2 WARNING! PUBLIC SAFETY NOTICE Lots of rain and violent thunderstorms that cause power outages can result in flooded basements. DO NOT, under any circumstances, enter a flooded basement without first making sure that the electric power is OFF. Make sure that the power has been TURNED OFF at the main switch or breaker and that it is not off merely due to a power outage. If the power suddenly comes on while you are in the water, YOU COULD GET ELECTROCUTED! Cut down your chances of a flooded basement by using a BATTERY OPERATED BACK UP SUMP PUMP SYSTEM from BASEMENT FLOOD PROTECTOR. These pumps turn on when the power turns off or for any other reason the water level rises in the pit. They can provide up to 48 hours back up protection without power, far longer than most power outages last. The battery automatically recharges when the power returns, providing completely independent operation. Since the pump is actuated by the water level in the sump pit, it also cuts in when the regular pump fails or cannot keep up, whether or not the power is on. These fully automatic stand by sump pumps completely eliminate the main causes of basement flooding. BASEMENT FLOOD PROTECTOR, INC. 707 Rose Rd., Lake Zurich, IL (847) BASEMENT WATERPROOFING WINDOW WELL COVERS SERVICE/SALES
3 BASEMENT FLOOD PROTECTOR, INC. 707 Rose Rd., Lake Zurich, IL (847) BASEMENT WATERPROOFING WINDOW WELL COVERS SERVICE/SALES System Checklist This checklist should be completed only by a qualified individual with experience dealing with battery backup sump pump systems. In the Chicago area, Basement Flood Protector, Inc.,has this service available. Battery voltage: resting/max v/ v If Tie-in, relief holes unobstructed Specific gravity test (# of floating balls) Mark circuit in panel for pumps And water level ok Alarm works properly Battery passed load test Pump(s) free of debris, and pumping capacities appear normal Switch(es) turn on/off automatically and at proper level Charger puts out correct amperage Any other alterations, deficiencies, comments: Clean equipment and area before leaving Check valve(s) operating properly No leaks, screws tight Discharge ok and flows away from foundation on outside, land slopes ok Date Checked Additional Recommendations: Date Checked 1. Check and clean all connections and battery terminals. 2. Run the system at least 4 times a year. 1st unplug the charger (to simulate a power outage) then run the system both by manually lifting the switch with your finger then automatically by unplugging the electric pump and allowing the battery pump to cycle. 3. Remember to unplug the charger and electric pump back into respective outlets. 4. Replace the battery every 4 years to ensure maximum battery life. 5. Plug the charger into a separate circuit (from the electric pump).
4 Owners Manual Battery Backup Sump Pump System Table of Contents Warning! Public Safety Notice Installation Section Equipment, Tools, Supplies Needed Notes Before You Begin Installing Pump and Switch Piping the Discharge Mounting the Charger Operation of the Charger Signal Sensor Testing Maintenance Section Battery Hydrometer Instructions System Checklist Troubleshooting Section Customer Quality Audit Warranty Section 1
5 Installation Section Every Installation is unique and could differ from the following description. Equipment Needed: Pump Switch Battery Charger PVC Pipe and Fittings Signal Sensor Alarm* Battery Case* * Optional Notes Before You Begin A note about the discharge pipe: We recommend a separate discharge pipe if possible. This means piping the PVC pipe from the Protector pump to the eventual outside discharge point independent of the electric sump pump s discharge pipe. The alternative is to pipe the discharge into the electric pump s discharge pipe using a y or t fitting (see note below concerning PVC fittings). Whenever using a check valve, always drill a 1/8th inch relief hole just above the male adapter (see picture #1). Failure to do so could result in air lock. Tools Needed: Flat Head Screwdriver Hacksaw Drill with Hole Saw and 1/4" 1/2" drill bit Utility Knife Other Supplies Needed: PVC Cement Check Valve or Rubber Connector (depending on installation) Black Electrical Tape Tie Wraps Mounting Hardware for Charger Picture #1 Tieing in may be necessary in cases such as: 1. a finished basement makes a separate pipe unfeasible 2. discharge pipe exits building through foundation below grade 3. very long run would significantly decrease pumping capacity The disadvantages of tieing in : 1. check valve failure could allow water to circulate instead of being discharged from the building 2. both pumps can t operate simultaneously at full capacity 3. the Protector would not be able to discharge water if pipe is blocked or frozen outside 4. if the storm or sanitary (check local plumbing code) sewer has filled up because of heavy rains, the Protector may not be able to pump water 2 A note about PVC: 1. Always use Schedule 40 PVC pipe and high pressure fittings (not DWV or drainage fittings). If you can t find the fitting you need at your hardware store, chances are that we stock it.
