1 Symmetra PX UPS kw 208 V Operation and Maintenance Manual
3 Symmetra PX kw, 208V Operation and Maintenance Manual
5 Contents IMPORTANT SAFETY INSTRUCTIONS SAVE THESE INSTRUCTIONS Symbols used in this guide ON, OFF & STAND-BY Switch Positions Total Power OFF Procedure Introduction Overview of System Components Weights Operation Functional Schematic Dual Mains / Single Mains Control Functions Control Screen Status Functions Status screens Set-up Functions Setup screens Accessories screen Logging Screen Display screens Diag screens Help screens Network Connection/APC Web Management Card Quick Configuration Module and Card Replacement How to replace Power Modules How to Replace Cards How to replace Intelligence Modules How to obtain replacement modules Replacement Parts and Numbers Symmetra PX kw, 208V Operation & Maintenance Guide REV01 i
6 Troubleshooting General Status General Fault Module failure Threshold Alarm Bypass System Start-Up (if applicable) Secure the UPS by Setting the Stabilizing Feet Level the UPS (Recommended) Power Module Installation Installing Securing Network Cable Installation (if required) System Start-Up Procedure Life Support Policy/Warranty Life Support Policy Factory Warranty ii Symmetra PX kw, 208V Operation & Maintenance Guide REV01
7 IMPORTANT SAFETY INSTRUCTIONS SAVE THESE INSTRUCTIONS This guide contains important instructions for the Symmetra PX that should be followed when handling the UPS, Battery Enclosures, and Batteries. Symbols used in this guide WARNING! Risk of Electric Shock. CAUTION! Read this information. Indicates important information. Indicates a heavy load that should not be lifted without assistance. Indicates that more information is available on this subject in a different section of this manual. Indicates that more information is available on the same subject in a different manual. Do not lift heavy loads without assistance. <40 lb lb lb >120 lb Symmetra PX kw, 208V Operation & Maintenance Guide REV01 1
8 IMPORTANT SAFETY INSTRUCTIONS WARNING! Hazardous electrically-charged parts inside the UPS are energized from the battery supply even when the AC power is disconnected. Follow Total Power Off Procedure to completely de-energize the system. CAUTION! For configurations including customer-supplied external batteries, refer to manufacturer s battery installation and maintenance instructions. ON, OFF & STAND-BY Switch Positions Indicates that a switch or current protection device is in the ON position. Indicates the OFF position for a switch or a breaker Indicates that a switch is in the STAND-BY position 2 Symmetra PX kw, 208V Operation & Maintenance Guide REV01
9 IMPORTANT SAFETY INSTRUCTIONS Total Power OFF Procedure WARNING! Before electrical installation begins, verify that the UPS is in the Total Power Off mode by following this procedure. UPS INTELLIGE NCE MODULE INTELLIGE NCE MODULE 1? Set the System Enable Switch to the STAND-BY position. SE YN SA TB EL ME XR Communica etr Op kw a era, PX tio 20 n 0V Gu ide tions Sy Ba 10 mm sic - 40 DOC UME NT STO RAG E CAUTION! To ensure solid stability, do not pull Battery Units out beyond the Red Disconnect Line unless completely removing them from the enclosure. Battery Enclosure 1 Set the DC Disconnect on ALL Battery Enclosures in your conﬁguration to the OFF position. BATTERY UNIT 2 Disconnect all Battery Units by removing or pulling out to Red Disconnect Line. BATTER Y UNIT 3 Set the upstream Utility Power to the OFF or LOCKED OUT position. If the UPS has dual mains supply, set both supplies to the OFF or LOCKED OUT position. Note: Follow proper lock out tag procedures. ON OFF Symmetra PX kw, 208V Operation & Maintenance Guide OFF REV01 3
10 Introduction After the UPS has been wired electrically, it is ready for start-up. This guide will allow you to quickly start up the UPS. It contains information on Safety, System Components, Securing the UPS, Module Installation, Network Cable Installation, Start-Up Procedure, and Basic Troubleshooting. 4 Symmetra PX kw, 208V Operation & Maintenance Guide REV01
11 ? Overview of System Components Intelligence Modules (2) Network Management Card Cable Power Module Bays PowerView Display Power Module Battery Communication Cable Bypass Static Switch Module System ID Card DOCUMENT STORAGE Symmetra PX kw, 200 V Basic Operation Guide Documentation Storage Tray Input / Output Chassis System Power Supply System Power Supply Cards (2) System Enable Switch S Y S T E M E N A B L E XR Communication Remote Computer Display Power View Interface Display/Computer Interface Port 1 Port 2 System Power Supply Smart Slots (2) Display / Computer Interface Card Battery Comm Card Terminators Reset PSU Sub Supply Switch Gear Monitor Card PSU Sub Supply Link RXTX 10/100 10/100Base-T Status AP9617 Network Management Card Switch Gear Monitor Card Network Management Card Symmetra PX kw, 208V Operation & Maintenance Guide REV01 5
12 ? Overview of System Components Weights UPS (empty) 600 lb. (275 kg) Power Module 60 lb. (26 kg) DOCUMENT STORAGE Symmetra PX kw, 200 V Basic Operation Guide 6 Symmetra PX kw, 208V Operation & Maintenance Guide REV01
13 Operation The PowerView is the user control interface used to configure the functionality, monitor the system, set alarm thresholds, and to provide audible and visual alarms. Four LED indicators report the operational status of the UPS. Liquid crystal display (LCD) Five navigation keys are used to select and open menu items, to access information, change system parameters, and to launch contextsensitive help. LOAD ON ON BATT BYPASS Chrg 100% Load 000% 120Vin 000Vout 60Hz Runtime: 00hr 30m ESC? 9 FAULT LOAD ON LED ON BATT LED BYPASS LED FAULT LED When green, the Symmetra PX UPS is providing power to the load equipment. When yellow, power is flowing from the batteries to the Power Modules. When yellow, power to the load is being supplied through the Static Bypass Switch. When red, an fault condition exists. 5 LCD Displays alarms, status data, instructional help, and configuration items. 6 7 UP and DOWN navigation keys ENTER key Selects menu items and accesses information. Opens menu items and input changes to system parameters. 8 9 HELP key ESC key Launches context-sensitive help. Returns to previous screen displayed. Symmetra PX kw, 208V Operation & Maintenance Guide REV01 7
