2 THANK YOU FOR CHOOSING RAIN BIRD We are aware that you have a choice, and we are happy you chose Rain Bird. The Eagle Rotor series offers a wide range of features plus easy maintenance. This manual shows how to perform common installation and maintenance procedures. If you have any comments or questions please call your local Rain Bird distributor. Table of Contents THANK YOU FOR CHOOSING RAIN BIRD... 2 Table of Contents... 2 Important Installation & Maintenance Tips... 2 Required Maintenance Tools...3 Eagle 700 Anatomy... 4 Arc Adjustment... 4 Pressure Regulation Adjustment... 5 Manual Operation... 5 Removing the Internal Assembly... 6 Installing the Internal Assembly... 6 Replacing the Nozzle... 7 Replacing the Stator... 7 Adjusting the Stator Setting... 8 Replacing the Motor... 8 Replacing the Selector Stem...8 Removing the Valve Assembly... 9 Removing / Installing the Top Serviceable Rock Screen and ReplacEable Valve Seat... 9 Installing the Valve Assembly... 9 Replacing the Solenoid Assembly Appendix 1 Eagle 1100/1150 Stator Setting Guide Appendix 2 Eagle Rotor Troubleshooting Guide Important Installation & Maintenance Tips To avoid debris problems, flush the system before installing the ROTOR on the swing joints (or pipe riser). If debris gets in the line, flush the line. For NPT and BSP thread configurations: Handbook of Design Guidelines and Precautions (Biesner 1987) recommends using sufficient wraps (2 5 depending on tape thickness) to insure that threads do not lock up on make up. DO NOT use pipe dope. For ACME thread configuration, you must use an ACME thread swing joint assembly. DO NOT use Teflon tape or pipe dope. Do not tighten. Turn the rotor back counter-clockwise one-quarter (¼) of a turn only. Thread the rotor onto the thread connection and securely hand tighten, making sure the top of the rotor is level. Rain Bird does not recommend using metal fittings with Eagle Rotors. If metal fittings must be used, hand tighten only. For hydraulic rotors, before you connect the hydraulic tubing, make sure you bleed the air from the tube of the hydraulic control module. For part-circle applications, locate the fixed left edge by rotating the nozzle turret counterclockwise.
3 On electric models, be careful to prevent any debris from entering the Pressure Regulating System when working on the valve or replacing the selector stem. Eagle Rotors may be installed at ground level in all soil types. Required Maintenance Tools To perform maintenance on Eagle Series Rotors, you will need the following tools: 1. Phillips-head screwdriver 2. Flat-head screwdriver (#2 size preferred) 3. Snap-ring pliers used to remove snap rings from inside the case of the Eagle Rotor. Rain Bird Part Number: For Eagle 900/950 Part #D02203, Model: SRP For Eagle 700/750, 500/550 Part #D02236, Model: SR Selector valve key used to manually operate and service electric Eagle Rotors. Rain Bird Part Number: For Eagle 900/950, 700/750, 500/550 Part #B41720, Model: EGL-SVK 7" Selector Valve Key Part #D02215, Model: DR-SVK-7 18" Selector Valve Key Part #D02221, Model: DR-SVK Nozzle pull-up tool used to lift rotor head in dry mode. (Eagle 1100 & 1150 Models only) Rain Bird Part Number: Part # Valve insertion tool used to insert the valve assembly to all Eagle models. Rain Bird Part Number: For Eagle 900/950 Part #D41700, Model: VTDR For Eagle 700/750, 500/550 Part #D41710, Model: VT Installation Socket for Top-Serviceable Rock Screen and Replaceable Valve Seat on all Eagle valve-in-head models. Rain Bird Part number: Part #D02237, Model: IS-TSRS 8. 3/8" Socket Wrench & Extension or 3/8" Speed wrench & Extension A 10" (25,4 cm) minimum extension is required for Eagle 700 & 500 cases, and 12" (30,5 cm) minimum extension is required for Eagle 900 cases.
4 Eagle 700 Anatomy Arc Adjustment Required Tool: Flat-head screwdriver 1. On Eagle 550, 750, and 950 Series partcircle rotors, the LEFT leg of the sprinkler s arc is the fixed leg. Align the left leg where it is needed for your desired watering pattern while installing the rotor case on the swing joint. NOTE: On Eagle 1100/1150 Series part-circle rotors, the RIGHT leg is the fixed leg. 2. For 550, 750, and 950 Series rotors, the RIGHT leg of the arc is the adjustable leg. It is shipped from the factory at approximately 180 degrees from the fixed leg. NOTE: For 1100/1150 Series rotors, the LEFT leg is the adjustable leg. 3. For best results, turn the head ON to see where both legs trip (the trip point is the point where the rotor turns and begins rotating in the opposite direction). To manually advance the nozzle housing, SLOWLY move it in the same direction it is currently moving. After noting where the head trips, return the head to the left trip point. 4. Using a flat-head screwdriver, turn the arc adjustment screw on top of the nozzle housing to reach your desired arc. Turn the screw counterclockwise to add arc, or clockwise to subtract arc. One complete turn of the adjustment screw equals approximately 20 degrees of arc.