6 2. Applying a PVC primer/cleaner to fittings and piping is recommended. Then, always use a liberal amount of PVC cement on both the male and female pieces being glued. (see picture #2) Insert male into female completely. Always cut pipe straight so as to maximize the amount of pipe surface being glued in the fitting. Allow to dry at least five minutes. A note about using hose clamps: Always use stainless steel clamps. Stainless steel clamps will be noted by SS or Stainless imprinted on the clamp. Be careful of clamps that claim stainless but only the band is stainless. You want the band and the gearing to be stainless. A note about setting the turn on and turn off level of the Protector: In general, the turn on level should be higher than the level at which the primary electric pump turns on (usually where the water stain in the pit is) but lower, if possible, than the incoming drain tile. The turn off level should be a couple inches higher than the red strainer of the Protector. A note about batteries: If you are purchasing a battery on your own we recommend either a sealed or an unsealed marine, deep cycle battery with an amp hour rating of at least 100ah, and a reserve rating of at least 175 minutes. The larger the amp hour and reserve ratings, the longer the pump will be able to run during a power failure. Sealed batteries can be used but their disadvantages are as follows: higher cost, shorter life (can t maintain water levels), less stored power. A newer technology called AGM (Absorbed Glass Material) may be used. Gel batteries are not recommended. Do not use automotive type batteries. They are not designed to hold large amounts of stored power, but rather to provide start-up cranking power (which is not needed for a battery backup sump pump system). Picture #3 The recommended battery should have a life span of about 3 years when being charged by an automatic charger, and more when being charged by the SmartCharge Pro. Do not charge and maintain the recommended battery with a trickle charger. Batteries may be doubled-up by wiring two or more batteries in parallel with heavy duty wires and terminals. This has the effect of doubling the battery size and therefore the amount of running time the pump(s) will be able to run during a power outage. However, if one battery goes bad, the others will quickly follow. The charging unit should be wired with the positive charging lead to the positive of one battery and the negative charging lead to the negative of the other battery. Check the manual of your charger to determine the maximum size battery it will maintain. Caution!! Always exercise extreme care when handling batteries. The recommended battery contains ACID which can burn skin and eyes. Avoid direct contact with the acid by wearing clothing and eye protection. Do not smoke or engage in any other activity that could cause a spark. It is also recommended that any metallic jewelry or tools be kept from the battery s terminals. Installing Pump and Switch 1. Attach fittings to pump pump. Place the slotted end of the supplied 90 degree PVC elbow over the rubber gasket on the discharge of the Protector 3500 pump (see picture #3). Tighten the supplied clamp (important: this clamp must be stainless steel) around the slotted end of the elbow and firmly screw the supplied male adapter into the threaded end. The 3500 is normally piped with 1 1 /4" or 1 1 /2" pipe. Picture # pump. The 4000 will include a 90 degree elbow with the rubber gasket inside the slotted end. Place this end over the discharge of the pump and tighten the stainless steel clamp securely. Firmly thread the male adapter into the other end of the 90 degree fitting. 3
7 The 4000 is usually piped with 1 1 /2" pipe pump. The 8000 includes a set of fittings that enable you to set the pump standing up on end (see picture 4A) and eliminate the need for a 90 degree fitting (which would take up too much room). The set of fittings attaches very snugly to the discharge. As long as the final installation of all piping is secure, the clamp does not need much tightening. The fittings allow the 3" discharge of the pump to be reduced to a 2" male adapter for the purpose of using a 2" discharge pipe. BFP SWITCH Max pump. The Max pump comes with a 1 1 /2" male adapter and a length of 1 1 /2" PVC pipe. Check that the pipe is glued into the fitting and the fitting is threaded into the bump base tightly (see figure E). 2. Set length of pipe. Use your hacksaw to cut a piece of PVC long enough so that it will extend about 3 feet above floor level once pump is placed at bottom of the pit (this means that you will likely cut a piece about 4-5 feet long). If a lot of debris or muck is at the bottom of the pit, it should be cleaned. The pump could sit on a brick if necessary. However, we do not recommend hanging the pump from the electric pump s pipe or sitting the Protector pump on top of the electric pump. Make all cuts straight so that the pipe will glue into the fittings properly. Use a liberal amount of PVC cement to glue the length of pipe snugly into the male adapter. Apply cement to both the inside of the fitting and around the outside of the pipe. (see picture #2) All glued connections should be allowed to dry for at least 5 minutes. This clamp goes around pipe with bracket like this Figure A 3. Relief hole. If you will be using a check valve for any reason, a 1/8" diameter relief hole needs to be drilled in the PVC pipe just above the male adapter on the 3500, 4000 and Max, and in the coupler on the This will prevent the pump from ever getting air locked. Drilling the hole at a downward angle will prevent the water stream from interfering with the operation of either pump or spraying out of the pit (see picture #1). 4. Setting up the switch. The pump should be positioned at the bottom of the pit next to the electric sump pump, which might need to be maneuvered slightly to allow for best placement (sometimes in small sump pits, a different switch for the electric pump can increase the amount of space). BFP Switch Slide one of the weights on the black nylon cord and tie a knot approximately 12" from the hook. Slide the second weight on the cord and, after tying a second knot 8" below the other knot, hang the cord from the hook on the switch (see figure A & figure C). Hold the switch about 6-12" above floor level against the pipe where you think it should eventually be clamped (see picture #4). Picture #4 Attach these ring terminals to battery Mate this plug to plug from pump Cord with weights hangs from here Plug this into Signal Sensor Picture #4A 4 Picture #5
