1 Page 1 of 73 P3 Companion Standard Dutch Smart Meter Requirements By order of: Reference: Enbin B1043 Date: April 18 th, 2008 Version: 2.2 Status: Final Author: KEMA Consulting Config. ID: B1043 Version: 2.2 final Project: Functional and technical specifications Smart Meters
2 Page 2 of 73 Change Summary Revision Created / Modified Date Approved Comment 1.00 H. Spelt 28-June-07 WG04 Original release 1.20 H. Spelt 12-Sep-07 WG04 NTA first draft 2.0 first draft 2.0 second draft 2.0 final draft H. Spelt 27-Nov-07 WG04 Table of Contents modified + security and protocol stacks added; introduction prepared H. Spelt S. Ermens H. Spelt S. Ermens 13-Dec-07 WG04 Ecel file integrated, new classes added in appendi, review comments DLMS meeting 4 December added, integrated Event and error handling document 21-Dec-07 WG04 - Update of Disconnector class (Appendi A3); - New OBIS codes added and Class id s. (ecel 13/12/07); - Review comments WG04 members added; - Security part added; - update event and error handling v0.3 (table event codes and error codes updated); - Latest ecel file object mapping dated 20/12/07 consistency check with CS P3 done 2.1 final H. Spelt 4-Feb-08 WG04 - Page 46 highlight reference added - OBIS codes changed for Limiter, Disconnect control and control log - Setup objects appended with attributes and OBIS codes - Selection of security suite 7 mentioned - References added/modified - Yellow markings updated/removed/added - Push/pull clarification added - Footnote 3 and 4 added - Rate 1 and 2 mapped on Low and Normal Tariff added as etra information - PLC objects added in Appendi B 2.11 draft H. Spelt 12-Feb-08 WG04 - Update of Event and error handling version 1.0 added (see chapter 4) - Active import (-A) changed to Active eport (-A) in chapter 6.2
3 Page 3 of draft H. Spelt 16-Mar-08 WG04 - Review remarks updated after the 21st February 2008 DLMS meeting with vendors - Including results of outstanding action points (event handling => 3 comments August for event codes added, - Chapter OBIS codes; OBIS for event codes corrected) - Chapters 2.1 and 2.2 added - TCP-UDP setup => added port no. (Default 4059) - IPv4 setup modified some parameters - PPP setup modifies some parameters - Ethernet setup parameter MAC_address modified - Comment added by August to review Message security paragraph 2.2 final H. Spelt 18-Apr-08 WG04 - Review remarks updated after the 19th March 2008 DLMS meeting with vendors - Chapters 2.1 and 2.2 were modified (conformance blocks replaced by services supported) - Message security paragraph rewritten - Firmware E upgrade description added (par. 5.13) - Two event codes (17,18) added of firmware upgrade - Some binding information was added in chapter 7.2 (M-bus devices) - Appendi A and B (new classes) was updated with latest modifications of DLMS UA - Added single action scheduler for firmware activation with OBIS code Distribution information Version Addressees Remarks 1.0 Members WG4 For Review 1.20 Members WG4 For Review 2.0 first draft Members WG4 For Review Manufacturers 2.0 second draft Members WG4 For Review Manufacturers 2.0 final draft Members WG4 For Review Manufacturers 2.1 final Members WG4 For Review Manufacturers Grid Operators 2.11 draft Members WG04 For Review 2.13 draft Members WG04 For Review 2.2 final Members WG4 Manufacturers Grid Operators For Review Issue list Version Activity 2.0 A few yellow markings/comments are (still) not clarified (especially chapter 7.2) 2.1 GPRS way of connection handling/setup (like push mechanism) not yet added 2.2 Add requirements for Ethernet communication, if necessary.
4 Page 4 of 73 CONTENTS 1 Introduction Scope System architecture Normative references Document list Logical devices and associations, M-Bus modelling (general concept) Clients PUBLIC CLIENT PRE ESTABLISHED CLIENT MANAGEMENT CLIENT Access right Communication profiles and services, security Communication profiles GPRS COMMUNICATION PROFILE ETHERNET COMMUNICATION PROFILE PLC COSEM Security Overview of Object Model Profile structure Dutch smart meter Event and error handling EVENTS EVENT LOGS ERROR HANDLING ALARM HANDLING AMR PROFILE STATUS CODE Abstract objects SAP assignment, Association LN,COSEM logical device name Identification numbers Clock Activity Calendar and Special Days Table Billing periods and profiles Error and Alarm Handling (error register, alarm register) Event Handling (events and logs) Fraud detection (event log) Power Failure (counter, thresholds and event log) Disconnector (Control and Log, scheduler) Limiter P1 objects (messages, readout list) Firmware upgrade Electricity related objects Identification numbers (i.e. firmware version) E registers (+A, -A, all rate registers) E profiles (15', daily) Instantaneous Values (voltage, current, power) Power Quality (Voltage sags and swells) M-bus related objects M Bus Master Setup Identification numbers Registers Profiles (hourly)... 48
5 Page 5 of Event Log (Class id = 7) Disconnector (Control and Log) Appendi A: Specification of new DLMS classes A.1 M-Bus Master Setup Interface Class (class_id:72) A.2 Limiter Interface Class (class_id:71) A.3 Disconnect control (class_id:70) Appendi B: PLC setup classes B.1 S-FSK Phy&MAC setup (class_id: 50) B.2 S-FSK Active initiator (class_id: 51) B.3 S-FSK MAC synchronisation timeouts (class_id: 52) B.4 S-FSK MAC counters (class_id: 53) B.5 S-FSK IEC LLC setup (class_id: 55) B.6 S-FSK Reporting system list (class_id: 56) B.7 ISO/IEC LLC Type 1 setup (class_id: 57) B.8 ISO/IEC LLC Type 2 setup (class_id: 58) B.9 ISO/IEC LLC Type 3 setup (class_id: 59) Appendi C: Specification of Image Transfer Mechanism C.1 Image Transfer Interface Class (class_id:18)... 72
6 Page 6 of 73 1 INTRODUCTION 1.1 Scope This document provides a companion standard for an Automatic Meter Reading (AMR) system for electricity thermal, (heat & cold), gas and water meters. The scope of this standard is on: Residential electricity meters Residential thermal (heat & cold) meters Residential gas meters and gas valve Residential water meters This companion standard focuses on the P3 interface for Electricity meters. P0 Independent Services Provider Other Services Module P1 Metering system P3 CAS P4 Supplier E P2 G W/T Grid operator Figure 1.1: Meter interfaces overview The goal of this companion standard is to reach an open, standardized protocol implementation based on DLMS/COSEM. This companion standard is the result of a combined effort of the major Dutch grid operators and different manufactures who defined the necessary DLMS/COSEM object mapping.
