choice. Transients may be missed, and portable sensors such as magnetically coupled vibration sensors do not have the sensitivity or frequency response of permanently mounted sensors. This reduces the sensitivity to initial failure conditions. Walk-around monitoring may be appropriate for less critical assets or assets with lower repair cost. Maintenance scheduling is also an important factor in reducing maintenance cost. Rotating equipment is subject to rapidly escalating collateral damage. It is important that maintenance be performed before damage occurs. The solution is to increase the frequency of monitoring as equipment wear accumulates. The PlantWeb Advantage In the PlantWeb architecture, the AMS Suite: Machinery Health Manager combines online monitoring information with a range of analytical tools to identify rotating equipment that needs service urgently. The AMS Suite: Machinery Health Manager uses vibration monitoring, IR thermography, oil analysis, ultrasonics, and motor diagnostics to give you a better view of actual condition of rotating equipment. Bearing failure, for example, is a common problem with rotating equipment. PeakVue software can detect and identify very high-frequency noise associated with early bearing wear. You get warning of problems before accumulating damage that can significantly increase the cost and time for repairs.
5 Field Instruments Field instruments such as transmitters and analyzers are quite reliable, but there are so many of them in the typical plant that total device maintenance costs are high. However, most instrument maintenance is not required. To reduce device maintenance cost, you can: Use online monitoring and predictive intelligence to eliminate unnecessary maintenance Monitor devices online to eliminate routine field checks Automate scheduled maintenance procedures Extend the interval between scheduled maintenance activities such as calibrations Automate data capture during maintenance Field Instruments >> The Smart Instrument Advantage Smart instruments, when monitored online, help automate maintenance procedures. For example: If you suspect a functional or performance problem, you can check instrument health using asset management software before going to the field. If devices check out, unnecessary maintenance is eliminated. Many smart devices diagnose their own health and provide alerts if maintenance is needed or performance is deteriorating. On these types of devices, routine checks can be eliminated. Scheduled maintenance activities can frequently be automated using a capability called "methods." A method will automatically execute many maintenance activities such as sensor trims, and provide guidance to the maintenance technician where human interaction is needed. Methods are device specific and can both improve the speed of maintenance and reduce or eliminate errors. You can also use smart calibrators and calibration management software. These tools help you to: Optimize calibration routes Automate calibration procedures Review calibration as-found and as-left information and extend the time between calibration for devices that don't drift over time. Capture maintenance activity results automatically for upload into the asset management system. These results can include calibration data; documentation of methods executed; and time, date, and personnel information. Using smart calibration techniques reduces typical device calibration time by 50%. In addition, the typical interval between calibrations can be doubled. The result can be a 75% reduction in instrument calibration cost. These changes can cut device maintenance cost and increase productivity dramatically.
6 The PlantWeb Advantage The proven reliability of PlantWeb's Rosemount, Rosemount Analytical, and Micro Motion transmitters reduces maintenance needs right from the begining. Built-in performance monitoring and diagnostics in these devices help you focus your maintenance efforts where they are needed. For example, transmitters can fail if electronics are exposed to excessive temperatures. But temperature monitoring and alarming in PlantWeb instruments can alert you about the problem in time. This can help you to find the cause and remedy it. Similarly, the sensor fouling detection diagnostic in our ph transmitters can trigger a maintenance request before fouling causes process problems or even automatically initiate cleaning of the sensor. AMS Suite: Intelligent Device Manager software consolidates all information related to valves and instruments for easy access. It also provides a robust, user-friendly tool for many maintenance tasks, from initial device configuration through troubleshooting and record keeping. For example, the software's remote monitoring and diagnostic capabilities dramatically increase the speed of equipment checks. What might have been a 25-minute check in the field becomes a two-minute task. This task can be performed online from the maintenance shop or control room without exposing workers to hazardous environments. AMS Device Manager software also helps cut instrument calibration time almost