8 Picture #6 BFPVM Switch This switch is simply mounted to the pipe above the protector pump using the supplied stainless steel clamp (see figure B. Use the rubber stopper to adjust the turn-off level and position the switch itself to adjust the turn-on level. Most of the references to the switch in section 5-7 refer to the other switch, the BFP switch. Placement should be such so that the Protector pump and switch will not interfere with the electric pump or switch (and vice versa). Also be certain that neither switch could get caught up on the side of the pit or anything else. 6. Connecting pump and switch (BFP switch only). When finished drilling, place the Protector pump back at the bottom of the pit, fit the pit cover over the discharge pipe and maneuver everything into an optimal position. Use the supplied hose clamp to fasten the switch to the discharge pipe (see picture #7). Feed the black cord with weights from below the pit cover through the 1/4"-1/2" inch hole you drilled and hook it onto the switch. The weight of the cord/weights assembly will pull the switch arm to the down position (off). Make any necessary adjustments in the knots to get the weights to the proper on/off levels. Use your utility knife to cut off any excess black cord below the bottom weight to prevent any accidental hang-ups. Connect the plug from the switch to the plug from the pump. Tie wrap the wires to the pipe to prevent them from falling into the pit where they could interfere with the operation of one of the pumps. 5. Drilling holes in pit cover. Holding the pump and discharge pipe in the pit at the desired location, use a pencil to mark the floor where the pipe stands up straight. (see picture #5) Remove The Protector, slide pit cover over pit and drill the hole using a hole saw 1/2" bigger than the diameter pipe being used. Set pump and discharge pipe into pit through the new hole in the pit cover. Next to this hole, drill a 1/4"-1/2" diameter hole where you have determined the weights from the switch will hang (see picture #6, BFP switch only). For Max pump: The best thing to do for easy access to the pumps is to cut the pit cover similar to the following diagram shows. for electric sump pump discharge pipe 1/4" hole for switch cord slot for Max pump column & discharge pipe 5 Figure B
9 Picture #7 Picture #8 7. Connect the switch to battery. PLEASE BE CAREFUL BEFORE PROCEEDING. BE SURE ALL PIPING IS GLUED PROPERLY AND CLAMPS ARE TIGHT. Connect the battery lead wires to the battery: brown is positive, black is negative. As long as you have attached the weight/cord assembly properly and the switch has clicked to the down position, the Protector will not turn on. However, if you manually lift the switch arm the pump will operate (be careful not to knock off the black cord. Tip: put a dab of glue on the hook the cord hangs from to help prevent it from accidentally being knocked off in the future). Don t tighten down the wing nuts or other fastening assembly on your battery yet. The charger leads still need to be attached. Tie-in Installation Piping the discharge. If the installation requires a tie-in, (see figure C) cut the electric pump s discharge pipe at the appropriate location and glue in a high pressure PVC Y fitting. (Note: For flow reasons and the possibility of check valve failure, it is usually better to glue the Y into the horizontal run of the discharge rather than the vertical, if possible.) Both the electric sump pump and the Protector discharge pipes need a check valve and 45 and/or 90 fittings to complete the tie-in (See picture #8). Note: this picture has the completed pipe for a separate discharge in place, but shows where a y fitting might go (installer s left hand) and the height at which a check valve might be placed (installer s right hand).) Please read the section above concerning the disadvantages and criteria for tie-ins. VERY IMPORTANT: When a check valve is used, a relief hole is needed. This 1/8th inch hole should be drilled in the PVC pipe a couple inches above the elbow connector to the pump. Drill the hole so the water will spray out at a downward angle to avoid splashing and interference with other items (see picture 1). Figure C 6
10 Separate Pipe Installation Figure D If a separate pipe is being installed, drill through the outside wall with appropriate drilling equipment (see picture #9) and pipe the discharge down to the pipe coming from the Protector. A rubber connector should be located on the discharge pipe about two feet from the floor to make future service on either pump more accessible (see figure D). A check valve would be used if the pipe has a lengthy run or is required by local code. The Protector s discharge pipe must eject water to a location that has sufficient run-off away from the building. The piping above the rubber connector or check valve varies greatly depending on the installation. In general, exercise sound plumbing practice by piping the discharge pipe to the outside using the shortest distance and the least number of bends. The horizontal section of the discharge pipe that will exit the basement should be piped at a downward angle to the outside. 7
11 Figure E 8
12 Picture #9 Mounting the charger. The charging unit should usually be located on the wall within a foot or so of the sump pit. Avoid placing the charger in such a way that it would be directly over the battery (staggering it over about one foot would be better). Also avoid placing the charger inside a confined area (a closet is usually o.k.). Holding the charger to the desired place on the wall, use a pencil to mark the keyholes (see picture #10). If you are mounting the charger to concrete, plastic molly anchors with screws are recommended. If you are mounting to drywall, use 1" or longer wood screws into studs or heavy duty hollow wall anchors where you can t utilize a stud. Plug in the charger and connect to the battery according to the directions included with the charger. The SmartCharge Pro units include a detailed information booklet that contains important safety and operation instructions. Be sure that the charger does what its manual says it will do. Operating the Charger (Reprinted from the SmartCharge Pro manual) The Intelligent Multi-Stage Charger CAUTION: Read and follow all safety rules and operating instructions before use of this product. WARNING: To reduce the risk of explosion, explosive gases, or injury while using your battery charger, follow the precautions listed below. Read all instructions and cautions printed on the battery charger, battery, and equipment using battery. Use charger only on rechargeable Lead Acid deep cycle, marine types of batteries. Use only attachments recommended by the manufacturer. The use of attachments not recommended by the manufacturer may result in fire, electric shock, or injury. Place battery as far away from charger as cable will permit. Do not operate the charger if it has a damaged power cord or plug. Have the cord replaced. Never charge a frozen battery, allow the battery to thaw before charging. Do not disassemble charger. Return to manufacturer if service is required. To reduce risk of electrical shock, unplug the charger from the outlet before attempting any maintenance or cleaning. Always charge battery in a well ventilated area. This charger is not intended to be used as a power supply. Do not expose charger to rain or snow. Personal Safety Precautions For your own personal safety, follow these precautions: Wear complete eye and clothing protection when working with batteries. Do not drop any metal tool or metal object onto the battery. Never smoke or allow a spark or flame in the vicinity of the battery. Avoid touching your eyes while working with batteries. Remove all personal metal items from your body such as rings, watches and bracelets. Clean battery casing with baking soda to neutralize the acid. Ground A/C Power Cord Connections The charger should be grounded to reduce the risk of electric shock. The charger is equipped with an electric cord having an equipment grounding conductor and a grounding plug. The plug must be plugged into an outlet that is properly installed and grounded in accordance with all local codes and ordinances. 9 Picture #10