7 Page 7 of System architecture The communication interface P3 and P3.1 (see figure 1.2) is based on the DLMS/COSEM standard. References to the DLMS/COSEM standard are included in section 1.3. This companion standard P3 only includes deviations, clarifications or additions to the standard as defined in the relevant standard documents. P3.2 and P0 interface (see also figure 1.2) are not part of this companion standard. The P1 and P2 interfaces are described in separate companion standards. OSM CAS P3.2 DC P3 P3.1 PLC P1 Electricity meter P2 Gas meter GPRS, Ethernet P0 PDA Laptop Figure 1.2: DLMS/COSEM infrastructure P3 1.3 Normative references The following standards are referred to in this companion standard. For undated references the latest edition applies. Ref No Document Description DLMS UA ed.8, DLMS UA ed.6, DLMS UA ed.3, 2007 DLMS UA 1002: ed.1, 2003 Blue book, COSEM Identification System and Interface Classes Green book, DLMS/COSEM Architecture and Protocols Yellow book, DLMS/COSEM Conformance Testing Process White book, COSEM Glossary of Terms 1 A new version (edition 9) of the Blue book is in development. The new version of the blue book will describe the new Classes and OBIS codes mentioned in this Companion standard and gives also the description of the new encryption and authentication mechanism. 2 A newer version (edition 7) of the Green book will have the definition of PLC Communication Profile and also the description of the new encryption and authentication mechanism.
8 Page 8 of 73 Ref No Document Description 5 IEC IEC IEC IEC IEC Ed 1.0: IEC Ed.1.0: IEC Ed.1.1: IEC Ed 1.0: IEC Ed 2.0: IEC Ed 2.0: IEC Ed 2.0: NTA 8130 NL: ISO/IEC ISO/IEC EN EN : B101: Smart Meter Requirements 22 Cosem security 23 Project: DLMS/COSEM over PLC Distribution automation using distribution line carrier systems Part 4: Data communication protocols Section 32: Data link layer Logical link control (LLC) Distribution automation using distribution line carrier systems Part 4-511: Data communication protocols System management : CIASE protocol Distribution automation using distribution line carrier systems Part 4-512: Data communication protocols System management using profile Management Information Bases (MIB) Distribution automation using distribution line carrier systems Part 5-1: Lower layer profiles The spread frequency shift keying (S-FSK) profile Electricity metering Data echange for meter reading, tariff and load control Part 21: Direct local data echange Electricity metering Data echange for meter reading, tariff and load control Part 42: Physical layer services and procedures for connection-oriented asynchronous data echange Electricity metering Data echange for meter reading, tariff and load control Part 46: Data link layer using HDLC protocol Electricity metering Data echange for meter reading, tariff and load control Part 47: COSEM transport layer for IP networks Electricity metering Data echange for meter reading, tariff and load control Part 53: COSEM Application layer Electricity metering Data echange for meter reading, tariff and load control Part 61: OBIS Object identification system Electricity metering Data echange for meter reading, tariff and load control Part 62: Interface classes Basisfuncties voor de meetinrichting voor elektriciteit, gas en thermische energie voor kleinverbruikers Information technology Telecommunications and information echange between systems Local and metropolitan area networks Specific requirements Part 2: Logical Link Control -Description Information technology -- Telecommunications and information echange between systems -- High-level data link control (HDLC) procedures Communication systems for and remote reading of meters Part 2: Physical and link layer Communication systems for and remote reading of meters Part 3: Dedicated application layer Etended Dutch Smart Meter specification WG04 interoperability & Communications (Milan Kozole); December 2007 COSEM interface classes for setting up and managing communication profiles using power line carrier (latest update of Gyozo Kmethy dated 29 February 2008) and Etension of the COSEM object model for smart metering ((latest update of Gyozo Kmethy dated 3 March 2008)
9 Page 9 of 73 Remark: The eisting IEC series do not describe and cover yet all functionality of DLMS/COSEM required by this companion standard P3. The standardization process of this new functionality will start when the new Green book (edition 7) and Blue book (edition 9) are approved/published by the DLMS User Association. 1.4 Document list Following table shows the complete set of documents that build up the Dutch Smart Meter Requirements, of which this tender document is a part of. # Document name postfi description  Main The main document of the Dutch Smart Meter Requirements, containing all definitions and most of the use cases and requirements  Tender Tender document, containing additional general requirements, use cases and performance requirements  P1 Companion standard P1  P2 Companion standard P2  P3 Companion standard P3
10 Page 10 of 73 2 LOGICAL DEVICES AND ASSOCIATIONS, M-BUS MODELLING (GENERAL CONCEPT) In DLMS/COSEM, metering equipment is modelled in physical and logical devices. The actual device is the physical device. The physical device can contain multiple logical devices. For this companion standard it is decided that there will be only 1 logical device (the management logical device). Physical device Management device Association object Logical device name Logical Other object Other object 2.1 Clients The logical device has at least 3 associations: Public client (client Id 16), management client (client Id 1) and pre-established client (client Id 102). There will be no direct connection to the M-bus device (used by P2) via the P3 interface. Access to the M-bus device has to be done with the objects offered by the logical device Public client Public client is for test purpose. Due to the fact that the public client is with lowest security (no security), it must not allowed to read metering data, or perform any programming. The services which must be supported within the Public client are: - Block transfer with Get - Get - Selective access