14 Operation Press ESC ESC system status information. until you get to the Top-Level Status Screen, which provides you with basic Chrg 100% Load 000% 120Vin 000Vout 60Hz Runtime: 0hr 0m Top-Level Status Screen (factory default) Press Enter to open the Top-Level Menu screen. This screen is the launching pad to command, configure, and monitor the system. Selector Arrow Control Status Setup Accessories Logging Display Diags Help Top-Level Menu Press Up and Down to navigate the selector arrow and view all sub-menu screens. Bat Voltage: 218V Bat Capacity 100.0% Runtime: 01hr 30min 32 Batts, 00Bad Battery Module Status Screen Capacity: 80.0kVA Fault Tolerance: n+1 Total UPS Modules: 9 Bad UPS Modules: 00 Power Module Status Screen Scroll arrows indicate additional screens Press Up, Down and Enter to move input arrow to select and enter information. Low Batt Dur: Shutdwn Dly: Return Dly: Return Bat Cap: 2min 20sec 0sec Low Batt Dur: Shutdwn Dly: Return Dly: 0% Return Bat Cap: Shutdown Menu 10min 20sec 0sec 0% Shutdown Menu Input arrows indicate changeable options 8 Symmetra PX kw, 208V Operation & Maintenance Guide REV01
15 Operation Functional Schematic Dual Mains / Single Mains Only present in single mains installations. Bypass Input Mains Input Bypass Static Switch Module Power Module Load Control Functions Turn load on/off: 1 Graceful Turn Off Start Runtime Cal Turn Load On 2 UPS LOAD IS OFF Control Sub-Menu Load Off Screen Turn into/out of bypass: 1 UPS into Bypass Do Self Test Simulate Power Fail Graceful Reboot Control Menu 2 UPS IS BYPASSED Bypassed Screen Symmetra PX kw, 208V Operation & Maintenance Guide REV01 9
16 Operation Control Screen From the Control screen, you can select the following items: UPS into Bypass Do Self Test Simulate Power Fail Graceful Reboot Graceful Turn Off Start Runtime Cal Turn Load On/Off Place into or return from maintenance bypass operation Initiate a system of self-tests and diagnostics. Simulate a power failure Turn off and start load equipment in an ordinary manner. Shut down load equipment in an orderly manner. Begin runtime calibration of the UPS. Apply power to or shut down the Symmetra PX UPS 10 Symmetra PX kw, 208V Operation & Maintenance Guide REV01
17 Operation Status Functions Verify general module status: Control Logging Capacity: 80.0kVA 1 Status Display 2 Fault Tolerance: n+1 Setup Diags Total Pwr Modules: 9 Accessories Help Bad Pwr Modules: 0 Top-Level Menu Sub-Sub-Sub-Sub-Sub Status Screen Verify voltage on all phases: 1 Control Status Setup Accessories Logging Display Diags Help 2 0 Vin Vbyp Vout Top-Level Menu Status Screen Verify battery voltage/capacity: 1 2 Control Logging Status Display Setup Diags Accessories Help Top-Level Menu Bat Voltage: 218.6V Bat Capacity: 100.0% Runtime: 1hr 30min 32 Batts, 0 Bad Sub-Sub-Sub-Sub Status Screen Symmetra PX kw, 208V Operation & Maintenance Guide REV01 11
18 Operation Status screens The status screen display information regarding load, battery, power module voltage, and current. Status Screen 1. Vin Vout Iout The input voltage (V), output voltage (V), and output current (A) for each phase (1-3). Status Screen 2. %load assuming no redundancy Percentage of the load in relation to the total capacity of all power modules. Status Screen 3. %load allowing for n+ redundancy Percentage of the load, allowing for the redundancy in your system. Status Screen 4. Frequencies The input and output frequency in hertz (Hz). Status Screen 5. Batt Voltage Batt Capacity Runtime #Batts #Bad Actual voltage of the DC bus (volts). Percentage of battery capacity available The available runtime for battery operation in hours and minutes The number of installed battery modules. The number of failed battery modules. 12 Symmetra PX kw, 208V Operation & Maintenance Guide REV01
19 Operation Status Screen 6. Capacity: kva Fault Tolerance Total Pwr Modules Bad Pwr Modules The system load capacity. The configured redundancy for your UPS (n+0, n+1, n+2...). The number of power modules installed The number of failed power modules installed Status Screen 7. Alarm Thresholds Fault Tolerance n+0 Runtime hr min load: kva Settings configured for the thresholds that trigger alarms. The alarm threshold for reduced redundancy. The alarm threshold for reduced runtime. Alarm indication of the load exceeding the configured redundancy Status Screen 8. Self Test Lst Xfr Status IM RIM Status of the last self-test Information on the last transfer to battery operation. General UPS status. Status of the main intelligence module. Status of the redundant intelligence module. Set-up Functions Display parameters are set to factory defaults. Changing factory default settings: Control Logging 1 Status Display 2 Setup Accessories Diags Help Top-Level Menu Settings: Shutdown Defaults Output Freq Settings Menu Alarms Bypass Copy Other Symmetra PX kw, 208V Operation & Maintenance Guide REV01 13
