1 GREEN TAG/RED TAG AMERICAN SOCIETY OF CERTIFIED ENGINEERING TECHNICIANS ORLANDO CHAPTER ORLANDO, FL February 7, 2013
2 2012 FLORIDA STATUTES Inspection of fire control systems, fire hydrants, and fire protection systems. - - (2) Fire hydrants and fire protection systems installed in public and private properties, except one-family or two-family dwellings, in this state shall be inspected following procedures established in the nationally recognized inspection, testing, and maintenance standards NFPA-24 and NFPA-25 as set forth in the edition adopted by the State Fire Marshal. Quarterly, annual, 3-year, and 5 year inspections consistent with the contractual provisions with the owner shall be conducted by the certificateholder or permittees employed by the certificateholder pursuant to s , except that: (a) Public fire hydrants owned by a governmental entity shall be inspected following procedures established in the inspection, testing, and maintenance standards adopted by the State Fire Marshal or equivalent standards such as those contained in the latest edition of the American Water Works Association s Manual M17, Installation, Field Testing, and Maintenance of Fire Hydrants. (b) County, municipal, and special district utilities may perform fire hydrant inspections required by this section using designated employees. Such designated employees need not be certified under this chapter. However, counties, municipalities, or special districts that use designated employees are responsible for ensuring that the designated employees are qualified to perform such inspections.
3 2012 FLORIDA STATUTES Continued (3) The inspecting contractor shall provide to the building owner or hydrant owner and the local authority having jurisdiction a copy of the applicable inspection report established under this chapter. The maintenance of fire hydrant and fire protection systems as well as corrective actions on deficient systems is the responsibility of the owner of the system or hydrant. Equipment requiring periodic testing or operation to ensure its maintenance shall be tested or operated as specified in the Fire Prevention Code, Life Safety Code, National Fire Protection Association standards, or as directed by the agency having jurisdiction, provided that such agency shall not require a sprinkler system not required by the Fire Prevention Code, Life Safety Code, or National Fire Protection Association standards to be removed regardless of its condition. This section does not prohibit governmental entities from inspecting and enforcing firesafety codes. FFPC, NFPA Existing life safety features obvious to the public, if not required by the Code, shall be either maintained or removed. A The presence of a life safety feature, such as sprinklers or fire alarm devices, creates a reasonable expectation by the public that these safety features are functional. When systems are inoperable or taken out of service but the devices remain, they present a false sense of safety.
4 RULE 69A A Standards of the National Fire Protection Association and Other Standards Adopted. (1) Except as specifically modified by statute or by State Fire Marshal s rules, the Florida specific edition of NFPA 101, the Life Safety Code, 2009 edition and the Florida specific edition of NFPA 1, the Uniform Fire Code, 2009 edition, as adopted within Rule Chapter 69A-60, F.A.C., entitled the 2010 edition of the Florida Fire Prevention Code, are hereby adopted and incorporated by reference and are applicable to those buildings and structures specified in paragraphs (a) and (b) of subsection (1) of Section , F.S. In Addition, the following standards, except as specifically modified in the rule chapters in Rule Title 69A are hereby adopted and incorporated by reference and shall take effect on the effective date of this rule, as a part of the uniform fire safety standards adopted by rule by the State Fire Marshal and are applicable to those buildings and structures specified in paragraphs (a) and (b) of subsection (1) of Section , F.S.: NFPA edition, Standard for the Inspection, Testing, and Maintenance of Water-Based Fire Protection Systems, except that quarterly flow tests shall be required for those systems supplied by a municipal water supply.
5 2012 FLORIDA STATUTES Requirements for installation, inspection, and maintenance for fire Protection systems. 2)Equipment shall be inspected, serviced, and maintained in accordance with the manufacturer s maintenance procedures and with applicable National Fire Protection Association standards. The inspection of fire protection systems shall be conducted by a certificateholder or holder of a permit issued by the State Fire Marshal. The permitholder may perform inspections on fire protection systems only while employed by the certificateholder. This section does not prohibit the authority having jurisdiction or insurance company representatives from reviewing the system in accordance with acceptable oversight standards.