in half, from an average of 47 to 25 minutes. And its automatic documentation of maintenance tasks virtually eliminates the manual data entry that eats up so much "wrench time." Valves Eliminating unnecessary rebuilds and maintenance can reduce valve maintenance cost. Repeated studies show that between two-thirds and three-fourths of valves are rebuilt when they could be fixed by making some adjustments without removing the valve from the line. Many valves pulled for service need no maintenance at all. The key to reducing valve maintenance cost is to know the valve's actual condition. One low-cost way to determine valve condition is by using smart valve instruments, such as digital valve controllers. There are three levels of functionality available: Level 1. A valve diagnostic tool can be connected to the smart valve instrument by the signal wires. The diagnostic sweep is conducted one valve at a time from the maintenance shop. This reduces cost, as the maintenance technician need not be physically present near the valve. Level 2. A smarter diagnostic tool combined with a smart valve instrument can batch valves for testing. With this capability, several valves are selected as a group, and valve diagnostics are run automatically testing one valve at a time. The technician is free to do other work while a report for each valve is compiled. Level 3. Using continuous valve diagnostics in a running process is least expensive. The smart valve instrument continuously performs self-diagnostics while the process runs. In addition, many on-demand diagnostics can be executed while the process is online identifying problematic valves and alerting maintenance. This maximizes maintenance resource productivity and minimizes downtime.
7 If the valve is not equipped with a smart valve instrument, valve condition is typically determined by performing valve diagnostics using PC-based tools. These tools are connected to a valve, and the valve is stroked to determine condition. Disadvantages of this technique are that the valve must be removed from service, and the tools brought to the field and connected to the valve. In addition, these tools can be used only on one valve at a time. This is expensive, but much less than unnecessary valve rebuilds. Valves >> Diagnostics to Minimize Valve Maintenance Cost Valve diagnostics can not only alert you to existing problems, but also to conditions that can lead to future wear-related problems. This plot indicates that friction will exceed the recommended limit in one month. This will enable you to schedule replacement of the valve packing before process quality, availability, or throughput is affected. A simple green, yellow, and red valve status indicator shows if the valve needs future maintenance, needs maintenance now, or has failed. On-line diagnostics are continually running in the background during the valve's normal process operation. Detailed information on the bottom of the Event Log gives plant personnel meaningful and actionable information. Advanced diagnostics give a valve health summary with a simple "green, yellow, red light" indicator. Green is healthy, yellow is maintain soon, and red is maintain now. Diagnostics also give probable causes and fixes for valve problems. This reduces troubleshooting time, and helps technicians fix problems correctly and quickly.
8 The PlantWeb Advantage In the PlantWeb architecture, valve diagnostics can tell you (often while the valve is still in service) if conditions like seat wear, packing friction, or air supply leakage are approaching the point where maintenance is needed. This capability both minimizes maintenance cost, and helps maintain valve performance at the levels necessary to achieve needed quality and throughput. The net result is higher first pass production levels and lower operations and maintenance cost. Process Equipment There are two primary avenues to reduce maintenance cost for process equipment such as turbines, pumps, and compressors. One avenue is to have better process control to reduce process extremes. Temperature and pressure cycling, for example, can stress plant equipment. They can also cause premature degradation in unexpected places such as catalyst beds. Better process control will reduce variability. This minimizes the chance for the process to exceed constraints and place equipment under undue stress. The second avenue to reduce maintenance cost is to monitor plant equipment for performance and efficiency. Performance monitoring is available for equipment as diverse as boilers, heat exchangers, pumps, compressors, turbines, and columns. All these are subject to periodic maintenance to clear scaling, fouling, or plugging. By monitoring actual performance of these assets, and performing maintenance only when performance deteriorates, maintenance cost can be reduced. Monitoring actual performance of process equipment can reduce maintenance cost. A heat exchanger was scheduled for maintenance, but based on performance, maintenance was deferred. If heat exchanger efficiency or capacity were deteriorating, the plot would drop over time.