20 Operation Setup screens From the Setup screen, you can select the following items: Shutdown Configure the following system shutdown conditions: Low Batt Dur: Low battery duration is the time from low battery signal to the shutdown of the load. This signal is sent to the server using shutdown software (PC + PCNS). Shutdwn Dly: Shutdown delay is the time from when the UPS receives a shutdown command (usually sent by a server) to the shutdown of UPS power to the load equipment. This delay allows load equipment time to finish shutdown processes. Return Dly: Return delay is the amount of time the UPS wants to turn on after a power outage has ended. Defaults Output Frequency Alarms Return Bat Cap: Return battery capacity is the minimum percentage of battery capacity required for the UPS to turn the load on. Return all UPS settings to their default values. Set the desired output frequency Redundancy: The state of redundancy that will trigger an alarm. Choices are: N+0 an alarm will occur only when there is more load than all functioning power modules can support; N+1 an alarm will occur when there are no spare power modules in good condition; N+2 an alarm will occur when there is only one functioning power module. Load: When the load is greater than this threshold, an alarm will sound. Bypass Copy Other Runtime: When the time the UPS can power the load is less than this threshold, an alarm will sound. This alarm is the result of an increase in load or a decrease in battery capacity. Set the conditions in which the UPS will automatically go into bypass operation. Copy the UPS settings. Self Test: Set the UPS to perform a self-test automatically at periodic intervals. USP ID: Provide a unique name for the UPS. Vout Reporting: Set the reporting to the number of the tap to which the most significant load is wired on the output transformer. Output: Set the UPS output voltage. BatFrAmpHour: Set the Ampere-Hour rating of external battery enclosures that are not APC Symmetra PX Battery Enclosures. 14 Symmetra PX kw, 208V Operation & Maintenance Guide REV01
21 Operation Accessories screen Control Status Setup Accessories Top-Level Menu Logging Display Diags Help From the Accessories screen, you can view the status of APC accessories connected to the UPS. Logging Screen Control Status Setup Accessories Top-Level Menu Logging Display Diags Help The Logging screen allows you to customize the UPS log. The following items are accessible from this screen: View Log View Statistics Configure Logging List Event Groups Point to an entry in the log and press the Enter key to view a description of the event. The display logs the most recent 64 events. View statistics of the events logged. Set the type of events that are recorded in the log. To log a type of event, choose On. View the list of event types. Power Events UPS Control Events User Activities UPS Fault Events Measure UPS Events For each group, press the Enter key to display each event listed under the group. Clear Log Clear all events currently stored in the log. Symmetra PX kw, 208V Operation & Maintenance Guide REV01 15
22 Operation Display screens Control Status Setup Accessories Top-Level Menu Logging Display Diags Help The Display screens allow you to customize the UPS display interface. The following items are accessible from this screen: Date: Password Information Beeper Contrast Config Set the correct date (day:month:year) and time (hour:minute). Protect the password against unauthorized configuration changes. View the model number, serial number, date of manufacture, and revision number of the display interface. Configure the audible alarm interface.: At UPS At Disp Vol Click Set the contrast on the LCD. Personalize the Top-Level Status screen. Choose each line you want displayed from a list of options. To change a line, move the selection arrow to the line you want to change and press the ENTER key. Scroll up or down the list to find the data you want displayed and press the ENTER key to save you changes. Press the ESC key to discard your changes. Diag screens Control Status Setup Accessories Top-Level Menu Logging Display Diags Help The Diagnostic screens provide information for use in troubleshooting. The following items are accessible from this screen: 16 Symmetra PX kw, 208V Operation & Maintenance Guide REV01
23 Display Display/Computer Interface XR Communication Port 1 Reset Link-RX/TX 10/100 10/100Base-T Status AP9617 Network Management Card Operation Fault & Diagnostics Lists any failures found. If any status except ON or OK is displayed, a module or card must be replaced. The Faults and diagnostics screen will describe the location of the failed module/ card. If you do not have a redundant intelligence module installed, you must place the UPS in bypass operation before you remove an intelligence module. Lists external device status. If any status except ON or OK is displayed, a module, card or battery must be replaced. If you do not have a redundant intelligence module installed, you must place the UPS in bypass operation before you remove an intelligence module. Help screens To access the display interface context-sensitive help screens, press the? key. Network Connection/APC Web Management Card Computer Interface Remote Computer Power View Interface 10/100Base-T Reset Link-RX/TX 10/100 Status AP9617 Network Management Card Serial port DOCUMENT STORAGE Symmetra PX kw, 200 V Basic Operation Guide 20-foot Network Cable supplied with the UPS. Symmetra PX kw, 208V Operation & Maintenance Guide REV01 17
24 Operation Quick Configuration Disregard the procedures in this section if you have an APC InfrastruXure Manager as part of your system. See the InfraStruXure Manager s documentation for more information. You must configure three TCP/IP settings before the Management Card can operate on a network: IP address Subnet mask Default Gateway From the PowerView Display: 1 Control Status Setup Accessories Logging Display Diags Help 2 Web/SNMP Mngmnt Card Network Setup View Network Setup Top-Level Menu Accessories Menu 3 IP>> Mask>> Gway>> Accept changes 4 IP>> Mask>> Gway>> Accept changes Network Set-up Screen Network Set-up Screen If a Default Gateway is unavailable, use the IP address of a computer located on the same subnet as the Management Card that is usually running. The Management Card uses the Default Gateway to test the network when traffic is very light. See Watchdog Features in the Introduction of the Network Management Card User s Guide CD (.\doc\usrguide.pdf) for more information about the watchdog role of the Default Gateway. The Management Card User s Guide CD is located in the documentation storage tray. 18 Symmetra PX kw, 208V Operation & Maintenance Guide REV01