6 2012 FLORIDA STATUTES Disciplinary action; fire protection system contractors; grounds for denial, nonrenewal, suspension, or revocation of certificate or permit.- 2) The following acts constitute cause for disciplinary action: (a) Violation of any provision of this chapter or of any rule adopted pursuant thereto. (g) Improperly servicing, repairing, testing, or inspecting a fire protection system, standpipe system, or underground water supply main connecting to the system. 3) The State Fire Marshal is authorized to take the following disciplinary action: (a) She or he may suspend the certificateholder for a period not to exceed 2 years from all operations as a contractor during the period fixed by the State Fire Marshal, but she or he may permit the certificateholder to complete any contracts then incomplete. (b) She or he may revoke a certificate for a period not to exceed 5 years.
7 RULE 69A A Standards of the National Fire Protection Association to be Complied With. The following standards of the National Fire Protection Association which are adopted in Rule Chapter 69A-3, F.A.C., including the editions as adopted therein, shall be complied with by all those holding certificates of competency as fire protection system contractors pursuant to the provisions of Chapter 633, F.S.: (22) NFPA 25, Standard for the Inspection, Testing, and Maintenance of Water-based Fire Protection Systems, except that quarterly flow tests will be required for those systems supplied by a municipal water supply. Declaratory statement Casselberry Only a duly certified firesafety inspector or a certified fire protection contractor may flow water as part of an inspection.
8 2012 FLORIDA STATUTES Standard service tag required on all fire extinguishers and preengineered systems; serial number required on all portable extinguishers; standard inspection tags required on all fire protection systems. 3) The State Fire Marshall shall adopt by rule specifications as to the size, shape, color, information, and data contained thereon of inspection tags to be attached to all types of fire protection systems and information required on an inspection report of such an inspection.
9 RULE 69A Rule: 69A Prev Up Next Rule Title: Inspection Requirements for Fire Protection Systems Department: DEPARTMENT OF FINANCIAL SERVICES Division: Division of State Fire Marshal Chapter: FIRE PROTECTION SYSTEM CONTRACTORS AND SYSTEMS Add to Favorite Latest version of the final adopted rule presented in Florida Administrative Code (FAC): Effective Date: History Notes: 5/18/2008 Specific Authority FS. Law Implemented , , , (2)(e) FS. History New , Amended , Formerly 4A , Amended Rulemaking notices presented in Florida Administrative Weekly (FAW) since Jan 6, 2006 and Rule versions presented in Florida Administrative Code (FAC)
10 RULE 69A A Inspection Requirements for Fire Protection Systems. (1) A Fire Protection Contractor, contracting to perform inspecting, testing, and maintenance service on a fire protection system shall comply with the requirements of Chapter 633, F.S., and the applicable NFPA standards as adopted in Rule Chapter 69A-3, F.A.C. (2) Each system that has been inspected, tested, or maintained by a fire protection contractor, or his or her permitted Water-Based Fire Protection Inspector, shall have a record tag of durable and weather resistant material placed on the riser. (Suggested changes Identify each type of system and location of control valve) (3) Inspection Tags. (a) After inspection and testing, an inspection tag shall be completed indicating all work that has been done, and then attached to the system riser in such a position as to permit convenient inspection and not hamper activation or operation. A new inspection tag shall be attached to the system riser each time an inspection and test service is performed. (Suggested changes Main water control valve)
11 RULE 69A (69A continued) (b) Inspection tags must be a minimum dimension of 133 mm (5 ¼ inches) in height and 89 mm (3 ½ inches) in width, and a maximum dimension of 178 mm (7 inches) in height and 102 mm (4 inches) in width. (c) Inspection tags shall bear the following information in an easily read format: 1. DO NOT REMOVE BY ORDER OF THE STATE FIRE MARSHAL. This particular information shall be in a minimum of 10 pt type and in all capital letters; 2. The licensed Fire Protection System Contractor I or II s name and licensed physical address; 3. The license number of the Fire Protection System Contractor I or II; 4. The permit number of the Water-Based Fire Protection Inspector; 5. The permitted Water-Based Fire Protection Inspector s signature; New rules effective July of 2008 required inspectors to be NICET Level I to renew their permits and must be NICET Level II by next renewal. 6. The day, month and year (to be punched), and 7. The facility name and address.