13 DANGER Never alter the AC cord or plug provided. If it will not fit outlet, have proper outlet installed by a qualified electrician. Improper connections can result in a risk of an electric shock. Description Congratulations on your purchase of the state-of-the-art SmartCharge Pro. This charging unit was specially designed to be used in conjunction with The Protector brand of battery backup sump pump system (though compatibility with most systems is likely). The SmartCharge Pro utilizes microprocessor technology and years of practical experience in the sump pump business to bring you the best charging unit ever designed for backup sump pump use. During a power outage or sump pump failure, your backup sump pump system (BSPS) is only as good as your pump and your battery. But most manufacturers have mistakenly stopped there and forgotten that the way in which a battery is charged is perhaps the most crucial process for dependability. In our experience (since 1974) a common complaint has been that when the BSPS was finally needed, the battery was dead or nearly dead. We feel that the SmartCharge Pro improves this dilemna. There are a couple elements that make the charging unit for a BSPS extremely important for the reliability of the BSPS as a whole: First, the nature of a BSPS demands that the battery be fully charged and ready for duty at all times. This requires the charging unit to constantly monitor the condition of the battery and maintain it at a full charge 24 hours a day, 7 days a week. However, charging a battery has always, until now, reduced the life of a battery drastically. Trickle chargers (often included in the cheaper off-theshelf BSPS s at most improvement and hardware stores) are the worst culprits. They constantly feed some amount of amperage into the battery. Even if the amperage is small, they will heat the battery, evaporating the fluids, warping the plates, and slowly destroy the battery (sometimes as quickly as 6 months). Even fully automatic chargers either charge to a dangerously high voltage or they perpetually turn on and off between two pre-set voltage levels, possibly leading to the overheating and destruction found with trickle chargers. A second element is that the charger is the only component of the BSPS that must work all the time, not just in an emergency. Reliability and a long life depend on the quality of components used in design and construction of the unit. We have spared no expense (parts were not selected based on price, etc.) to bring you this charger (and you probably paid a little more than for a similar charger). For example, the electronics are top quality, the wiring and assembly is completed by hand, and even the unique case designs are for maximum heat dispersion. How Is This Charger Different? Intelligence. Our programmers and designers have found that a multi-stage approach to charging allows a battery to retain far greater strength for a much longer period of time, and to allow for faster charging. For many years, multi-stage charging required far too many components to be feasible or cost effective for home use as a battery charger. But, utilizing microprocessor technology, cost and size have been reduced. In brief, multi-stage charging is a four phase method that prevents a flooded cell battery from aging prematurely. This technology is also used in expensive equipment such as heart rate monitors and other medical equipment. Instead of trickle charging or charging to a preset voltage over and over, the SmartCharge Pro goes through extensive calculations about the battery, monitoring through timers, tests, and temperature. The result is a system that will maintain a full charge but not heat the battery. This means you will not have to add water as often and can therefore rest assured that your battery is being charged by the charger, not destroyed. (We pause here to insist that you continue checking your battery, including water level, on a regular basis.) 10
14 Operating Instructions 1. Make sure you have a 12 volt battery. 2. Check battery posts for polarity. Battery will be marked by each post. POSITIVE (pos, p, or +) and NEGATIVE (Neg, N, or -). 3. Plug charger AC cord into a 120 VAC grounded outlet. (It is recommended that you plug into an outlet on a separate circuit from the one your electric sump pump is plugged in to.) 4. Connect POSITIVE (RED STRIPE or tag indicating positive) charger lead to POSITIVE battery post and connect NEGATIVE (ALL BLACK) charger lead to NEGATIVE battery post. 5. The RED, GREEN, and YELLOW lights should be lit followed by the YELLOW and GREEN lights turning off after a couple seconds. This process is so that you know all three LEDs work. 6. After a couple more seconds, the YELLOW light will illuminate indicating that the charger is now charging the battery. After some amount of time (determined by the size of the SmartCharge Pro unit and the amount of charge needed by the battery), the yellow light will enter a flashing mode for minutes. 7. The GREEN light will come on when charging is completed. The Lights Red Light On - Power On. Anytime the household current is on and the leads to the battery are polaritycorrect, the red light will be illuminated. Green Light On - Fully Charged Battery. A constant green light indicates that the battery is at a full charge. Yellow Light On - Charging. Anytime the charger is feeding the battery with juice the yellow light will illuminate. Red Light Flashing - Voltage Low, Check Battery. This indicates that the SmartCharge Pro, through its various testing capabilities, has determined that the battery voltage is too low for a prescribed charging time. It is likely that the battery needs to be replaced because of its inability to hold a strong enough charge. However, first do the following: 1. First check that all connections are tight. Picture #12 11 Picture #11 2. Next check the battery cells for proper water level and fill any low cells with distilled water. 3. Next, unplug the charger, plug back in, and check the SmartCharge Pro again after at least 24 hours. 4. If the red light flashes again it may be time for a new battery. Call (847) for service. Yellow Light Flashing - Voltage High, Unit In Maximum Charge Mode. Recheck In 1 /2 hour. The SmartCharge Pro has entered one of the four phases of charging. It is normal for this light to flash after Protector system has operated, or power or connection to battery has been interrupted. However, if the light flashes for more than an hour at a time or enters a flashing mode more than once within a couple hours please check your battery as described in the previous paragraph. Trouble Checklist The charger is designed to work automatically. However, if a problem does occur, check the following: Problem Cause Solution No RED Light Charger is not Plug charger in plugged in AC outlet Test outlet by plugging is dead in something you know works. If dead, check circuit or call electrician No YELLOW Poor battery Clean and reconnect light connections terminals to battery posts. Battery is Green light should charged be on No GREEN Battery still Wait light charging If some other combination of lights seems unusual, unplug and re-plug charger and double check that the LED s go through the process described in #5 above.
