1 Ontario Electrical Safety Code 25 th Edition/ 2012 Ted Olechna Director, Codes and Standard Chief Engineer 1
2 What I Will Cover ESA s role is as the regulator Highlight of 2012 Code changes The Code and new Green technology Ontario differences 2
3 Electrical Safety Authority Bill 35, the Electricity Act, 1998 Section 113 (1) The Electrical Safety Authority, subject to the approval of the Lieutenant Governor in Council, may make regulations, - prescribing the design, construction, installation, protection, use, maintenance, repair, extension, alteration, connection and disconnection of all works and matters used or to be used in the generation, transmission, distribution, retail or use of Electricity in Ontario; Electrical For Your Safety Authority 2011 E-Tech marketing Forum
4 Electrical Safety Authority Mission and Vision Our Mission: To Improve electrical safety for the well being of the people of Ontario. Long Term Vision: An Ontario free of electrical fatalities and serious injury, damage or loss. Electrical For Your Safety Authority 2011 E-Tech marketing Forum
5 Regulations OESC is mandatory The OESC is passed into law by the Provincial Government Utility Regulations 2004 Contractor Licensing 2005 Product Safety 2007 Electrical For Your Safety Authority 2011 E-Tech marketing Forum
7 CEC CODE changes OESC 2012 Major changes 273 proposals were submitted to the CSA 175 proposals 10 new interpretations are approved and in the new edition Ontario amendments 11* Ontario amendments are changed; plus Rule 2-005, An application for inspection not required is amended (to be finalized in Fall 2011) 7
8 Basic Exemption - proposed The following are the changes under consideration: Modify the existing Rule to include owner occupied dwelling unit when the work is performed by a licensed electrical contractor; New amendment to allow unit owners to replace certain light fixtures & switches within an Owner-Occupied Single Dwelling; New amendment to permit wiring from approved class 2 extra low voltage power supply within an Owner-Occupied Dwelling Unit; New amendment to allow the replacement or connection of specific listed appliances by specific trades, in accordance to their designation, within an owner-occupied dwelling; and New amendment to allow the repair of utilization equipment by specific trades, in accordance to their designation, within an owner-occupied dwelling. 8
9 General Cable Ampacity Tables 1 to 4 Temperature Limitations OESC 2012 Major changes Overcurrent protection for No. 14, 12 and 10AWG conductors Grounding conductor size for AC systems Cablebus installation Tamper resistant receptacles Receptacle(s) on a roof top for equipment maintenance Receptacles exposed to the weather 9
10 Green Energy Installations OESC 2012 Major changes Renewable energy systems New Section 64 Solar photovoltaic systems Section 50 changes Electric vehicle charging infrastructure 10
11 Electric Vehicle Charging Systems Code Sections 2,8,26 and 86 11
12 Ontario Amendment Appendix B note to Rule 2-000(h) New Appendix B note to Rule 2-000(h) For electrical vehicles; This Code applies to electrical vehicle supply equipment and requires it to be approved and installed in accordance with applicable Code requirements. This Code does not apply to the inlet or on-board charging equipment as defined by Rule that does not provide bidirectional power feed, as specified by Rule
13 Demand factors for EV equipment Rule 8-200(1)(a) and (3) When determining the minimum ampacity of service or feeders conductors supplying: a single dwelling, any electric vehicle charging equipment loads shall be considered with a demand factor of 100%. New Rule 8-200(1)(a)(vi) in apartment and similar building shall be added with a demand factor of 100% New Rule 8-202(3)(d) As required by the Building Code The electric vehicle charging equipment loads shall not exceed 80% of the rating of the overcurrent device, Rule 8-104(5). 13
14 Demand factors for EV equipment Rule 8-200(1)(a) and (3) Demand factors in a single dwelling A typical single family dwelling with 2000 ft² (186 m²) of living area: 14
15 Electric vehicle systems Rule Receptacles for charging equipment Amended Rule (1)(a) (1) Each receptacle for the purpose of electric vehicle charging shall be labeled in a conspicuous, legible, and permanent manner identifying it as an electric vehicle charging receptacle and shall be (a) a single receptacle of CSA configuration 5-20R supplied from a 125 V branch circuit rated not less than 20 A; or (b) of the appropriate CSA configuration in accordance with Diagram 1 or 2 when supplied from a branch circuit rated at more than 125V or more than 20 A. 15