9 Now or Later Maintenance cannot always take place as soon as a potential problem is first detected. Production needs often require equipment to remain in operation even if it needs maintenance. That's possible when predictive diagnostics let you see that the equipment will continue to safely deliver adequate performance until the next scheduled downtime. In that case, you can weigh the value of continued production against the potentially higher repair costs and performance degradation from leaving the equipment in service. Effective index shows equipment efficiency. Deviation cost shows cost of inefficiency. By using the two, the optimum time for maintenance can be predicted based on production versus cost. Similarly, if asset health is predicted to deteriorate below acceptable levels before the next scheduled downtime, performing maintenance during a current shutdown before it is actually needed may be more profitable. Operators and Maintenance Costs Operators can significantly affect maintenance cost. They can increase cost by operating equipment in ways that cause excess stress and wear, and by initiating maintenance requests when equipment is operating correctly. This is typically caused by a lack of operating tools that determine if equipment is operating within limits and performing correctly. Without these tools, operators must develop a "feel" for the process. Maintenance requests are frequently based on the operators' impressions. Most of these maintenance checks find no problem. Such "no problem" checks are expensive, as they must be comprehensive to really determine if there is a fault. If, however, operators have easy access to basic information on the health and performance of both the control and physical assets of the plant such as transmitters, valves, rotating equipment, and process equipment, they can work more effectively with the maintenance team to identify and prioritize actual maintenance needs. For example, digital communications using protocols such as FOUNDATION fieldbus provide status information with the process variable. This information shows if the variable is good, bad, or uncertain. With this information the operator can verify if a value is good without performing a check at the device. This way, operators know that they are controlling on "known good information."
10 Although operators can take advantage of easy access to asset health and performance information, it is also important not to overwhelm them with data they don't need especially when they're busy dealing with abnormal process situations. For that reason, asset-related alerts should be sent to operators only when an equipment problem is known and may affect process operation. Tools such as the AMS Suite: Asset Portal give operators a quick view of the health of a broad variety of plant assets. When operators can verify equipment health without a check by maintenance, work requests and overall maintenance costs are reduced. The PlantWeb Advantage Operators can also easily check equipment condition to anticipate and adjust for potential problems. The AMS Suite: Asset Portal provides an integrated, high-level view of information on valves, instruments, rotating equipment, and process equipment in a single browser-based interface. This access to predictive diagnostics and other asset data also enables operators to determine when equipment health is (or, more likely, is not) causing process problems. When process or equipment problems occur, PlantWeb Alerts notify the right people without flooding operators with unnecessary alarms. This capability relies on powerful software in Emerson field devices, AMS Suite software, and DeltaV and Ovation systems to immediately: Analyze the incoming information Categorize it by who should be informed Prioritize it by severity and time-criticality Inform the recipients about what is wrong and advise them what to do about it in clear, everyday language
11 Monitoring for Control Problems Identifying and reducing process control problems especially excess variability can help reduce maintenance costs. Identifying excess, correctable variability All processes have some variability. It is impossible to eliminate it. However, process variability is frequently in excess of what is optimum. Excess process variability contributes to higher maintenance costs in a variety of ways. It ranges from equipment stress leading to failures, to creating an operator demand for more equipment checks. By monitoring loop performance, automatically calculating actual versus minimum variability, and making that information available to the operator, loops in need of improvement can be identified and fixed. This will reduce variability-induced equipment stress and wear, and maintenance costs associated with that equipment. More importantly, if an operator feels that a loop is not responding properly, but a check on variability shows good control, a maintenance check can often be eliminated. It is important to understand that although reducing variability can help quality and throughput, it may carry potential maintenance cost. For example, a faster control execution cycle or more aggressive tuning can reduce variability. It may also cause the valve to move much more frequently. This accelerates valve wear. A majority of loops with excess variability can be improved, however, without a significant effect on asset life or maintenance cost. In many cases, a reduction in variability will increase the life of assets. Identifying other control problems Loops may not respond as expected due to conditions such as being control limited, or because associated loops are in the incorrect mode. If these causes are not identified, equipment problems may be suspected, and maintenance checks performed. By identifying control problems, corrective action can be taken by changing mode, tuning, or using other options before maintenance is called for. Monitoring equipment for health and performance can reduce maintenance cost by half, reduce troubleshooting time by 90%, improve first pass quality, and improve throughput. This makes online monitoring and diagnostics one of the most powerful techniques available to improve plant profits. [End of course]
2002 Emerson Process Management. All rights reserved. View this and other courses online at www.plantwebuniversity.com. Maintenance 101 Understanding maintenance strategies Overview Why do I need a strategy?