25 ? XR Communications Module and Card Replacement WARNING! Only trained persons familiar with the construction and operation of the equipment and the electrical and mechanical hazards involved, may install and remove system components. How to replace Power Modules 1 INTELLIGENCE MODULE INTELLIGENCE MODULE To de-activate the module, turn Locking Latch (with arrow pointing towards the module) counterclockwise until it points downwards. DOCUMENT STORAGE Symmetra PX kw, 200 V Basic Operation Guide Symmetra PX kw, 208V Operation & Maintenance Guide REV01 19
26 Module and Card Replacement Pull out the module. Display shows message saying it has decreased the number of power modules. Reverse procedures for installation. 2 Unscrew springactivated knobs on both sides of the module until they pop out. Standing on either side of the UPS, 2 people can now pull the module almost free of the UPS (the lock mechanism prevents the module from being pulled clear of the UPS). With the module still resting in the UPS, release the lock by pushing the black plastic tab on either side of the module 3 INTELLIG ENCE MODULE INTELLIG ENCE MODULE 2? Sy Ba 10 m sic - 40metr Op kw a er, PX at 20 ion 0 GuV id e XR Commun ications DOCU MENT STO RAGE Power Module will not start unless Locking Latch is engaged. How to Replace Cards System Power Supply Display Remote PowerView Display / Computer Display Disp lay / Interface Rem ote PowerVi ew Port Por t Port mun icatio System 2 Power Supply 1 Por t XR Com 1 XR Communication Com pute Interfacer Com pute r Inte rface 2 n Reset Sub Link- RX/T 10/10X 0 Supply AP961 7 Net work 10/10 0Base -T Manag Statu Sy m Ba 10 m sic - 40 etra O kw pe PX ra, 20 tio 0 n V G ui de PSU DOCU MENT STOR AGE s ement Car d Switch Gear Monitor Card System Loosen the 2 Phillips screws at both sides of the card. Carefully pull out the card. Reverse procedures for installation. Display shows message saying it has registered the new card. 20 Power Supply Display Disp Rem ote PowerVi ew System lay / Com pute r Inte Port mun PSU icatio Power Supply rface 1 Port XR Com 2 n Sub Supply Switch Gear Monitor Card Symmetra PX kw, 208V Operation & Maintenance Guide REV01
27 Module and Card Replacement How to replace Intelligence Modules One intelligence module can be replaced without interrupting power to the connected equipment provided another functioning intelligence module is installed. Loosen the 2 Phillips screws at both sides of the module (top of module). As soon as the left side screw is loose, the module will be deactivated. Display shows message saying it has decreased the number of cards. Reverse procedures for installation. INTELLIGENCE MODULE INTELLIGENCE MODULE INTELLIGENCE MODULE INTELLIGENCE MODULE How to obtain replacement modules To obtain a replacement module, contact APC Customer Support at 1 (800) In the event of a module failure, the display interface may display additional fault list screens. Press any key to scroll through these fault lists, record the information, and relay it to the representative. 2. If possible, call APC Customer Support from a telephone that is within reach of the Symmetra PX UPS display interface so that you can gather and report additional information to the representative. 3. Be prepared to provide a detailed description of the problem. A representative will help you solve the problem over the telephone, if possible, or will give you a return material authorization (RMA) number. If a module is returned to APC, this RMA number must be clearly printed on the outside of the package. 4. If the Symmetra PX UPS is within the warranty period, repairs will be performed free of charge. If it is not within the warranty period, there will be a charge for repair. Review APC s warranty policy. Symmetra PX kw, 208V Operation & Maintenance Guide REV01 21
28 Module and Card Replacement See section on Warranty for more information 5. If the Symmetra PX UPS is covered by an APC service contract, have that information available and give ti to the representative. Replacement Parts and Numbers Part 80kW Enclosure Only 10kW Power Module Intelligence Module Symmetra 3-Phase 80 kva Bypass Static Switch Module System Power Supply Card PSU Supply Board Display and Computer Interface Card Switch Gear Monitoring Card System ID Card Battery Communication Card Web Card, SNMP Battery Enclosure only No SYCF80KF SYPM10KF SYMIM4 SYSW80KF SYCSPS SYCSS SYCDCI SYCSGMON SYCSYSID SYCXRCOM AP9617 Web/ Management Slot Card SYCF8BF WARNING! Only trained persons familiar with the construction and operation of the equipment, and the electrical and mechanical hazards involved, may install and remove system components. 22 Symmetra PX kw, 208V Operation & Maintenance Guide REV01
29 Troubleshooting This section lists all of the alarm and status messages that are displayed on the UPS display interface. A suggested corrective action is listed with each message to help you troubleshoot problems. If a problem is reported, ensure that the system component in question is correctly installed (refer to section on Modular & Card Replacement. General Status Display Message Meaning Corrective Action Input Freq outside configured range AC adequate for UPS but not for bypass Low/No AC input, startup on battery Intelligence Module inserted Intelligence Module removed Redundant Intelligence Module inserted Redundant Intelligence Module removed The input frequency to the UPS is outside the configured range. The output frequency will not synchronize with the input frequency. Normal bypass is not available. The Symmetra PX UPS will function online with the input voltage, but in the event that bypass is required, the input voltage is not adequate to power the load equipment. Input voltage is not adequate to start the Symmetra