1 GOT WATER? Nuclear power plants are usually built next to lakes, rivers, and oceans. 1 Not for the scenic views that such locales provide, but because water can absorb the waste heat produced by the plants. Nuclear power plants consume vast amounts of water during normal operation to absorb the waste heat left over after making electricity and also to cool the equipment and buildings used in generating that electricity. In event of an accident, nuclear power plants need water to remove the decay heat produced by the reactor core and also to cool the equipment and buildings used to provide the core s heat removal. This issue brief describes the reliance of nuclear power plants on nearby bodies of water during normal operation and under accident conditions. All of the 104 nuclear reactors currently licensed to operate in the United States are light 2 water reactors. Sixty-nine (69) are pressurized water reactors (PWRs) and 35 are boiling water reactors (BWRs). In a PWR, water flowing through the reactor core is heated by its thermal energy. Because this water is maintained under high pressure (over 2,000 pounds per square inch), it does not boil even when heated to over 500ºF. The hot water flows from the reactor vessel and enters thousands of metal tubes within the steam generator. Heat passes through the thin tube walls to boil water at lower pressure that surrounds the tubes. The water leaves the tubes about 10ºF cooler and returns to the reactor vessel for another cycle. Steam leaves the steam generator and enters the turbine. The steam spins the turbine, which is connected to a generator that produces electricity. The steam exits the turbine into the condenser. Water from the nearby lake, river, or ocean flows through thousands of metal tubes in the condenser. Steam flowing past outside these tubes cools and changes back into water. The condensed water flows back to the steam generator for another cycle. The water leaves the condenser tubes up to 30ºF In a BWR, water flowing through the reactor core is heated by its thermal energy and boils. The steam flows from the reactor vessel to the turbine. The steam spins the turbine, which is connected to a generator that produces electricity. The steam exits the turbine into the condenser. Water from the nearby lake, river, or ocean flows through thousands of metal tubes in the condenser. Steam flowing past outside these tubes cools and changes back into water. The condensed water flows back to the reactor vessel for another cycle. The water leaves the condenser tubes nearly 30ºF warmer and returns to the nearby lake, river, or ocean. 1 An exception to the rule is the Palo Verde nuclear plant. Built in the arid region west of Phoenix, Arizona, cooling water is brought to the facility. 2 Another type of reactor uses heavy water water enriched in deuterium, an isotope of hydrogen, that makes it heavier than regular or light water. Washington Office: 1707 H Street NW Suite 600 Washington DC FAX: Cambridge Headquarters: Two Brattle Square Cambridge MA FAX: California Office: 2397 Shattuck Avenue Suite 203 Berkeley CA FAX:
2 Page 2 of 14 warmer and returns to the nearby water supply. The water needs of and usage by PWRs and BWRs are essentially identical. Both types of nuclear power reactors are about 33 percent efficient, meaning that for every three units of thermal energy generated by the reactor core, one unit of electrical energy goes out to the grid and two units of waste heat go out to the environment. Two modes of cooling are used to remove the waste heat from electrical generation: oncethrough cooling and closed-cycle cooling. In the once-through cooling system, water from the nearby lake, river or ocean flows through thousands of metal tubes inside the condenser. Steam flowing through the condenser outside the tubes gets cooled down and converted back into water. The condensed water is re-used by the plant to make more steam. The water exits the condenser tubes warmed up to 30ºF higher than the lake, river, or ocean temperature and returns to that water body. In the closed-cycle cooling system, water flows through thousands of metal tubes inside the condenser. Steam flowing through the condenser outside the tubes gets cooled down and converted back into water. The condensed water is re-used by the plant to make more steam. Water exits the condenser tubes warmed nearly 30ºF higher than upon entry to the condenser tubes. The water leaving the condenser tubes flows to a cooling tower. Air moving upward past the water spraying downward inside the cooling tower cools the water. The water collected in the cooling tower basin is pumped back to the condenser for re-use. Water from the nearby lake, river, or ocean is needed to make-up for the water vapor carried away by the air leaving the cooling tower. ONCE-THROUGH COOLING SYSTEMS The once-through cooling system begins at the intake structure. A typical intake structure is shown in the graphic. The river, lake, or ocean is on the left and the plant is on the right. The bar rack is a lattice of metal bars intended to prevent large debris (e.g., logs, two-liter bottles, etc.) from entering. Workers can remotely operate a trash rack rake along the surface of the bar rack to dislodge accumulated debris. The traveling screen is a small metal mesh that moves in a loop. The traveling screen prevents small debris and fish from entering. Depending on the location, intake structures, such as the one shown, can be equipped with protection against ice with an outer barrier guarding against chunks of ice in the water and air bubblers to ward off ice
3 Page 3 of 14 buildup on the traveling screens. Nuclear power plants use two to four circulating water pumps for each reactor unit. Each circulating water pump with its electric motor stands nearly 40 feet tall and supplies over 100,000 gallons of water. The piping from the discharge of the circulating pumps runs underground from the intake structure to the turbine building. The circulating water system pipes rise from the ground to deliver water to the main condenser located directly beneath the low pressure turbines in the turbine building. The main condenser typically consists of three metal barn-like structures called waterboxes. Each low pressure turbine exhausts steam into its own waterbox. The circulating water pipes route water within thousands of metal tubes through the waterboxes. Heat is transferred from the steam flow past the outside of the tubes through the thin metal walls to the water inside. The steam cools down and condenses back into water which collects in the bottom of the waterboxes in what is called the hotwell. In some plants, like the one illustrated in the graphic, the condenser tubes run the length of the waterboxes. Other designs have the condenser tubes running the width of the waterboxes. After exiting the condenser tubes, the warmed water flows back to the lake, river, or ocean. The water from the hotwell is recycled by the condensate and feedwater pumps back to the steam generators (in PWRs) and to the reactor vessel (in BWRs) to make more steam. The design and operation of the main condensers in once-through and closed-loop cooling systems prevents radioactively contaminated water from leaking into the nearby lake, river, or ocean if one or more of the condenser tubes breaks. The cool water flowing inside the tubes condensing steam outside the tubes creates a vacuum inside the waterboxes relative to the outside pressure. That vacuum helps pull steam out of the low pressure turbines sitting atop the condenser waterboxes. In addition, should one or more condenser tubes break, the vacuum causes lake, river, or ocean water within the tubes to leak into the waterboxes rather than radioactively contaminated water within the waterboxes from leaking into the tubes. Lake: This image shows the thermal discharge from a nuclear plant into a lake. The warm water (red) discharged from the circulating water system enters the lake via a long canal and then cools as it flows counterclockwise around the lake, guided by a long weir wall. The cooled water (dark blue) is drawn back into the plant s intake structure for another cycle.