15 Signal Sensor Mount the optional Signal Sensor alarm unit (see picture #11) to the PVC discharge pipe (above any check valves or rubber connectors) or to the spot designated on the charger (certain models only) (see picture #12). Locate the white plug coming from the pump switch. This plug clicks into the connector at the bottom of the Signal Sensor. With the rocker switch on the Signal Sensor in the Alarm Ready position, the Signal Sensor alerts you audibly when the Protector system operates. The horn will sound on and off with the Protector pump turning on and off. With the rocker switch in either Alarm Ready or Alarm Off the LED light will illuminate the first time the Protector operates and stay illuminated until the Reset Light position on the rocker switch is depressed. If during a storm, the Protector is called into action but you would rather not hear the horn turning on and off, simply move the rocker switch to Alarm Off for the duration. It is also recommended that Alarm Off be selected if you are leaving for vacation or an extended period of time. That way the horn will not be using battery power (although minimal) during an outage, therefore reserving power for the pump. Testing Test by running water slowly into the pit. Test again. Be certain that the Protector will turn on and off at the water levels you feel most appropriate (see the note at the beginning of the installation section for help on how to determine these levels). Double check that all PVC joints are glued well, hose clamps are tight, electrical connections are tight, and wires are tie wrapped or taped neatly and free from entanglement. Maintenance Section Battery The battery is the part of the system needing periodic maintenance. An unsealed battery (recommended) will need its water checked every couple months. If the water level is low, distilled water should be added to within one inch of overflow. You can also check the specific gravity of your battery with the glass hydrometer included with the Protector. Note: sealed batteries cannot be tested with a hydrometer. Hydrometer instructions: (Not to be used on maintenance free batteries) Perform check with hydrometer before adding water to battery. If water was recently added, wait at least 24 hours before using hydrometer. Pop caps off battery cells Draw fluid from battery cells into tester. Number of balls floating indicates condition of battery. 4 balls floating - Cell is at full charge. 3 balls floating - Cell is at % charge. 2 balls floating - Cell is at 50-75% charge. 1 ball floating - Cell is at 25-50% charge. 0 balls floating - Cell is dead. We recommend replacing battery if more than one cell reads 50% or less. Even new batteries sometimes produce only 3 floating balls. Refasten caps to battery. Always rinse hydrometer with clean water. IMPORTANT: Please note that a hydrometer is an easy, convenient way to check your battery, but is not necessarily faultless. The most accurate test of a battery is with a load tester, volt meter, and a trained eye. Basement Flood Protector, Inc. recommends a thorough system check once every one or two years by a skilled technician. We want your system to operate at its full potential when you need it most! Troubleshooting Section Pump won t run: Bad connection in wiring Switch not on or switch defective Pump humming, but not pumping water: Possible jam in impeller. Remove red strainer (submersible models) from base of pump and clean out impeller. Pump pumps slow: Wires are reversed (motor running in reverse) Obstruction in pipe Too long or high of a pumping length Brand new battery tests low on hydrometer: It is normal for only 3 balls to float, even on new batteries. This does not mean your battery is bad. Charger question: Consult the charger s system guide 12
16 Basement Flood Protector, Inc. warrants to the original retail purchaser that all of its pump and switch products are free from defective materials and workmanship for the period indicated below: All pump and switch products are warranted for three (3) years from the date of purchase. Batteries have a 2-year prorated warranty. During the indicated period, the dealer is authorized, based on valid bill of sale, to make an immediate no-charge replacement. Alternately, the defective product may be returned directly to the factory, postage prepaid with the original bill of sale. Basement Flood Protector, Inc., at its option will either repair or replace the product and return it postage prepaid. This warranty does not extend to products that prove to be operative or that have been subject to misuse or physical abuse, or to wiring or installation that is either improper or contrary to instructions provided. Alteration or repair, except at Basement Flood Protector s factory, voids this warranty. No representative or other person is authorized to assume for Basement Flood Protector, any additional liability in connection with the sale of its products or to alter this warranty in any way. All implied warranties and incidental or consequential damages are disclaimed and/or limited to the full extent allowed by law. Some states do not allow the above limitation or exclusion may not apply to you. This warranty gives you specific legal rights and you may also have other rights which vary from state to state. FOR WARRANTY SERVICE, WRITE TO: Basement Flood Protector, Inc. 707 Rose Rd. Lake Zurich, Illinois BASEMENT FLOOD PROTECTOR (REGISTERED TRADEMARK) Limited Warranty This warranty does not cover product problems resulting from: a) handling liquids hotter than 120 ; b) handling inflammable liquids, solvents, strong chemicals or severe abrasive solutions; c) normal wear; d) user abuse, including immersing the control system; e) commercial or industrial use; f) improper connection or installation of the battery or BFP system. This Limited Warranty becomes effective only if the numbered warranty card (below) is filled out and mailed to Basement Flood Protector within ten (10) days of purchase. Limited Warranty #BFP Limited Warranty #BFP Please fill out the information below and return it to Basement Flood Protector, Inc. 3 Year Warranty Owner s name City/State/Zip Address Tel. # Place of Purchase: Name City/State/Zip Tel. # Date Purchased Installed by: Name Address City/State/Zip Tel. # Type of Service: Residential Suburban Commercial or Industrial City Rural Battery: Make Model # rated reserve capacity My Protector Pump is installed with this AC sump pump: Age (approx.) Make Model H.P. Discharge pipe/size Age of house Do you have friends, neighbors, or relatives that would be interested in a Basement Flood Protector product? Receive a $20 gift from us if your referral purchases a system from us. Name Address City/State/Zip Tel. # Name Address City/State/Zip Tel. # over
17 BASEMENT FLOOD PROTECTOR, INC. BATTERY SUMP PUMPS WINDOW WELL COVERS BASEMENT WATERPROOFING 707 ROSE RD. LAKE ZURICH, IL (847) Dear Valued Customer: Thank you for contacting our company and giving us the opportunity to work with you on your project. If we can be of help in the future, please call us! We re always available to discuss your needs. We take pride in our work and are constantly striving to maintain our high quality. Would you help us by taking a minute to answer the following questions? Your comments are valuable and will help us serve you better in the future. Thank You. CUSTOMER QUALITY AUDIT Were we responsive to your needs? Before the job Yes No During the job Yes No After the job Yes No Was the job started on time? Yes No completed on time? Yes No left clean? Yes No General Comments: Were our workers courteous? Yes No Did we do everything we agreed to do? Yes No Were you satisfied with the price and value of the job we did? Yes No Were you pleased with the quality of our work? Yes No Would you consider us for future projects such as foundation crack repair or drain tile systems? Yes We invite you to write in any additional comments No REFERRALS: Name: Phone Number: Name: Phone Number: Receive a $20 gift from us if your referral purchases a system from us. May we use your name as a reference on future jobs? Yes No Name Signature Date Phone Number Address City State Zip
18 Protect Your Family Supports over 500 lbs! Lifetime Warranty (HD) Safe Nobody Makes a Better Cover Than Basement Flood Protector! 30 years experience since 1974! Options available Escape Ladders Quick Lock Security Lock Light & Scene Liners Danger! Prevents injuries to children & animals Custom & Attractive Safety/Security Window Well Covers (custom made to fit any size or shape) Contructed of virtually unbreakable GE Lexan plastic and rust free aluminum angle. Highest quality material and workmanship. Danger! Thief Beautiful Secure Dark and Uninviting Light-enhancing Liners Safe, fast escape with optional Quick Lock >90% light transmittal Year Round Service With a Smile! Simple Process: 1. You call us with your information. 2. We custom make the covers at your home, usually within 1 week. 3. You enjoy safe, secure, attractive covers for the life of your house.