11 Page 11 of Pre established client The pre-established client is for broadcast purposes. It has to be used by the data concentrator, each time a broadcast service is needed. The services which must be supported within the Pre established client are: - Block transfer with Set - Set - Selective access - Action Management client The management client (Client Id 1) is the client to be used by the data concentrator or the central access server in the case of GPRS and Ethernet meters, for regular point to point connections with the meters. This client must be able to perform any allowed operation on the devices, gathering with its own privileges, the ones of the public client and the pre-established client. Additionally, this client is the addressee of the event notification request. It has Get, Set, Action and Event notification facilities. The services which must be supported are within the Management client:: - Block transfer with Get - Block transfer with Set - Set - Get - Selective access - Event notification - Action 2.2 Access right For each client, access right of each attribute for all the objects defined inside this document must be managed. This concerns Get, Set and Action access right. According to the client, a given attribute may not be accessible either for Get or Set or Action facility. When the get, set or action service is not managed for an attribute, the result to return back in the case of an access attempt must be read-write-denied result. This must not be consider as a protocol error. Management client must be able to manage all the necessary attributes access for a normal eploitation and maintenance of any network used. There will be no direct connection to the M-bus device (used by P2) via the P3 interface. Access to the M-bus device has to be done with the objects offered by the logical device..
12 Page 12 of 73 3 COMMUNICATION PROFILES AND SERVICES, SECURITY This chapter gives the required and selected communication profiles and the security requirements to be implement for the P3 interface. There are three communication profiles selected for the Dutch Smart meter. These are: GPRS Ethernet PLC DLMS/COSEM will use only the pull mechanism for the application layer 3. The description how the E-meter will establish a GPRS connection has been added to the profiles part (see chapter 3.1.1). The profile for GPRS meters and Ethernet uses standard COSEM TCP/IP profile as defined in IEC or in DLMS UA Green Book edition 6. The TCP/UDP based profile is given in figure 3.1. Log_Dev_1 (management) COSEM Application layer ACSE DLMS ASE # 01 COSEM Transport layer COSEM wrapper The DLMS/COSEM TCP based profile uses the standardized port number Transport layer TCP or UDP DLMS/COSEM Port 4059 Network layer IP Data link layer e.g. Ethernet Physical layer e.g. Ethernet Figure 3.1: TCP/UDP based profile 3 The operation principle used in this document is based on client / server model. Ecept for the Event notification which is based on unsolicited message sending for alarm management, for all the other services the client always asks for a request and the server send back the response of the concerned request. With respect to event notification, a GPRS meter shall be able to send an unsolicited message. The grid operator shall have the ability to configure which alarms will be sent unsolicited. Also channel set-up will be initiated by the GPRS meter.
13 Page 13 of 73 The required setup objects for TCP/UDP, IPv4 and PPP will be described below. For the detailed attribute descriptions and methods see chapter 4.2 for the relevant paragraph of the Blue book . TCP-UDP setup (Class ID: 41) To set up the TCP or UDP sub-layer of the COSEM TCP or UDP based transport layer 1 Logical name Octet-string 0-b: TCP-UDP_port long-unsigned Default IP_reference octet-string 4 MSS long-unsigned Min=40, ma=65535, default=576 5 nb_of_sim_conn unsigned Value=1 6 inactivity_time_out long-unsigned Default=180 An instance of the TCP-UDP setup class contains all data necessary to set up the TCP or UDP sub-layer of the COSEM TCP or UDP based transport layer of a TCP-UDP/IP based communication profile. In TCP-UDP/IP based communication profiles, all AAs between a physical device hosting one or more COSEM client application processes and a physical device hosting one or more COSEM server application processes rely on a single TCP or UDP connection. The TCP or UDP entity is wrapped in the COSEM TCP-UDP based transport layer. Within a physical device, each application process client application process or server logical device - is bound to a Wrapper Port (WPort). The binding is done with the help of the SAP Assignment object. On the other hand, a COSEM TCP or UDP based transport layer may be capable to support more than one TCP or UDP connections, between a physical device and several peer physical devices hosting COSEM application processes. NOTE When a COSEM physical device supports various data link layers (for eample Ethernet and PPP), then an instance of the TCP-UDP setup object is necessary for each of them. IPv4 setup (Class ID: 42) Handles all information that is related to the IP Address settings associated to a given device and to a lower layer connection on which these settings are used. 1 Logical name octet-string 0-b: DL_reference port octet-string 3 IP_address double-long-unsigned 4 multicast_ip_address array 5 IP-options array 6 Subnet_mask double-long-unsigned 7 gateway_ip_address double-long-unsigned 8 use_dhcp_flag boolean 9 primary_dns_address double-long-unsigned 10 secondary_dns_address double-long-unsigned An instance of the IPv4 setup class handles all information that is related to the IP Address settings associated to a given device and to a lower layer connection on which these settings are used.