4 Page 4 of 14 River: This drawing shows the discharge piping routed along the river bottom to diffuse the warm water discharged from the circulating water system into the river. The diffuser pipes extend out into the river along its bed for optimal mixing between the warm discharge water and the cooler river water. Ocean: This drawing shows the underground piping routed from offshore intake and discharge points for a coastal nuclear plant. The intake and discharge points in this case are nearly one mile offshore. The water usage by a once-through cooling system depends on the size of the nuclear power reactor it services. As detailed in Attachment 1, the minimum amount of water needed in a once-through cooling system can be estimated from the following equation using the electrical output of the reactor in megawatts (Mwe) and the differential temperature of the cooling water passing through the condenser ( T, ºF): Flow, gpm = 14,295 * Mwe T For example, the typical 1,000 Mwe nuclear power reactor with a 30ºF T needs approximately 476,500 gallons per minute. If the temperature rise is limited to 20ºF, the cooling water need rises to 714,750 gallons per minute. Some of the new nuclear reactors being considered are rated at 1,600 Mwe. Such a reactor, if built and operated, would need nearly 1,144,000 gallons per minute of once-through cooling for a 20 degree temperature rise. Actual circulating water system flow rates in once-through cooling systems are 504,000 gpm at Millstone Unit 2 (CT); 918,000 gpm at Millstone Unit 3 (CT); 460,000 gpm at Oyster Creek (NJ); 311,000 at Pilgrim (MA); and 1,100,000 gpm at each of the twp Salem reactors (NJ).
5 Page 5 of 14 Once-through cooling systems have posed problems for nuclear power plants when the cooling water doesn t go through once. Among many examples: The operators at Point Beach Unit 2 in Wisconsin manually tripped the reactor from 100 percent power on May 15, 2004, after a diver inspecting the intake structure for potential damage from the previous winter had his tether, air, and communications lines became snagged and a rescue diver was unable to free him. After the reactor was tripped, the operators shut down the circulating water pumps. Both divers emerged unhurt from the water. The reactor resumed operations five days later. The operators at Point Beach Unit 2 in Wisconsin manually tripped the reactor from 70 percent power on June 27, 2001, after a large number of Alewives blocked the traveling screens. The reactor resumed operations five days later. On April 4, 1998, a diver entered the intake bay for Calvert Cliffs Unit 1 in Maryland to lower a stop log. A problem developed and the diver was transported to the Calvert Memorial Hospital where the diver was pronounced dead on arrival. In January 1996, the Wolf Creek nuclear plant in Kansas experience the build-up of frazile ice at its intake structure that led to a reactor trip and impairment of the essential service water system. The NRC fined the plant s owner $300,000 in July 1996 for not taking steps to prevent the ice build-up and for less than stellar response to the build-up once it occurred. The NRC fined the owner of Salem Unit 1 in New Jersey $500,000 in October 1994 for violations stemming from an event on April 7, 1994, when marsh grass floating in the Delaware River blocked the traveling screens at the intake structure. The operators reduced the reactor power level as the build-up decreased the amount of cooling water flowing through the plant. They made a series of mistakes along the way and the reactor automatically shut down for safety reasons. On December 22, 1991, a 36-inch diameter pipe carrying cooling lake water to the plant ruptured just outside the plant s buildings. Approximately 2.9 million gallons of water spilled from the broken pipe before operators closed a valve to isolate the broken piping section. Some of the water leaked into the plant and caused minor flooding damage. The reactor, which had been running at 73 percent power, was manually shut down by the operators. Operators shut down the FitzPatrick nuclear plant in New York on October 19, 1990, after wind blew lake debris onto the traveling screens at the intake structure. The heavy buildup increased the pressure across the traveling screens, causing them to bow inward. When debris started slipping past the bowed section of the screens, the operators shut down the plant to minimize the impact of the debris intrusion. Operators shut down Millstone Unit 1 in Connecticut on October 4, 1990, after a storm caused a heavy build-up of seaweed on the traveling screens at the intake structure. The build-up caused the instruments monitoring the differential pressure across the screens to go offscale high. The operators initially did not believe this instrumentation and delayed shutting down the circulating water pumps. By the time the pumps were shut down, three of the five traveling screens had collapsed from the excessive pressure. In September 1984, a flotilla of jellyfish attacked the St. Lucie nuclear plant in Florida, forcing both of its nuclear reactors to shut down for several days due to lack of cooling water.