16 Electric vehicle systems Rule (3) EV charging sites in commercial garages New Rule (3) (similar to new Rule (4)) Charging equipment installed in commercial garages or on premises of flammable liquid and gas dispensing and service facilities described in Section 20 shall comply with Rule and shall not be located in the hazardous area as described in Rule
17 Electric vehicle systems Rule Height of vehicle charging equipment New Rule The height of the electric vehicle charging equipment shall be located at a height of not less than 450mm and not more than 1.2m above the floor level. 17
18 Solar Photovoltaic installations Section 50 18
19 Agenda Changes/additions to existing Rules Marking PV source and output circuit voltage PV circuit current rating Overcurrent protection Wiring methods Attachment plug 19
20 Agenda New Rules and requirements: Voltage drop AFCI protection for DC circuits Grounding Inverter 20
21 Rule Photovoltaic dc arc-fault circuit protection It is the direction in Ontario that DC AFCI will not be required until May 1 st,
22 Rule Wiring methods (Amended) Newly developed Solar cables type RPV & RPVU in Part II Standard A new standard CSA C22.2 No. 271 (published May 2011), Photovoltaic Cables specifies the requirements for photovoltaic single-conductor and multiconductor thermoset-insulated wires and cables rated 600 V, 1000 V and 2000 V. The standard applies to conductors installed between solar panels and from solar panels to the inverter or combiner box or from combiner box to inverter. 22
23 Rule Wiring methods (Amended) Newly developed Solar cables type RPV & RPVU Part I Standard tables New cables type RPV and RPVU are also recognized in Tables 6, 10B and 19 23
24 Rule Attachment Plugs (Amended) Used to be , renumbered to fit. New Subrule (2) added to require the attachment plugs to be of a type that requires the use of a tool to open, when: Readily accessible; and Used in circuits operating at over 30V 24
25 Rule Power Conditioning Unit (New rule) Utility Interactive systems, Inverters approved for the purpose Connection to other sources Only inverters and AC modules approved and identified as interactive shall be permitted in interactive systems. This is existing direction in Ontario as per current Bulletin 84-1-* 25
26 Rule Power Conditioning Unit (New rule) Multiple 1-phase inverters form 3-phase interactive system Unbalanced interconnection 1) Single-phase inverters and AC modules in interactive renewable energy systems shall not be connected to 3-phase systems, unless the interconnected system: a) Is designed to provide balanced 3-phase output; b) Complies with Rules and ; and c) Complies with the supply authority requirements This is existing direction in Ontario as per current Bulletin 84-1-* 26
27 Renewable energy systems Code Sections 64
28 Special terminology Rule Renewable Energy. energy derived from resources that are naturally replenished, such as sunlight, wind, water, tides, and geothermal heat.
29 Rule Renewable Energy System a complete system enabling a renewable energy source to be connected to a utilization load. Special terminology.
30 Rule Special Terminology Small wind system. A system consisting of one or more wind turbines with a rated output up to and including 100 kw. Small wind systems
31 Rule Special Terminology a system consisting of one or more wind turbines with rated power output exceeding 100 KW rated power output. Large wind systems
32 Stationary Fuel Cell
33 MICRO-HYDROPOWER SYSTEMS 33
34 Hydrokinetic system a system operating as an interconnected or stand-alone system and consisting of one or more hydrokinetic turbines that convert the kinetic energy of flowing water into electrical energy with a rated output of up to and including100 kw.
35 STORAGE BATTERIES RULE
36 General Rule Overcurrent protection Where a circuit breaker is backfed ( LOAD to LINE rather than LINE to LOAD ) it shall be approved for the purpose. Circuit breakers labelled LINE and LOAD are not approved to be backfed.
38 General Rule Interconnections to other circuits Where the renewable energy system is not intended to be interconnected with the supply authority the system shall be designed so that it is impossible to have both systems connected at the same time.