5 NOTE: 1150 Series rotors adjust in the direction opposite from other Eagle Rotors (clockwise to add arc and counterclockwise to subtract arc), and are adjustable from 15 to 360. Refer to the arrows on the rotor case. Turn on the rotor and let it run through the forward and backward trip points to verify the arc setting. Repeat steps 1 through 4 as needed. You may also pull the internal assembly out of the rotor and adjust the arc. Then reinstall the internal assembly and check for performance. Pressure Regulation Adjustment Electric model rotors only Required Tool: Flat-head screwdriver To adjust the pressure regulator, use a flat-head screwdriver to turn the adjustment screw in the center of the selector on top of the rotor head. Turn the screw clockwise to increase pressure, and counterclockwise to decrease pressure. One full turn is approximately 10 psi (.7 Bars). NOTE: For Eagle 1100/1150 Series rotors only, an Orange dot indicates a pressure setting of 120 psi (8,3 Bars). Factory pressure settings are indicated with a Blue dot for 70 psi (4,8 Bars), a White dot for 80 psi (5,5 Bars), and a Red dot for 100 psi (6,9 Bars). Manual Operation Electric model rotors only Required Tool: Selector valve key Pour l ouverture manuelle de l arroseur, tournez le sélecteur se trouvant sur le dessus à l aide de la clé spéciale. To manually operate the rotor, use the selector valve key to turn the selector on top of the rotor to the desired position shown on the rotor case. IMPORTANT NOTE: Locate main nozzle arrow on top of the rotor. Stand to the left of the arrow to avoid getting sprayed. During pop-up, a flushing action occurs. Stand at arms reach to reduce getting wet. When you are finished operating the rotor, return the selector to the AUTO position. The selector has three settings: - COUNTERCLOCKWISE = manual ON - CLOCKWISE = AUTO - CENTER = OFF
6 Removing the Internal Assembly IMPORTANT NOTE: Make sure the sprinkler does not operate automatically while you are removing the internal assembly. On electric models, turn the selector to OFF, as shown in Manual Operation above. For hydraulic and SAM models, turn off the water. CAUTION: Before removing the internal assembly, always tighten the nozzle housing screws securely. DO NOT remove the nozzle housing screws with the internal assembly removed from the case. Required Tool: Flat-head screwdriver 1. While pressing down on the center of the nozzle housing, insert a screwdriver into the slot on the snap ring and pry up the snap ring from the top of the rotor case. NOTE: You MUST press down on the nozzle housing when removing the snap ring. 2. Insert a flat-head screwdriver into the groove (or under the small tabs) on the outside edge of the bearing guide and use the screwdriver to gently pry up the internal assembly. 3. Lift the internal assembly up and out of the case. For older 900/950 models only: a red or black u-cup seal may slip off into the case. Simply take it out. NOTE: Check the bearing guide O-ring for swelling. If it is swelled (or stretched) allow it to dry out or replace it with a new one. Installing the Internal Assembly 1. PART-CIRCLE ROTORS: To find the leftstop, turn the nozzle housing to the right until it reaches its trip point. Then turn the nozzle housing back to the left until it trips again. The location of the arrow on top of the nozzle housing indicates the direction of the nozzle. Align the arrow on the nozzle housing with the left edge of the grass line (left edge of your watering pattern). Then make your right arc adjustment 2. Lower the internal assembly back into the case and press down firmly until the internal assembly seats securely and evenly in the case. 3. Position the snap ring in the groove on the top of the rotor case with the bottom of the snap ring facing down. Press the end of the snap ring without the screwdriver slot into the groove. Press and twist the snap ring down in a circular motion until it is installed about two-thirds of the way. Step on or pound the snap ring (with your hand or a screwdriver handle) to insert it the rest of the way. Make sure the snap ring fastens securely in place and is flush with the top of the rotor case. FULL-CIRCLE MODELS: Installing the full-circle internal assembly is the same as the part-circle, except that you do not need to adjust the arc.