6 Page 6 of 14 Operators shut down Millstone Unit 1 in Connecticut on September 1, 1972, after condenser tube failures allowed water from the Atlantic Ocean to be pumped into the reactor vessel. Serious chloride corrosion from the sea water disabled 114 of the 120 local power range monitors in the reactor core and required replacement of feedwater spargers and several other components before the reactor could restart. CLOSED-LOOP COOLING SYSTEMS If cost were the only factor in the decision, nearly all nuclear power plants would feature once-through cooling systems because pumping vast amounts of water through the condenser is usually the cheapest option. Closed-cycle cooling systems are used when the nearby water source lacks sufficient water volume to allow the large flow rate needed for once-through cooling or when environmental limits on thermal pollution dictate that waste heat be rejected to the air and not just to the body of water. Two types of cooling towers are used in closed-cycle cooling systems: natural draft and mechanical type. The natural draft cooling towers have become iconic symbols of nuclear power plants even though not all nuclear power plants have them and many non-nuclear power plants also use them. Natural Draft Cooling Tower: Underground piping carries warm water from the condenser in the turbine building to the tower. The pipe rises vertically in the center of the tower. Smaller distribution piping branches out from the main pipe to spray the warm water onto a feature labeled heat exchange packing in the graphic. This device functions to further diffuse the water spray into small water droplets. This enhances the cooling by the air drawn upward through the rainfall by the chimney effect. The cooled water collects in the cooling water basin where another underground pipe carries it back to the condenser. Natural draft cooling towers are quite tall. For example, the tower for Unit 2 at the Nine Mile Point nuclear plant in New York is approximately 540 feet tall and 450 feet in diameter at the base. The tower s reinforced concrete walls are 36 inches thick at the base and the lip and 8 inches thick at the throat. It required nearly 16,500 cubic yards of concrete and 1,230 tons of reinforcing steel. Mechanical Type Cooling Tower: Underground piping carries warm water from the condenser in the turbine building to the tower. The pipe rises vertically to force the water to the distribution plume at the top of the tower. Smaller piping and conduits branch out from the plume to distribute the warm water onto louvers. This flow path diffuses the watery into small droplets. This enhances the cooling by the air drawn through the water droplets by the motor-driven fans. The cooled water collects in the cooling water basin where another underground pipe carries it back to the condenser. Mechanical type cooling towers are shorter than natural draft cooling towers. For example, each of the two mechanical type cooling towers at Vermont Yankee are approximately 50 feet tall, 60 feet wide, and 463 feet long.
7 Page 7 of 14 The closed-cycle cooling system label is a bit of a misnomer because plants with mechanical type cooling towers consume water from nearby lakes, rivers, and oceans and also return water to those bodies. Water is needed to compensate for the water vapor leaving the cooling towers with the cooling air flow. The amount of makeup is far less than the amount of water needed for once-through cooling systems, but it is not negligible. When both reactors at the Susquehanna nuclear plant in Pennsylvania operate in summer, nearly 30 million gallons of makeup water per day (or nearly 21,000 gallons per minute) are needed from the river to compensate for cooling tower drift. Water must also be discharged from closed-cycle cooling systems in order to control the chemistry of the recycled water and to limit the build-up of sediment and other debris in the cooling tower basins. The Susquehanna nuclear plant uses another 11 million gallons per day (about 7,600 gallons per minute) from the river that balances the discharge flow rate back to the river for cooling tower basis chemistry control. Actual circulating water system flow rates in closed-loop cooling systems are 480,000 gpm at Davis- Besse (OH); 552,000 gpm at Hope Creek (NJ); and 580,000 gpm at Nine Mile Point Unit 2 (NY); Closed-loop cooling systems have also posed problems for nuclear power plants: The operators reduced the power level of the Vermont Yankee nuclear plant to less than 60 percent on August 21, 2007, after a cell collapsed in one of two mechanical type cooling towers. The company blamed the collapse on wooden supports weakened by years of iron salt and fungus. The repaired cooling tower was returned to service on September 13, On May 22, 2006, the Catawba Unit 2 cooling tower overflowed when its upper level screens clogged. The overflow followed unsealed electrical conduit penetrations into the 1A Diesel Generator Room. Workers discovered the water intrusion and stopped it before the emergency diesel generator was damaged from flooding. A subsequent evaluation of the existing flood protection measures showed that emergency diesel generator could have been damaged by flooding in 15 minutes under design maximum rainfall conditions. Workers sealed penetrations to restore adequate flood protection capabilities. The owners of the Palisades nuclear plant in Michigan informed the NRC on February 1, 1977, that the transmission lines and towers had heavy ice build-up from the cooling tower vapor drift. Prior to this event, the plant s safety studies had considered the simultaneous loss of all four reactor coolant pumps to be incredible. The owner maintained the reactor power level below 60 percent until analyses of the de-energization of the reactor coolant pumps and the structural integrity of the transmission towers were completed.
8 Page 8 of 14 SERVICE WATER SYSTEMS In addition to the water used by once-through or closed-cycle cooling systems to handle the waste heat rejected from the condensers, nuclear power plants also take water from the nearby lakes, rivers, and oceans to cool other equipment. The service water system takes water from the nearby water source and supplies it to plant equipment such as the chillers for air conditioning units, lubricating oil coolers for the main turbine, aftercoolers for air compressors, and heat exchangers for closed-loop cooling systems providing cooling water to other equipment like the spent fuel pool heat exchangers. After cooling these components, the service water system returns the warmed water to the nearby source, labeled ultimate heat sink in the diagram. Unlike once-through and closed-cycle cooling systems that are not used when the nuclear plant is shut down (explaining why the visible plumes from cooling towers cease when plants shut down for refueling), the service water systems operate 24 hours a day, 7 days a week. During periods when the reactor is shut down, the service water system cools the components that are in turn cooling the reactor. Actual service water system flow rates are 37,000 gpm in winter and 52,000 gpm in summer at Hope Creek (NJ); 24,000 gpm at Millstone Unit 2 (CT); 30,000 gpm at Millstone Unit 3 (CT); and 13,500 gpm at Pilgrim (MA). Service water systems have posed problems at nuclear power plants, including: Operators shut down Unit 1 at the LaSalle nuclear plant in Illinois on June 28, 1996, and Unit 2 on the following day following the discovery of foreign material in the service water tunnel. Contractors had been injecting a polymer foam sealant into cracks in the concrete floor of the pump house. They drilled holes near the cracks to better seal the cracks. Some of the holes passed completely through the concrete, enabling the polymer foam sealant to collect in the service water tunnel. The NRC fined the company $650,000 for failure to manage the activity. The NRC stated The injected foam sealant material created a significant safety issue by threatening to block the intake of both units safety-related service water systems, systems required to mitigate the consequences of a design basis accident. Operators shut down the Perry nuclear plant in Ohio on March 26, 1993, after an underground 30- inch pipe carrying service water from the pump house at the lake to the turbine building ruptured. Water from the broken pipe flooded portion of the site and entered unsealed electrical conduits and flowed under doors to flood some buildings to six to eight inches deep. Operators stopped the service water pumps 16 minutes after the pipe ruptured.