39 General Rule Interconnected system connections (1) The output from a utility-interactive inverter or power conditioner shall be connected to the line side of the service disconnecting means in accordance with Section 84, except as permitted in Subrule (3).
40 General Rule Interconnected system connections Cont d
41 General Rule Systems in access of 750 V dc Where the maximum system voltage of a renewable energy source exceeds 750 V dc it shall comply with the requirements of Section 36 and any other requirements applicable to these installations.
42 Other Code changes 42
43 Receptacles General Tamper resistant requirements New Subrule (12) Tamper resistant receptacles now required in child care facilities
44 Receptacles General Receptacles exposed to weather Rule is amended to require 15A and 20A (125V and 240V) receptacles exposed to weather to be provided with cover plates suitable for wet locations that will provide shielding with and without a plug inserted into the receptacle.
45 Rule (1) & (2) Receptacles General Receptacles exposed to weather As per Rule (1) Requires to be marked Wet Location Only When Cover Closed As per Rule (2) Requires to be marked WET Locations whether or not a plug is inserted into it.
46 Installation of lighting equipment Circuit connections Amended Subrule (4) Fluorescent luminaire disconnect means. (4) The connection of branch circuit conductors exceeding 150 volts-to-ground to the conductors of each fluorescent luminaire utilizing double-ended lamps shall be made by one of the following ways;
47 Administrative Rule 2-022(3) Approval of LED luminaires New Rule 2-022(3)(c)(ii) Luminaires with LED lamps supplied from a class 2 powers supply are required to be approved. 47
48 Administrative Rule Approval of LED luminaries New Appendix B note to Rule 2-022(3)(c) Decorative light strings, signs or displays with LED lamps other than LED luminaries that are connected to approved class 2 power supplies are not required to be approved. 48
49 Wiring methods Rule (1) Use of rigid non-metallic conduit in fire alarm systems Amended Rule (1) Conductors of a fire alarm systems are now permitted to be installed in rigid nonmetallic conduit without being embedded in 50mm of masonry (as per current ESA Bulletin 32-3-*) 49
50 Wiring methods Rule (1) Use of rigid non-metallic conduit in life safety systems Amended Rule (1) Conductors described in Rule (Life Safety, Emergency etc.) are now permitted to be installed in rigid non-metallic conduit without being embedded in 50mm of masonry (as per current ESA Bulletin 46-4-*). 50
51 New Cable types in Tables 11, 12 and 19 Table 19, Armoured cable types ACG & ACGWU ACG90 a 14 AWG to 6 AWG multi-conductor aluminum interlocked armoured cable with aluminum bonding conductor in intimate contact with armour designed for applications permitting the use of the armour as a means of equipment bonding. ACGWU90 Same construction as the ACG90 with the addition of the overall jacket.
52 New Cable types in Tables 11, 12 and 19 Table 19, Cable Type ACG & ACGWU The construction of ACG & ACGWU cables incorporates a full size aluminum bond conductor in direct intimate contact with the interlocked armour.