PX UPS. If start-up proceeds, the Symmetra PX UPS will function in battery operation. An Intelligence Module has been installed into the Symmetra PX UPS. An Intelligence Module has been removed from the Symmetra PX UPS. An intelligence Module has been installed into the Symmetra PX UPS. An Intelligence Module has been removed from the Symmetra PX UPS. Option 1: Improve the frequency of the incoming voltage. Option 2: Widen range of acceptable incoming frequency using the display interface. Select Start-UP, Setup, OUtput, Freq Select). Option 3: Proceed with startup. Normal bypass is not available. Option #1: Improve the incoming voltage. Option #2: Proceed with startup. Normal bypass is not available. Option 1: Cancel start-up until acceptable input voltage is present. No corrective action necessary. Check that the intelligence modules are properly inserted and that the fastening screw is tight. No corrective action necessary. Check that the intelligence modules are properly inserted and that the fastening screw is tight. Symmetra PX kw, 208V Operation & Maintenance Guide REV01 23
30 Troubleshooting Display Message Meaning Corrective Action # of batteries changed since last ON # of Pwr modules changed since last ON At least one battery module has been added or removed from the UPS since the last time the Power ON command was used. At least one battery module has been added or removed from the UPS since the last time the Pwr ON command was used. Check that all battery units are installed correctly. Check that all power modules are properly inserted, the two fastening screws are tight, and the locking latch is engaged. # of batteries increased At least on battery module has been added to the system. # of batteries decreased At least one battery module has been removed from the system. No corrective action necessary. Ensure that all battery units are properly inserted. # of Pwr Modules increased # of Pwr Modules decreased # of External Battery Cabinets increased # of External Battery 0Cabinets decreased Redundancy Restored At least one power module has been added to the system At least one power module has been removed from the system. At least one external battery cabinet has been connected to the Symmetra PX UPS At least one external battery cabinet has been disconnected from the Symmetra PX UPS A loss of power module redundancy occurred and the redundancy has been restored. Either additional modules have been installed or the load has been reduced. No corrective action necessary. Check that all power modules are properly inserted, the two fastening screws are tight, and the locking latch is engaged. No corrective action necessary. Ensure that all Battery Enclosure s communication cables are properly connected and that the LEDs are illuminated on the Battery communication cards. No corrective action necessary. 24 Symmetra PX kw, 208V Operation & Maintenance Guide REV01
31 Troubleshooting General Fault Display Message Meaning Corrective Action Need Bat Replacement The Redundant Intelligence Module is in control UPS Fault On Battery Shutdown or unable to transfer to batt due to overload Load Shutdown from Bypass. Input Freq/Volts outside limits Fault, Battery Charger Failure One or more battery modules are in need of replacement The Main Intelligence Module has failed, and the redundant intelligence module is functioning as the primary intelligence module. A fault has occurred in a power module. This will always occur with a power module failure message. The Symmetra PX UPS has transferred to battery operation due to the input going out of acceptable range. At this time the batteries will discharge until the input is restored to an acceptable range. The Symmetra PX UPS has shut down because an overload occurred and bypass is not available. The Symmetra PX UPS has transferred to battery operation because the input is out of acceptable range. The battery charger in one or more of the power modules failed Refer to Module Replacement Section for procedures. Replace the Main Intelligence Module.Refer to Module Replacement Section for procedures. Contact APC Technical Support at (1) (800) No corrective action necessary. Note: Runtime is limited in duration. Prepare to shut down the Symmetra PX UPS and the load equipment or restore incoming voltage. Option 1: Reduce the load to eliminate overload. Option 2: If possible, add power modules to eliminate overload. Option 3: Replace failed power modules to eliminate overload. Correct the input voltage problem. Refer to Module Replacement Section for procedures. Fault, Internal Temp exceeded normal limits Input circuit breaker tripped open The temperature of one or more battery units has exceeded system specifications. The input circuit breaker on the Symmetra PX UPS is open. Input voltage is disconnected to the Symmetra PX UPS. Ensure that the ambient temperature meets the specifications of the system. Option 1: If this occurs with an overload condition, decrease the load and reset the breaker. Option 2: If no overload condition exists, reset the breaker. If it trips open again, contact APC Technical Support at (1) (800) System level fan failed A cooling fan in the Symmetra PX UPS failed. Contact APC Technical Support at (1) (800) Symmetra PX kw, 208V Operation & Maintenance Guide REV01 25
Symmetra LX Operations Guide For use with Symmetra LX UPS Models: 200 V, 4 8 kva 208/240 V, 4 8 kva 220/230/240 V, 4 8 kva 200 V, 4 16 kva 208/240 V, 4 16 kva 220/230/240 V, 4 16 kva Symmetra LX Rack-mount
Installation Guide Smart-UPS X External Battery Pack SMX120BP Inventory Inspect the contents upon receipt. Notify the carrier and dealer if there is damage. Two bezels Tie brackets used to secure multiple
Smart-UPS On-Line Step-Down Transformer SRT5KRMTF Safety Messages Read the instructions carefully to become familiar with the equipment before attempting to install, operate, service or maintain the transformer.