7 Replacing the Nozzle IMPORTANT NOTE: Make sure the sprinkler does not operate automatically while you are changing the nozzle. On electric models, turn the selector to OFF as shown in Manual Operation on page 7. For hydraulic and SAM models, turn off the water. NOTE: Make sure the snap ring is securely in place before removing the nozzle housing screws. Required Tools: Phillips-head screwdriver; Flat-head screwdriver; (Eagle 1100/1150 may require a nozzle pull-up tool) 1. Use a Phillips-head screwdriver to loosen the nozzle housing screws. 2. Remove the nozzle housing screws and cover. 3. Use a flat-head screwdriver to pry the nozzle housing out of the case. Then press the old nozzle out of the nozzle housing. 4. Press the replacement nozzle assembly into the nozzle housing, making sure the nozzle front is flush with the outside of the housing. An O-ring seal is required on the following Eagle nozzles: All nozzles for the 700/750/950; the 900 models #20, #26, #28, #30, #32; and all 900 high performance nozzles. CAUTION: If the nozzle is not flush and seated properly in the nozzle housing, the rotor may not perform properly. NOTE: When changing nozzle to a different size, you may also need to change the stator to maintain consistent rotation. On Eagle 1100 & 1150 you may need to adjust to a new STATOR SETTING. Replacing the Stator IMPORTANT NOTE: Make sure the sprinkler does not operate automatically while you are changing the stator. On electric models, turn the selector to OFF, as shown in Manual Operation on page 7. For hydraulic and SAM models, turn off the water. Required Tool: Flat-head screwdriver NOTE: Before replacing the stator, you must remove the internal assembly. NOTE: The purpose of the stator is to control the speed of the rotor. When changing the stator, make sure to use all the parts in the nozzle/stator kit. NOTE: For 1100/1150 Series Rotors, unscrew the bottom screen (counterclockwise) using the four posts on the bottom screen to remove the stator. 2. Replace with the appropriate stator replacement kit. Position the poppet (if required) as shown on the Rotor Stator Instruction Sheet. Snap the new stator/internal screen onto the rotor and place the internal assembly back in the case. See Installing the Internal Assembly. 1. For Eagle 550, 750, and 950 Series Rotors, use a flat-head screwdriver to pry the stator and/or internal screen from the internal assembly.
8 Adjusting the Stator Setting NOTE: Eagle 1100/1150 Series Rotors only Eagle 1100/1150 Rotors allow you to adjust the stator setting to more precisely control rotation speed. Refer to Appendix 1 for rotation speeds produced by various stator settings and nozzle combinations. IMPORTANT NOTE: Make sure the sprinkler does not operate automatically while you are adjusting the stator setting. On electric models, turn the selector to OFF, as shown in Manual Operation on page 7. For hydraulic and SAM models, turn off the water. 1. Use the four pegs on the internal assembly bottom screen to turn the screen counterclockwise and remove it. 2. Turn the white knob on the stator to adjust the stator to the desired setting (from 1 to 16). See stator guide. 3. Replace the bottom screen and turn it clockwise until it is hand tight. NOTE: Before adjusting the stator setting, you must remove the internal assembly Replacing the Motor NOTE: Eagle 1100/1150 Series Rotors only Eagle 1100/1150 Rotors allow you to remove and clean or replace the internal motor if it becomes clogged with rocks or debris. IMPORTANT NOTE: Make sure the sprinkler does not operate automatically while you are replacing the motor. On electric models, turn the selector to OFF, as shown in Manual Operation on page 7. For hydraulic and SAM models, turn off the water. NOTE: Before replacing the motor, you must remove the internal assembly is used as a hook may also help in loosen the motor from the internal. 4. To reinstall the motor, align the two grooves on the side of the motor with the raised rib on the inside of the internal assembly. Then lower the motor into place. Make sure to fully insert the motor into the internal assembly. 5. Align the groove on the side of the stator with the raised rib on the inside of the internal assembly and replace the stator. Then replace the bottom screen and turn it clockwise until it is hand tight. 1. Turn the bottom screen counter-clockwise to remove it, as shown in step 1 of Adjusting the Stator Setting 2. Lift out the stator. 3. To replace or remove the motor pull in the direction of the arrow. A large allen wrench Replacing the Selector Stem IMPORTANT NOTE: Electric model rotors only Turn off the water to the sprinkler before attempting to replace the selector stem. Make sure you relieve the pressure on the rotor by closing the isolation or main valve. Required Tool: Eagle selector valve key 1. Insert the HEX end of the Eagle selector valve key into the selector cap on top of the rotor. Turn the tool counter-clockwise to loosen the selector cap. 2. Remove the selector cap from the case. 3. Remove the selector stem cartridge from the case. Before replacing the selector cartridge, make sure that the selector seal is flat and seated in the bottom of the selector housing. Place the selector stem cartridge into the selector housing making sure the stem is pointed to the OFF position. Tighten the selector cap, using the HEX end of the selector valve key tool. Press down hard while tightening. NOTE: If debris has entered the Pressure Regulating system, you may be able to flush the debris out without disassembly. Slightly loosen the selector cap