2012 Canadian Electrical Code, Part I (CEC) Top Fifteen changes 1) Tamper resistant receptacles. 2009 CEC Required in dwelling units 2012 CEC Expanded to child care facilities First introduced in the 2009
*** Provide this document to the inspector along with ALL system installation instructions *** Project Address: Scope: Standard plan for the installation of grounded microinverter solar PV systems, not
County of Riverside Building and Safety Department Mike Lara Director Photovoltaic Permitting Guidelines The information provided in this document is general and is intended only as a guide. Each project
What are the basic electrical safety issues and remedies in solar photovoltaic installations? Presented by: Behzad Eghtesady City of Los Angeles Department of Building and Safety Topics Covered Photovoltaic
City of San Diego Residential Photovoltaic Systems Inspection Guidelines The purpose of inspections by DSD staff is to ensure compliance with the California Electrical Code (CEC), other applicable codes
2011/2008/2005 NATIONAL ELECTRICAL CODE SOLAR PV CODE COMPLIANCE REFERENCE PAGE 1 OF 5 This Reference provides a very comprehensive list of aspects of a solar PV installation that could be reviewed, clarifying
Department of Community Development Building Division 4800 West 92 nd Avenue Westminster, Colorado 80031 For Information call (303) 658-2075 Fax (303) 706-3922 www.westminsterpermits.com Top Commercial
9229 Waterford Centre Dr. Bldg C, Suite 110 Austin, Tx 78758 Application Bulletin 103 - NEC Reference Guide for SolarBridge-Enabled AC Module Installers Current Version: 13 AC Modules are a new product
RESIDENTIAL ELECTRICAL REQUIREMENTS (REVISED 3/28/2008) PERMIT REQUIREMENTS: Signed completed Electrical Permit application form. Minnesota law requires all electrical work is to be performed by licensed,
City of Cotati Building Division 201 W. Sierra Ave. Cotati, CA 94931 707 665-3637 Fax 792-4604 INSTALLATION GUIDELINES for SOLAR PHOTOVOLTAIC SYSTEMS 1 Any PV system on a new structures should be included
PV and the Electrical Code Page 1 PV and the Electrical Code Canadian Solar Industries Association (CanSIA) PV and the Electrical Code Page 2 This course was prepared by the Canadian Solar Industries Association
ELECTRICAL GUIDELINES FOR SINGLE-FAMILY HOME OWNERS: Chapter 12 of the Burlington Code of ordinances allows owner occupants of single family homes to do their own wiring if they choose. If you choose to
ELECTRICAL INSPECTION BULLETIN (Effective 2000-03-01) Rule 28-900 Standby Generator Installations Due to the increasing number of standby generator installations being established to maintain continuity
Module The Solar America Board for Codes and Standards (Solar ABCs) Expedited Permit Process provides a means to differentiate systems that can be permitted quickly and easily due to their similarity with
12 SOLAR PHOTOVOLTAIC POWER by John Ware IT IS PLANNED for BS 7671:2008 to include a new Section 712 providing additional requirements for safety applicable to solar photovoltaic (pv) power supply systems.
ARTICLE 690 Solar Photovoltaic (PV) Systems INTRODUCTION TO ARTICLE 690 SOLAR PHOTOVOLTAIC (PV) SYSTEMS You ve seen, or maybe own, photocell-powered devices such as night lights, car coolers, and toys.
1. How do we accomplish grounding of furnaces and / or water heaters on two wire circuits? 250.134 Equipment Fastened in Place or Connected by Permanent Wiring Methods (Fixed) Grounding. Unless grounded
Solar Panel Installations Page 1 of 6 SINGLE-FAMILY RESIDENTIAL CHECKLIST City of Hayward Development Services Department Revised: 7-09-15 PERMIT REQUIREMENTS Permits are required for all solar panel installations.
Electrical for Detached Garages: Updated Feb 19, 2016 for 2015 CE Code in force Jan. 1, 2016 * Garage construction requires permits (electrical, building) * Permits must be applied for at the time. * Dial
White Paper SolarEdge Three Phase Inverter System Design and the National Electrical Code June 2015 Revision 1.5 Shalhevet Bar-Asher; SolarEdge Technologies, Inc. Bill Brooks, PE; Brooks Engineering LLC
Significant Changes in the 2011 NEC Prepared by Bryan Holland City of North Port Code-Wide Code Change Section 90.5(C). Fine Print Notes are now referred to as "Informational Notes." The purpose, intent,
NEC 2014 Code Changes Articles 400-408.55 CHANGES FROM 2011 TO 2014 CODE ARE IN RED Chapter 4 Equipment for General Use ARTICLE 400 Flexible Cords and Cables 400.4 Types Flexible cords and flexible cables
DEVELOPMENT AND RESOURCE MANAGEMENT DEPARTMENT BUILDING AND SAFETY SERVICES 2600 Fresno Street, Third Floor Fresno, California 93721-3604 (559) 621-8082 FAX (559) 498-4357 RESIDENTIAL PHOTOVOLTAIC SUBMITTAL
OCA #230100 First Published in The Wichita Eagle on January 2, 2015 ORDINANCE NO. 49-897 AN ORDINANCE AMENDING SECTIONS 4.A.080, 4.1.020, 4.1.110, 4.2.010, 4.2.070, 4.2.125, 4.2.170, 4.2.175 AND 4.2.220;
Name of School: OPTIONAL INFORMATION Date of Inspection: Vocational Program/Course/Room: Signature of Inspector: ELECTRICAL - WIRING DESIGN AND PROTECTION SELF INSPECTION CHECKLIST Guidelines: This checklist
Residential Solar Service Agreement (RSSA) Customer Sited Solar Photovoltaic Systems This Agreement is made and entered into this day of, 20, ( Effective Date ) by and between the Orlando Utilities Commission
CITY OF SONOMA TOOKIT DOCUMENT #1 Submittal Requirements for Solar Photovoltaic Installations 10 kw or Less in One and Two Family (Duplex) Dwellings This information bulletin is published to guide applicants
Request for Proposals for Photovoltaic System Installation Presented by: Prepared by: Location: Contact: Date: Capitol Hill Housing Foundation Bonneville Environmental Foundation, Renewable Energy Group
2011 National Electrical Code Changes Alan Manche, P.E. Director, Industry Standards d 2011 NEC Facts 5,016 public proposals 2,910, public comments 22 Certified Amending Motions at the NFPA Annual Meeting
Solar Water Heating and Photovoltaic Electrical Systems Installed on One or Two Family Dwellings I. BACKGROUND As awareness of renewable energy and green building options increases, solar energy systems
2014 NEC Guide Lines for Home Owner Doing Electrical Work on their Property A brief summary of the most used code references for residential wiring State of Idaho Division of Building Safety Electrical
ALL STAR ELECTRIC COMPANY 10,000 Trumbull SE, Suite #F Albuquerque, NM 87123 (505) 856-1010 voice & fax NM License 21880 www.allstarelec.com On-Site Power System Specialists: Photovoltaics, Wind Turbine
READ THIS MANUAL BEFORE PROCEEDING WITH THE INSTALLATION. FAILURE TO FOLLOW THE INSTALLATION INSTRUCTIONS MAY VOID YOUR WARRANTY! The main power to any existing system must be disconnected prior to the
Appendix C Electrical Grounding Low-Voltage Equipment Grounding The most frequently cited Office of Safety and Health Administration (OSHA) electrical violation is improper occupational grounding of equipment
BOARD OF BUILDING AND SAFETY COMMISSIONERS VAN AMBATIELOS PRESIDENT E. FELICIA BRANNON VICE-PRESIDENT JOSELYN GEAGA-ROSENTHAL GEORGE HOVAGUIMIAN JAVIER NUNEZ CITY OF LOS ANGELES CALIFORNIA ERIC GARCETTI
CANADIAN 2012 ELECTRICAL CODE Saskatchewan Interpretations Electrical Inspections Department Effective: December 1, 2012 For Free Distribution This publication is also available on the SaskPower website:
MISCELLANEOUS ELECTRICAL JOBS REQUIRING PERMITS 01. SAFETY INSPECTION of service equipment at FPL Power Source 02. Construction GFI power outlets (Temp Pole for Construction) 03. 90 day temporary power
AJ s Technical Tips: Designing a Small Solar PV System Part IV; Selecting Wires for the System A little while back Simon Nyukuri of Kitale wrote to ask me about sizing wires and cables for solar PV systems.
Connecting the Power of the Sun DC Disconnects for Solar Photovoltaic Installations DC disconnects for solar photovoltaic installations Solar energy is heating up Interest in renewable energy sources has
CHAPTER 2 EXAMPLES AND TABLES COMMENTARY AT 210.20(A) EXCEPTION An overcurrent device that supplies continuous and noncontinuous loads must have a rating that is not less than the sum of 100 percent of
(b) Recognized field evaluation marks (2) Approval (b) Recognized of devices field on evaluation class 2 circuits marks (2) Approval of devices on class 2 circuits Bulletin 2-7-29 Approval of electrical
H5HK Series Installation Instructions 3 Phase Electric Heater Kits 7.5 and 0 TON Package A/C Systems Description Installation of 08/40V and 480V H5HK 3 Phase Heater Kits in 7.5 and 0 TON Packaged Air Conditioners.
LOS ANGELES BASIN CHAPTER OF ICC MONTHLY CHAPTER MEETING ALHAMBRA, CA TOP 10 CHANGES 2013 CALIFORNIA ELECTRICAL CODE 2013 CALIFORNIA ENERGY CODE (ELECTRICAL) RON TAKIGUCHI, P.E. BUILDING OFFICIAL -CITY
Butte County Department of Development Services PERMIT CENTER 7 County Center Drive, Oroville, CA 95965 Main Phone (530)538-7601 Permit Center Phone (530)538-6861 Fax (530)538-7785 FORM NO DBP-71 PERMIT
Western Riverside County Code Uniformity Program City of Riverside Building & Safety Division Residential Electric Vehicle (EV) Charger Guidelines PHONE (951) 826-5697 3900 Main Street, Riverside, CA 92522
DC disconnects for solar photovoltaic installations Connecting the power of the sun Solar energy is heating up Interest in renewable energy sources has never been greater, and the fastest growing of these
Electrical safety of grid-connected solar installations in Western Australia December 2011 Level 1, 303 Sevenoaks Street (cnr Grose Avenue) Cannington, Western Australia 6107 PO Box 135 Cannington WA 6987
Electrical Code Requirements for Commercial and Residential Buildings Presented by Bob Nuzzi State Electrical Inspector Entrances to and from Electrical Equipment Rooms 2005 NEC Section 110.26(C)(2) Large
MicroFIT Connection Application Guidelines These guidelines serve to ensure the efficient processing and implementation of your project. Please read and follow them carefully and completely in order to
Homeowner Information Guide Electrical Safety British Columbia Safety Authority The following information should be carefully reviewed before performing any electrical work. The information contained in
Residential Electrical Inspection Checklist Based on the 2008 National Electrical Code Generally, Minnesota law requires all electrical work to be performed by licensed, bonded and insured electrical contractors
AC Module Installation Guide Content for ET-P660250AC May 9, 2012 2011-2012 ET Solar Group All Rights Reserved. No part of this publication may be reused in any manner nor in any form or format without
BUILDING CODE MANUAL COUNTY OF LOS ANGELES DEPARTMENT OF PUBLIC WORKS BUILDING AND SAFETY DIVISION Based on the 2014 LACBC #161 6807 Article 1 04-04-16 Page 1 of 4 EXPEDITED PERMITTING FOR SMALL RESIDENTIAL
Common Electrical Hazards in the Workplace Including Arc Flash Presented by Ken Cohen, PhD, PE & CIH (Ret.) 1 What s New In February 1972, OSHA incorporated the 1971 edition of the National Fire Protection
The U.S. Department of Labor projects that electrician careers will grow to 698,200 by 2022. Train now for affordable Electrician careers and get wired for success. Residential Electrician Diploma Program
Article 10 - ADMINISTRATIVE SECTION 10.1 TITLE These Administrative Regulations along with the requirements included in the 2011 Edition of the National Electrical Code (NFiPA-70-2011) as adopted by the
Instruction Bulletin EAV85226 08/2014 Wiser Panel Meter, Model Number WISERCTPM200 Installer s Guide Retain for future use. Product Description Kit Contents The Wiser Panel Meter is for use in energy management
A C M o d u l e Installation Guide Content for P250xV-240 microinverters May 15, 2012 2011-2012 SolarBridge Technologies, Inc. All Rights Reserved. No part of this publication may be reused in any manner
8146/5 Series Breaker Panelboards DISTRIBUTION BREAKER PANELBOARDS FOR HAZARDOUS & CORROSIVE ENVIRONMENTS Breaker Panels Features: Wide variety of Flameproof branch circuit breakers for Zone 1 & Division
1 RESIDENTIAL Screen Enclosures Orange County Residential Code Compliance Alternative design method for screen enclosures R301.2.1.1.3 PLAN REVIEW Engineered plans must state that the Alternative Design