14 Page 14 of 73 There shall be an instance of this class in a device for each different network interfaces implemented. PPP setup (Class ID: 44) Handles all information that is related to PPP settings associated to a given physical device and to a lower layer connection on which these settings are used. 1 logical_name Octet-string 0-b: PHY_reference Octet string 3 LCP_options LCP_options_type 4 IPCP_options IPCP_options_type 5 PPP_authentication 4 PPP_auth_type There shall be an instance of this class for each network interface of a physical device, using the PPP protocol. 3.1 Communication profiles The three specific communication profiles are given in the following paragraphs GPRS communication profile GPRS Application Process COSEM Interface Objects IEC , Application Layer COSEM Application Layer IEC COSEM IP Transport Layers IEC COSEM Wrapper TCP or UDP IP Media Dependant Lower Layers Data Link Layer Physical Layer SNDCP LLC RLC MAC GSM Radio Figure 3.2: GPRS communication profile 4 Be aware that if care is not brought to these attribute, even they are managed by the manufacturers, they may be unusable. For eample: as the same way the length of the meter Id is fied, the specification must determine the maimum length of user name & password too
15 Page 15 of 73 A GPRS modem setup object stores all the necessary data for a GPRS modem management. For the detailed attribute descriptions and methods see chapter 4.2 for the relevant paragraph of the Blue book . GPRS modem setup (Class ID: 45) A GPRS modem setup object stores all the necessary data for a GPRS modem management. 1 logical_name octet-string 0-b: APN octet-string 3 PIN_code long-unsigned 4 quality_of_service structure The connection setup mechanism used by the grid operators will be described in this chapter!! Ethernet communication profile Ethernet Application Process COSEM Interface Objects IEC , Application Layer COSEM Application Layer IEC COSEM IP Transport Layers IEC COSEM Wrapper TCP or UDP IP Media Dependant Lower Layers Data Link Layer Physical Layer Ethernet Figure 3.3: Ethernet communication profile
16 Page 16 of 73 Ethernet setup (Class ID: 43) Handles all information that is related to Ethernet settings associated to a given physical device and to a lower layer connection on which these settings are used 1 logical_name Octet-string 0-b: MAC_address Octet-string No default value An instance of the Ethernet setup class handles all information that is related to Ethernet settings associated to a given physical device and to a lower layer connection on which these settings are used. There shall be an instance of this class for each network interface of a physical device, using the Ethernet protocol PLC The profile for meters using the PLC medium as defined in IEC (has to be updated) or in DLMS UA Green Book edition 7 (in development) is pointed out below. COSEM Application model IEC / 6-62 COSEM Application model IEC / 6-62 COSEM Client AP COSEM Client AP Application process COSEM COSEM Server AP Server AP (Log. device) (Log.... device) COSEM Application layer IEC Application layer COSEM Application layer IEC SAP SAP CIASE IEC PLC network management SAP SAP CIASE IEC SAP SAP SAP SAP COSEM transport layer Transport IEC layer Wrapper layer To/From LLC Transport layer COSEM transport layer IEC Wrapper layer To/From LLC TCP TCP IP network layer Network layer IP network layer SAP SAP SAP SAP SAP SAP To/From CIASE SNDCP To/From CIASE To/From CIASE Subnetwork Dependent Convergence Protocol: Protocol selection and segmentation SAP SAP SAP SAP SAP SAP To/From CIASE SNDCP To/From CIASE To/From CIASE LLC ISO/IEC LLC IEC IEC Data link layer ISO/IEC CO-less LLC LLC layer LLC ISO/IEC LLC IEC IEC Data link layer ISO/IEC CO-less LLC ISO/IEC HDLC based MAC ISO/IEC HDLC based MAC PLC S-FSK lower layer profile IEC MAC + Phy layer PLC S-FSK lower layer profile IEC The ISO/IEC LLC layer may co-eist with IEC LLC layer and IEC data link layer used in eisting implementations. On the server side, only one of them may be implemented. On the Client side, one or more of them may be implemented.the Client (concentrator) finds out the kind of LLC layer used by the server during the Discovery / Registration process and maps the LLC type to the System title.
17 Page 17 of 73 The PLC solution requires support of ISO/IEC , allowing to plug in TCP/IP later. This can co-eist with the IEC LLC layer and the IEC data link layer used in eisting implementations. The selected LLC layer is ISO/IEC LLC layer. The other two are only allowed for backwards compatibility reasons. The nine PLC setup objects are given below with their OBIS codes. For the detailed attribute descriptions and methods see appendi B and . S-FSK Phy&MAC setup (Class ID: 50) 5 1 Logical name Octet-string 0-0: S-FSK Active Initiator (Class ID: 51) 1 Logical name Octet-string 0-0: S-FSK MAC synchronisation timeouts (Class ID: 52) 1 Logical name Octet-string 0-0: S-FSK MAC counters (Class ID: 53) 1 Logical name Octet-string 0-0: S-FSK IEC LLC Setup (Class ID: 55) 1 Logical name Octet-string 0-0: S-FSK Reporting system list (Class ID: 56) 1 Logical name Octet-string 0-0: ISO/IEC LLC Type 1 setup (Class ID: 57) 1 Logical name Octet-string 0-0: ISO/IEC LLC Type 2 setup (Class ID: 58) 1 Logical name Octet-string 0-0: ISO/IEC LLC Type 3 setup (Class ID: 59) 1 Logical name Octet-string 0-0: The choice of the modulation band (attribute 6 frequency) (see appendi B.1) must be mutual agreed between the vendors to reach operability. A selection of which modulation band to use, shall be tuned after practical eperiences in the field. The selection depends of the architecture of the Dutch Grid in general.
18 Page 18 of COSEM Security Both access and message security are required to address the requirement for confidentiality and authentication in DLMS/COSEM communication protocol. COSEM Security should be implemented as described in DLMS UA Green Book edition 7 and DLMS UA Blue Book edition 9. Because these documents are not yet published the COSEM security requirements and way to implement are given in reference . Access Security DLMS/COSEM access security provides Low Level Security (LLS) and High Level Security (HLS) authentication mechanisms. LLS enable client only authentication with password and HLS enable client/server authentication with challenge mechanism. Authentication is used for association establishing. Associations offer specific view to COSEM objects with associated access rights to individual objects. During the setup of the connection (the application association) HLS should be used. The Management Logical device should be accessible without security. Message Security DLMS/COSEM message security provides encryption and authentication of the COSEM APDU with standard symmetric key algorithms. It provides combined confidentiality and authentication using GCM cipher mode of operation. Encryption is used to provide confidentiality for data. The data to be protected is called plaintet. Encryption transforms the data into Ciphertet. Ciphertet can be transformed back into plaintet using decryption. Message authentication and encryption should be used in all situations and the Advanced Encryption Standard (AES) is the selected algorithm for ciphering. Selected Security Suite: Security Suite Id Authentication Algorithm Encryption Algorithm 7 AES-GCM-128 AES-GCM-128 Note: Security Suite 7 uses Combined Mode of operation with Authentication and Encryption. This choice covers etensive security at authentication and encryption level and realise full interoperability.
19 Page 19 of 73 4 OVERVIEW OF OBJECT MODEL The object model of the Dutch smart meter is divided in three parts: a. Abstract objects (chapter 5) b. Electricity related objects (chapter 6) c. M-bus related objects (chapter 7) Before all the required objects for the Dutch smart meter are described in more detail in the mentioned chapters an overview will be given of all required profiles. Further an eplanation of the event and error handling is described in paragraph 4.2 of this chapter for better understanding how the required objects for covering that functionality are related to each other. 4.1 Profile structure Dutch smart meter In figure 4.1 the profiles are summarized which will be required in relation to the Dutch smart meter requirements. The Monthly billing values (combined) object is described in more detail in paragraph 5.5 (Abstract objects). The Daily load profile values (E only) and 15 min load profile values are described in more detail in paragraph 6.3 (Electricity related objects). The Hourly load profile values (per channel) are part of paragraph 7.4 (M-bus related objects). 0-0: monthly billing values (combined) captured object list = clock;+a rate 1;+A rate 2; A rate 1; A rate 2;M-bus register channel 1 to 4 capture period = triggered from a single action scheduler at the end of every month profile entries = 13 (13 month) Note: Just for storage in case of problems, not read by CAS regularly P3 0-4: : : Daily load profile values (E only) 1-0: min load profile values (E only) 0-2: : Hourly load profile values (per channel) captured object list = clock; E-status; +A rate 1, 2; A rate 1, 2; capture period = s (daily) profile entries = 10 (10 days) captured object list = clock; E-status; +A; A capture period = 900 s (15 min) profile entries = 960 (10 days) captured object list = clock; status; M-Bus register capture period = 3600 s (60 min) profile entries = 240 (10 days) Note: All load profiles contain eactly one entry per capture period (no gaps, no additional entries). This also applies in case of time shifts and/or power outages Note: Either captured every hour or once a day P3 P3 P3 (P1) Figure 4.1: Structure of profiles of Dutch Smart meter
20 Page 20 of Event and error handling This paragraph gives an overview of the event and error handling based on DLMS objects for the Dutch smart meter to fulfil the requirements stated in . Standard Event Log Error Register Alarm Register >0 Alarm Events Filter Filter Filter Filter Filter Filter All general events, e.g changes of the clock, changes of the configuration, clearing of profiles, all kind of self check errors, activation of new parameters, activation of new time of use, etc. Control Log 100 entries Events related to the disconnector, e.g connect, disconnect, changing of the disconnector threshold. Power Failure Log Duration of long power outages Fraud Detection Log 10 entries 10 entries Events related to fraud attemps, e.g removal of terminal cover, removal of meter cover, strong DC field detection, access with wrong password M-Bus Event Log 30 entries All events concerning the M-bus devices, e.g changes of the clock, communication erros, etc. 30 entries M-Bus Control Logs Filter Changes of the states related to a M- Bus disconnector, e.g. a gas valve, (connect, disconnect). 1 instance per M-Bus device 10 entries A lot of events are generated by the meter itself or by its environment. All these events are logged in several event logs. The objects are described in chapters 5, 6 and 7 in more detail. Additionally they are also used to set and clear errors as well as to trigger alarms. The diagram above gives an overview about the handling, the details of the objects are described in the chapters 5, 6 and 7.
Page 1 of 23 P1 Companion Standard Dutch Smart Meter Requirements By order of: Date: April 22 nd, 2011 4.0 Status: Final Page 2 of 23 Change summary Version Change 4.0 The P1 document has been rewritten
EXCERPT FROM Companion Specification for Energy Metering COSEM interface classes and OBIS identification system DLMS User Association device language message specification DLMS User Association 2014-09-12
PE ELECTRIC POWER INDUSTRY OF SERBIA Updated by Deepview FUNCTIONAL REQUIREMENTS AND TECHNICAL SPECIFICATIONS OF AMI/MDM SYSTEM Version 3.0 April 2014 TABLE OF CONTENTS ABBREVIATIONS... 9 APPLIED STANDARDS...
Installing the RDSP-3000A-NIST Master Clock. Ethernet Connect the RJ-45 connector to a TCP/IP network. Equipment The following equipment comes with the clock system: RDSP-3000A-NIST Master Clock Module.
Communication system for the management of electrical installations INTEGRAL REMOTE MANAGEMENT SOLUTION cirwatt b series MID Approval Technology for energy efficiency PLC Communications (Power Line Communication)
Smart Wireless Communication Management System General R-Win is a smart communications adapter for management of wireless communications in a SCADA/Distributed Control System. The R-Win system includes
En Configuring the WT-4 for ftp (Ad-hoc Mode) Mac OS X Introduction This document provides basic instructions on configuring the WT-4 wireless transmitter and a Mac OS X (10.5.2) ftp server for transmission
1 REMOTE CONTROLLER ACCESS This paper summarizes the installation and configuration procedures needed to enable accessing your Communicator and controllers via the Internet. The information contained in
User s Guide PMCM-ETHCC-0208 2/2008 ACCESS 9340 and 9360 Meter Ethernet Communications Card 9340-60-ETHER TABLE OF CONTENTS INTRODUCTION... 2 Supported Ethernet Protocols... 2 Hardware... 2 Meter Firmware...
Polycom HDX Systems, Version 3.0.5 A warning about operating in a maximum security environment The maximum security profile is designed to lock down communications to the most stringent requirements of
MODEL ATC-2004 TCP/IP TO RS-232/422/485 CONVERTER User s Manual 1.1 Introduction The ATC-2004 is a 4 Port RS232/RS485 to TCP/IP converter integrated with a robust system and network management features
Smart Business Architecture for Midsize Networks Network Management Deployment Guide Introduction: Smart Business Architecture for Mid-sized Networks, Network Management Deployment Guide With the Smart
Introduction En Configuring the WT-4 for Upload to a Computer (Infrastructure Mode) This document provides basic instructions on configuring the WT-4 wireless transmitter and a computer for transmission
Version 2.0 About This Guide 2 About This Guide This user guide is intended for Photovoltaic (PV) system owners, installers, technicians, maintainers, administrators, and integrators who are authorized
The irnetbox Manager User Guide Chris Dodge RedRat Ltd April 2014 For irnetbox Manager 3.05 1 Contents 1. Introduction...3 2. Initial Network Configuration...3 3. Finding irnetboxes...3 3.1 Device Information
IntesisBox ModBus Server - KNX Gateway for integration of KNX equipment into Modbus (RTU and TCP) control systems. Integrate KNX based lighting control into your SCADA, BMS, PLC "talking" Modbus. Master
FOUNDATION Fieldbus High Speed Ethernet Control System Sean J. Vincent Fieldbus Inc. Austin, TX, USA KEYWORDS Fieldbus, High Speed Ethernet, H1, ABSTRACT FOUNDATION fieldbus is described in part by the
Data Link Protocols Relates to Lab. This module covers data link layer issues, such as local area networks (LANs) and point-to-point links, Ethernet, and the Point-to-Point Protocol (PPP). 1 TCP/IP Suite
Module 8 Introduction Subject of this chapter What s in this Chapter? This chapter describes the implementation of a TSX ETY 110 module. This chapter contains the following sections: Section Topic Page
3DLevelScanner II Different Ways of Connecting to 3DLevelScanner II A.P.M Automation Solutions LTD. www.apm-solutions.com Version 3.0 2 Different Ways of Connecting to 3DLevelScanner II Version 3.0 Table
MODEL ATC-2000 TCP/IP TO RS-232/422/485 CONVERTER User s Manual 1.1 Introduction The ATC-2000 is a RS232/RS485 to TCP/IP converter integrated with a robust system and network management features designed
52-20-15 RMON, the New SNMP Remote Monitoring Standard Nathan J. Muller Payoff The Remote Monitoring (RMON) Management Information Base (MIB) is a set of object definitions that extend the capabilities
WP2 Subject: with the CRYPTO-BOX Version: Smarx OS PPK 5.90 and higher 0-15Apr014ks(WP02_Network).odt Last Update: 28 April 2014 Target Operating Systems: Windows 8/7/Vista (32 & 64 bit), XP, Linux, OS
OCS Training Workshop LAB14 Email Setup Introduction The objective of this lab is to provide the skills to develop and trouble shoot email messaging. Overview Electronic mail (email) is a method of exchanging
An Economical and Practical Solution For Remote Automactic M-Bus Smart Meter Reading by GPRS In The Worldwide! GPRS M-Bus Master User Manual Mx Series Ver 1.00 Date Issued: 2015-07-28 All rights reserved
Home Passport Gateway Series Simplify your Life with Smart Solutions HPGW Series - Home Passport Gateway Series HPGW Series is Home Passport Gateway, representing a breakthrough product in the intrusion
UIP1868P User Interface Guide (Firmware version 0.13.4 and later) V1.1 Monday, July 8, 2005 Table of Contents Opening the UIP1868P's Configuration Utility... 3 Connecting to Your Broadband Modem... 4 Setting
Firmware version: 1.10 Issue: 7 AUTODIALER GD30.2 Instruction Manual Firmware version: 2.0.1 Issue: 0.6 Version of the GPRS transmitters configurator: 22.214.171.124 Date of issue: 07.03.2012 TABLE OF CONTENTS
Guideline for setting up a functional VPN Why do I want a VPN? VPN by definition creates a private, trusted network across an untrusted medium. It allows you to connect offices and people from around the
PRILINK http://www.prilink.com Tel: 905-882-4488 1-866-261-0649 Fax: 905-597-1139 Sales@prilink.com Support@prilink.com Table of Contents Overview...3 Important Terms...3 Units of Digital Information...3
Remote Client / Web Client USER MANUAL T Series Digital Video Recorder Remote Client Program... 3 Remote Client Program Installation... 4 Remote Client... 6 Main Window... 6 Site Registration... 7 Group
Technical Manual (TLT-2H GPS/GSM Vehicle Tracker) V1.5 Product main features Real-time SMS query coordinates time position, Phone Position active help feature speed alarm function historical data uploading
PRILINK http://www.prilink.com Tel: 905-882-4488 1-866-261-0649 Fax: 905-597-1139 Sales@prilink.com Support@prilink.com Table of Contents Overview...3 Important Terms...3 Units of Digital Information...3
OPEN meter Open Public Extended Network metering 7 TH FRAMEWORK PROGRAMME OPEN meter Project Author: Nicolas Arcauz email@example.com Date: December 8th, 2010 Venue: Stanislaw Staszic Palace, Varsaw
For Air4G-W24 9.50 This document forms the release note relevant to the specific product release as stated above. It covers new features, performance and any limitations of the product known at the time
NMS300 Network Management System User Manual June 2013 202-11289-01 350 East Plumeria Drive San Jose, CA 95134 USA Support Thank you for purchasing this NETGEAR product. After installing your device, locate
Version 6 [Released: 09 DEC 2009] In this release, we modified the database setup screen of the RLT installer to default to SQL server information (the recommended database). The Transcript has been modified
Easily Connect, Control, Manage, and Monitor All of Your Devices with Nivis Cloud NOC As wireless standards develop and IPv6 gains widespread adoption, more and more developers are creating smart devices
11.1. Performance Monitoring Windows Reliability and Performance Monitor combines the functionality of the following tools that were previously only available as stand alone: Performance Logs and Alerts
Cellular Engine GSM FTP AT Commands GSM_FTP_ATC_V1.1 Document Title GSM FTP AT Commands Version 1.1 Date 2010-12-28 Status Document Control ID Release GSM_FTP_ATC_V1.1 General Notes offers this information
Part Number 129777-01 Revision A, January 1996 3500 Monitoring System Rack Configuration and Utilities Guide Copyright 1995 Bently Nevada Corporation All Rights Reserved. No part of this publication may
(VoIP) Configuration ENGINEERING REPORT No: 02-003 Introduction This report describes interfacing the IPCS VoIP Gateway Model EGW-902 to an ESTeem Model 192E Wireless Ethernet radio modem in a demonstration
Setup Manual and Programming Reference Stanford Research Systems Revision 1.05 (11/2010) Certification Stanford Research Systems certifies that this product met its published specifications at the time
PowerLogic ION Enterprise 5.6 Power Management Software User Guide April 2007 Notices This section describes the symbols used in this guide. Danger This alerts you to things that may cause serious injury
This document outlines: Cyclades ACS Advanced Console Server Appliances Release Notes Version 3.3.0-5 September 24 nd 2010 1. Update Instructions 2. Appliance Firmware Version Information 3. Enhancements
CyBro OPC Server User Manual rev. 31 (applies to CyBro OPC Server v3.0.4 and later) 2003-2013 Cybrotech Ltd www.cybrotech.co.uk Index Index... 1 General... 2 Installation... 2 Activation code... 2 Configuration...
USER GUIDE Cisco Small Business WBPN Wireless-N Bridge for Phone Adapters December 2011 Cisco and the Cisco Logo are trademarks of Cisco Systems, Inc. and/or its affiliates in the U.S. and other countries.
APPLICATION NOTE Contents The DMP Software Family... 1 Stand-Alone Link Software... 1 Add-on Modules for Link Software... 1 System Link End-User Panel Management Software... 2 Simple Registration and Activation...
orrelog Syslog Windows Tool Set (WTS) Configuration File Directives And Help The CO-sysmsg.cnf file contains all the parameters and specifications related to the program s operation. This file is found
Introduction En Configuring the WT-4 for ftp (Infrastructure Mode) This document provides basic instructions on configuring the WT-4 wireless transmitter and a ftp server for transmission over an infrastructure
Prestige 310 Cable/xDSL Modem Sharing Router User's Guide Supplement Domain Name Support Enhanced WAN Setup Remote Node Support PPPoE Support Enhanced Unix Syslog Setup Firmware and Configuration Files
Digi Connectware Manager: Dynamic IP Address Support White Paper Abstract In the world of TCP/IP, each network device receives an identifier called an IP address. Unfortunately, there are a finite number
Dale Pennington, Managing Director, Utiliworks Consulting LLC, New York, USA Meter Data from Cradle to Grave, do you know where your Data is? Getting Started Create your project team such that all critical
Controller 5000GL Controller 5000GL provides flexible system architecture with options of GBUS and LOCAL BUS communications to field devices, to meet a wide range of site requirements. GGBUS L LOCAL BUS
Ethernet Port Quick Start Manual THIS MANUAL CONTAINS TECHNICAL INFORMATION FOR THE ETHERNET PORT OF EDI SIGNAL MONITORS with Ethernet Version 1.5 firmware. DETAILS OF THE ECCOM OPERATION ARE DESCRIBED
Gigabyte Content Management System Console User s Guide Version: 0.1 Table of Contents Using Your Gigabyte Content Management System Console... 2 Gigabyte Content Management System Key Features and Functions...
Kaseya 2 Syslog Monitor Quick Start Guide for Network Monitor 4.1 June 5, 2012 About Kaseya Kaseya is a global provider of IT automation software for IT Solution Providers and Public and Private Sector
70072-0104-14 TECHNICAL 06/2009 Modbus and ION Technology Modicon Modbus is a communications protocol widely used in process control industries such as manufacturing. PowerLogic ION meters are compatible
Network Attached Storage Jinfeng Yang Oct/19/2015 Outline Part A 1. What is the Network Attached Storage (NAS)? 2. What are the applications of NAS? 3. The benefits of NAS. 4. NAS s performance (Reliability
Exploring the Remote Access Configuration Utility in Ninth-Generation Dell PowerEdge Servers The Remote Access Configuration Utility supports local and remote server management in ninth-generation Dell
Panduit Corp. 2010 TDP43ME NetPS PA26306A01 Rev. 01 11-2010 Network Printer Server Control Center for Ethernet Module NOTE: In the interest of higher quality and value, Panduit products are continually
LMX9838 Firmware Release Note 1.0 Introduction The National Semiconductor LMX9838Bluetooth Serial Port module is a highly integrated radio, baseband controller, memory device, crystal, antenna and loop
GSM Cellular Engine GSM TCPIP Application Notes GSM_TCPIP_AN_V1.1 Document Title GSM TCPIP Application Notes Version 1.1 Date 2011-09-22 Status Document Control ID Release GSM_TCPIP_AN_V1.1 General Notes
About This Guide 3 About This Guide This user guide is intended for Photovoltaic (PV) system owners, installers, technicians, maintainers, administrators and integrators who are authorized to configure
Quick Note 34 Configuring Syslog alerting on a TransPort router TransPort Support March 2013 1 Contents 1 Introduction... 3 1.1 Outline... 3 1.2 Assumptions... 3 1.3 Corrections... 3 1.4 Version & Revision
OBM (Out of Band Management) Overview With the growth of IP, routers deployed into an IP network must not only be accessible by the network operator for maintenance and configuration purposes, but secure
Serial Device Server - RS232/RS485 to Ethernet converter USR-TCP232-300 Hard version: V2.0 File version: V1.1 2011-8-17 Serial Device Server - RS232/RS485 to Ethernet converter is an Equipment for convert
Chapter 3 Safeguarding Your Network The RangeMax NEXT Wireless Router WNR834B provides highly effective security features which are covered in detail in this chapter. This chapter includes: Choosing Appropriate
C-GEP 100 Monitoring application user manual 1 Introduction: C-GEP is a very versatile platform for network monitoring applications. The ever growing need for network bandwith like HD video streaming and
General The Watchdog AW-4, in short AW-4, can be controlled and monitored by a centralized monitor server. This server is located in a large Dutch server centre with high speed connections, directly connected
IntesisBox KNX TCP master Gateway for integration of TCP slave devices into KNX control systems. Integrate any TCP slave device into KNX. KNX TCP slave EIB Bus IntesisBox Ethernet slave LinkBoxEIB Configuration
User Manual Single Phase Energy Meter HXE12-KP Hexing Electrical Co., Ltd. www.hxgroup.cn [2013.3] Meter User Manual-HXE12-KP 2 / 30 Introduction Range of validity Purpose Target group The present user