Instruction Manual & Safety Warnings Table of Contents Important Safety Warnings and Instructions Electrical precautions 1 Battery preparation 1 Battery precautions 1 Introduction Items included in system
Battery Backup Sump Pump System Instruction Manual Battery Operated SUMP TEST Push to Test System RESET Push to Silence Pump Alarm Warning BATTERY FUSE WATER POWER What to do Terminals corroded or battery
WWW.BURCAM.COM 2190 Boul. Dagenais West TEL: 514.337.4415 LAVAL (QUEBEC) FAX: 514.337.4029 CANADA H7L 5X9 firstname.lastname@example.org Your pump has been carefully packaged at the factory to prevent damage during shipping.
Backup Sump Pump Systems 1 SSPMA MEMBERS Barnes Pumps / Crane Pumps & Systems Champion Pump Company, Inc. Franklin Electric / Little Giant Glentronics Inc. Goulds Water Technology, a xylem brand Liberty
CHARGING SYSTEMS INTERNATIONAL INSTALLATION AND OPERATING INSTRUCTIONS FOR THE FOLLOWING BATTERY CHARGING SYSTEMS: MODELS MAX AMPS/BANK NO. OF BANKS BATTERY SYSTEM PRO XL 6 1 12 DUAL PRO XL 6 2 12/24 PRO
Owners & Installation Manual for the Sheridan, Mountainair, Pine Valley and Old Forge Ceiling Fan Family Part of the Kiva Lighting Family Custom Lighting and Fans Since 1992 1312 12th St NW Albuquerque,
Pro Series C11 Combination Primary and Backup Sump Pump System Instruction Manual & Safety Warnings Table of Contents Important Safety Warnings and Instructions Electrical precautions 1 Battery preparation
IMPORTANT INSTRUCTIONS & OPERATING MANUAL Houston 50 Inch Electric Wall Mounted Fireplace Black / White Model Number:MFE5050BK Model Number:MFE5050WH Read these instructions carefully before attempting
S33 Sump Pump INSTRUCTIONS AND SERVICE MANUAL VERTICAL FLOAT SWITCH S33V1 & S33V1C AUTOMATIC S33P1 & S33PC-1 (CONTROL WITH SERIES PLUG) NOT SHOWN AUTOMATIC S33A1 & S33A1C R WARNING risk of electric shock.
12 Volt 30 Amp Digital Solar Charge Controller User s Manual WARNING Read carefully and understand all INSTRUCTIONS before operating. Failure to follow the safety rules and other basic safety precautions
Installation Manual 4414000B Model 441 Battery Backup System *Do not throw away or lose this manual. IMPORTANT: Prior to installation, record Model, Serial Number, and Code Number from pump nameplate for
ITC-BTTN Cellular Bluetooth Gateway Owner s Manual 1 2 Table of Contents Introduction...3 Package Contents...3 XLink Connections Diagram...4 Setup...5 Pairing your Bluetooth Cell Phone to the XLink...6
Automatic Phone-Out Home Monitoring Systems Power Outage and Freeze Alarm Model Number: THP202 Power Outage, Freeze and Flood Alarm Product Description Model Number: THP201 These monitoring systems are
ATS Overhead Table Shelf System INSTRUCTION MANUAL ATS Overhead Table Shelf System Instruction Manual Warranty Newport Corporation warrants this product to be free of defects in material and workmanship
Remote Faucet Pump System USE &CARE GUIDE See Important Safeguards on page 2 An exclamation point within an equilateral triangle is intended to alert user to the presence of important operating and maintenance
1/3 HP Submersible Sump with Vertical Float Switch Item 68476 Specifications Float Switch Operation Height 7.1 IN. ON / 2.8 IN. OFF Electrical Requirements 120V~ / 60Hz / 7.6A Power Length Maximum Capacity
RV Battery Savvy To properly maintain and extend the life of your RV batteries you need to have a basic understanding of what a battery is and how it works. Batteries used in RVs are lead acid batteries.
