1 Inverter / Charger Installation General Operations and AC and DC Connections
2 The Inverter is just one piece. Sometimes, a tendency is to mount the inverter and batteries, and make it work It is better if we pay attention to the other practices that make a good, reliable installation.
3 Elements of the Inverter / Charger
4 Elements of the Inverter / Charger DC to AC Inverter; AC to DC Battery Charger; Transfer Switch between using AC Incoming Power or Battery Power; Transfer Switch to choose between two different AC Sources; Relays to perform a variety of user selected functions; and Computer with LCD screen and user input for customizing most of the variables.
5 Applicability This presentation is based on the Xantrex Model SW inverter, observed most frequently during field visits, and is applicable to models SW 4048 and SW 5548, which were most prevalent. With minor variations, this information can be applied to Outback Power equipment and other manufacturers equipment.
6 Modes of Operation: AC IN Operational The SW can be connected into an electrical scheme in many different ways. However, some common elements remain unchanged from installation to installation. The over-riding purpose of the SW is to provide continuous power to the loads (AC OUT). If there is power (with the proper characteristics) at the AC IN terminals, then the equipment will utilize this power to: Power the Loads (AC OUT); and Charge the Batteries through the built-in Battery Charger. The following diagram shows the operation and power flow when there is proper power supply at the AC IN terminals:
7 Modes of Operation: AC IN Operational
8 Operation: When AC IN Power is lost When power is lost to AC IN, the on-board computer switches the transfer switch so that the AC OUT loads are fed from the battery through the DC to AC Inverter, and the inverter is turned on. This happens nearly instantaneously. When this situation occurs, the entire load is powered by the battery bank. Of course, this can not go on forever, and when the battery bank reaches a programmed low state of charge (depicted by low voltage) the system turns off. (Alarms can be installed to warn operators of impending cut-out, see section 10.2)
9 Modes of Operation: AC IN Operational
10 AC IN 1 and AC IN 2 The SW model inverter/charger includes provisions for two AC Inputs. Field visits did not reveal any field application where both inputs were used. In many cases, both inputs will not be needed, but there are many applications where they would be useful. The basic system diagram changes only at the AC IN provisions:
11 AC IN 1 and AC IN 2
12 Connections to the Real World The SW equipment is strictly the core equipment necessary to monitor and switch power sources to feed the given load. In order to become part of the entire wiring system, it is essential to use proper wire sizes, and the proper fusing and disconnecting means to (a) protect the wiring, (b) protect the equipment, and (c) protect people. In many cases, when improper auxiliary equipment is used (or not used at all) not only is the result unsafe, but it also results in improper operation, battery failure and un-powered loads. These problems can be avoided by following some guidelines on connecting the SW equipment to the rest of the electrical system. In the next section, the manual will discuss AC OUT connections, AC IN connections, and finally DC and battery connections.
13 Connections to the Real World
14 AC OUT Connections All of the AC terminal blocks inside the SW AC box (on the left hand side of the unit) will accept up to #6 AWG conductors (16mm2). It is advised that this #6, 10mm2, or 16mm2 wire be used. The AC OUT terminals should be supplying only a predetermined set of loads. These loads should have been the basis of the selection of the size of the battery bank and the size of the inverter. These loads should be fed from a separate, dedicated circuit breaker panelboard connected to the AC OUT terminals. The conductors carrying the load current from the SW to this panelboard should land first in either a fused disconnect switch, or a main circuit breaker on the panelboard.
15 AC OUT Connections
16 AC IN Connections There are several options for AC IN connections: AC IN from a grid supply only AC IN from a generator supply only AC IN from both a grid supply and a generator supply AC IN from a combined grid / generator supply. The following section discusses each option.
17 AC IN 1 Grid Supply
18 AC IN 1 Grid Supply Even though the output of the inverter is limited to either 33 or 46 amps, it is important that the 60 amp circuit breaker is used and conductors feed the AC IN terminals. This is because when the grid power is on, it is performing two functions: First it is feeding the loads, and secondly it is powering the battery charger. The battery charger could draw up to as much as 30 amps depending on how the settings are programmed. If it is not possible to provide a 60 amp supply to the ACIN 1 terminals of the SW, then certain settings MUST be changed in the programming, and the design needs to be studied to be sure that the batteries will receive enough charging power. See the discussion under Programming for more information on this subject.