9 Page 9 of 14 In November 1991, the NRC fined the owner of Millstone Unit 3 in Connecticut $50,000 for inadequate corrective actions after workers identified reduce service water flow but did not fix the problem until a test conducted to answer NRC s questions demonstrated that emergency diesel generator B was getting only 15 percent of the cooling water flow it needed. Following this discovery, operators manually shut down Millstone Unit 3 on July 25, 1991, to disassemble and clean the service water system piping. A security officer responding to an alarm on the door to the service water tunnel discovered two contract workers smoking marijuana. The workers were fired and escorted from the plant site. Workers entered the containment building at Indian Point Unit 2 in New York on October 17, 1980, to investigate a probable cause for an automatic reactor trip earlier that day. They discovered water on the containment floor a lot of water. A small service water leak from components inside the containment collected over an extended period of time until the lower 9 feet of the reactor vessel was submerged. Approximately 100,000 gallons of water had leaked, undetected, over an undetermined period of time. Operators shut down the Unit 2 reactor at Arkansas Nuclear One on September 3, 1980, after the NRC resident inspector identified the service water flow rate though the containment cooling units was less than that required by the technical specifications. Workers found that Asiatic clams caused extensive flow blockage of the service water system. GOT DILUTION? Nuclear power plants, whether using once-through cooling or closed-loop cooling, continuously discharge large amounts of water back into the nearby lake, river, or ocean. When leaks develop in the tubes within the condensers, the higher pressure of the lake, river, or ocean water within the tubes causes it to leak into the plant rather than radioactively contaminated liquid leaking out from the plant. But the water being discharged from nuclear plants often contains radioactivity. Nuclear power plants have systems called liquid radwaste systems that collect and treat radioactively contaminated water. The liquid radwaste systems have deminerlizer and filter units to treat the water. To the extent possible, the treated water gets recycled to the plant. At times, the liquid radwaste systems release the treated water to the nearby lake, river, or ocean. Such releases are controlled and monitored. The liquid radwaste system tank to be discharged is sampled to ascertain its radioactive contents (i.e., radioactive concentrations times the amount of water in the tank). If the radioactive contents are below federal limits on liquid releases, the water in the tank can be pumped into the discharge flow from the once-through or closed-loop cooling system. Mixing the liquid radwaste system release flow with the discharge flow dilutes the radioactivity concentration, which is further reduced when the discharge mixes with lake, river, or ocean water. Thus, when the water discharged from a nuclear power plant contains radioactivity, it is by design and not by accident.
10 Page 10 of 14 WATER NEEDS DURING ACCIDENT CONDITIONS The discussions above regarding once-through cooling systems, closed-loop cooling systems, and service water systems apply to water needs during normal operating conditions, the day-to-day process of making electricity. This section covers the water needs of a nuclear power plant in event of an accident. An accident at a nuclear power reactor reduces, but does not eliminate, the amount of cooling water needed by the plant. The reactor unit will no longer be generating electricity, so the tremendous volume of water needed by a once-through cooling system and the makeup volume of water needed to compensate for water vapor lost from a closed-loop cooling system are no longer required. It is additionally assumed that the reactor unit is disconnected from its electrical grid during the accident, so the volume of water needed by the service water systems for cooling of components normally used in day to day operations is also not needed. But what is needed during an accident is a volume of water to remove the heat still being generated by the reactor core and to cool emergency equipment and the rooms housing it. Three things are required: a source of water (called the Ultimate Heat Sink or UHS), two or more pumps to move water between the UHS and the plant, and a source of electricity for the motor-driven pumps. The Limerick Generating Station in Pennsylvania uses two natural draft cooling towers (center) to remove heat during normal operation and a pond with water sprays (oval at upper left) as the UHS during accidents for the two reactors below the cooling towers. The Grand Gulf Nuclear Station in Mississippi uses a natural draft cooling tower during normal operation and mechanical type cooling towers (upper left) in event of an accident. The South Texas Project uses a large lake for cooling during normal operation and a much smaller U-shaped pond for its UHS. The North Anna Power Station in Virginia, like Limerick, uses a pond with water sprays running here as its UHS. The Vermont Yankee nuclear plant uses two mechanical type cooling towers during normal operation and two special cells in one of those towers in event of an accident. The UHS can be the same nearby lake, river, or ocean used by the nuclear plant to absorb waste heat during normal operation or it can be a different, dedicated water source. However configured, the UHS is supposed to provide all of the nuclear power reactor s cooling water and makeup water needs for the first 30 days of an accident.
11 Page 11 of 14 Two or more pumps are used to take water from the UHS and supply it as cooling water or makeup water during the reactor. The schematic drawing to the left of the emergency service water (ESW) system for the Wolf Creek nuclear plant in Kansas represents the typical post-accident cooling system. ESW pump A to the upper right draws water from the UHS and provides cooling water to emergency components like the control room s air conditioning condenser, the cooler for the emergency diesel generator, the containment air coolers, and the cooler for the safety injection pump room. After cooling these components, the water flows back to the UHS. ESW pump A can also provide makeup water to the component cooling water (CCW) system, the auxililary feedwater system, and/or the spent fuel pool (SFP) via the piping lines shown in the lower right corner. ESW pump B to the upper left mirrors the cooling and makeup water functions provided by ESW pump A for the redundant set of emergency components. When a lake, river, or oceans serves as the UHS, the water needed by the ESW system during an accident are in the 10,000 to 30,000 gallons per minute range. Because the normal supply of electricity backfeed from the electricity generated by the nuclear plant itself or power from the electrical grid cannot be relied upon in event of an accident, nuclear power plants 3 have emergency diesel generators (EDGs) onsite. The EDGs provide the electricity to emergency equipment during an accident, including the ESW pumps. The EDGs and the ESW pumps have a symbiotic relationship most EDGs 4 have their engines cooled by water supplied by the ESW pumps while the ESW pumps have their motors powered by electricity supplied by the EDGs. Nuclear plants have experienced ESW system problems, including: In January 2004, the NRC issued a White finding to the owner of the Perry nuclear plant in Ohio for allowing workers twice to reassembly ESW pump A improperly leading to its failures. The operators at the Ginna nuclear plant in New York reduced the reactor power level from 97 percent to 50 percent on January 20, 2004, because ice build-up on the intake structure s screens partially blocked the in-flow of water from the lake. The water level in the intake structure the source of water for the pumps dropped nearly nine feet below normal. Had the water level dropped another foot, the ESW pumps would have been unable to supply water to emergency equipment and procedures would have guided operators into declaring a Site Area Emergency. 3 The exception to the rule being the Oconee nuclear plant in South Carolina which relies on backup power from the nearby Keowee hydroelectric dam. 4 The exception to the rule are a small handful of nuclear power plants with air-cooled EDGS.