ISA108 Intelligent Device Management (IDM) Intelligent Digital Devices - Have Self-Diagnostics and More Eight-channel two-wire temperature transmitter Intelligent two-wire on/off valve 2 Fully integrated
Cooling Tower Monitoring Wireless Vibration Monitoring for Motor and Gearbox Combinations Cooling tower fans operate under different load conditions. They often only run at peak load for short periods.
2002 Emerson Process Management. All rights reserved. View this and other courses online at www.plantwebuniversity.com. Fieldbus 202 Reliability and redundancy Overview Wiring reliability Segment reliability
AMS Suite: Intelligent Device Manager Product Data Sheet AMS ValveLink SNAP-ON Application Communicate with both HART and Foundation fieldbus FIELDVUE digital valve controllers in the same application.
Predictive Maintenance-Facility, Ground Support Equipment, Page 1 of 5 Technique Predictive maintenance is a technique that allows for a systematic method of monitoring and trending of equipment condition.
Maximizing return on plant assets Manufacturers in nearly every process industry face the need to improve their return on large asset investments. Effectively managing assets, however, requires a wealth
2005 Emerson Process Management. All rights reserved. View this and other courses online at www.plantwebuniversity.com. SIS 401 - Smart SIS 15 minutes In this course: 1 Overview 2 Why It Matters 3 What
with the DeltaV TM system AMS Suite: Intelligent Device Manager with the DeltaV system Manage your HART, FOUNDATION fieldbus, WirelessHART, and Profibus DP devices using a single, integrated application
FIELDBUS DIAGNOSTICS: LATEST ADVANCEMENTS OPTIMIZE PLANT ASSET MANAGEMENT Stephen Mitschke, Manager-Fieldbus Products Fieldbus Foundation Acceptance of the Fieldbus Foundation s open, nonproprietary technology,
Uniformance Asset Sentinel Advanced Solutions A real-time sentinel for continuous process performance monitoring and equipment health surveillance What is Uniformance Asset Sentinel? Honeywell s Uniformance
Online Hydro Machinery Monitoring Protection, Prediction and Performance Monitoring Solutions 2011, Emerson Process Management. The contents of this publication are presented for informational purposes
Equipment Performance Monitoring Web-based equipment monitoring cuts costs and increases equipment uptime This document explains the process of how AMS Performance Monitor operates to enable organizations
TURBINE FAN COMPRESSOR GEARBOX BOILER GENERATOR PUMP MOTOR Reliability Solutions for Mechanical Equipment Understanding Machinery Health for Increased Availability and Maximum Performance Is Your Machinery
Machinery Health Management Whitepaper June 2014 Predictive Maintenance with Multi-Channel Analysis in Route and Analyze Mode Presented at EuroMaintenance 2014, Helsinki, Finland, by Johan Van Puyenbroeck.