19 AC IN 1 Grid Supply
20 AC IN 2 - Generator
21 AC IN 2 - Generator The amount of power that can be drawn from the generator needs to be calculated (based on the size of the generator and other loads the generator may have to supply). If, for example, a 6KW generator is dedicated to this inverter, then the maximum power that can be obtained from the 6KW generator (if it is single phase) is 6000w / 120V or 50Amps. In this case, a 40 amp breaker to feed the SW and a therefore, 40A wire will be sufficient. If the generator is designed to support other loads as well, then how much of its power can be dedicated to the SW equipment needs to be determined and the breaker and conductors needs to be sized accordingly. The proper programming needs to be completed to match this value. The equipment needs to be programmed so that it does not try to pull any more power than the circuit breaker feeding it (or any more power than the generator feeding it.). This would trip the breaker and/or overload the generator. See the section on Programming for more information.
22 AC IN from both Generator and Grid
23 AC IN from both Generator and Grid When both grid power supply and generator power supply are available, the above is the preferred method for connecting to the system, particularly when the generator size requires a smaller circuit breaker and feeder that would be allowed by the grid input power. However, in most cases with grid and generator available, the two sources are combined in a transfer switch, with one set of conductors going into the SW, as shown below.
24 AC IN from both Generator and Grid
25 AC IN from both Generator and Grid Discuss pros and cons of the combined Generator / Grid AC IN wiring versus the separate Generator and Grid AC wiring.
26 AC IN and OUT Connections Summary of AC IN and AC OUT Connections There are several different configurations possible for the AC IN and AC OUT connections. Key factors to consider in planning the installation are: Sizing of the conductors for the greatest possible current that they may experience; Using dedicated, separate, AC OUT circuit breaker panelboards for the loads decided to be powered by the SW; Bringing separate AC IN 1 Grid conductors and AC IN 2 Gen conductors to the SW equipment panel; and Providing disconnecting means for the ACIN 1, AC IN 2, and AC OUT conductors to be able to isolate the SW equipment from any power wires. Additionally, the SW Cabinet should be installed in a readily accessible location (not in a storeroom), where ventilation from left to right is unobstructed, to provide adequate cooling.
27 AC IN and OUT Connections All of things cost money and take added effort, but compare the cost of the electrical work to the cost of the medical equipment we are trying to protect.
28 DC Connections
29 DC Connections Discussion topics here will include: Proper DC Cable connections to the SW Cabinet; Overcurrent / Disconnecting means in the DC Input cables; Connecting Strings of Batteries; and Paralleling the Strings of Batteries.
30 Connecting the DC Cables to the Inverter
31 Polarity IT IS EXTREMELY IMPORTANT THAT POLARITY IS NOT REVERSED AT THESE TERMINALS. THIS IS ONE OF THE FEW CONDITIONS THAT IS NOT PROTECTED WITH INTERNAL PROTECTION ON THE SW EQUIPMENT. IF BATTERY POWER IS APPLIED AT THESE TERMINALS WITH REVERSE POLARITY, BESIDES PHYSICAL DAMAGE, MOST OF THE INTERNAL POWER TRANSISTORS WILL BE DESTROYED RESULTING IN NON-WARRANTY DAMAGE AND THE UNIT WILL HAVE TO RETURNED FOR EXPENSIVE REPAIRS.
32 DC Cable from Battery to Inverter
33 Battery Cable Sizing (use 4/0)
34 DC Cable from Battery to Inverter Current Limiting Fuses in Positive Cables (4/0) Positive and Negative Cables kept together. DC Circuit Breakers in positive feed to individual inverters. System shown is Outback
35 Series Connections Sometimes the series connections are made with copper bus bars. These are 2V batteries, in sets of 24 in series
36 Series Connections More often, series connections are made with cables. These are 12V Batteries in sets of 4 in series
37 Connecting Batteries
38 Connecting Batteries
39 Paralleling Batteries ILSCO common bus terminal blocks for 4/0 cables 4 Strings of 48VDC batteries connected in parallel, and 2 home run cables back to cabinet.
40 Keep the Battery Cables Together We need to always keep the positive and negative battery cables together, as long as possible. As battery cables are separated by a distance, they have much more inductance than if they are close together. This induction creates an induced current which opposes the applied current. This leads directly to loss of inverter performance and greatly reduced efficiency. With cables separated by 48, the inductance can be 3 times greater than the inductance recognized if the cables are together. The result can be as dramatic as the inverter failing to allow certain loads to start, because it can not get the required current to flow in the batteries. This has been seen in cases where installers have done a very neat job in the installation but have grouped all positive cables on one side of a wall, and the negative cables on the other side.