9 as shown in STEP 1 until water starts to flow from the cap. WARNING: The rotor will likely turn on. After a few seconds, tighten the cap back on. NOTE: If possible, keep the line pressure to a minimum (20-30 psi or 1,4 to 2,1 Bars) during this process. Removing the Valve Assembly IMPORTANT NOTE: Turn off the lateral mainline valve to the sprinkler before replacing the rotor valve. Required Tools: Flat-head screwdriver; snap-ring pliers NOTE: Remove the internal assembly, and remove any water remaining in the case before removing the valve. remove it from the case. Remove the second snap ring in the same way. Lift out the valve with the snap-ring pliers. Push down on top of the valve with the blunt end of a hammer or screwdriver to relieve any pressure on the valve. Insert the snap-ring pliers into the case and grasp the top snap ring. Pull up to release the snap ring and Removing / Installing the Top Serviceable Rock Screen and ReplacEable Valve Seat Required Tools: Installation Socket (P/N: ) 3/8" Socket Drive or 3/8" Speed Wrench; Drive Extension Attach the installation socket to the socket drive/drive extension. Insert the installation socket and socket drive/drive extension assembly into the case. Align the installation socket to the slots on the top serviceable rock screen. Twist the Drive Extension counter-clockwise to remove the rock screen and clockwise to install the rock screen. Installing the Valve Assembly Required Tool: Valve insertion tool 1. To install the valve assembly, insert the two snap rings into the valve insertion tool, with their rounded edges facing down, and the slotted tabs on the snap rings 180 degrees apart. 2. Insert the valve into the valve insertion tool. Align the pilot flow port on the valve with the large rounded notch of the valve tool. 3. Insert the valve tool into the rotor case, aligning the two ribs on the inside of the case with the notches on the side of the tool. Push the handle down until the head of the tool reaches the bottom of the case. Then push down firmly on the tool to seat the valve and the snap rings. Remove the valve tool, and check to make sure that both snap rings are securely in place. Reinstall the internal assembly and upper snap ring. Turn on the water and test the valve by operating the sprinkler manually
10 Replacing the Solenoid Assembly IMPORTANT NOTE: Turn off the water to the sprinkler, and make sure the plunger area of the selector assembly is kept clean and free of debris. Required Tool: Selector Valve Key selector housing and hand tighten. Firmly tighten the base nut with the selector valve key. 4. Slide the U-Frame and coil onto the solenoid tube (post) and re-install the orange cap. 1. Twist the orange cap counterclockwise and remove it. Slide the U-frame and coil assembly off the solenoid tube (post). 2. Using the selector valve key, place the key against the solenoid base nut and align with the holes in the base nut. Holding the tool firmly, twist counterclockwise and remove the solenoid tube (post)/base nut and plunger assembly. 3. Before re-installing the new solenoid assembly, be sure the o_ring is seated properly. Place the solenoid tube (post)/base nut and plunger assembly against the Appendix 1 Eagle 1100/1150 Stator Setting Guide Blue Nozzle Stator Setting Full-circle rotation time (Min:Sec) 80 psi (5,5 Bars) 100 psi (6,9 Bars) :28 2:08 2:02 5 2:39 2:26 2:22 6 3:09 2:50 2:24 7 3:37 3:13 2: :26 2: Yellow Nozzle Stator Setting 110 psi (7,5 Bars) Full-circle rotation time (Min:Sec) 80 psi (5,5 Bars) 100 psi (6,9 Bars) :57 1:52 1:41 5 2:20 1:59 1:51 6 2:32 2:15 1:58 7 2:38 2:20 2:08 8 3:05 2:27 2:16 9 3:10 2:52 2: :30 2:55 2: : psi (7,5 Bars) Orange Nozzle Stator Setting Full-circle rotation time (Min:Sec) 80 psi (5,5 Bars) 100 psi (6,9 Bars) :52 1:36 1:27 5 2:09 1:48 1:41 6 2:25 2:04 1:57 7 2:31 2:08 2:11 8 2:51 2:38 2:26 9 3:15 2:41 2: :20 2:50 2: :28 3:00 2: :00 3:38 2: :52 3: : Green Nozzle Stator Setting 110 psi (7,5 Bars) Full-circle rotation time (Min:Sec) 80 psi (5,5 Bars) 100 psi (6,9 Bars) :45 1:35 1:24 5 1:57 1:40 1:30 6 2:16 1:47 1:45 7 2:30 2:02 1:59 8 2:37 2:06 2:10 9 2:39 2:30 2: :45 2:36 2: :15 2:40 2: :22 3:04 2: :49 3:22 2: :26 3: : psi (7,5 Bars)