March 2009 Predictive Maintenance in a Mission Critical Environment This paper discusses the need to proactively protect mechanical and electrical support systems in data processing centers and data storage
On-line PD Monitoring Makes Good Business Sense An essential tool for asset managers to ensure reliable operation, improve maintenance efficiency and to extend the life of their electrical assets. Executive
January 2013 Page 1 You can easily engineer and operate your process automation system from the Maintenance Station, Graphical view and annunciation of intelligent device alerts Fieldbus and HART Powerful
InsulGard Medium voltage motors Generators Switchgear Bus duct Cable terminations Maximize your uptime Why InsulGard? Economics and safety Insulation failures cost time and money. What s even more damaging
A PublicAtion of the international Society of AutomAtion Asset management systems increase reliability and efficiency Make use of technology to overcome barriers to better maintenance practices By Augie
2002 Emerson Process Management. All rights reserved. View this and other courses online at www.plantwebuniversity.com. Buses 101 Field Level Networks Overview Types of buses Sensor bus Device bus Fieldbus
RecipCOM Expertise, reciprocating compressor monitoring and protection tailored to your needs Do your reciprocating compressors have sufficient protection? Due to the increasing demands on availability
TROUBLE SHOOTING The information contained in this section provides a guide for troubleshooting the pumps. It is a problem solving tool aimed at reducing unnecessary machine downtime. Following the fault-logic
ARC VIEW JANUARY 22, 2009 Emerson Asset Optimization Business Breaks New Ground By Larry O Brien Summary Emerson continues to put significant emphasis on its Asset Optimization business, a strategic element
wp_eddl device diagnostics ra 31/03/2010 16:14:00 Intelligent Device Management: Device Diagnostics Device diagnostics can be carried out using a handheld communicator in the field, a laptop in the workshop,
Asset Management with Foundation Fieldbus Technology G. Mooney OGNL-OGES Presentation What is Asset Management Present Status/Ongoing Developments Future Direction Summary What is Asset Management in Plant
2002 Emerson Process Management. All rights reserved. View this and other courses online at www.plantwebuniversity.com. Fieldbus 402 Choosing a host system Overview Supplier experience Designed for fieldbus
GE Mine Performance powered by Predix Increase throughput and availability If you re like most mining companies, you need to improve both your processes and your equipment availability to optimize throughput
Ovation Machinery Health Monitor Benefits: Improves asset performance by delivering distributed control, machinery protection and predictive machinery health monitoring on a single common platform Increases
GE Intelligent Platforms Mine Performance from GE Predictivity Increase throughput and availability If you re like most mining companies, you need to improve both your processes and your equipment availability
Selecting Sensors for Safety Instrumented Systems per IEC 61511 (ISA 84.00.01 2004) Dale Perry Worldwide Pressure Marketing Manager Emerson Process Management Rosemount Division Chanhassen, MN 55317 USA
Process Operators and Maintenance Staff Work Hand-in-hand with DCS-embedded Condition Monitoring Erkki Jaatinen Metso, Tampere, Finland ABSTRACT The capabilities of an on-line condition monitoring system
Loop Scout Loop and Alarm Performance Management Service Designed primarily for the I/E Technician and non-phd Control Engineer, Honeywell s Loop Scout service monitors control systems, detects and prioritizes
LEADING PROVIDER OF CONDITION MONITORING SERVICES Specialising in Electrical and Mechanical Testing ndtservicesgroup.com.au ndtservicesgroup.com.au A INDUSTRY LEADERS IN CONDITION MONITORING SERVICES QUALITY
PM Optimization An EAM Best Practice Overview Presented by Matt Midas Senior Account Executive Park City, UT August 4, 2014 Agenda GenesisSolutions/ABS Group Overview Key Building Blocks for PM Optimization
MANAGING ASSETS USING PERFORMANCE SUPERVISION Michel Ruel P.E. President, Top Control Inc. email@example.com 49, Bel-Air, suite 103 Lévis, Qc G6V 6K9 Canada ABSTRACT In today s highly competitive worldwide
PdM Overview Predictive Maintenance Services Objective Assessments Maximize Uptime, Lower Costs Predictive Maintenance (PdM) solutions from Rexnord Industrial Services help manage the condition of your
The Turbine Control Experts Experts in Steam and Gas Turbine Control For nearly five decades, Emerson Power & Water Solutions has been an industry leader in providing control solutions for every aspect
DEXTER TM Ship Health Monitoring Software Smart Solutions for Energy Efficiency & Reliability DEXTER Leveraging Data for Cost Avoidance In today s economic and environmental climate, efficiency is critical.