12 RULE 69A (69A continued) 8. Affixing this tag shall not be construed to invalidate the owner s responsibility to maintain the system as provided in Section , F.S. 9. The reverse of the non-compliant tag shall include at least four separate boxes for the listing of repair work as follows: a. Date of Repair: b. Repaired by (Signature): c. Print Name: d. Type of Repair: e. Permit Number: (if repair is made by a Water Based Fire Protection Inspector, Permit Number must be noted.) Repairs that are made are to be noted on reverse side to tag. Typically repairs are done by service technicians (not certified inspectors). Therefore, existing tag remains and no green tag would be placed on the system until the next scheduled inspection. (d) Inspection tags may be printed and established for a five-year period of time.
13 RULE 69A (69A continued) (e) An inspection tag shall only be removed by the Fire Protection System Contractor or his permitted Water-Based Fire Protection Inspector. You may have an opinion as to low long a tag should remain on the system but no specific information is included in the rule. WFS intention is to leave the tags on the system and change them at the next annual inspection since the quarterly requirements are not as inclusive as the annual. (4) Compliance and Noncompliance Tag. (a) If a fire protection system is found to be in compliance with the applicable NFPA standards, a GREEN Compliance Tag shall be attached to either the main riser or main control valve in such a manner as to be plainly visible and not more than 60 inches above the finished floor. Note that the rule specifies main riser or control valve and not more than 60 inches above the floor. Control valve may be outside! May be at the base of a standpipe riser!
14 RULE 69A (69A continued) (b) If a fire protection system is found to have deficiencies and is not in compliance with the applicable NFPA standards, a completed RED Noncompliance Tag shall be attached to the main control valve of the system to indicate that corrective action is necessary. If the system is operational but not in compliance with the applicable NFPA standards, the building owner or authorized representative and occupant shall be notified by copy of the NFPA 25 inspection report within 30 days of the inspection. If the system is not operational, the contractor or inspector shall notify the building owner or authorized representative, the occupant, and the authority having jurisdiction within 24 hours of the time of the inspection. (Suggested changes Building owner or authorized representative shall notify the occupants) Note the only location for the Red Tag is on the main control valve. As well, the notification requirement specifies the timing but not the method.
15 RULE 69A (69A continued) (5) The contractor shall maintain all records of any fire protection system having been inspected, serviced and maintained. (6) These records shall be made available to the State Fire Marshal upon request. (7) The contractor or his or her permitted Water-Based Fire Protection Inspector shall complete in detail the inspection reports as required in NFPA 25, as adopted in Rule Chapter 69A-3, F.A.C., that outlines all points of the inspection, test, and maintenance as required by the applicable NFPA standards. A copy of the inspection report shall be provided to the owner at the completion of each inspection performed. (Suggested changes or authorized representatives within 30 days of the inspection) (8) The inspection report shall include a detailed explanation of every deficiency, and indicate if the inspection is a weekly, monthly, quarterly or annual inspection. The inspection report shall include the name of the permitted Water-Based Fire Protection Inspector, the inspector permit number, the inspector s signature, the date and time of the inspection, and the signature of the owner or the owner s representative. Requirements for information not previously on most inspection reports. Also, many times Owner or Owner s representative not on site to sign report.
16 RULE 69A (69A continued) (9) Pursuant to the provisions of Section , F.S., it is the owner s responsibility to maintain the fire protection system. Affixing an inspection tag as required herein does not invalidate responsibility nor shall a transfer of risk be construed. (Suggested changes and notify the occupants of impairments and deficiencies in accordance with this rule)
17 NFPA 25 NFPA Chapter 1 Administration 1.1 Scope This document establishes the minimum requirements for the periodic inspection, testing, and maintenance of water-based fire protection systems, including land based and marine applications this standard applies to fire protection systems that have been properly installed in accordance with generally accepted practices. Where a system has not been installed in accordance with generally accepted practices, the corrective action is beyond the scope of this standard. It is assumed that an existing system was reviewed and approved for compliance and commissioned properly when it was initially placed in service. Inspections required by this standard are not intended to reveal installation flaws or code compliance violations. It is clearly not the intent of this standard to evaluate a system year after year for compliance with an installation standard. It is not practical to expect an inspector (permit holder) to perform a detailed evaluation of the design and installation aspects of a fire protection system each year as the costs would be prohibitive. Such an evaluation should be conducted by a registered or certified design professional and should only be conducted when required by the building code or insurance company. All inspectors aren t trained to make these kinds of determinations.