Unpacking, Installation, and Customization NetShelter WX Enclosure AR100 AR100HD Contents Unpacking... 1 How to Unpack the Enclosure............................... 1 Please Recycle..........................................
MGE Galaxy 3500 Series 10-40 kva 380/400/415 V 10-30 kva 208/220 V Operation Table of Contents About this Manual... 1 Find Updates to this Manual... 1 Safety... 2 Overview... 3 r Interface... 3 Display
Installation Guide Smart-UPS On-Line External Battery Pack SRT96BP/72BP Important Safety Messages Read the instructions carefully to become familiar with the equipment before trying to install, operate,
Out-of-Band Management Card AP9608 Installation Manual Related Documents For information on using the Out-of-Band Management Card after installation and startup, see the online User s Guide specific to
APC Step-Down Transformer Models: AP9621, SURT005, SURT006, SUTF3, SYTF2, SYTF2J, SYTF3 and SYTF3J User s Manual English 990-7820D, July 2003 TABLE OF CONTENTS APC Contact Numbers and Support Visit the
Operation Manual Smart-UPS C Uninterruptible Power Supply 1000/1500 VA Rack-Mount 2U 120/230 Vac su00812a Product Description The APC by Schneider Electric Smart-UPS is a high performance uninterruptible
Galaxy 3500 10-40 kva 380/400/415 V and 10-30 kva 208/220 V Operation 09/2014 www.schneider-electric.com Legal Information The Schneider Electric brand and any registered trademarks of Schneider Electric
Installation Basic Rack Power Distribution Unit AP9559 This manual is available in English on the enclosed CD. Dieses Handbuch ist in Deutsch auf der beiliegenden CD-ROM verfügbar. Este manual está disponible
Emergency Power-Off System The Emergency Power-Off (EPO) System consists of one or more wall-mounted, push-button EPO boxes. Each EPO box provides a single point of equipment shutdown for up to eight APC
Installation and Operation Back-UPS 1250, 1300, 1500 Inventory bu001a Safety and General Information This unit is intended for indoor use only. Do not operate this unit in direct sunlight, in contact with
Back-UPS Pro 1300/1500 Installation and Operation Inventory Safety Do not install the Back-UPS in direct sunlight, in excessive heat, humidity, or in contact with fluids. Connect the battery bu059a bu058a
Back-UPS Pro 900 Installation and Operation Inventory Safety bu001a (2) Do not install the Back-UPS in direct sunlight, in excessive heat, humidity, or in contact with fluids. Connect the battery bu059a
Crow Limited Warranty (Crow) warrants this product to be free from defects in materials and workmanship under normal use and service for a period of one year from the last day of the week and year whose
Back-UPS Pro 400/550 Installation and Operation Inventory USB cable UPS Connect the battery User manual & CD warranty registration card CAT-5 cable Cable strap hook & cable strap Remove the battery door.
Item #2016-6 AC Inverter 700W USB User s Manual User s Manual Read before using this equipment Thank you for purchasing the Slim Line 700 Watt USB Inverter. With minimal care and proper treatment it will
Operation Manual Smart-UPS X Uninterruptible Power Supply Low Voltage (100-127 V) SMX2000RMLV2U SMX2200RMLV2U SMX3000RMLV2U SMX3000RMLV2UNC SMX3000RMJ2U High Voltage (200-240 V) SMX2200RMHV2U SMX3000RMHV2U
+ Installation and Operation Manual Back-UPS BX800CI-AS/BX1100CI-AS Inventory Safety and General Information bu001c This unit is intended for indoor use only. Do not operate this unit in direct sunlight,
Dolphin 9900 Mobile Computers Dolphin 9900 Dolphin 9950 Dolphin 9951 with Windows Mobile 6.1 Quick Start Guide Dolphin 9900 Series Quick Start Guide Out of the Box Verify that the box contains the following
List of Events This section lists all events that are written to the Event Log. Some of these events can be configured through the Configuring Events to Take Actions page, and these are listed in the first
User Manual Smart-UPS TM C Uninterruptible Power Supply SRC250 SRC450 110/120/230 Vac Tower/Rack-Mount 1U Smart-UPS TM C Uninterruptible Power Supply 250/450 VA 110/120/230 Vac Tower/Rack-Mount 1U English
Back-UPS RS 700 Installation & Operation Inventory Safety Do not install the UPS in direct sunlight, in excessive heat, humidity, or in contact with fluids. Do not connect a laser printer or hair dryer
Installation Smart-UPS VT MGE Galaxy 3500 Maintenance Bypass Panel 10-40 kva 400 V Contents Safety.................................................. 1 Save these instructions...................................