12 Page 12 of 14 The NRC fined the owner of Nine Mile Point Unit 1 $200,000 in May 1991 for conducting maintenance at the intake pump screenhouse without realizing that the ESW system had been unintentionally disabled by the positioning of a gate. With the River Bend reactor in Louisiana shut down for refueling on April 19, 1989, workers applied a freeze seal to a 6-inch diameter ESW pipe. By freezing the water in this section of the pipe, workers would be able to open the downstream piping to perform maintenance. When the freeze seal failed, approximately 15,000 gallons of water poured out of the opened piping onto the auxiliary building floor. The flood damaged electrical equipment causing a short that started a fire in one electrical cabinet and disabled the system being used to cool the reactor core at the time. Operators at Susquehanna Unit 1 in Pennsylvania declared an emergency on May 24, 1986, when the ESW system was declared inoperable. The operators manually shut down the reactor, which had been operating at 100 percent power. Two days earlier, the shaft on one of the ESW pumps sheared. Workers determined its cause to be excessive corrosion and that the shaft on the remaining ESW pump was susceptible to the same failure mode. On June 10, 1972, an operator supporting maintenance on a 10-foot diameter butterfly valve in the circulating water system at Quad Cities Unit 1inadvertently caused it to close. The valve s closure caused the pressure in the piping to rise until a rubber expansion joint in a recirculating line ruptured. In the six minutes it took to contact the control room and have the operators turn off the circulating water pumps, the water pouring from the ruptured expansion joint flooded the turbine building basement to a depth of nearly 16 feet. The flood submerged the four ESW pumps as well as the cooling water pumps for emergency diesel generator No. 1 and the swing emergency diesel generator No. 1/2. NUCLEAR BORN KILLERS Nuclear power plants, whether using once-through or closed-cycle cooling, withdraw large amounts of water from nearby lakes, rivers, and oceans. In doing so, aquatic life is adversely affected. A 2005 study, for example, of impacts from eleven coastal power plants in Southern California estimated that the San Onofre nuclear plant impinged nearly 3.5 million fish in 2003 alone about 32 times more fish than the other 10 plants combined. Untold numbers of fish larvae and other life entrained in the water do not survive journeys through nuclear power plants. The more water the plants use, the more aquatic life we lose. SUMMARY Nuclear power plants use water when they are operating, when they are shut down, and if they have accidents. So, nuclear power plants need water all of the time. Some nuclear power plants rely on cooling towers to lessen their water needs, but even the reduced needs can require tens of thousands of gallons per minute. The connection between a nearby lake, river, or ocean and a nuclear power plant might suggest the primary nuclear safety hazard is radioactively contaminated liquid leaking into the water being discharged back into that source. But as the accidents and incidents detailed in this backgrounder suggest, the real hazard involves the water not getting to the plant or the water leaking into the plant. Prepared by: David Lochbaum Director, Nuclear Safety Project Union of Concerned Scientists
13 Attachment 1: Got Math? The minimum flow rate of water needed in a once-through cooling system to remove the waste heat from a nuclear power reactor is given by the following equation: Q = m * C P * ΔT where: Q = waste heat load, BTU per hour m = once-through cooling system flow rate, pounds mass per hour C P = specific heat of water, 1 BTU/pound mass ºF ΔT = temperature difference, ºF A nuclear power reactor generating one thousand megawatt hours of electricity (1,000 Mwehours) has a waste heat load of nearly 2,000 megawatt hours. Q = 2,000 megawatt hours * 1,000,000 watts / megawatt * BTU / watt Q = 6,830,000,000 BTU per hour Assuming the water flowing through the condenser rises 30ºF (e.g., ΔT = 30ºF), the oncethrough cooling system flow rate is calculated: m = Q / ( C P * ΔT) m = 6,830,000,000 BTU per hour / (1 BTU per pound mass ºF * 30ºF) m = 228,000,000 pounds mass per hour Converting this flow rate from pounds mass to gallons: Flow = 228,000,000 pounds per hour * ( gallons / pound) * (1 hour / 60 minutes) Flow = 476,000 gallons per minute = 686 million gallons per day A more general equation for estimating the minimum flow rate in a once-through cooling system: Flow = Mwe * 14,295 / ΔT where: Flow = once-through cooling system flow rate, gallons per minute Mwe = electrical output of the nuclear power reactor, megawatts ΔT = temperate rise of the once-through cooling system water, ºF Some of the new nuclear power reactors being discussed have an electrical output of 1,600 megawatts. For a 30ºF temperature rise, a 1,600 Mwe nuclear power reactor needs: Washington Office: 1707 H Street NW Suite 600 Washington DC FAX: Cambridge Headquarters: Two Brattle Square Cambridge MA FAX: California Office: 2397 Shattuck Avenue Suite 203 Berkeley CA FAX:
14 Page 14 of 14 Flow = 1,600 Mwe * 14,295 / 30ºF = 762,384 gallons per minute Unless the nearby source of water is an ocean, large river, or large lake, it may be incapable of absorbing all of the waste heat being rejected by a nuclear plant using a once-through cooling system. The equation, slightly modified, can be used to assess the potential impact of oncethrough cooling on a river. Q = m * C P * ΔT where: Q = waste heat load, BTU per hour m = river flow rate, pounds mass per hour C P = specific heat of water, 1 BTU/pound mass ºF ΔT = temperature difference, ºF Taking the waste heat rejected from that 1,000 Mwe nuclear power reactor (6,830,000,000 BTU per hour) and assuming that the thermal pollution discharge cannot cause the river water temperature to rise more than 5ºF, the equation can be rearranged to determine the minimum river flow rate: m = Q / (C P * ΔT) m = 6,830,000,000 BTU per hour / (1 BTU per pound mass ºF * 5ºF) m = 1,370,000,000 pounds mass per hour Converting this flow rate to cubic feet per second (cfs), a more conventional river flow measure: cfs = 1,370,000,000 pounds mass / hour * (1ft 3 / 62.4 pounds) * (1 hour / 3600 seconds) cfs = 6,077 cubic feet per second The U.S. Geological Service maintains an online National Water Information Service at that provide real time reporting of river flow rates. For example, the USA Streamflow Table on November 2, 2007, reported results from 8,428 monitoring locations across the country. The results show that only one the Pamlico River near Washington, NC at 7,920 cfs of several dozen monitored locations in North Carolina had a flow rate exceeding 6,077 cfs.
Pressurized Water Reactor The core of a typical pressurized water reactor (PWR) contains about 100 tons of nuclear fuel. The fuel consists of uranium dioxide pellets loaded in metal fuel rods placed in
Boiling Water Reactor The core of a typical boiling water reactor (BWR) contains about 100 tons of nuclear fuel. The fuel consists of uranium dioxide pellets loaded in metal fuel rods placed in a square
General Electric Systems Technology Manual Chapter 2.8 Reactor Water Cleanup System TABLE OF CONTENTS 2.8 REACTOR CLEANUP SYSTEM... 1 2.8.1 Introduction... 2 2.8.2 System Description... 2 2.8.3 Component
Boiling Water (BWR) s This chapter will discuss the purposes of some of the major systems and components associated with a boiling water reactor (BWR) in the generation of electrical power. USNRC Technical
CONDENSERS AND CONDENSER COOLING SYSTEMS INTRODUCTION Conventional cooling methods of thermal power plants are extremely water intensive processes. Once-through cooling needs large natural bodies of water
Geothermal Energy Using Water-Source Heat Pumps By VIRSTAR Corporation Geothermal Expertise Since 1978 All information contained herein is the exclusive property of VIRSTAR Corporation, all rights reserved.
UNITED STATES NUCLEAR REGULATORY COMMISSION OFFICE OF NUCLEAR REACTOR REGULATION WASHINGTON, DC 20555-0001 June 16, 2011 NRC INFORMATION NOTICE 2011-12: REACTOR TRIPS RESULTING FROM WATER INTRUSION INTO
10 Nuclear Power Reactors Figure 10.1 89 10.1 What is a Nuclear Power Station? The purpose of a power station is to generate electricity safely reliably and economically. Figure 10.1 is the schematic of
1 (8) SUMMARY OF EU STRESS TEST FOR LOVIISA NUCLEAR POWER PLANT 1 LOVIISA NUCLEAR POWER PLANT Loviisa town is located approximately 90 km eastwards from Helsinki at the coast of Gulf of Finland. Loviisa
Basic Design Information for Boiling Water Reactors BWR3 & BWR4 Source: U.S. NRC - http://www.nrc.gov/reactors/generic-bwr.pdf A boiling water reactor (BWR) uses steam generated in the reactor to directly
POLICY ISSUE (INFORMATION) October 26, 2011 SECY-11-0149 FOR: FROM: SUBJECT: The Commissioners Eric J. Leeds, Director Office of Nuclear Reactor Regulation SUMMARY FINDINGS RESULTING FROM THE STAFF REVIEW
Arkansas Nuclear One: Pictures of an Accident Fission Stories #181 Dave Lochbaum, director, Nuclear Safety Project Union of Concerned Scientists Fission Stories #139 described the March 31, 2013, event
HOW DOES A NUCLEAR POWER PLANT WORK? O n t a r i o P o w e r G e n e r a t i o n P U T T I N G O U R E N E R G Y T O U S G O O D E O N T A R I O P O W E R G E N E R A T I O N What a Nuclear Reactor Does
ONLINE DATA APPENDIX Deregulation, Consolidation, and Efficiency: Evidence from U.S. Nuclear Power Lucas W. Davis UC Berkeley and NBER Catherine Wolfram UC Berkeley and NBER February 2012 This study is
4658.4500 PLUMBING SYSTEMS; NEW CONSTRUCTION. Subpart 1. Installation. All plumbing systems must be installed and tested according to this chapter and chapter 4715, the Minnesota Plumbing Code. Subp. 2.
Your Boiler Room: A Time Bomb? Is you boiler room a potential Time Bomb? A few basics you need to know to work safely in the boiler room: Two potentials for explosions in a boiler room: Water/steam side
Electro-hydraulic power stations Water head created by dams built across rivers or similar running water paths is utilized by water turbines to turn hydraulic energy into mechanical energy suitable for
BASEMENT FLOODING Prevention Guide for Homeowners 1 Did You Know? Floods are the most common hazards in Canada. Water damage is a common cause of loss for homeowner insurance. A heavy rainfall can result
Portable leak detection instrument improves heat rate at electric power plant. By Terrence O'Hanlon, CMRP Reliabilityweb.com By using a ruggedized portable ultrasonic leak detector, Mr. Brian Thorp, PdM
Nuclear Information and Resource Service 1424 16 th Street NW Suite 404 Washington, DC 20036 Tel. 202-3428-0002 www.nirs.org FACT SHEET Natural Disasters and Safety Risks at Nuclear Power Stations November
SANITARY SEWER BACKUP Causes & Prevention A. PURPOSE The purpose of this publication is twofold: 1. It provides homeowners with basic information on the causes of sanitary sewer backups. 2. It provides
April 2014 Nuclear Energy s Economic Benefits Current and Future Executive Summary The nuclear energy industry plays an important role in job creation and economic growth, providing both nearterm and lasting
GUIDE 26 June 2000 YVL 2.1 Nuclear power plant systems, structures and components and their safety classification 1 General 3 2 Safety classes 3 3 Classification criteria 3 4 Assigning systems to safety
A Guide to Trouble-Free Cooling Towers A basic understanding of cooling tower operation and maintenance will help keep a cooling water system running in top condition, year after year By David M. Suptic
Tampa Bay Seawater Desalination Plant Project History How The Plant Works Desal Fun Facts 2575 Enterprise Road, Clearwater, FL 33763-1102 Phone: 727.796.2355 / Fax: 727.791.2388 www.tampabaywater.org Tampa
Underground Storage Tanks An Informational and Guidance Document for the University Community. Please contact Yale Environmental Health and Safety for latest Regulatory Requirements. A typical UST installation
How Ground/Water Source s Work Steve Kavanaugh, Professor Emeritus of Mechanical Engineering, University of Alabama Ground Source s (a.k.a. Geothermal s) are becoming more common as the costs of energy
Fats, Oil and Grease Best Management Practices Manual Information, Pollution Prevention, and Compliance Information For Food Service Facilities Pinellas County Utilities Water Quality Management Division
MARYLAND DEPARTMENT OF THE ENVIRONMENT Oil Control Program, Suite 620, 1800 Washington Blvd., Baltimore MD 21230-1719 4 410-537-3442 410-537-3092 (fax) 1-800-633-6101 http://www.mde.state.md.us Maryland
Stephen Lowe ASHRAE Hampton Roads Chapter Past President AECOM Design Mechanical Engineering Discipline Manager, Virginia Beach Division Professional Engineer Commonwealth of Virginia, NCEES BSME University
Exelon Generation 200 Exelo11 Way Kennett Square. PA 19348 www.pxeloncoroi.c cm 10 CFR 50.55a August 13, 2015 U.S. Nuclear Regulatory Commission Attn: Document Control Desk Washington, DC 20555-0001 Peach
POLLUTION PREVENTION FACT SHEET: AUTOMOBILE MAINTENANCE Description This pollution prevention measure involves creating a program of targeted outreach and training for businesses involved in automobile
P a g e 1 Generating Current Electricity: Complete the following summary table for each way that electrical energy is generated. Generating Electrical Energy Using Moving Water: Hydro-Electric Generation
Glossary of Heating, Ventilation and Air Conditioning Terms Air Change: Unlike re-circulated air, this is the total air required to completely replace the air in a room or building. Air Conditioner: Equipment
Chapter 1: Review Lecturer: Dr Ibrahim Rida Electrical Engineering Department University of Hail First Semester (112) 2011/12 1.2. ENERGY SOURCES Energy resources are the various materials that contain
later damage - Loss ControL axisinsurance.ca Table of Contents EXECUTIVE SUMMARY... 1 FACILITY SYSTEMS WATER DAMAGE... 2 Frozen Pipes.....................................................................................
The integrity evaluation of the reactor building at unit4 in the Fukushima Daiichi nuclear power station May 2012 Government and TEPCO s Mid-to Long Term Countermeasure Meeting Management Council Outline
A cure for water damage in real estate Presented for BC Non-Profit Housing Association by Jeff Shearman, Zurich Services Corporation 2010 Zurich Canada Focused on our customer Reduce overall risk by reducing:
Data Realty Colocation Data Center Ignition Park, South Bend, IN Owner: Data Realty Engineer: ESD Architect: BSA LifeStructures Project Overview Data Realty is a data center service provider for middle
INTRODUCTION here was an accident at Three Mile Island Unit 2 on March 28,1979. It caused extensive damage to the plant's nuclear fuel core. Most of the plant's major systems were relatively undamaged.
GEOTHERMAL HEATING AND COOLING INTRODUCTION Geothermal Heating and Cooling Systems provide space conditioning -- heating, cooling, and humidity control. They may also provide water heating -- either to
TYPICAL FIRE SAFETY INSPECTION VIOLATIONS The following is a list of typical violations often found by inspectors and a generic solution. You can use this list to improve the safety of your facility, to
Chemical Decontamination and Fluid Handling Services Westinghouse is a global industry expert in decontamination and fluid handling processes, with proven abilities in decontamination and remediation work.
Demystifying HVAC Test Your HVAC Knowledge By Ron Prager How much do you know about HVAC? Try testing yourself with the following questions and then take a look at the answers on the following page. 1)
April 30, 2013 1 Facility Stabilization and Deactivation C.1.3 - (Period 3) After facilities are turned over by USEC and accepted by DOE: Perform minimal stabilization and deactivation activities for facilities
DISTRICT OF COLUMBIA WATER AND SEWER AUTHORITY a guide to PREVENTING SEWER BACKUPS AND FLOODING Sewer backups and flooding can damage District homes and businesses. Sewer blockages are most commonly found
APPENDIX F Baker County Mason Dam Hydroelectric Project FERC No. P-12686 Turbidity Monitoring Plan April 2011 857 Table of Contents 1.0 Introduction 1 2.0 Purpose and Scope 2 3.0 Turbidity Monitoring and
Overview NEW JERSEY Page 1 The Plant (CUP) provides electricity via a cogeneration system, chilled water for environmental cooling, steam for heating, and compressed air primarily for HVAC control Serves
Serial No. MNS-15-072 September 10, 2015,. DUKESteven Vice D. President Capps, ENERGYMcGuire Nuclear Station Duke Energy MGOIVP 1 12700 Hagers Ferry Road Huntersville, NC 28078 0: 980.875.4805 f: 980.875.4809
CITY OF NORTH RIDGEVILLE 7307 AVON BELDEN ROAD NORTH RIDGEVILLE, OH 44039 (440) 353-0819 WWW.NRIDGEVILLE.ORG WHY IS THERE WATER IN MY BASEMENT? There are two major sources of water in a basement as the
Hartford Steam Boiler One State Street P.O. Box 5024 Hartford, CT 06102-5024 Tel: (800) 472-1866 www.hsb.com July 2014 Safety should only be inspected, tested and maintained by qualified trained personnel.
KNOWLEDGE: K1.01 [3.3/3.5] P21 Which one of the following contains indications of cavitation in an operating centrifugal pump? A. Low flow rate with low discharge pressure. B. Low flow rate with high discharge
Did You Know? All nuclear power in the United States is used to generate electricity. Did You Know? Steam coming out of the nuclear cooling towers is just hot water. Nonrenewable Uranium (nuclear) Uranium
SECTION 5 COMMERCIAL REFRIGERATION UNIT 22 CONDENSERS UNIT OBJECTIVES After studying this unit, the reader should be able to explain the purpose of the condenser in a refrigeration system. describe differences
Flood Checklist The following may serve as a checklist when preparing for a flood. This checklist should be tailored to processes/operations, flood protection equipment and flood potentials at your specific
BP WIND ENERGY POLICIES AND PROCEDURES Document Control Details 1.0 Purpose/Scope 1.1 This procedure provides the minimum requirements to be followed for the storage of flammable or combustible materials
CASE STUDY PRODUCED WATER EXECUTIVE SUMMARY Pentair Porous Media has worked with a major global oil & gas producer to optimize the performance of the filtration and separation at their United States mid-continent
Fire Pump Plan Review March 2010 Date of Review: / / Permit Number: Business/Building Name: Address of Project: Designer Name: Designer s Phone: Contractor: Contractor s Phone: Occupancy Classification:
Oil and Coolant Circulating Heating System Model - OCSM Installation & Operation Manual 216280-000 REV 2 Identifying Your System The HOTSTART heating system is designed to heat fluids for use in marine
Case Study: Innovative Energy Efficiency Approaches in NOAA s Environmental Security Computing Center in Fairmont, West Virginia Prepared for the U.S. Department of Energy s Federal Energy Management Program
UNITED STATES NUCLEAR REGULATORY COMMISSION OFFICE OF NUCLEAR REACTOR REGULATION WASHINGTON, D.C. 20555-0001 June 1, 2005 NRC INFORMATION NOTICE 2005-14: FIRE PROTECTION FINDINGS ON LOSS OF SEAL COOLING
12.5: Generating Current Electricity pg. 518 Key Concepts: 1. Electrical energy is produced by energy transformations. 2. Electrical energy is produced from renewable and non-renewable resources. 4. Electrical
Factory owners must ensure the boiler is: * Registered with the Boilers and Pressure Vessels Division, Labour Department * Examined by an appointed examiner and has a valid certificate of fitness * Supervised
c h i l l e r G l o s s a ry of Te rm s A p p r o a c h Temperature difference between the leaving fluid and the evaporating refrigerant ARI Standard Conditions 54 F. water inlet; 44 F. water out; 35 F.
THREE Heating and Cooling 17 Condensation Drain Line The line that drains condensed moisture away from your heating and/or cooling unit needs periodic maintenance. If your unit is located in the attic,
Section 19.0 Cross Connection Control Policy 19.1 Responsibility 19.1.1 The Elkhart Water Utility has the responsibility to supply safe, potable water from the source to the point of delivery defined as
Environmental Benefits of Pervious Concrete Concrete Can Be Recycled When the time comes to demolish a concrete structure or pavement, the material need not be wasted. It can be crushed and used as aggregate,
Boiler feedwater treatment The service life of pipes, boiler systems, pumps and fittings in thermal hot-water and steam-boiler systems is determined to a great extent by the quality of the boiler water.
Cooling Systems Jim Lukanich, CWT ChemCal, Inc. Grapevine, TX Cooling Water Systems Water is used for cooling because of its capacity to remove and store heat and availability. Cooling water is used in
Boiler & Pressure Vessel Inspection discrepancies and failures Water Heaters / Pressure Vessels Pressure Vessels are inspected once every three years. This requires a test of A: safety relief devices B:
MUELLER FALLING FILM CHILLERS MUELLER FALLING FILM CHILLERS ARE DESIGNED TO COOL ANY FLUID TO WITHIN 2 F OF ITS FREEZE POINT. The primary application for Mueller s falling film chiller is to cool food-grade
8 90 2010 PulteGroup, Inc. All Rights Reserved. drains All the water you use leaves the home through a drain. Maintaining drains prevents clogging, overflows, water damage, and other problems. care and
Piping System Model as a Life Cycle Document White Paper Introduction When designing piping systems, a variety of documents are created providing the details necessary to design, purchase, build, and test
Preventing Sewer Backups To safeguard your home against flooding from sewer backups, you should understand your home's basic plumbing and the preventative techniques discussed in this brochure. Basement
Building Foundation and Structure Overview The construction of the Hall of Waters building began in 1936, and was constructed over the original site of the Siloam and Sulpho-Saline Springs. The original
Federal Wage System Job Grading Standards for Air Conditioning Equipment Operating, 5415 Table of Contents WORK COVERED... 2 WORK NOT COVERED...2 TITLES... 2 GRADE LEVELS... 2 HELPER AND INTERMEDIATE JOBS...
Belgian Stress tests specifications Applicable to all nuclear plants, excluding power reactors 22 June 2011 Introduction Considering the accident at the Fukushima nuclear power plant in Japan, the European
Plant Maintenance Special Section Quad Cities new steam dryers project For the first time ever, Exelon performed the replacement of a pair of steam dryers. EXELON G ENERATION S Q UAD Cities nuclear power
Table V Troubleshooting Checklist for Refrigeration Systems TROUBLE POSSIBLE CAUSE CORRECTIVE MEASURE High condensing pressure. Low condensing pressure. Air or non-condensable gas in system. Inlet water
Routine and Emergency Boiler Operation Learning Outcome When you complete this module you will be able to: Describe the routine safe and efficient operation of a packaged boiler. Learning Objectives Here
Most mechanical systems such as automobiles, simple and complex machines, and power generators contain many moving parts that are in contact with each other. In addition, some of these mechanical systems
1. The leading cause of property losses is from liquid damage. A review of Zurich North America claims data highlights the problem. 2. Water damage originates from a number of sources: Domestic water lines
CONDENSATION IN REFRIDGERATED BUILDINGS By: Steve Salisbury Nov. 10, 2010 (revised Nov. 14, 2013) Introduction The following discussion reviews the basic causes of condensation in refrigerated buildings
What Is a Cross-Connection? A cross-connection is a direct arrangement of piping that allows the potable (safe drinking) water pipe to be connected to a pipe supply that contains a contaminant or pollutant.
Your consent to our cookies if you continue to use this website.