18 NFPA 25 NFPA Chapter 1 Administration This standard does not require the inspector to verify the adequacy of the design of the system. A The requirement to evaluate the adequacy of the design of the installed system is not part of the periodic inspection, testing and maintenance requirements of this standard. However such evaluation is the responsibility of the property owner or designated representative as indicated in Sections and
19 OBSERVATION FORM OBSERVATIONS NAME: ADDRESS: CITY, STATE, SITE ADDRESS INSPECTOR: SIGNATURE: DATE: ZIP: While performing the inspection of your water -based fire protection system to verify that the system is operational and address "normal wear and tear" of the system in accordance with the with the requirements of NFPA #25, we identified various potential issues as noted below. It is the Owner's responsibility to have these investigated to determine any system modifications required. Identification of design and/or installation flaws or code compliance violations is outside the scope of NFPA #25. No engineering survey or comprehensive evaluation was completed as part of this inspection and should not be interpreted to mean one was performed. 7/1/2009
22 NFPA 25 Chapter 3 Definitions Inspection A visual examination of a system or portion there of to verify that it appears to be in operating condition and is free of physical damage. The intent of the inspection, as described in NFPA 25, is to look for obvious signs of damage or wear and, most important, to verify that water control valves are open. Deficiency none (2002) Deficiency (2011 Proposed) For the purposes of inspection, testing, and maintenance, a condition in which a system or portion thereof is damaged, inoperable, or in need of service Impairment A shutdown of a system or portion there of Impairment (2008) A condition where a fire protection system or unit or portion thereof is out of order, and the condition can result in the fire protection system or unit not functioning in a fire event. A Impairment Temporarily shutting down a system as part of performing the routine inspection, testing, and maintenance on that system while under constant attendance by qualified personnel, and where the system can be restored to service quickly, should not be considered an impairment. If the system is down for more than 4 (10 hours in 2008) hours for system modification or emergency repairs, there should be a procedure in place as far as notification of proper parties, may involve evacuation of the building, fire watch and other procedures as required by your insurance company and local fire marshal.
23 NFPA 25 Inspection: (1) no signs of leakage (2) free of corrosion (3) free of foreign materials (4) free of paint (5) free of physical damage (6) in proper orientation 2008 includes position of deflector in relation to the ceiling slope (7) glass bulb full (8) no obstruction to spray pattern Inspect annually from the floor level Painted sprinklers should never be cleaned and reinstalled, because the paint can get under the sprinkler cap and act like an adhesive, delaying or preventing sprinkler operation. A light overspray can be tolerated when a representative sample is tested to verify the sprinklers will operate as intended. Sprinklers shall not be altered in any respect or have any type of ornamentation, paint, or coatings applied after shipment from the place of manufacture.
24 NFPA 25 Note: nothing is mentioned about escutcheons. A missing, painted or corroded escutcheon will not affect sprinkler operation Sprinklers that are subject to recall shall be replaced per the manufacturer s requirements The minimum clearance required by the installation standard shall be maintained below all sprinklers. Stock, furnishings, or equipment closer to the sprinkler than the clearance rules allow shall be corrected. A Where documentation of the installation date is not available, the start date for the interval should be based upon the sprinkler s manufacture date.