Safety Information Read these instructions completely before using the product and save them for future use. Before using the Jump-N-Carry to jump-start a car, truck, boat or to power any equipment, read
Electric Water Heater OWNER S MANUAL FORCE 10 MARINE COMPANY 23080 HAMILTON ROAD RICHMOND, BC CANADA V6V 1C9 TEL: (604) 522-0233 FAX: (604) 522-9608 If your water Heater is Damaged or you have questions
TM F OR A BOVEGROUND POOLS INSTALLATION AND OPERATION MANUAL How Solar Pool Heating Works Why SunHeater TM Works Best Using your pool pump, water is automatically pumped through the solar collector. The
MASTER Water Conditioning Corp. www.masterwater.com Installation and Operation Manual MBA-MM-1040/10/13/1665 MULTI MEDIA FILTERS with the 263/742 Logix Control Valve June 2010 Table of Contents Page No.
Installation Instructions For Slider Casement Air Conditioners NOTE: These instructions describe installation in a typical wood framed window with a wood SLIDE-BY sash, or installation in a metal CASEMENT
FIREPLACE HEATER FOR THE FOLLOWING MODELS: EE-8075W EE-8075O EE-8075R EE-8075BK If you have any questions about the operation of your fireplace heater, please contact Crane Customer Care. Toll Free: 888-599-0992
ProMariner ProMariner Visit ProMariner Online at www.pmariner.com, for a Complete Selection of Quality Marine Products... Here are just a few: ProSport Series - Recreational Sport Fishing & Boating Waterproof
FASCINATION 700 HVLP TANNING PRO SYSTEM USER MANUAL Congratulations on choosing the Fascination 700 HVLP Tanning Pro System! Your system includes the following items: 1 Fascination 700 HVLP Tanning Pro
4 3. SEISCO PARTS & SERVICE REMOVAL AND REPAIR GUIDE A. Changing the Control Board B. Replacing a Heating Element C. Thermistor Replacement D. High Limit Switch Replacement E. Level Detector Replacement
SRA-125/SRAX-125 Double-Rail Lift-Out Rail System Installation & Service Manual with Parts List For MG, WG, WGL, and Grinder Pumps for Effluent & Sewage CAUTION! Read these safety warnings first before
FUTURE CALL PICTURE CARE PHONE MODEL: FC-1007 USER MANUAL Please follow instructions for repairing if any otherwise do not alter or repair any parts of device except specified. IMPORTANT SAFETY INSTRUCTIONS
SAVE THESE INSTRUCTIONS This manual contains important safety and operating instructions for the automatic battery charger. Do not expose charger to rain or snow. Do not use and an attachment not recommended
9-27-2010 National- Spencer Inc. 19.2V HEAVY DUTY GREASE GUN PRODUCT SPECIFICATION Charger Input Power 110 VAC Battery Output Power 19.2V Battery Capacity 1500 MAH Battery Pack Charge Time 1 Hour Maximum
User s Guide Oreck Air Purifier with HEPA Filtration Important! Read this manual carefully, and keep for future reference. Enjoy Congratulations on your purchase of the Oreck Air Purifier with HEPA Filtration.
READ BEFORE INSTALLING UNIT For Slider Casement Air Conditioners To avoid risk of personal injury, property damage, or product damage due to the weight of this device and sharp edges that may be exposed:
User Manual Instructions for installing the Sure Stitch on the Next Generation Quilting Frame. Parts Included: 1: Display Console 1: Control Box 2: Encoder (Wires attached) (Not Shown) 1: 5v Power Supply
525 Installation Instructions Thank you very much for purchasing PIAA product. Please read this entire manual before installation and use of this product. For Installers Please give this Installation Manual
Overview READ ENTIRE INSTRUCTIONS BEFORE STARTING INSTALLATION PARTS LIST A. Flush valve B. Lever mounting base C. Flush handle assembly D. Grey/Blue float stop E. Grey float (Full Flush) F. Flush valve
OASIS-PLUS 120V INFORMATION & OPERATING INSTRUCTIONS READ ALL INSTRUCTIONS BEFORE OPERATING READ ALL INSTRUCTIONS BEFORE OPERATING OZONE IS A POWERFUL OXIDIZER AND MUST BE USED WITH CARE 56041852 WARNING:
Solar Home System User Manual AEHSHS0110W2L Solar Home System 2 Lamps All rights reserved Specifications subject to change without prior notice 2 Dear Customer, Thank you for purchasing Schneider Electric
SDX Submersible Depth Transmitter User Manual January 2011 USER INFORMATION Stevens makes no warranty as to the information furnished in these instructions and the reader assumes all risk in the use thereof.
Battery Charger For Nickel Cadmium and Nickel-Metal Hydride Rechargeable Batteries Model PSN Series Operating Instructions WARNING CONCERNING THE REMOVAL OF COVER: CAUTION: TO PREVENT THE RISK OF ELECTRIC
WWW.BURCAM.COM 2190 Dagenais Blvd. West TEL: 514.337.4415 LAVAL (QUEBEC) FAX: 514.337.4029 CANADA H7L 5X9 email@example.com Your pump has been carefully packaged at the factory to prevent damage during shipping.
www.hunterfan.com Table of Contents What to Expect with Your Installation 30 inches Hanging the Fan Wiring 8 Maintenance, Operation & Cleaning Light Kit 13??? 14 1 9 Troubleshooting 11 5 Blades Motor Housing
CEILING FAN OWNER'S MANUAL READ AND SAVE THESE INSTRUCTIONS MODEL: 52P-646-5RV-187 52P-646-5RV-323 FAN RATING AC 120V. 60Hz CUL LISTED MODEL : AC-552A 1. TOOLS AND MATERIALS REQUIRED Philips screw driver
W A Electric Window Opener Electric Window Opener for Awning and Roof Windows Congratulations! You have just purchased one of the many fine products. For ease of installation and continued enjoyment of
Progressive Industries, Inc. EMS Electrical Management System Complete Installation Guide and Operating Instructions for: Model EMS-HW50C Rated at 240V/50A Manufactured by: Progressive Industries, Inc.