11 Appendix 2 Eagle Rotor Troubleshooting Guide Problem Possible Cause Correction Cracked rotor case High pressure Minimize water/air hammer. Check the system s pressure regulating valve. Replace case if needed. Improper installation Check installation for over tightening. Check case for chemical damage. Replace case if needed. Freeze damage Make sure to winterize system properly. Blow out water line if susceptible to freezing temperatures. Replace case if needed. Failure to pop up and/or seal properly Sand or rock particles may have wedged between the bearing guide and the riser Low pressure Jammed or clogged selector assembly Tube crimped or pinched, or blockage in tubes Solenoid coil not working Pull the internal assembly and clean. Brush any rocks or debris away from the head of the rotor. See solutions for Problem #6 Low Pressure. Clear or clean poppet, or replace selector assembly. Make sure tubes are not bent or pinched. Check tubes for blockage. Clear tubes, if needed. Check solenoid for proper operation. Replace if needed. Failure to turn on No power to solenoid Check for power to solenoid. Selector/PRS set to OFF Check selector and PRS. Set to AUTO or ON, as desired. Jammed solenoid plunger Clean out debris around plunger. Replace plunger assembly, if needed. Failure to turn off Cracked selector housing Check and replace housing. Selector/PRS set to MANUAL Turn stem to AUTO or OFF, as desired. Diaphragm failure Replace valve assembly. Valve housing cracked Replace valve. Jammed solenoid plunger Clean out debris around plunger. Replace plunger assembly, if needed. Plugged valve filter Remove valve. Clean and reinstall filter screen. Debris under plunger and selector housing volcano Clean out area around selector volcano and plunger. Freeze damage (Hydraulic rotor will not open. Water continually drains at controller while attempting to open valve). Failure to winterize Make sure to winterize the system properly. Repair and replace damaged parts as needed. Low pressure Mechanical failure to retract Incorrect valve assembly in the rotor Plugged or damaged nozzle PRS out of adjustment PRS not holding pressure setting Broken valve filter screen Blockage in tubes or case probe Tube crimped or pinched Debris obstructing internal assembly screen Inlet rock screen clogged Debris in PRS assembly Retract spring may be installed with an end coil doubled over, preventing internal retraction Check for proper valve assembly. Replace if needed. Clean or replace nozzle. Adjust pressure by turning adjusting screw using a screwdriver. Replace PRS cartridge in selector. Replace screen and clean out valve assembly. Locate and clear blockage. Repair or replace tube. Clean internal assembly screen. Remove case. Clean and reinstall rock screen. Clean out any debris between poppet and lower stem. Remove internal assembly and without disassembling, compress the spring down until you free up the end coil. Reseat the end coil and reinstall the internal assembly.
12 Problem Possible Cause Correction Sand or rock particles may have wedged between the bearing guide and the riser Pull the internal assembly and clean. Brush any rocks or debris away from the head of the rotor. Non-rotation/ Stalling / Tripping Stator missing, or wrong stator installed Remove internal assembly. Check for proper stator. Debris or algae clogging the internal assembly screen Clean internal screen. Nozzle clogged Inlet screen clogged Clean nozzle. Clean inlet screen. This may be difficult if debris has fallen back down out of sight. Examine and clean thoroughly. Arc was misadjusted and left in neutral Turn the nozzle housing through the next trip point. Arc setting too small Reset arc to no less than 45 degrees. Sprinkler rotates too slowly Insufficient water pressure See solutions for Problem #6 Low Pressure. Improper nozzle/stator combination Check for proper stator configurations and nozzle/stator combinations. Clean as needed. Blinded filter screen Clean as needed. Short radius Improper sprinkler spacing Review spacing requirements. Blockage in tube Locate and clear blockage. Jammed poppet Clear poppet or replace selector assembly. PRS set too low Reset PRS. Solenoid plunger jammed Clean out debris around plunger and free plunger. Selector/PRS not set Set selector to AUTO or MANUAL. correctly Low pressure See solutions for Problem #6, Low Pressure. Course design problems Check capacity vs. nozzle size, number of heads, spacing, etc. Wind Raise water pressure, review watering schedule, renozzle. Incorrect stator configuration Verify proper stator/nozzle match. Weeping Leakage between inlet seal and case seat Check for debris lodged between seat and seal. Replace or repair damaged inlet seal on valve. If case seat is damaged, replace case. Copyright 2003 by Rain Bird Corporation. 970 W. Sierra Madre Avenue, Azusa, CA U.S.A. All rights reserved. Reproduction or translation of any part of this work without written permission of Rain Bird Sales, Inc., is prohibited.