January Page Entrained Gas Diagnostic with Intelligent Differential Pressure Transmitter Dave Wehrs - Director, Pressure Engineering Andrew Klosinski - Application Engineer, Pressure Diagnostics Emerson
Reliability Solutions Product Data Sheet AMS 6500 ATG API 670 compliant TSI protection system Integrated prediction functionality including PeakVue technology and band filter Interface with other applications
Energy savings in utility systems 2016 Page 1 of 15 Table of Contents Executive summary... 3 Compressed Air Systems... 4 Running costs and energy losses... 5 Compressed Air Leakage... 6 Low Dew point...
Electric Rope Shovel Monitoring Apply Online Condition Monitoring to Move Toward Zero Unplanned Downtime Unplanned downtime can be both risky and expensive The mining pit is an inherently dangerous environment.
Improve reliability with essential asset monitoring Improvements in plant reliability reduce risk of catastrophic events, lower maintenance cost By Nikki Bishop in the control process industries can be
Manage Essential Assets with Automated Monitoring Automated asset monitoring is the next step in predictive maintenance Pete Sharpe, Nikki Bishop, Robert Montgomery In most facilities, real-time monitoring
Mining, Oil & Gas: Abstract With the majority of Australia s mineral, oil and gas reserves situated in remote locations, resource companies can struggle to get timely access to the data they need to make
Medium voltage service MySiteCare and MyRemoteCare Reliable asset condition monitoring 2 Maintenance strategies What is the best approach? Condition-based maintenance Maintenance based on monitoring equipment
SWITCHING STRATEGIES: MOVING TO CONDITION- BASED MAINTENANCE By David Stevens, Technical Manager & Trainer, AVT Reliability Balancing cost reduction and efficiency improvement targets is a common source
Online Transformer Insulation Monitoring System BushingGard Product Focus Maximizing Transformer Uptime and Reliability Critical Energy Transfer... Large power transformers are found around the world at
PART ONE of a predictive maintenance series Predictive Maintenance Overview Predictive maintenance programs come in all shapes and sizes, depending on a facility s size, equipment, regulations, and productivity
Level Instrumentation for the Refining Industry Moving to a Higher Level Performance Delivering Results for You and Your Plant The Power to Deliver Results Rosemount level devices power Emerson s PlantWeb
Understanding the Benefits of Vibration Testing November 15, 2012 Agenda Introductions / History Benefits of Vibration Testing Overview of Vibration Testing Bearing Faults 9 Stages of Bearing Wear Traditional
Technical Whitepaper Realize more value from System 800xA Apply Asset Management for more benefits Whitepaper by David Huffman October 2014 In a marketplace where the competition almost exclusively limits
October 2014 Page 1 Smart Wireless Gateway 1552WU An Emerson Smart Solution integrates WirelessHART data from remote areas of your plant. Scalable Reduced cost Safer deployment Secure and reliable communications
Proactive Asset Management with IIoT and Analytics by Ralph Rio in Industrial Internet of Things, Analytics & Big Data Summary The Industrial Internet of Things (IIoT) with advanced analytics, offers new
Rather than a one-size-fits-all approach, reliability managers should examine major machine sections to determine well-suited oil and grease characteristics. Today s global economy has put many paper facilities
The Basics of Predictive / Preventive Maintenance Maintenance costs, as defined by normal plant accounting procedures, are normally a major portion of the total operating costs in most plants. Traditional
Wireless Sensor Networks WIB Seminar 25 april 2007 John van Gorsel Product Manager Emerson Developed an Architecture to Extend Plant Visibility Wirelessly Plant Network Asset Tracking Security Wireless
January 2013 Page 1 S-series FOUNDATION Fieldbus I/O Use DeltaV state-of-the-art S-series FOUNDATION fieldbus I/O for your process control system. Increase I/O capacity while reducing wiring Maximize smart
January 2013 Page 1 You can easily engineer and operate your process automation system from the Professional Station Powerful, graphical engineering capabilities Robust and secure plant operations Integrated
Enhancing Business Performance using Integrated Visibility and Big Data Manish Sharma Marketing Leader GE Energy Management Manish.Sharma1@ge.com Photograph of Speaker ARC Advisory Group GE Energy Management
February 2016 Page 1 Operate your automation system at the DeltaV Operator Station. Robust and secure plant operations Real-time and historical-trend display Integrated system and device diagnostics Introduction
ProSmart Predictive Condition Monitoring ProSmart Identifying and Solving problems before they impact production. Time is the most valuable thing a man can spend. Theophrastus, Philosopher MINIMIZING PROCESS
Oil and Coolant Circulating Heating System Model - OCSM Installation & Operation Manual 216280-000 REV 2 Identifying Your System The HOTSTART heating system is designed to heat fluids for use in marine
Supplement to Monitoring and Control Tools for Implementing PAT Terry Blevins and James Beall AUTHORS Innovations in process analysis and control offer significant opportunities for improving pharmaceutical
Optimization of Preventive Maintenance and Operator Essential Care Results Oriented Reliability and Maintenance Consulting and Training Rate your Current Operator Essential Care & Preventive Maintenance
DUFFERIN-PEEL CATHOLIC DISTRICT SCHOOL BOARD JOB DESCRIPTION POSITION TITLE: Air Conditioning Mechanic DEPARTMENT: Plant TITLE OF IMMEDIATE SUPERVISOR: Supervisor, Maintenance Services Position Summary
LOWIS Enabling better decision making for artificial-lift optimization Get More from Your Wells Optimizing production is no longer an option it s a necessity. But unleashing the potential of your artificially
White Paper PN FGD_TWP_H2S_Hydrogen_Sulfide_Gas_Understand_Danger January 2015 Detecting Hydrogen Sulfide Gas and Understanding its Danger in the Field Introduction Many oil fields, especially mature ones,
Waters Corporation Waters 2690/5 USER & TROUBLESHOOTING GUIDE Contents 2690/5 Theory Setup procedures. Troubleshooting the 2690/5 User maintenance of the 2690/5 Spare Parts 2 2690/5 Theory 2690/5 Solvent
Fleet Management and Compliance How to improve driver safety and simplify regulatory compliance while saving time and money For with people in them Thecompanies Virtues of Driving HoS Compliance When you
Pump Maintenance - Repair Brian Trombly Mo Droppers Cummins Bridgeway, Gaylord, Mi The basic centrifugal pump consists of two main elements: 1. The rotating element which includes an impeller and a shaft.
Nine Steps to Oil Analysis Success Robert Scott, Noria Corporation When oil analysis programs fail or are abandoned by a company, it is often because no apparent benefits from the program have been realized.
Factory Acceptance Testing Comments on this report are gratefully received by Johan Hedberg at SP Swedish National Testing and Research Institute mailto:firstname.lastname@example.org -1- Summary According to the
Remote Services Managing Open Systems with Remote Services Reduce costs and mitigate risk with secure remote services As control systems move from proprietary technology to open systems, there is greater
Your MRO Supplier Acceptance Testing We Provide Total Maintenance Support to all Rotating Equipment, Process Control Systems, and Stand Alone Units through Programs Our Services Condition Based Maintenance
Automation in the Oil and Gas Industry: Past, Present, Future Larry Irving VP, Oil and Gas Industry Agenda Automation of the past Current capabilities Challenges in the industry for tomorrow Promise of
April 2015 Streamline Device Commissioning Introducing AMS Device Manager Bulk Transfer The phrase define once, use many times describes the efficient method of configuring and commissioning HART and FOUNDATION
Your consent to our cookies if you continue to use this website.