NFPA 25, Table A.3.3.7: Identifying & Classifying Deficiencies & Impairments Presented by Terry Victor To receive credit for this seminar, you must 1) sign in on Sign-In sheet, 2) attend seminar in its
DEPARTMENT OF CONSUMER AND INDUSTRY SERVICES DIRECTOR'S OFFICE CERTIFICATION OF FIRMS FOR FIRE ALARM SYSTEMS AND FIRE SUPPRESSION SYSTEMS IN STATE-REGULATED FACILITIES (By authority conferred on the state
Page 18 ABOUT CODE CORNER CCFS would like to remind you to check with your local Authority Having Jurisdiction (AHJ) for questions and opinions concerning your local Fire and Building Codes. The information
1.0 Policy Statement The University of New Haven has developed a Fire Alarm and Protection Impairment Plan in accordance with the National Fire Protection Associations (NFPA) codes. Specific codes referenced
1 FLORIDA ALARM CONTRACTOR ALARM CONTRACTING LAW Continuing Education Course ADVANCED 4HR MODULE PRESENTED BY THE ALARM ASSOCIATION of FLORIDA, Inc. www.fla-alarms.org alarms.org email@example.com
MERCER ISLAND FIRE DEPARTMENT FIRE COMMERCIAL SPRINKLER STANDARDS COMMERCIAL FIRE SPRINKLER SYSTEMS Page 1-5 SCOPE: Fire sprinkler systems in the City of Mercer Island shall meet the criteria as set forth
527 CMR 23.00: ISSUANCE OF CERTIFICATES FOR THE SERVICING OF PORTABLE FIRE EXTINGUISHERS AND THE INSTALLING AND SERVICING OF FIXED FIRE EXTINGUISHING SYSTEMS Section 23.01: Purpose 23.02: Applicability
Fire Prevention Coffee Break Training February 2015 Agenda Hood Permit Policy Amendment- Fire Marshal Lund FAQ s and Alternative Design FPE Phelan Coordination Issues During Final Testing Questions and
THE RULES OF THE SAFETY FIRE COMMISSIONER ARE HEREBY FURTHER AMENDED BY ADDING A NEW CHAPTER 120-3-2 3 E N T I T L E D RULES AND REGULATIONS FOR INSTALLATION; INSPECTION; RECHARGING, REPAIRING, SERVICING
Sec. 121.50. - Short title. Sec. 121.51. - Definitions. Sec. 121.52. - Alarm permit and fee. Sec. 121.53. - False fire alarm fees and fines. Sec. 121.54. - Suspension, revocation, or reinstatement of alarm
IAC 6/17/09 Public Safety Ch 275, p.1 CHAPTER 275 CERTIFICATION OF AUTOMATIC FIRE EXTINGUISHING SYSTEM CONTRACTORS 661 275.1(100C) Establishment of program. There is established within the fire marshal
LOUISIANA DEPARTMENT OF PUBLIC SAFETY AND CORRECTIONS OFFICE OF STATE FIRE MARSHAL, CODE ENFORCEMENT AND BUILDING SAFETY H. Butch Browning State Fire Marshal Bobby Jindal Governor Licensing Law and Rules
CITY OF SPRING LAKE PARK Code Enforcement Department 1301 81 st Avenue NE Spring Lake Park MN 55432 Business Phone 763-784-6491 Fax 763-792-7257 INSPECTION, TESTING AND MAINTENANCE OF FIRE PROTECTION SYSTEMS
Metropolitan Washington Airports Authority Office of Public Safety Fire & Rescue Department Fire Code Enforcement Division Fire Protection System Impairment Requirements For Contractors and Service Personnel
STATE OF OKLAHOMA 2nd Session of the 44th Legislature (1994) HOUSE BILL NO. 1984 By: Phillips AS INTRODUCED An Act relating to professions and occupations; amending 59 O.S. 1991, Sections 1002, as amended
DEPARTMENT OF PUBLIC SAFETY CODE ENFORCEMENT AND CERTIFICATION OF INSPECTORS FOR PUBLIC SCHOOLS, CHARTER SCHOOLS AND JUNIOR COLLEGES 8 CCR 1507-30 [Editor s Notes follow the text of the rules at the end
Please type or print clearly. Incomplete applications will not be processed. Typical processing time is 5 business days. 1. Property Address (MANDATORY) Applicant must provide a physical property address
Procedure No 400.10 Subject: Fire Protection Impairment Program Reference: NFPA (see bottom of page 5) Effective Date: March 2008 Distribution All Employees Review Date: April 2008 Purpose: To establish
Article XIII. Alarm Systems November 16, 1991, May 5, 2012 Section 1. Title and Purpose This bylaw shall be known as the Alarm System Bylaw. The purposes of this bylaw are to encourage alarm users to maintain