INSTALLATION & SERVICE INSTRUCTIONS 690 Series Rotary Sprinkler Introduction The 690 Series Rotary Sprinkler is designed for irrigation of large turf areas such as golf courses, parks, recreational fields
IMP 8740.3 Industrial Regulator Series 1800/2000 Instructions and Parts List AMC Quality System QMI is Accredited by: ISO 9002 Certified Dutch Council for Accreditation Instructions: Industrial Regulator
Fleck 4650 Service Manual TABLE OF CONTENTS JOB SPECIFICATION SHEET...1 INSTALLATION AND START-UP PROCEDURE...1 CONTROL VALVE DRIVE ASSEMBLY...2 CONTROL DRIVE ASSEMBLY FOR CLOCK...3 BYPASS VALVE ASSEMBLY...4
LEFTY SPEED DLR DAMPING CARTRIDGE This document explains how to properly remove, disassemble, inspect, reassemble and reinstall the Lefty Speed DLR2 damping cartridge. It is a document to be used in conjunction
Instruction Sheet P/N 160780 01 Stainless Steel Single and Dual Circulation Kits Introduction The single and dual high-pressure circulation kits allow you to vary and control the circulation rate of coating
November 25, 2013 Dry 111a 1. description The Viking is a quick-opening device, with an integral anti-flood assembly, used to increase the operating speed of a differential type dry pipe valve. An accelerator
DAZZLE Installation Instructions 08.80 Spread Lavatory Faucet with Speed Connect Drain* Congratulations on purchasing your American Standard faucet with Speed Connect drain, a feature found only on American
BAL Accu-Slide System I. Table of Contents TABLE OF CONTENTS I. TROUBLESHOOTING... 2 - Section 1.01: Common Problems/Solutions... 2 II. GETTING STARTED... 5 - Section 2.01: Tools You Will Need... 5 - Section
Pulley Assembly and Timing Belt Tools Needed ½ or ¼ Cold Chisel & Pair of large pliers Allen Wrenches: (3/16) (5/16) (5/32) (3/32) Open Head Wrenches: (5/8) (1/2) (9/16) Ratchet Sockets: (5/8) (1/2) (9/16)
4 3. SEISCO PARTS & SERVICE REMOVAL AND REPAIR GUIDE A. Changing the Control Board B. Replacing a Heating Element C. Thermistor Replacement D. High Limit Switch Replacement E. Level Detector Replacement
HAND SHOWERS AND HAND SHOWER ACCESSORIES BEFORE YOU BEGIN HOW TO USE THESE INSTRUCTIONS Please read these instructions carefully to familiarize yourself with the required tools, materials, and installation
SYMPHONY Spread Lavatory Faucet with Speed Connect Drain Congratulations on purchasing your American Standard faucet with Speed Connect drain, a feature found only on American Standard faucets. Speed Connect
Overview READ ENTIRE INSTRUCTIONS BEFORE STARTING INSTALLATION PARTS LIST A. Flush valve B. Lever mounting base C. Flush handle assembly D. Grey/Blue float stop E. Grey float (Full Flush) F. Flush valve
Installation Instructions.00 SINGLE CONTROL KITCHEN FAUCET Thank you for selecting American-Standard...the benchmark of fine quality for over 00 years. To ensure that your installation proceeds smoothly--please
Dual Flush Toilet Conversion Kit EURO BUTTON MODEL WWW.SMARTERFLUSH.COM Table of Contents Smarter Flush Conversion Kit Tip Sheet...3 Overflow Water Conserver...4 Satisfaction Guarantee...5 Parts List/Parts
OPERATION AND MAINTENANCE MANUAL 5-1/4 B-84-B-5 FIRE HYDRANT INDEX AMERICAN - DARLING 5-1/4 IN. B-84-B-5 FIRE HYDRANT OPERATION AND MAINTENANCE MANUAL OPERATION AND MAINTENANCE REPAIRS Operation and Maintenance...
Fiberstars Lighted Laminar Flow Fountain Installation Manual 79-15037-00 REV Xx http://www.fiberstars.com Page 1 of 8 SAVE THESE DIRECTIONS! These directions are provided to ensure the proper installation
WATER VALVE OWNER S MANUAL 004-027-8742-00 REV051811 295 East Corporate Place Suite 100 Chandler, AZ 85225 Toll Free: 1.800.621.5886 Phone: 480.893.7607 Fax: 480.753.3397 Paramount@1Paramount.com www.1paramount.com
Part Installation Procedure CrossTrainer Upper Pulley Assy FIGURE 1 The following procedure explains how to install the Upper Pulley Assembly for the Pro / Elite Cross Trainer. Parts Needed Upper Pulley
www.hunterfan.com Table of Contents What to Expect with Your Installation 30 inches Hanging the Fan Wiring 8 Maintenance, Operation & Cleaning Light Kit 13??? 14 1 9 Troubleshooting 11 5 Blades Motor Housing
SIMPLEX UNICAN LOCKS CHANGING THE CODE / COMBINATION 900 Series 1000 Series L1000 Series LP1000 Series EE1000 Series 2000 Series 2015 Series 2400/2500 Series 3000 Series 3100 Series Simplex 5000 Series
Dive Rite 200 & 300 Bar Isolator Manifold Service Manual Principal Photography and Text by Pete Nawrocky Copyright 2003 Lamartek Inc. D/B/A Dive Rite 0 Warning This manual is only to be used as a guide
R 2000 Service Manual Rol-Lift Series: T and E Developed by Generic Parts Service This manual is intended for basic service and maintenance of the Rol-Lift pallet jack. The pallet jacks you are servicing
Dry 122a 1. PRODUCT DESCRIPTION The Viking is a quick-opening device. When installed with the required external Anti-flood Device, the assembly is designed to increase the operating speed of Viking Model
Teledyne Isco Syringe Pumps: Care and Maintenance ~ Overview ~ This bulletin provides instructions for performing normal periodic maintenance required by Teledyne Isco syringe pumps, followed by servicing
SECTION G2: CABLE PROCESSOR MODULE MAINTENANCE Cable Processor Module overview WARNING! When tipping the Cable Processor Module back, (after removing the toggle arm pin), use extreme caution not to drop
Rebuild Instructions for 70001 and 70010 Transmission Brinn, Incorporated 1615 Tech Drive Bay City, MI 48706 Telephone 989.686.8920 Fax 989.686.6520 www.brinninc.com Notice Read all instructions before
PNEUMATIC CONTROL VALVES SERVICE AND MAINTENANCE PROCEDURES CONFIDENTIALITY NOTICE This document contains subject matter in which KMT Waterjet Systems has proprietary rights. Recipients of this document
Installation Manual Elo Touch Solutions Wall-mounting Kit for the 5501L IDS Touchmonitors SW602206 Rev B Table of Contents Chapter 1: Safety Warning... 3 Chapter 2: Kit Contents... 4 Included in Kit...
KEYPAD LOCK RETROFIT KIT INSTRUCTIONS FOR ASSEMBLY IMPORTANT READ & SAVE THESE INSTRUCTIONS Tools Required for Assembly 5/32 hex (Allen) wrench #2 Phillips screwdriver Isopropyl alcohol or alcohol wipes
TECHNICAL INFORMATION Models No. Description HP2070, HP2070F, HP2071, HP2071F 20mm (3/4") 2-Speed Hammer Drill CONCEPT AND MAIN APPLICATIONS L W NEW TOOL P 1 /13 W L These hammer drills have been developed
SIG 556 Match Sear/Hammer Installation ShootingSight LLC 2012 Safety Warning Always verify your firearm is unloaded before working on it. These instructions are meant as a supplemental guide to an armorer
POPPET BLOCK CONTROL MAINTENANCE AND SERVICE MANUAL USASI SCHEMATIC Normally closed, double three-way poppet valve, with open exhaust, manual and pilot actuated. POPPET BLOCK GAS OR OIL FLOW INTRODUCTION
FUEL PUMP/FUEL GAUGE SENDING UNIT 4.4 GENERAL s0660x8xx Stop the engine when refueling or servicing the fuel system. Do not smoke or allow open flame or sparks near gasoline. Gasoline is extremely flammable
BUILT-IN DISHWASHER INSTALLATION INSTRUCTIONS PLEASE READ COMPLETE INSTRUCTIONS BEFORE YOU BEGIN LEAVE INSTALLATION INSTRUCTIONS AND USER'S GUIDE WITH OWNER ALL ELECTRIC WIRING AND PLUMBING MUST BE DONE
COMET PLUNGER PUMP SERVICE MANUAL INDEX 1. SAFETY INSTRUCTIONS, OPERATING PROCEDURES AND LIMITS... 1 1.1 Installation and Start-up Information 2. TORQUE SETTING CHART... 1-2 2.1 AXD Series Pump 2.2 LW/ZW
For exploded diagram and part number information, refer to the Spare Parts Catalog available on our website at www.rockshox.com. Information contained in this publication is subject to change at anytime
Joplin Rebuild Instructions This is a step by step list of instruction on how to rebuild the Crankbrothers Joplin post. It may not always be required to completely tear-down the post to do the work needed
CYLINDER OPERATED G-SERIES ACTUATOR USED ON PEC ECCENTRIC VALVES Instruction D10022 August 2012 Instructions These instructions provide information about G-Series Cylinder Actuators. They are for use by
Before repairing your toilet, you must determine which type of toilet you have. Pressurized Toilets If you have a pressurized toilet, it is recommended that you call a licensed plumbing contractor to repair
REPAIR AND MAINTENANCE MANUAL Professional Pest Control Application Equipment Prime Line Sprayers B&G Equipment Company 135 Region South Drive, Jackson, GA 30233 800.544.8811 Phone 678.688.5601 Fax 678.688.5633
SD 3001F PRINTED IN U.S.A. SD 3001F/0707 A B TYPE E MAIN VALVE C D E TYPE E Main Valve Sizes 3 /8 through 12 The Spence Type E Main Valve is of normally closed, single seat design featuring packless construction,
SET-UP AND INSTALLATION FOR LEAD SCREW CARTRIDGE ASSEMBLY 82-13-1 O-Ring (Rear) The Lead Screw Assembly is shipped separately. Note: Install Electrical and Pneumatic Circuitry. Be Sure electrical and pneumatic
For Your Records and Warranty Assistance For reference, also attach your receipt or a copy of your receipt to the manual. Vancouver Model Name 21321, 21328 Model No. Type A Models Owner s Guide and Installation
Owners & Installation Manual for the Sheridan, Mountainair, Pine Valley and Old Forge Ceiling Fan Family Part of the Kiva Lighting Family Custom Lighting and Fans Since 1992 1312 12th St NW Albuquerque,
A Publication of HOW TO CHANGE / REPLACE YOUR WET/DRY VAC FILTER NOV 2013 INTRODUCTION 2 FIVE EASY STEPS TO REMOVE OR REPLACE 3 TIPS IN DEPTH 4 WARNINGS AND NOTES : 4 ACCESS THE FILTER : 4 REMOVE THE FILTER
HYDRAULIC TABLE CART 500-LB. OWNER S MANUAL WARNING: Read carefully and understand all MACHINE ADJUSTMENT AND OPERATION INSTRUCTIONS before operating. Failure to follow the safety rules and other basic
Spark plug thread repair for Ford Triton cylinder heads Step-by-step instructions: Identification Installation Verification Specifically designed and tested for 4.6L, 5.4L, and 6.8L 2 and 4 valve heads,
INSTALLATION & START-UP INSTRUCTIONS FLECK 5600 METER WATER SOFTENER SYSTEMS 1999-2007 QualityWaterForLess.com - 1 - email@example.com Preface: Thank you for your purchase of a new Water Softener
D. L. Martin Company INGROUND, ROPED, AND HOLELESS JACK SEAL REPLACEMENT TYPICAL HYDRAULIC JACK HEAD ASSEMBLY 1 TOOLS REQUIRED: 1) Container to hold hydraulic fluid. 2) Clean rags and protective covers
Universal Installation and Maintenance Instructions 71CD-1212 Spill Containment Bucket IMPORTANT: Please read these instructions completely and carefully before installing Universal s 71CD-1212 Spill Containment
Trillium 40 Axis Spring Tensioner Wire Replacement Instructions 1 Overview The objective is to replace the broken axis spring tensioner wire. This requires the following tasks: 1. Remove the seismometer
Inspecting and Replacing Brushes in Bodine Type 33A, 42A, and 32A (PMDC) Motors or Gearmotors The permanent magnet DC (PMDC) motors and gearmotors manufactured by Bodine Electric Company are unique compared
MODEL G300 BRAKE BLEEDER Installation, Operation & Repair Parts Information Branick Industries, Inc. 4245 Main Avenue P.O. Box 1937 Fargo, North Dakota 58103 REV060616 P/N: 81-0035G 1 THIS PAGE INTENTIONALLY
Parts checklist 2 a c e f h b d g c e d y aa x z i p n m l r q o j k w s t v u bb dd bb cc ee a b c d e f g h i j k Handle Solution trigger Brush on/off Soap on/off Power on/off Clean water tank release
Series 10 Steering Control Unit Parts and Repair Information Design -002 Series 10 Steering Control Unit Table of Contents Introduction ID Tag...........................................................................................................................2
CYLINDER OPERATED G-SERIES ACTUATOR USED ON PFW & PTW TAPERED PLUG VALVES Instruction D10191 July 2016 Instructions These instructions provide information about G-Series Cylinder Actuators. They are for
3 rd Generation Personal 3D Printer Quick Start Guide See Inside for Use and Safety Information The USB Mass Storage Device Contains the User Guide and Quick Start Guide in other Languages Congratulations
Date: August 2011 / Page 1 of 6 CRYOGENIC AND LOW TEMPERATURE SERVICE TRIAD SERIES BALL VALVES (FP2000/FP3000 and SP2000/SP3000 WITH CRYO OR LOW TEMP EXTENSION) INSTALLATION - MAINTENANCE MANUAL DESIGN
INSTR3010 0406 Installation and Operating Instructions Installation Instructions for SS EPE-316L Series Congratulations on your purchase of this Aqua-Pure high flow, single housing filtration system. This
BETTIS SERVICE INSTRUCTIONS DISASSEMBLY AND REASSEMBLY FOR MODEL STR10XX-M4 DOUBLE ACTING SERIES PNEUMATIC ACTUATORS PART NUMBER: 111586 REVISION: "A" RELEASE DATE: May, 1995 Page 1 of 18 1.0 INTRODUCTION
Y Meridian Lateral Files Instructions! WARNING Failure to observe stated capacities below will result in unsafe usage conditions, causing possible product damage or personal injury. Important Loading Information