41 Sum-UP We have Covered Elements of the Inverter / Battery System Connections to the Real World AC OUT Connections AC IN Connections DC Connections Still to come: Programming Operations and Maintenance Troubleshooting
HM-W536 Install Guide 9/13/2013 IMPORTANT SAFETY INSTRUCTIONS Warning - When using electrical devices, basic safety precautions should be followed to reduce the risk of fire, electrical shock or injury.
SUBJECT: How to wire a motor starter Number: AN-MC-004 Date Issued: 2/08/2005 Revision: Original A motor starter is a combination of devices to allow an induction motor to start, run and stop according
OVER THE COUNTER ELECTRICAL PERMIT CHECKLIST FOR RESIDENTIAL SOLAR PHOTOVOLTAIC SYSTEMS Contractors can apply for an Over The Counter (OTC) permit where the PV system meets the requirements listed in this
4KVA/5KVA Parallel Installation Guide 1. Introduction This inverter can be used in parallel with two different operation modes. 1. Parallel operation in single phase with up to 4 units. The supported maximum
Qualitative Analysis of Power Distribution Configurations for Data Centers White Paper #4 2007 The Green Grid. All rights reserved. No part of this publication may be used, reproduced, photocopied, transmitted,
*** Provide this document to the inspector along with ALL system installation instructions *** Project Address: Scope: Standard plan for the installation of grounded microinverter solar PV systems, not
Application Note Automatic management of two different energy sources General description This application note explains how a user can easily switch between two different energy sources at the entry of
Solar Home System User Manual AEHSHS0110W2L Solar Home System 2 Lamps All rights reserved Specifications subject to change without prior notice 2 Dear Customer, Thank you for purchasing Schneider Electric
Technical Note Freedom/Fleet Power 512-0084-01-01 Rev 1 Troubleshooting Guide, Freedom and Fleet Power Inverter/Chargers Overview This document is a guide for troubleshooting inverters, battery chargers,
Features: INSTALLATION Install in accordance with NFPA 70. DORMA MODEL PS-406BB POWER SUPPLY INSTALLATION INSTRUCTIONS Up to 1.95 Amps Load Capacity Class 2 Rated Outputs Overload, Over Voltage, and Short
NEWTECH PRO 1-2-3 KVA ONLINE UNINTERRUPTIBLE POWER SUPPLY USER MANUAL firstname.lastname@example.org / www.tuncmatik.com Table of Contents 1. Important Safety Warning 2 1-1. Transportation 2 1-2. Preparation 2 1-3.
ESP PANELS TM & SYSTEM COMPONENTS Instruction and connection manual Panel range System monitoring Panel ESP-SYSTEM AC circuit breaker panel ESP-AC-20A-11 DC circuit breaker panel ESP-DC-20A-11 Blank panel
AC Input Output Bypass switches are confusing to many experienced installers. Outback Power Systems continues to expand flexibility and capability thus making this subject even more confusing. This document
BB800 Off-Grid Solar System KEY PRODUCT FEATURES Control Box & Charge Controller 1000W of Solar Panels 4x200Ah of SLA Batteries in series 2KW Inverter Output Power Solar Panel & Battery Mounting Our entry
12 SOLAR PHOTOVOLTAIC POWER by John Ware IT IS PLANNED for BS 7671:2008 to include a new Section 712 providing additional requirements for safety applicable to solar photovoltaic (pv) power supply systems.