DOMESTIC ELECTRICAL INSTALLATION CERTIFICATE (Requirements for Electrical Installations BS 7671 IEE Wiring Regulations) DETAILS OF THE CLEINT Client and address ADDRESS OF THE INSTALLATION Installation
PV Pv math Math by John Wiles As we look at the PV array in a PV system, we find that many installers and inspectors are confused by the new system voltage calculations that may be required by the Code
Fire Alarm System Monitoring - CAN/ULC-S561-03 Brian McBain ULC Regulatory Services May 4, 2011 Copyright 1995-2007 Underwriters' Laboratories of Canada. All rights reserved. No portion of this material
Addendum #2 Contract UK-11-13 Utilities Kingston Purchase and Replacement of Switchgear at Kingston Hydro Substation MS11 March 25, 2011 Delivered to: All RFP recipients Total number of pages: Nine (9)
Continuing Education Courses Presented by: The Electrical Association of Philadelphia **New Jersey licensees, you MUST have your 34 hours of continuing education completed by MARCH, 2012. This includes
PLEASE NOTE This document, prepared by the Legislative Counsel Office, is an office consolidation of this regulation, current to August 1, 2013. It is intended for information and reference purposes only.
SINGLE FAMILY DWELLING ELECTRICAL SERVICES RATED 225 TO 600 AMPS A. PURPOSE 1. The following information includes the basic permit application requirements for a 120/240 volt single phase Electrical Service
EQUIPMENT SUMMARY 20 LG 300W solar panels 1 SMA SE6000AUS Inverter Everest Solar Systems Cross Rail Racking System QuickMount PV Quick Hook Curved Tile Mount QMCTH SHEET INDEX T01 COVER PV01 SITE MAP &
1. Purpose Electrical Practices for Construction Work The purpose of this Code is to provide practical guidance and set minimum safety requirements for electrical practices on all construction sites in
This PDF contains the Oregon Electrical Law (ORS 479) and the Oregon Administrative Code (Division 918-251 thru 311). This document was created using the codes and statutes in effect as of 15 April 2008.
ADI 9510-B Advantium 2 Plus Alarm INSTALLATION AND OPERATING INSTRUCTIONS Carefully Read These Instructions Before Operating Carefully Read These Controls Corporation of America 1501 Harpers Road Virginia
Solar Kit Complete solution to optimize your photovoltaic system April 2012 Mounting and selection quick guide On Grid Solar Kit rooftop installation INSTALLATION WITH OVERLAID SUB-STRUCTURE (A.1, A.2)
THE MANITOBA ELECTRICAL CODE 12 TH EDITION AUGUST, 2015 Manitoba Regulation 124/2015 Including Technical Interpretations A publication issued by Manitoba Hydro This publication is also available on the
NOTICE OF INTENT Department of Revenue Policy Services Division Income Tax Credits for Wind or Solar Energy Systems (LAC: 61:I.1907) Under the authority of R.S. 47:287.785, R.S. 47:295, R.S. 47:1511, and
FACILITY FIRE PREVENTION AND EMERGENCY PREPAREDNESS INSPECTION CHECKLIST Date of Inspection: Conducted by: Location: Reviewed by: Date of Review: Comments or additional corrective action taken as a result
Building Permit Application Administrative Use Only PARENT PERMIT NUMBER (Required if part of another project) PERMITTEE: PERMITTEE ADDRESS: E-MAIL ADDRESS: ARCHITECT/ENGINEER: PHONE: PHONE: ARCHITECT/ENGINEER
COUNTY OF LOS ANGELES BUILDING AND SAFETY DIVISION ELECTRICAL CODE FEE SCHEDULE (Title 27 of the County of Los Angeles Code, Ord No. 2013-0049) Effective July 1, 2014, Electrical Permit Fees in the unincorporated
ADOPTION OF THE NATIONAL ELECTRICAL CODE, 2005 That a certain code, three (3) copies of which are now on file and have been on file for a period of not less than 21 days in the office of the Village Clerk