ORDINANCE NO. 2010-O-01 AN ORDINANCE AMENDING ORDINANCE 2009-O-05 REGULATING AND CODIFYING THE AUTOMATIC FIRE ALARM AND DETECTION SYSTEM CODE OF THE DEERFIELD-BANNOCKBURN FIRE PROTECTION DISTRICT WHEREAS,
Chapter 8 ALARM SYSTEMS [HISTORY: Adopted 5-18-2004 by the Annual Town Meeting, Art. 27. Amendments noted where applicable.] Noise -- See Ch. 40. GENERAL REFERENCES ~ 8-1. Title and purpose. A. This bylaw
Chapter 693 1999 EDITION Plumbers GENERAL PROVISIONS 693.010 Definitions 693.020 Application 693.025 Insurance required of certain providers of low-flow showerheads or faucet aerators LICENSING 693.030
Pinellas County Ordinance Sec. 122-1. Identification of commercial vehicles. (a) Definitions. As used in this section: Commercial vehicle is defined as any vehicle, commercial in its design and structure,
SOCIETY OF FIRE PROTECTION ENGINEERS (SFPE) NATIONAL SOCIETY OF PROFESSIONAL ENGINEERS (NSPE) NATIONAL INSTITUTE FOR CERTIFICATION IN ENGINEERING TECHNOLOGIES (NICET) POSITION STATEMENT THE ENGINEER AND
Rancho Cucamonga Fire Protection District Prevention Bureau Standard Title: Fire Alarm and Monitoring Systems Standard # 9-3 Effective: May 2002 Number of Pages: 7 Revised: January 2014 INTENT The intent
Texas Insurance Code Article 5.43-2 Fire Detection and Alarm Devices & 28 TAC 34.600 the Fire Alarm Rules Texas Department of Insurance State Fire Marshal s Office P. O. Box 149221 Austin, Texas 78714-9221
CHAPTER 2010-176 Council Substitute for Council Substitute for Committee Substitute for Committee Substitute for House Bill No. 663 An act relating to building safety; amending s. 196.031, F.S.; specifying
EXHIBIT A SCOPE OF WORK 1. (Contractor) shall provide fire alarm system maintenance/repair/testing services as described herein to the California Department of Veterans Affairs (hereinafter CDVA, CalVet,
Winnipeg Fire Department Fire Prevention Branch Manitoba Fire Code Life-Safety Equipment Maintenance Requirements The Fire Prevention Branch of the Winnipeg Fire Department has prepared this document of
HOUSE BILL No. 2114 AN ACT concerning the vehicle dealers and manufacturers licensing act; relating to vehicle bonds; amending K.S.A. 2000 Supp. 8-2404 and repealing the existing section. Be it enacted
PART 1 GENERAL 1.01 Scope of Standard A. This standard provides general requirements of The University of Texas at Austin for the design and construction of standpipe systems to include combination standpipe
Alachua County False Alarm Ordinance CHAPTER 121. ALARM SYSTEMS *Cross references: Business licenses and regulations, tit. 6; noise control, ch. 110; sheriff, ch. 271; construction codes, ch. 331; fire
Pedicab and Neighborhood Electric Vehicle (NEV) Certificate of Operation Application Guide INSTRUCTIONS 1. Fill out application completely. Incomplete applications cannot be processed. 2. The application
CHAPTER 67.2 RESIDENTIAL BUILDING CODE 1. APPLICABILITY. This Chapter shall have, along with the Code adopted hereby, the scope and applicability set out in said code except as modified by the provisions
EULESS FIRE DEPARTMENT FIRE MARSHAL S OFFICE INFORMATION LINE: Revised 2/12 Fire Chief Wes Rhodes Fire Marshal Paul Smith EFD-FMO 3-2 2009 International Fire & Building Code as Amended NFPA Standards Adopted
www.icc-es.org (800) 423-6587 (562) 699-0543 A Subsidiary of the International Code Council ICC EVALUATION SERVICE, LLC, RULES OF PROCEDURE FOR EVALUATION REPORTS 1.0 PURPOSE These rules set forth procedures
GENERAL ASSEMBLY OF NORTH CAROLINA SESSION H 1 HOUSE BILL Short Title: Building Code Reg. Reform. (Public) Sponsors: Referred to: Representatives Brody, Riddell, Cotham, and Watford (Primary Sponsors).