AYYEKA Rethink Water Monitoring WAVELET WATER QUALITY MONITORING KIT ON OFF QUICK START GUIDE AYYEKA IMPORTANT! Use with pressure applications up to 145 PSI. Contact AYYEKA SUPPORT center for technical
BC-5000 BATTERY CAPACITY TESTER OPERATIONS MANUAL COFKO LLC. COPYRIGHT 2010 1 UNPACKING As you unpack your new BC-5000 battery capacity tester, inspect the tester for signs of shipping damage. If shipping
MODE ALARM Portable Air Conditioner OWNER S MANUAL Read these instructions before use 8 Model: MF08CESWW Voltage rating: 115V~60Hz Power rating : 800W Customer Support : 1-800-474-2147 For product inquiries
All about the Use & Care of your Iron Important Safeguards... 2 Iron Safety Instructions... 3 Parts and Features...4 TA B L E O F C O N T E N T S Using Your Iron...6 Cleaning and Maintenance... 8 Warranty...9
ADI 9510-B Advantium 2 Plus Alarm INSTALLATION AND OPERATING INSTRUCTIONS Carefully Read These Instructions Before Operating Carefully Read These Controls Corporation of America 1501 Harpers Road Virginia
*01610* LESTRONIC II 48 VOLT AUTOMATIC BATTERY CHARGER MODEL 18710 TYPE 48LC25-8ET AC Input: DC Output: Battery Specifications: Specifications 120 volts, 15 amps, 60 Hertz, single-phase 48 Volts, 25 Amps,
Sump, Effluent and Sewage pumps INSTALLATION MANUAL Read and save these instructions. This manual contains very important Safety Warnings and Operating Instructions. You will need to refer to it before
Portable Air Conditioner Owner's Manual Model:3 in 1 12,000 Btu/h Series 3 Please read this owner s manual carefully before operation and retain it for future reference. CONTENTS 1. SUMMARY...1 2. PORTABLE
TESTING, SERVICE & REPAIR GUIDE (For SH Space Heating Models & RA Water Heating Models) WARNING - HIGH VOLTAGE AC electrical circuits are connected to this heater. Do not attempt any service work on the
Model Number: Serial Number: Information Manual Installation and Troubleshooting Instructions for Electric Tankless Residential Water Heaters. ATTENTION: IF YOU ARE NOT A LICENSED PLUMBER OR A LICENSED
WWW.BURCAM.COM 2190 Boul. Dagenais West TEL: 514.337.4415 LAVAL (QUEBEC) FAX: 514.337.4029 CANADA H7L 5X9 firstname.lastname@example.org Your pump has been carefully packaged at the factory to prevent damage during shipping.
Electric Mini Tank Water Heaters CMT-1.3 CMT-2.5 CMT-4.0 CMT-ST70 Tempering valve Optionally available Installation and Operating Instruction Manual Table of Contents Important Safety Instructions 3 General
Portable Air Conditioner OWNER S MANUAL Read these instructions before use 8 Model: MN12CES / MN10CESWW Voltage rating: 120V~60Hz Power rating : 1100W (MN12CES) Power rating : 900W (MN10CESWW) Customer
Bottom Loading Water Dispenser Model # 601000 TO REDUCE THE RISK OF INJURY AND PROPERTY DAMAGE, USER MUST READ THIS MANUAL BEFORE ASSEMBLING, INSTALLING & OPERATING DISPENSER. SAVE THIS MANUAL FOR FUTURE
Jump-N-Carry Models 300, 400, 660, 950, 4000 & 12/24 Thank you for purchasing the best jump-starter unit on the market. Your unit has been equipped with special features to make the jump-starting process
45131 Wireless Alarm System Window/Door Sensor User s Manual Choice ALERT Control all Sensors & accessories from one location Table of Contents Important Safeguards 4 Introduction 5 Installation 6 Assigning
I N S T A L L A T I O N I N S T R U C T I O N S F O R T H E H i l k o i l Energy S aving Hot Water Kit IMPORTANT: These installation instructions are meant to be used as a guide for woodstove owners and
Model A Turn Signal Kit Installation Guide Consumer Hot Line: 888-471-LOGO 770-476-7322 In Atlanta, GA http://www.logolites.com P/N: 100-005/G 2003 3407 Hwy. 120 Duluth, GA 30096, USA Logo Lites and the
Rechargeable Power Pack User s Manual 2013 VTech Printed in China 91-009656-000 US INTRODUCTION The Rechargeable Power Pack makes it easier than ever to keep the InnoTab 3 or InnoTab 3S charged and ready
RI-215A Operator s Manual Part Number: 71-0045RK Revision 0 Released: 10/3/05 Warranty RKI Instruments, Inc., warrants gas alarm equipment sold by us to be free from defects in materials and workmanship,
90 STEALTH The MOST Versatile and Easiest To Use Towed Vehicle Braking System available! PROFESSIONAL INSTALLERS: Please return these instructions to the owner, for the owner s future reference INSTALLATION
Oceanscience Cable Chimp II Cableway ROV System User Guide and Warranty Page 1 Table of Contents Introduction Page 3 Overview Page 3 Setup and Operation Page 5 Remote Control Page 6 Power Management Page
Adorable Humidifiers Tower Fan MODEL# EE-5605 PLEASE READ THESE AND SAVE ALL INSTRUCTIONS TO ENSURE THE SAFE AND EFFECTIVE USE OF THIS APPLIANCE. TABLE OF CONTENTS Table of Contents P.1 Important Safety
Owner s Manual 1 Dear Customer, Thank you for purchasing this product. For optimum performance and safety, please read these instructions carefully. User Memo: Date of purchase: Dealer name: Dealer address: