1 Small Commercial Business Energy Audits Recognizing and addressing the special requirements of the small business market segment.
2 Class 4 Class 4: Lighting Fundamentals Basic Lighting Technology Advanced Lighting Technologies The Lighting Survey
3 Class 4 Reading Assignment Review
4 Class 4 Why Does Lighting Matter? Lighting represents about 22% of electricity consumption in typical retail store, not including effect on cooling loads Lighting retrofits can save 30-50% of lighting energy, as well as 10-20% of cooling energy 4 Lighting is a major determinant of workers satisfaction with their indoor environment, and has been shown to directly affect productivity
5 Class 4 Lighting Technologies 3 Generations Fluorescent & HID Incandescent Improving efficiencies (lumens per watt) LED
6 Class 4 Lighting Technology: Efficacy Efficacy = lumens per watt Source: Virginia Energy Savers Handbook (2005)
7 Class 4 Lighting Terminology: Basic Ballast Candela Efficacy Efficiency Fixture Footcandle Lamp Life Lens Lumen Reflector
8 Class 4 Lighting Fixture Types Lighting fixtures may send all or most of their light downward (A), upward (B), or a mixture of the two (C). Discussion: What do you think are the implications of the different ways these fixture distribute light?
9 Class 4 Lighting Power Density (LPD) Maximum lighting power permitted per unit area of a building classification or space function. Expressed as the ratio of lighting power consumption to floor area: Watts per Square Foot (W/ft 2 ) Used in standards and code to define allowable lighting installations Let s do a practice calculation.
10 Class 4 Basic Lighting Retrofit Calculation Savings = (Existing W New W) x Burn Hours/yr. Sample Problem If a fixture currently uses a 60-watt bulb, and is left on 4 hours per day, how much will you save by switching to a 13-watt CFL bulb for the same number of hours? DISCUSSION: What happens to the retrofit savings if the number of burn-hours is reduced by controls?
11 Class 4 Newer Technologies T5, T5HO and High-Performance T8 HID sources (metal halide, high-pressure sodium) LED Induction lighting (outdoors) Next generation technologies
12 Class 4 High-Performance Fluorescents and HID T5, T5HO and HPT8 High-output fixtures for high-bay applications HID improves characteristics of high-pressure sodium (HPS) and metal halide (MH) Low-wattage lamps Good color rendering properties Higher efficacy, longer average rated life and greater light output than incandescent lamps DIMMABLE with special ballast daylight harvesting ; can be used with occupancy controls
13 Class 4 T5 and T5HO Lamps 5/8 in diameter 40% smaller than T8 lamps; almost 60% smaller than T12 lamps Need special ballasts to operate Slightly shorter, so cannot replace T8 or T12 lamps without changing sockets and ballasts Standard output: 14, 21, 28 and 35 watts High-output (T5HO): 24, 39, 54 and 80 watts Efficacy equivalent to T8 lamps, but compact size reduces materials used in manufacture, potential for toxic substance contamination, and packaging materials so may have less environmental impact
14 Class 4 High Performance T8 Systems HPT8 can be considered against T5 Fixtures can be re-fitted Improved lamp and ballast performance Higher lumens Longer life Higher CRI rating No issues with dimming
15 Class 4 LED Lighting Systems Very high efficiency % of fluorescent wattage for similar light output Longer lamp life - up to 100,000 hours (5-10 times fluorescent lamp life) Very effective and efficient for colored light applications, as they require no filtering Dimmable Lots of activity in creating retrofit kits
16 Class 4 LED Lighting Systems Increase efficiency at low temperatures (where fluorescents lose efficiency) Makes them especially effective for refrigerated cabinet retrofits
17 Class 4 LED Lighting Systems Barriers and Disadvantages High first-cost, but declining Point sources fixture must mask or glare can result Pure color source must be blended and/or filtered to produce whites at various points on spectrum ( warm-to-cool ) Must provide for high heat dissipation at electronics New technology early failure risk Photo Credit: U.S. Dept. of Energy
18 Class 4 Next Generation Fiber Optic Fiber Optic cable excited by source, such as solar or LED High CRI provides bright, accurate illumination purest white light available No UV radiation, so no material fading Lights without transmitting heat through the cable, so reduces ambient temperature and heat risk to merchandise Many light points serviced by only one illuminator allowing for easy access for routine maintenance
19 Class 4 Next Generation Induction Lighting Contain no electrodes or filaments, so has an extremely long lamp life (up to 100,000 hrs.) Can produce a substantial amount of light in a relatively compact package High installed cost, but can be cost-effective in applications where maintenance is difficult, hazardous or costly (e.g., escalator wells, highceilinged spaces, parking garages, signage, exterior pedestrian lighting) Lower-wattage induction lamps (20 and 23 watts) also available as direct replacements for medium-base and CFL lamps Photo Credit: Philips
20 Class 4 The Lighting Survey Used to compile detailed information on lighting systems from an electrical and light distribution standpoint.
21 Class 4 The Lighting Survey: Key Steps Identify, define, designate AREAS that will be surveyed rooms and other areas, by building, floor, etc. Identify, designate and document the types of fixtures and lighting technologies, including controls Determine operating hours in various spaces Conduct the room-by-room survey Measure lighting levels for a sampling of all types of areas and fixtures
22 Class 4 The Lighting Survey: Other Considerations Method of hanging Height of tasks & fixture mounting height Ceiling type Lighting quality issues Room surface reflectances Colors of major objects and room surfaces Occupant feedback/complaints Strategy: Use a tablet computer to help make your lighting survey more comprehensive. Take photos of spaces and fixtures; sketch a floor plan and add details during your walkthrough; refer to spec sheets on the fly.
23 Small Commercial Business Energy Audits Recognizing and addressing the special requirements of the small business market segment.
24 Class 5 Class 5: Lighting Controls & Commissioning Lighting controls Schedule- and Occupancy-based Daylighting Lighting Quality (Intro) Commissioning
25 Class 5 Reading Assignment Review
26 Class 5 Controls Scheduling at lighting control panels Occupancy sensors Automatic dimming controls & daylighting
27 Class 5 Occupancy Sensors Good application for rooms or areas with periodic use patterns Provide cost-effective energy savings without compromising lighting service to occupants Sensor performance is based upon: Sensitivity degree to which sensor can detect motion Field of view angle of view, determining both coverage area and coverage pattern Coverage area physical limits of sensor s ability to detect motion
28 Class 5 Occupancy Sensor Types PIR (Passive Infrared) Changes in temperature across segmented field of view Ultrasonic Doppler Shift of frequency of bounced sound waves Sound waves not blocked by partitions, corners Hybrid Combines both technologies in a single device
29 Class 5 Performance & Application Proper Specification Matters Sensor location: Wall, ceiling Sensor location: Range of detection and obstructions Sensor selection: Wrong type for kind of motion in the area
30 Class 5 Sensor Issues & Strategies Operational Issues False triggering Failure to turn on False turn-off (failure to see occupant) Vacancy Sensor manual on, automatic off Ultrasonic waves reflecting from a moving object, changing in pitch and bouncing back toward sensor Design Strategies Automatic on-switching for public areas; manual for private/semi-private areas Reduce sensitivity of sensor or reposition to prevent false triggering Make sure people can see which luminaires are turning on and off when they push a manual switch Make sure controlled luminaire groups correspond to occupancy patterns
31 Class 5 Occupancy Sensors: Bi-Level Lighting Use when you don t want to turn off lighting completely Control alternate fixtures Pre-wired fixtures
32 Class 5 Daylighting Benefits Energy savings Reduced operational costs Reduced maintenance (shorter burn hours) Look for architectural features and opportunities. Simple Daylighting Techniques A mix of top- and side-lighting, light shelves, high-reflectance ceilings, and wall diffusion provides fairly uniform deep-plan daylighting without the glare of direct sun.
33 Class 5 Daylighting Dimmable ballasts required Sensor maintains setpoint lighting level dims electric lighting in relation to available day light Control perimeter fixtures
34 Class 5 Solatube Tubular daylighting uses passive technology to balance illumination intensity, consistency, and thermal performance Captures the sun s rays at the roof level, then transfers them indoors through highly reflective tubing
35 Class 5 Commissioning the Lighting System After Installation Make sure light levels meet design levels Make sure color (CCT) is as specified Aim accent lights Calibrate lighting controls to ensure all lighting systems perform as designed
36 Class 5 Lighting Quality Goals of an effective and efficient lighting system: Provide enough light for people to see and work comfortably throughout the day Provide bright and uniform lighting in a space (with some caveats) Do not create glare, distracting reflections, or discomfort for workers or visitors Make colors and skin tones appear natural
37 Class 5 Lighting Quality: Getting A Retrofit That Works Energy Savings Client Satisfaction
38 Class 5 Lighting Quality: Getting A Retrofit That Works
39 Class 5 More Lighting Terminology Color Rendering Index Correlated Color Temperature Glare Illuminance Light distribution Light level Luminance Luminous intensity Luminous efficiency
40 Class 5 Illuminance Levels The IESNA Lighting Handbook provides recommended illuminance levels for various applications.
41 Small Commercial Business Energy Audits Recognizing and addressing the special requirements of the small business market segment.
42 Class 6 Class 6: Lighting Quality Lighting Quality Color Glare and Other Retrofit Design Considerations
43 Class 6 Reading Assignment Review
44 Class 6 Light Meter Lab Considerations Different tasks require difference levels of illuminance The IESNA provides a reference for recommended light levels A light meter is used to measure illuminance, or the density of luminous power Equipment Light meter
45 Class 6 Light Meter Lab Exercise 1. Using the light meter, measure the illuminance levels in four different spaces (indoor/outdoor) 2. Compare your measured readings with those recommended by the IESNA; note whether your measurements fall within the recommended ranges 3. Discuss if those ranges feel appropriate to you. Additional Resources The Lighting Handbook, IESNA, 10 th Edition
46 Class 6 Color and Light Correlated color temperature (CCT) specification of the color appearance of the light emitted by a lamp, measured in degrees Kelvin (K) Gives a good indication of lamp s general appearance Warm = 2,700K, Cool = 10,000K Color Rendering Index (CRI) ability of a lamp to render colors, on a scale of CRI of 70 or higher assures that colors and skin tones appear natural CRI of 80 or higher recommended in high-end retail stores where rendering of skin tones and merchandise is key Changes in color characteristics may improve a store environment, but should be approached carefully, with preretrofit sample installations.
47 Class 6 Color Rendering Index (CRI) Color rendering can have a HUGE impact in the display of product!
48 Class 6 Correlated Color Temperature
49 Class 6 Glare Fixtures that are uncomfortably bright to look at or work under (direct glare) Fixtures that cause reflections in computer screens (indirect/reflected glare) Rule of Thumb: Select lighting fixtures that do not direct a lot of light toward people s eyes or onto their computers. Luminous intensity: Amount of light coming from a fixture in a particular direction, measured in candelas (cd) The number of candelas a fixture will produce at various angles will indicate whether comfortable to look at or too bright
50 Class 6 Spacing Criteria Fixtures should not be installed too far apart from each other or too far away from the walls Incorrect spacing causes uneven lighting and areas that will be too dark for people to see properly Always install within manufacturer s recommended spacing criteria Distance between walls and adjacent lighting fixtures should not exceed ½ of manufacturer s spacing criteria Special fixtures (wall-wash) can be used to direct light onto walls or to the ceiling (fixtures suspended from the ceiling)
51 Class 6 Lighting Design Considerations Appearance of space and light fixtures should fit the image of the business Color appearance Direct glare Reflected glare Horizontal and vertical illuminance Light distribution on surfaces Points of interest (accent lighting) Luminance of room surfaces System control and flexibility
52 Class 6 Understanding lighting needs What first impression do you want to have on visitors? (e.g., high-tech, modern, new, bright, spacious) What does the lighting system have to do? What tasks or activities? Will computers be used? What atmosphere should the lighting create? (intimate like a restaurant vs. bright, spacious like an office)
53 Class 6 Lighting Types Ambient: General lighting, usually provided with fixtures mounted on, into or near the ceiling; lighting people need to move around the space Accent: Lighting that makes the space more interesting or is used to direct people s attention to areas of interest (e.g., decorative, wall sconces, track lighting) Task: Provided in particular areas where people will be performing a certain task (e.g., desk lighting offices, lighting over a check-out counter in a retail store)
54 Class 6 How do these types of lighting work together? What is the relationship between ambient and accent lighting? How do you reduce the need for ambient lighting? Focal highlighting Quantity of light on displays Aiming flexibility of accent lighting
55 Class 6 Lighting Equipment Selection Basics Light distribution (diffuse, directional) Performance characteristics (lumen output, life, color, wattage) How light should enter the space (down, up, sideways)
56 Class 6 Special Effects Modeling of object/shadows Visual priority/organization
57 Class 6 Store Types and Typical Lighting Configurations Store type: Basic High-activity, self-service Mass merchandising/discount stores hardware, fast food, grocery, bulk sales Lighting purpose: Light all merchandise uniformly; good visibility for reading labels; bright, clean stimulating environment Lighting strategy: Ambient lighting with limited accent lighting Lighting Levels: fc ambient lighting
58 Class 6 Store Types and Typical Lighting Configurations Store type: Intermediate Average level of activity, most common type Clothing, stationery, beauty shop, gourmet shops, accessories, housewares, furniture, small objects Lighting purpose: Sufficient uniform illumination to see and examine product and read labels Lighting strategy: Ambient lighting with limited accent lighting Lighting Levels: fc ambient lighting, fc accent lighting
59 Class 6 Store Types and Typical Lighting Configurations Store type: Higher-end Lower level of customer activity, more personalized sales assistance, more expensive/exclusive merchandise Jewelry, gifts, antiques, fine clothing/accessories Lighting purpose: Sufficient uniform illumination to see and examine product and read labels Lighting strategy: Ambient + limited accent Lighting Levels: fc ambient, fc accent lighting
60 Class 6 Color Temperature Lab Considerations What is color temperature? Why is color temperature an important consideration in retail environments? How does color affect consumer behavior? Equipment Chroma meter Light box or similar setup with multiple bulb types/color temperatures Sample retail items (e.g., clothing, food, jewelry, makeup)
61 Class 6 Color Temperature Lab Exercise 1. Configure light box or similar setup with multiple light bulb types/temperatures 2. Use Chroma Meter to measure color temperatures produced by different bulbs 3. Place retail items in light box, observe changes in appearance; take notes on differences in appearance when viewed under various color temperatures Additional Resources Webinar: Fundamentals of Color, Konica Minolta
62 Class 6 Case Studies Energy-related(e.g., delamping may be possible if using lamps with higher color temperature [e.g., 4100 K vs K] that give off more blue light) Behavioral (i.e., light and shopping behavior)
Guide to new, energy-efficient lighting technologies for your business Commercial lighting systems are changing rapidly, with new or improved technologies continuously becoming available. Whether you re
Design Guidelines for Energy Efficient Lighting Systems Thank you for your interest in energy efficiency! According to the US Department of Energy, 51% of the energy used in commercial buildings is consumed
Open Office Plan Function and Orientation The open office plan on the top floor of the Westwood Community church holds 14 cubicles and doubles as the circulation space for the entire top floor. The area
AEDG Implementation Recommendations: Interior Lighting Sample Layouts for Office Buildings The Advanced Energy Design Guide (AEDG) seeks to achieve 30 percent savings over Standard 90.1-1999. This guide
Retrofit HID High Bay Fixtures to Long Life High Efficiency LED 2013 DyoCore Call us today for sales and pricing information: Toll Free: 877.849.6668 www.dyocore.com It is no hidden secret that LED bulbs
A NGuide a t i o n a l for G r i d Applicants a n d E v e r s o uand r c e Lighting Practitioners V4-20150202 Sustainable Office Design (SOD) is different than existing programs The new SOD Lighting Initiative
Shedding Light on Unexpected Market Response to High Bay Retrofits Wendy Tobiasson and Bill Biesemeyer, KEMA Services, Inc. Steve Baab, ComEd/Exelon Wayne Dobberpuhl, Arizona Public Service Co. Mary Ann
LowBay LowBay: All the power, none of the bulk Combining superior performance and energy-efficiency with a low-profile modern design, the C2D LowBay provides excellent quality of light for enhanced visibility
Small Business Lighting Business Customer Information Opportunity ID: For a free lighting assessment, please contact the Small Business Lighting program at 1-877-287-2250. Company name Date submitted Billing
Business lighting guide Table of contents Advantages of energy-efficient lighting... Take Control & Save Business Lighting Program overview... Implementation and lighting audit walk-through... Introduction
HIGH-BAY / LOW-BAY LIGHTING NEW ALTERNATIVES TO H.I.D. New from SPI LIGHTING, an exciting addition to our family of fluorescent alternatives to traditional HID high-bay and low-bay lighting. The IPS Series
WHAT S NEW IN THE 2013 CODE? Changes to mandatory Title 24 lighting requirements California's new Building Energy Efficiency Standards take effect in 2014. They improve the energy efficiency of homes by
The Revolution in Warehouse Lighting: LEDs and Intelligent Lighting Systems SUMMARY In a standard warehouse, lighting electricity can represent 38% of total operating expenses; 15% in a refrigerated facility.
$6.00 Volume 15, No. 3 Fall 2011 LicensedArchitect 2011 Chicago Architecture Conference - Tuesday, October 18 Accessibility Requirements for Hotels ALA Student Merit Winners CE Article - LED Illumination
COMBINING QUALITY DESIGN AND ENERGY EFFICIENCY FOR SMALL INDUSTRIAL FACILITIES Basics of Quality Lighting Economics of Energy Effective Lighting General Industrial Workspace Lighting Industrial Cleanrooms
Lighting for Schools James R. Benya, PE Benya Lighting Design December 2001 Lighting is and always has been an important factor in designing and operating schools. Until the 1950s, natural light predominated
The Coming Revolution in Lighting Practice BY SAM BERMAN Research on vision suggests that we have more to learn about the eye and energy efficiency Many engineering and architectural texts contain an incorrect
New WST-LED Best in Class LED Architectural Sconce June 2016 Confidentiality Statement The information in this presentation is confidential and proprietary, and may not be used, reproduced or distributed
GE Lighting Solutions Albeo LED Luminaire Modular High & Low Bay Lighting (ABHX - Series) imagination at work Product Features The award winning Albeo ABHX-series LED Luminaire utilizes innovative heat-sinking
Lighting Control in the Office Space Lutron Electronics Co., Inc. 2008 AIA/CES Program Registration This program is registered with the AIA/CES for continuing professional education. As such, it does not
New Mexico Small Business Lighting LIGHTING RETROFIT REBATE For use with invoices dated on or after March 15, 2011 Business Customer Information Company name Date submitted Billing address City State ZIP
Lighting Retrofit Application for Business Customers 2015 A Cash Energy Efficiency Program brought to you by: Instructions for Use: For complete instructions, please refer to the Terms and Conditions on
High performance industrial lighting 50% energy against traditional fittings Up to 75% energy saving with sensing Zero maintenance, no need to relamp IK10 rated durable construction Advanced LED lighting
Business Energy Rebates Application Business Energy Rebates make it easy and affordable for you to select energy efficient products for your business. and mail-in rebates are available for energy efficient
Application and Instructions SCE&G s EnergyWise for Your Business Program is designed to help nonresidential customers replace aging, inefficient equipment and systems with energy-efficient technologies.
Light in Design An Application Guide IES CP-2-10 IES Consumer Publication CP-2-10 LIGHT IN DESIGN This publication is based on the book Light in Design, authored by William F. (Bill) Blitzer, a talented
nd cover The Little black book of lighting For Film and Video Index to Kino Flo Lighting Handbook Introduction to Lighting with Kino Flos..... 2 KinoFloProducts... 4 Lighting Interviews....................
Application Guide Healthcare Lighting Appealing Spaces with Healthier Bottom Lines Lighting That s Healthy For Your Patients and Your Budget Hospitals and other healthcare facilities are among the most
LUM Technical Information Professional Downlight with innovative Energy Saver technology Availability: 4 weeks to order A: Product benefits Complete Kit for simple installation 16 Kit versions High-intensity
Big Ass Light High Bay LED Big Ass Light offers high-performance, high-efficiency luminaires engineered to be the ideal fixture for your environment. Designed for long-term performance, High Bay LEDs are
Fluorescent T8 Fixtures with High Efficiency Electronic Ballasts Replacing T12 Fluorescent with Magnetic Ballast -- Rebate per fixture All 4 foot lamps and ballasts must be on Consortium for Energy Efficiency
Light Control and Efficacy using Light Guides and Diffusers LEDs 2012 Michael Georgalis, LC Marketing Manager, Fusion Optix October 11, 2012 Agenda Introduction What Is Light Control? Improves Application
203, January 9 Energy meets efficiency MASTER LElamps imtone MASTER LElamps imtone deliver the warm, defined beam and the shift to warmer color during dimming that is provided by halogen and GLS, while
BRSP - 10 Page 1 Solar radiation reaching Earth s atmosphere includes a wide spectrum of wavelengths. In addition to visible light there is radiation of higher energy and shorter wavelength called ultraviolet
LED Application Series: Outdoor Area Lighting Building Technologies Program LED Application Series: Outdoor Area Lighting LED technology is rapidly becoming competitive with high-intensity discharge light
Lutron Linear Recessed and Video Conference Fixture Solutions Lutron Linear Recessed and Video Conference Fixture Solutions What are linear recessed and video conference fixtures? Lutron fixture solutions
Eaton s commitment to supplying energy saving innovative products is the driving force behind. follows in the tradition of highly efficient large space luminaires which have the performance and flexibility
Highbay and Lowbay LED Luminaires Energy-efficient, low-maintenance lighting for commercial and industrial applications High Performance Highbay and Lowbay LED Luminaires AccuLite Highbay and Lowbay LED
Announcing... Realtime Distance Learning For Lighting-Involved Professionals The Association of Energy Engineers, in conjunction with the University of Wisconsin-Madison Engineering Professional Development
324 Optilux LED Low Bay and High Bay 327 Optilux CFL Low Bay 330 Low Bay 332 High Bay 333 IP65 High Bay 334 Architectural High Bay and Pendants 336 325 PIR Sensors 338 Pre-Wired T8 Non Corrosive For LED
CONSERVATION AND LIGHTING Light is essential for the examination and enjoyment of collection items. But in a museum light also means damage: dyes and pigments fade or change appearance and the materials
ENERGY SAVER Energy efficient lighting Technology report Second edition 2014 Published by: Office of Environment and Heritage Department of Premier and Cabinet 59-61 Goulburn Street, Sydney Australia Ph:
DuroSite TM High Bay Lighting LED White Lighting Brochure for Industrial Applications CE version Application: The first of its kind, the Dialight DuroSite TM LED High Bay luminaire was designed specifically
Save money, reduce energy use and earn incentives by improving the energy efficiency of your business. Georgia Power s Commercial Energy Efficiency Program makes incorporating energy-efficient improvements
Company Profile Light Emitting Designs is a world-leading manufacturer of high quality LED lighting fixtures. The company s patented technologies and innovative optical design enables reliability and ultra-high
C A S E S T U D I E S Commercial/Office Space Newmark Knight Frank Making -Efficiency Their Standard Orange Health Care Center Gets an -Efficiency Check-up 1 Long Wharf Drive in New Haven owned by Newmark
1-light LED Lighting Products Contents Indoor series 02 - T8 Tube light rotatable Los Angeles - LED Series 05 - T8 Tube light PIR Tokyo - LED Series 06 - T5 Tube Light Valencia - LED Series Outdoor series
Small Office ( Encon Building) Site Report High Efficiency Office: Low Ambient/ Task Lighting Pilot Project HMG Project No: 0515r PG&E ET project #0820 Date: September 30, 2009 Submitted to: Daryl DeJean,
4 LIGHTING DESIGN CONSIDERATIONS This chapter, Lighting Design Considerations, and Chapter 5, Applications, discuss the methods and tools needed to produce integrated lighting applications that use advanced
Quality alu LED LED PROFILES - PRODCUT CATALOGUE 2010 Quality Aluminum LED Manufacturer & Designer NEW RECESSED SLIM LINE 15mm Introduction: It is recessed type of the aluminum LED profile to build into
Lighting with Artificial Light The basics of lighting Lighting with Artificial Light page 1 What is light? The visible part of electromagnetic radiation, which is made up of oscillating quanta of energy
Leaders In Industrial LED Lighting Solutions CleanLED Highbay/Lowbay Energy Efficient LED Lighting Solutions For Industry Introduction The Safelux Lighting CleanLED Highbay and Lowbay fixtures are high
Lutron Linear Recessed and Video Conference Fixture Solutions Lutron Linear Recessed and Video Conference Fixture Solutions What are linear recessed and video conference fixtures? Lutron fixture solutions
Display/Exhibit/Museum Museums and art galleries collect, preserve, analyze, and display natural artifacts and examples of human achievement and their impact on us. Effective exhibit lighting must balance
Lutron High Bay Fixture Solutions Lutron High Bay Fixture Solutions Why high bay fixtures? Lutron high bay fixtures enhance light quality and provide energy-efficient alternatives to traditional HID fixtures.
www.edison-opto.com Solid-State Lighting Series 6W MR16 DATASHEET Features High Brightness LED Light source Ecologically Friendly Energy Efficient General Information... 1 Product Dimensions... 2 Product
ECOPTIMO T8 Version 11.6 Features and Benefits Lifetime & Warranty Very high Energy Savings: More than 50% energy savings over traditional tubes Extremely bright High Ra-color Rendering Index Top Uniformity:
GE Lighting Evolve LED Area Light Scalable Area Light (EASA) imagination at work Product Features The next evolution of the GE Evolve LED Area Light continues to deliver outstanding features, while adding
1. I want to replace my fixture and put LED tubes in it. Do I get rebates for both the fixture and the tubes? No. This type of project qualifies for the LED tube rebate only. 2. Can I install any LED product
Operating Lights marlux with centrixbeam LIGHT OF THE NEXT GENERATION Light & Lights Ideal by itself, perfect in combination KLS Martin is the only source where you can get the X8 and X6 combination lights,
BUILDING TECHNOLOGIES PROGRAM Lighting Development, Adoption, and Compliance Guide I Lighting Development, Adoption, and Compliance Guide BUILDING TECHNOLOGIES PROGRAM Lighting Development, Adoption, and
LED High Bay FBX An economical LED high bay Enjoy flexibility and savings along with quality illumination Enjoy flexibility and savings along with quality illumination The Philips Day-Brite/Philips CFI
User operations and preferences in a test room equipped with advanced natural and artificial light sources Michele Zinzi, Gaetano Fasano ENEA-UDA Italian Agency for Energy, Environment and New Technologies,
PARKING FACILITY LIGHTING FOR SAFETY AND SECURITY by Donald R. Monahan, P.E. Principal Walker Parking Consultants/Engineers, Inc. 5350 South Roslyn Street, Suite 200 Englewood, Colorado 80111 (303) 694-6622
Schools GUIDE TO ENERGY EFFICIENT ND COST EFFECTIVE LIGHTING This guide provides information on how to improve the effectiveness of lighting in school buildings by using energy efficient lighting technology
RETROFIT LIGHTING & CONTROLS SOLUTIONS Automotive Dealerships The Challenge and the Opportunity There are over 17,000 automotive dealerships in North America and on average, they use up to 18% more energy
5 Energy Efficiency Best Practice Guide Contents 1 Introduction 4 2 The business benefits of good lighting 5 2.1 Improved productivity 5 2.2 Improved safety 5 2.3 Improved colour rendering 5 2.4 Improved
Daylight Dividends Case Study Location... TomoTherapy Incorporated 1240 Deming Way Madison, Wisconsin 53717 Completed... 2003 Architect, Consulting Engineer, and General Contractor... PLANNING Design Build,
Industrial Green Building 101 Opportunities and Challenges Joanne Sawatzky Senior Project Manager, Light House Sustainability at Work Re-visioning a Sustainable False Creek Flats Light Industrial Green
THE HIGH BAY SERIES LOUVERSLED DIVISION OF LOUVERS INTERNATIONAL LED Fixture LED Fixture Short Specification: The LouversLED series of LED luminaires was designed and built with high performance, efficiency,
Indirect Wash LED Fixture 369771a 1 06.10.13 LutronR s provide a combination of horizontal and asymmetrical vertical illumination for optimal video conference lighting. The unique reflector design of this
PUNKT LAMP 110 The simplicity in design and quality in material has made the Punkt Lamp the preferred downlight among architects. The design is dominated by the inner shade in mouthblown glass, diffusing
HOW TO CONDUCT ENERGY SAVINGS ANALYSIS IN A FACILITY VALUE ENGINEERING STUDY Benson Kwong, CVS, PE, CEM, LEED AP, CCE envergie consulting, LLC Biography Benson Kwong is an independent consultant providing
Header Title Subheadline Electric Sign Energy Certification Service To California Energy Commission Title 24 Technical Requirements and Audit Instructions (ENVS) Electric Sign Energy Certification Service
Your consent to our cookies if you continue to use this website.