Operator s Manual 017-201-B1 9/06 EFFECTIVE: September, 2006 Alpha Technologies Power Alpha Technologies 1 Introduction to FXM Computer Communication There are several ways to connect a computer to the
ADI 9510-B Advantium 2 Plus Alarm INSTALLATION AND OPERATING INSTRUCTIONS Carefully Read These Instructions Before Operating Carefully Read These Controls Corporation of America 1501 Harpers Road Virginia
User's Guide Model 382260 80W 3-in-1 Switching DC Power Supply Introduction Congratulations on your purchase of the Extech 80W 3-in-1 Switching DC Power Supply. The Model 382260 has three output ranges
APC Smart-UPS RT SURTA48XLBP/SURTA48XLBPJ External Battery Pack User Manual Introduction/Before Installation About this Manual The APC Smart-UPS RT external battery pack (SURTA48XLBP or SURTA48XLBPJ) connects
User Manual English APC Smart-UPS 1000/1500 VA 100/120/230 VAC 750/1000XL VA 120/230 VAC Tower Uninterruptible Power Supply 990-1074C 06/2012 Introduction American Power Conversion Corporation (APC) is
543-0032-00, 943-0032-00 User s Manual 1 Comfort Alert Diagnostics Faster Service And Improved Accuracy The Comfort Alert diagnostics module is a breakthrough innovation for troubleshooting heat pump and
How to Set Up Your NSM4000 Appliance Juniper Networks NSM4000 is an appliance version of Network and Security Manager (NSM), a software application that centralizes control and management of your Juniper
LCD5500Z / PKP-LCD v3.x Installation Instructions TM Introduction The LCD5500Z / PKP-LCD keypad displays system status using an LCD screen. The keypad can be used on PowerSeries security systems with up
SNMP Web card User s Manual Management Software for Uninterruptible Power Supply Systems Table of Contents 1. Overview... 3 1.1 Introduction... 3 1.2 Features... 3 1.3 Overlook... 3 1.4 Installation and
PK5500 v1.1 Installation Instructions 1 2 3 4 5 6 7 8 9 * 0 # WARNING: Please refer to the System Installation Manual for information on limitations regarding product use and function and information on
User Manual English APC Smart-UPS 500 VA 100 VAC 750 VA 100/120/230 VAC Tower Uninterruptible Power Supply 990-1587A 12/2005 Introduction The APC Uninterruptible Power Supply (UPS) is designed to prevent
HP R12000 and R18000 DirectFlow UPS User Guide Abstract This document includes installation, configuration, and operation information for the HP R12000 and R18000 DirectFlow UPS. This document is for the
RI-215A Operator s Manual Part Number: 71-0045RK Revision 0 Released: 10/3/05 Warranty RKI Instruments, Inc., warrants gas alarm equipment sold by us to be free from defects in materials and workmanship,
Back-UPS 650 VA 120 V with AVR (BX650CI-LM) Overview Do not install the unit in direct sunlight, in areas of excessive heat or humidity, or in contact with fluids ON/OFF button Battery connector Circuit
User Manual English APC Smart-UPS SC 1000/1500 VA 110/120/230 Vac 2U Tower/Rack-Mount Uninterruptible Power Supply 990-1851C, 10/2005 Introduction The APC Uninterruptible Power Supply (UPS) is designed
User's Manual Heavy Duty Dissolved Oxygen Meter Model 407510 Introduction Congratulations on your purchase of Extech's Heavy Duty Dissolved Oxygen / Temperature Meter which simultaneously displays Dissolved
NEWTECH PRO 1-2-3 KVA ONLINE UNINTERRUPTIBLE POWER SUPPLY USER MANUAL firstname.lastname@example.org / www.tuncmatik.com Table of Contents 1. Important Safety Warning 2 1-1. Transportation 2 1-2. Preparation 2 1-3.
User Manual Smart-UPS Uninterruptible Power Supply 750/1000/1500 VA 100/120/230 Vac Rack Mount 2U Smart-UPS TM Uninterruptible Power Supply 750/1000/1500 VA 100/120/230 Vac Rack-Mount 2U EN 990-1194E 08/2014
Powerware Relay-Serial Card User s Guide Special Symbols The following are examples of symbols used on the UPS and accessories to alert you to important information: This symbol indicates that you should
MAKING MODERN LIVING POSSIBLE SOLAR INVERTERS Installation Guide GSM Option Kit FLX series www.danfoss.com/solar Safety Safety Safety Message Types WARNING Safety information important for human safety.
Induction Power Supplies 3kW; 135 400kHz (Integral Heat Station) User s Guide Model 3-135/400-3 Model 3-135/400-3W Rev E 12/1/04 Table of Contents 1. SPECIFICATIONS AND FEATURES...3 1.1. Output...3 1.2.
Metered Rack Power Distribution Unit AP7830 AP7840 Installation and Quick Start Contents Product Description and Inventory...................... 1 Additional documentation......................... 2 Inventory.....................................
Introduction BW TECHNOLOGIES GasAlertMicroClip Soft Tools Instruction Sheet The GasAlertMicroClip Soft Tools application is required to configure the GasAlertMicroClip detector ( the detector ). Software/Hardware
Progressive Industries, Inc. EMS Electrical Management System Complete Installation Guide and Operating Instructions for: Model EMS-HW50C Rated at 240V/50A Manufactured by: Progressive Industries, Inc.
Automatic Phone-Out Home Monitoring Systems Power Outage and Freeze Alarm Model Number: THP202 Power Outage, Freeze and Flood Alarm Product Description Model Number: THP201 These monitoring systems are
SNMP Web Management User s Manual For SNMP Web Card/Box Management Software for Off-Grid Inverter Version: 1.2 Table of Contents 1. Overview... 1 1.1 Introduction... 1 1.2 Features... 1 1.3 Overlook...