ADOPTED REGULATION OF THE DIVISION OF PUBLIC AND BEHAVIORAL HEALTH OF THE DEPARTMENT OF HEALTH AND HUMAN SERVICES LCB File No. R004-14 Effective April 1, 2014 EXPLANATION Matter in italics is new; matter
2013 Officers President Richard King BOMA SW Florida (954) 927-6119 Vice President Lacey Willard BOMA Gtr Tampa Bay (813) 273-8412 Treasurer Rick Beaver BOMA Jacksonville (904) 504-9405 Secretary Chris
Substitute for HOUSE BILL No. 2024 AN ACT enacting the Kansas roofing contractor registration act. Be it enacted by the Legislature of the State of Kansas: Section 1. Sections 1 through 18, and amendments
Form No. 1343 ALTA Plain Language Commitment Title Insurance Commitment ISSUED BY Issued By AGREEMENT TO ISSUE POLICY We agree to issue policy to you according to the terms of the Commitment. When we show
Session of 00 HOUSE BILL No. 0 By Committee on Insurance - 0 0 AN ACT enacting the Kansas professional employer organization licensing act. Be it enacted by the Legislature of the State of Kansas: Section.
Senate Bill No. 285 Senator Hardy CHAPTER... AN ACT relating to emergency medical services; revising provisions governing the exemption of certain air ambulances and attendants from the provisions governing
OKLAHOMA STATUTES TITLE 59. PROFESSIONS AND OCCUPATIONS PLUMBERS AND PLUMBING CONTRACTORS Section 1001. Citation Sections 1001 through 1023.1 of this title shall be known and may be cited as "The Plumbing
CHAPTER 6.60. - OPERATION OF COMMERCIAL AND RESIDENTIAL ALARM SYSTEMS Sec. 6.60.010. - Definitions. In this Chapter the following words and terms shall have the following meanings ascribed to them unless
CITY OF THOMPSON BY-LAW NUMBER 1384-91 [As amended by AM B/Ls 1755-2007 and 1791-2009] BEING A BY-LAW OF THE CITY OF THOMPSON TO REGULATE AND CONTROL ALARM SYSTEMS. WHEREAS pursuant to Section 287 of The
Environment of Care Fire Safety Management Plan 2014 Updated 4.29.2014 PURPOSE The purpose of the Fire Safety Management Plan is to ensure that all facilities are designed, constructed, maintained, and
Section 105 CMR 400.00: STATE SANITARY CODE CHAPTER I : GENERAL ADMINISTRATIVE PROCEDURES 400.001: Purpose 400.002: Authority 400.003: Citation 400.010: Scope of the State Sanitary Code 400.015: Effect
FIRE DEPARTMENT Bureau of Fire Protection and Life Safety www.cityofsanmateo.org 1900 O Farrell, Suite 140 San Mateo, CA 94403-1332 (650) 522-7940 FAX: (650) 522-7941 TDD: (650) 522-7047 MAINTENANCE AND
RULE Office of the Governor Real Estate Appraisers Board Appraisal Management Companies (LAC 46:LXVII.Chapters 301-309) Under the authority of the newly enacted Appraisal Management Company Licensing and
White Paper Scope of Practice Plumber, Underground Utility and Fire Sprinkler Contractors by Buddy Dewar, VP NFSA February 7, 2012 1 Executive Summary The Florida Legislature has clearly established contractor
Lubbock Fire Marshal s Office 1601 Mac Davis Lane Lubbock, Texas 79401 806-775-2646 Fax 806-775-3508 firstname.lastname@example.org Fire Alarm Submittal Requirements and Acceptance Testing To all Registered
IOWA STATE FIRE MARSHAL DIVISION Attn: Jeannie Shepherd 215 E Seventh Street; Des Moines, IA 50319 Phone: 515-725-6178 Fax: 515-725-6140 Email: email@example.com LICENSING APPLICATION CHECKLIST
SECTION 105 PERMITS SECTION 105 PERMITS 105.1 Required. Any owner or authorized agent who intends to construct, enlarge, alter, repair, move, demolish, or change the occupancy of a building or structure,
FLORIDA DEPARTMENT OF HEALTH BOARD OF DENTISTRY N-PROFIT CORPORATION PERMIT APPLICATION Applications will be accepted only if completed by an officer of the non-profit organization. Any questions not applicable