Proper Application of 415V Systems in North American Data Centers A White Paper from the Experts in Business-Critical Continuity Introduction Increasing pressure to reduce operating expenses and be more
Summary Argus Technologies Pathfinder10kW to Cordex3.6kW Shelf Replacement Procedure This is a general procedure on how to replace Pathfinder 48-10kW shelf with a Cordex 3.6kW shelf. Part Numbers 010-567-20
I=Inspected NI=Not Inspected NP=Not Present R=Not Functioning or In Need of Repair I NI NP R Inspection Item II. ELECTRICAL SYSTEMS A. Service Entrance and Panels Comments: Items noted during the visual
What are the basic electrical safety issues and remedies in solar photovoltaic installations? Presented by: Behzad Eghtesady City of Los Angeles Department of Building and Safety Topics Covered Photovoltaic
Ontario Electrical Safety Code 25 th Edition/ 2012 Ted Olechna Director, Codes and Standard Chief Engineer 1 What I Will Cover ESA s role is as the regulator Highlight of 2012 Code changes The Code and
Digital echo-charge Owner s Manual Xantrex Digital echo-charge Battery Charger Thank you for purchasing a Xantrex Digital echo-charge. Xantrex Technology Inc. takes pride in manufacturing quality products
YSmart Technology Co.,Ltd GWV Series Grid Tie Microinverter User Manual The copyright of this user manual belong to YSmart TechnologyCompany Limited. Without the written permission of the copyright holder,
Table of Contents www.eaton.com/dxups USER MANUAL ON LINE UPS 10000HXL31/15000HXL31/20000HXL31 Uninterruptible Power Supply Table of Contents 1. Brief introduction 1.1 System and model description---------------------------------------------------------------------1
FIT TIER 2 Application Application Information The below information Auto-Fills from your registration information: Building Permit Application Date: Project Completion Date: Name: Address: City: State:
INSTALLATION & SERVICE MANUAL Display Panel The PowerLine EMS TM is a specialized power distribution and energy management system intended to be used in recreational vehicles. The Control Module is housed
Automatic start of a generator General description This application note will help you to set your Xtender for an automatic start of a generator as per different parameters such as the output power, the
MCR1900 Media Converter 19-Slot Chassis Installation Guide Part #5500304-11 Copyright Statement This document must not be reproduced in any way whatsoever, either printed or electronically, without the
PV (photovoltaic) Basics There are generally two types of PV systems. The first and easiest (though the least flexible) is a grid tie system where the power generated by the solar panel (panels) runs an
12 Volt 30 Amp Digital Solar Charge Controller User s Manual WARNING Read carefully and understand all INSTRUCTIONS before operating. Failure to follow the safety rules and other basic safety precautions
Charge Regulator SCR 12 Marine Manual Many thanks for purchasing a superwind product. The SCR 12 Marine is a charge regulator of highest quality and will perfectly and reliably charge your batteries for
CHAPTER 5 PHOTOVOLTAIC SYSTEM DESIGN 5.1 Introduction So far in the development of this research, the focus has been to estimate the available insolation at a particular location on the earth s surface
OWNER'S MANUAL Model 20-1050CUL AC Power Inverter/Charger System OM/A96283 REV. A Table of Contents Section 1 Introduction... 1 Section 2 Installing the 20-1050CUL... 4 Section 3 Installing the IFM1 Interface
White Paper SolarEdge Three Phase Inverter System Design and the National Electrical Code June 2015 Revision 1.5 Shalhevet Bar-Asher; SolarEdge Technologies, Inc. Bill Brooks, PE; Brooks Engineering LLC
CM705B - Universal Expander Module CM707B - Plug On Zone Expander Security Systems EN Security System CM705B CM705B - Universal Expander Module The CM705B universal expander provides a cost effective way
TruPower-Portable-500W Solar Starter kit This Solar starter kit is an easy to use solar power supply system that is the complete solution for all your solar power needs. It is a solar generator that converts
HV Solar Inverter System GUI Overview January 2012 TMS320C2000 Systems Applications Collateral The HV Solar Inverter System GUI provides a simple interface to evaluate some of the functionalities of the
Understanding Emergency Power Off (EPO) White Paper #22 Executive Summary Emergency Power Off (EPO) is the capability to power down a piece of electronic equipment or an entire installation from a single
USER MANUAL EN Online UPS 6K/10K RACK Uninterruptible Power Supply System Please comply with all warnings and operating instructions in this manual strictly. Save this manual properly and read carefully
Solar inverters ABB PV + Storage REACT-3.6/4.6-TL 3.6 to 4.6 kw PV energy, combined with energy storage systems, can help increase self-consumption and energy selfsufficiency*. One of the biggest challenges
INSTALLATION GUIDE Card Reader & Controller with KIM Swipe Reader for Solitaire 850 / 950 / 850L Learnlok PK2930 Card Reader and Controller Model 3.5 with KIM Swipe Reader Table of Contents 1. Features..................................
..OR How To Protect your 3-Phase Equipment Investment with 3-Phase Monitors from Time Mark... TIME MARK CORPORATION 11440 EAST PINE STREET TULSA, OK 74116 USA tel 918 438-1220 fax 918 437-7584 www.time-mark.com
Grid PV-inverter 1500W/2000W/3000W/4000W/6000W Installation and Operation Manual 1 Only an electro-skilled person or trained assembly staff can install or open the Inverter. 2 Before you start Thanks for
RI-215A Operator s Manual Part Number: 71-0045RK Revision 0 Released: 10/3/05 Warranty RKI Instruments, Inc., warrants gas alarm equipment sold by us to be free from defects in materials and workmanship,
Samba OPLC SM35-J-R20 Installation Guide The Unitronics SM35-J-R20 offers the following onboard I/Os: 12 Digital Inputs, configurable via wiring to include: 1 HSC/Shaft-encoder Input, 2 Analog inputs (only
Owner s Manual VANNBus 70Series Power Management System With CAN Capable Smart Monitor TM Table of Contents Introduction. 3 Specifications.. 4 Theory of Operation... 5 Typical Applications...... 8 Installation
Specification Requirements DBL 700MX and 1000MX Series UPS Theory of Operation Upon loss of utility power, the UPS inverter shall continue to provide seamless pure sine-wave AC from the batteries without
MIDNITE SOLAR AND SOLAR WASHINGTON CHARGE CONTROLLERS 30 amp MPPT with load control for small systems, boats and RV s THE KID THE KID LED MODES The KID has a three LED bar graph plus four status LEDs that
1 Introduction This section of the handbook will guide you through the operation of the electrical system. Further technical details are contained in section 3 or in the supporting technical manual available
TROUBLESHOOTING PRELIMINARY To troubleshoot, one must first have a working knowledge of the individual parts and their relation to one another. Must have adequate hand tools Must have basic instrumentation:
EN Manual Solar Fountain Mobile Phone Charger Copyrights 2008 Victron Energy B.V. All Rights Reserved This publication or parts thereof may not be reproduced in any form, by any method, for any purpose.
Technical Teaching Equipment Photovoltaic Solar Energy Unit EESFB Products Products range Units 5.-Energy Electronic console PROCESS DIAGRAM AND UNIT ELEMENTS ALLOCATION Worlddidac Member ISO 9000: Quality
Paralleling Switchgear By Maurice D Mello, P.Eng. Systems Engineer, GE Consumer & Industrial, Canada What is Paralleling? Paralleling is the operation in which multiple power sources, usually two or more
Rectiverter Wiki The RECTIVERTER is a technology created by Eltek. The Rectiverter is a three port module with an AC input port, an AC output port, and a bidirectional DC port. It is intended for the use
User Manual of Grid Tie Inverter with Limiter Grid Tied Inverter With Limiter (GTIL) 1 www.chinesegrid.com 2014-8-1 All rights reserved Why we produced the GTI-L --- It is in response to the overwhelming
SWITCHEA EP Switchgear Cat generator set paralleling switchgear has been designed to integrate with Cat EMCP3 generator set controls. Now you can get greater efficiency, reliability and dependability all
GROUND DETECTION CIRCUITS FOR STATIONARY APPLICATIONS (IN PLAIN DOWN TO EARTH LANGUAGE) Matthew Theriault Designer Hindle Power Inc. Easton, PA SCOPE AND PURPOSE OF THE PAPER Why do we bother to monitor
Instruction Sheet 07-2013 Installation Instructions for Alarm Module Kit A043F059 1 Introduction The information contained within is based on information available at the time of going to print. In line
ASCO is the global leader in power switching and controls ASCO 90 Product Specifications Only (Panelboard Mounting),,. Suitable insulation must be behind switch unit.. Suitable for bus bar mounting. Lugs
Property of Motion Laboratories, Inc. Transformer Basics Information Guide 2014 Motion Laboratories, Inc. Created By: Jim Herrick / Michael Shaw Approved By: Peter Herrmann Page: 1 Transformer Definition
12 Volt 30 Amp Digital Solar Charge Controller Installation & Operation Manual This 30Amp charge controller is designed to protect your 12Volt Lead-acid or Gel-cell battery from being overcharge by solar
Scope This guideline defines the standard tests that all electrical systems and equipment must pass prior to final acceptance by the University. These tests are in addition to acceptance tests specified
Chapter 4 System Components and Configurations Major Components Balance-of-System System Classifications and Designs 2012 Jim Dunlop Solar Overview Identifying major PV system components and their functions,
Specifying a Variable Frequency Drive s Put on by Bruce Reeves and Jeremy Gonzales Dykman Electrical Covering the Western US For all of your VFD and Soft Start and Motor Needs How To Specify a Variable
Go Power! Manual GP TS-30 Go Power! Electric Inc. PO Box 6033 Victoria, BC V8P 5L4 Tel: 866-247-6527 Fax: 866-607-6527 Email: email@example.com Table of Contents 1. INTRODUCTION... 3 2. INSTALLATION...
CURRENT TRANSFORMERS INSTALLATION GUIDE Information contained within this document is subject to change without notice and does not represent a commitment on the part of PRI Ltd or its agents. E&OE. Copyright