StorTrends 3400 Hardware Guide for Onsite Support MAN-3400-SS 11/21/2012 Copyright 1985-2012 American Megatrends, Inc. All rights reserved. American Megatrends, Inc. 5555 Oakbrook Parkway, Building 200
08/17/12 Rev2 LTR Series General Specification 700 VA to 2.1 KVA 1.0 General LTR Series Uninterruptible Power Systems 700 VA - 2.1 KVA General Specification This specification describes the features and
Title Page Web/SNMP Management SmartSlot Card AP9606 User s Guide Thank You! Thank you for selecting the APC Web/SNMP Management SmartSlot Card. It has been designed for many years of reliable, maintenance-free
Quick Installation Guide TK-209K TK-409K Table of of Contents Contents English... 1. Before You Start... 2. How to Connect... 3. Operation... 1 1 2 4 Troubleshooting... 5 Version 09.07.2006 1. Before You
USER MANUAL Rev. 0.9 2007/10/26 Copyright 2006-2007 Cyber Power Systems, Inc. All rights reserved. PowerPanel Business Edition USER S MANUAL PowerPanel Business Edition provides power management Services.
PX100 MBP with Configurable Distribution High-performance, right-sized, 3-phase power protection with industry-leading efficiency, availability, and performance for small and medium data centers July 2012
APC Smart-UPS RT GUIDE SPECIFICATIONS FOR 3000VA, 5000VA and 6000 VA Smart-UPS RT 230VAC Uninterruptible Power Supply PART 1 - GENERAL 1.1 SUMMARY A. This specification describes the operation and functionality
Network Management Card AP9617 AP9618 AP9619 Installation and Quick-Start Manual How to Avoid Equipment Damage Disconnect UPS power You do not need to turn off a Symmetra or a Silcon model UPS to install
User Manual Humidity-Temperature Chart Recorder Model RH520 Introduction Congratulations on your purchase of the Extech RH520 Temperature + Humidity Chart Recorder. The RH520 measures and displays Temperature,
NortechCommander Software Operating Manual MAN-00004 R6 If the equipment described herein bears the symbol, the said equipment complies with the applicable European Union Directive and Standards mentioned
AMI MARINE (UK) LTD BRIDGE NAVIGATIONAL WATCH ALARM SYSTEM (BNWAS) Operation Manual KW810 This Manual and the information contained therein is the property of AMI Marine (UK) Ltd. It must not be reproduced
Installation Guide Back-UPS BN700MC Inventory Back-UPS bu075c Safety This UPS is intended for indoor use only. Do not operate this UPS in direct sunlight, in contact with fluids, or where there is excessive
EE7016 EchoStream Survey Kit Installation and Operation Manual - 06152B 1 Quick Start By following this procedure you can quickly configure the supplied equipment to perform a site survey. Review the main
FEATURES & APPLICATIONS Inexpensive 2 wire to 3 wire start controller for electric start high speed gas generators. Optimized for use with Outback Invertors. Supports three types of 3 wire generator control
User s Guide 400A AC Clamp Meter Model MA200 Introduction Thank you for selecting the Extech MA200 AC Clamp Meter. This meter measures AC Current, AC/DC Voltage, Resistance, Diode Test, and Continuity.
Builder MODEL 1010 Series Non-Programmable Single Stage Heat/Cool Thermostat USER MANUAL Compatible with low voltage single stage gas, oil or electric heating or cooling systems, including single stage
Wireless Router Setup Manual NETGEAR, Inc. 4500 Great America Parkway Santa Clara, CA 95054 USA 208-10082-02 2006-04 2006 by NETGEAR, Inc. All rights reserved. Trademarks NETGEAR is a trademark of Netgear,
CABLE MODEM QUICK START This Quick Start describes how to connect your Zoom cable modem to a cable modem service. This lets your cable modem provide Internet access to a computer or other device connected
YOU'RE HEARD, LOUD AND CLEAR. Web Page Interface Instructions for the 429 Series Tower Top Amplifier Systems Manual Part Number 7-9440 8625 Industrial Parkway, Angola, NY 14006 Tel: 716-549-4700 Fax: 716-549-4772
Installation and Operation Smart-UPS SUA22000-BR/SUA3000-BR 120 VAC English This manual and the safety guide are available in English on the enclosed CD and the APC Web site, www.apc.com. Este manual e
Connect the AC adapter with the amplifier BEFORE plugging the AC adapter into an outlet to avoid spark generation! User and Installation Guide BlueFIDELITYTM Bluetooth Audio Amplifier Model 300 Contents
1. Installing and configuring APC UPS Management 1.1. Objectives and Overview In this lab, you will learn how to install and configure the APC UPS power management suite and the Web/SNMP Management Card.
OWNER'S MANUAL P/N P474-0100 1 For All Non-Programmable Digital Thermostat TOTALINE 68 Dual Setpoint Very easy to program Thermoglow Backlight No batteries required Auto-Changeover Locking Keypad Meets
Memcom Emergency Telephone Installation Guide Ref No. 450 900 (GB) Version 2 + + Simple wiring for quick installation + + Integrated LCD display shows you what you have programmed + + All code based programming
User's Guide 99 Washington Street Melrose, MA 02176 Phone 781-665-1400 Toll Free 1-800-517-8431 Visit us at www.testequipmentdepot.com Back to the Extech 407780 Product Page Integrating Sound Level Datalogger