ORDINANCE NO. 2004-286 AN ORDINANCE regulating alarm monitoring companies and monitored alarm devices, imposing license fees, recovering costs related to responses to false alarms, and providing for enforcement
SECTION 9.12. ALARM SYSTEMS IN GENERAL, INCLUDING FIRE ALARM (a) Definitions. Alarm business shall mean any business operated for profit, which engages in the activity of altering, installing, leasing,
Title 153 - NEBRASKA STATE FIRE MARSHAL Chapter 19 - FIRE SPRINKLER SYSTEM INSPECTIONS Scope. Chapter 19 of Title 153 of the Nebraska Administrative Code is concerned with the certification of contractors
FLORIDA DEPARTMENT OF HEALTH BOARD OF DENTISTRY APPLICATION FOR TEACHING PERMIT Chapter 466.002, Florida Statutes Rule 64B5-7.005, Florida Administrative Code Applications will be accepted only if completed
IOWA STATE FIRE MARSHAL DIVISION Attn: Jeannie Shepherd 215 E Seventh Street; Des Moines, IA 50319 Phone: 515-725-6178 Fax: 515-725-6140 Email: firstname.lastname@example.org LICENSING APPLICATION CHECKLIST
ARTICLE XI ALARM SYSTEMS Section 15-232. DEFINITIONS ALARM SYSTEM means a device or system that emits, transmits, or relays a signal that is intended to notify the public safety department of an unauthorized
Chapter 3 ALARM SYSTEMS Chapter 3 ALARM SYSTEMS  ARTICLE I. - IN GENERAL ARTICLE II. - BURGLARY AND ROBBERY ALARMS ARTICLE III. - FIRE ALARMS FOOTNOTE(S): --- (1) --- City Code cross references Fire
Gypsum Fire Protection District Fire Sprinkler System Submissions Fire Sprinkler System Submissions for permit will fall under one of two categories: new installations or remodels. New installations or
Orange County Drainage District 8081 Old Hwy 90 Orange, Texas 77630 Main Office (409) 745-3225 Fax (409) 745-3004 PIPELINE AND UTILLITY PERMIT APPLICATION PACKET Contact the Orange County Drainage District
Attachment B (5/2000) VERMONT DEPARTMENT OF BANKING, INSURANCE, SECURITIES AND HEALTH CARE ADMINISTRATION INFORMATION FOR COMPLETING BIOGRAPHICAL REPORT Biographical Reports must be filed by each director,
Revised 9/14/2011 ALARM SYSTEM FEES Alarm system permit fee (annually) $50 Alarm system service fee $50 if in excess of 5 alarms per year (12 alarms for apartments) ARTICLE 4.500 ALARM SYSTEM BUSINESSES
1 RCNY 101-07 CHAPTER 100 Subchapter A Administration 101-07 Approved Agencies. (a) Definitions. For the purposes of this section, all terms used herein shall have the same meanings as set forth in the
56:8 136 Short title. This act shall be known and may be cited as the "Contractors' Registration Act." L.2004,c.16,s.1. 56:8 137 Definitions relative to home improvement contractors. As used in this act:
BUCKS COUNTY DEPARTMENT OF HEALTH RULES AND REGULATIONS FOR CONDUCTING AND OPERATING FOOD FACILITIES EFFECTIVE DATE: October 1, 2014 BUCKS COUNTY DEPARTMENT OF HEALTH RULES AND REGULATIONS FOR CONDUCTING
ARTICLE 17-09. CONTROLS AND REGULATIONS FOR ALARM USERS 17-09-010. Short title. This ordinance shall be known and may be cited as the "Alamogordo Alarm System Ordinance." 17-09-020. Purpose. The purpose
S.B. SENATE BILL NO. SENATORS FARLEY, HARRIS AND HARDY MARCH, 0 Referred to Committee on Health Human Services SUMMARY Revises certain provisions governing air ambulances. (BDR 0-0) FISCAL NOTE: Effect
ORDINANCE NUMBER 3325 AN ORDINANCE OF THE CITY COUNCIL AMENDING CHAPTER 15.48 OF THE MISSOULA MUNICIPAL CODE ENTITLED "ALARM SYSTEMS" BE IT ORDAINED that Chapter 15.48 of Missoula Municipal Code is hereby
ALARM SYSTEM REGULATIONS BE IT ENACTED by the County Legislature of the County of Cattaraugus as follows: SECTION 1. Legislative Intent. 1.1. It is the intent of this Local Law to regulate and control,