# Fire Alarm FAQs. Q: How many zone/circuit fire alarm panel do I need? Q: What candela strobes do I need?

Save this PDF as:

Size: px
Start display at page:

Download "Fire Alarm FAQs. Q: How many zone/circuit fire alarm panel do I need? Q: What candela strobes do I need?"

## Transcription

1 5/2/2014 Fire Alarm FAQs Question Answer Q: How many zone/circuit fire alarm panel do I need? Q: What candela strobes do I need? A: The size of a fire alarm panel is determined by a number of factors, including the size of the building, the number of devices, and the job's requirements. A zone is a defined area in a building in which related functional items work together. This could include things like alarm annunciation (the panel will indicate what area of the building the alarm occurred) and alarm notification (signals will only activate in particular areas of the building, not general alarm). On a conventional fire alarm panel, the terms zone and circuit are often interchanged (one circuit could cover one zone). On an addressable panel, the zones are created in software (you can assign devices to zones). Circuits on a fire alarm panel also have limits as to how many devices you can connect to them. The more devices, the larger the panel. It's also up to the engineer designing the system as to how he wants to divide up the building. A single zone conventional panel, for example, may be able to support enough devices to cover a given building, but you would be limited in terms of annunciation at the panel because you won't be able to tell where in the building the alarm came from. A: The brightness requirements (candela) of a strobe is determined by where it is being installed. The larger the room, the brighter the strobe. NFPA 72 National Fire Alarm Code sets the standards for this and provides a chart with different room sizes along with the strobe requirements for each. If an area needs multiple strobes, those strobes must also be synchronized with each other (flash at the same time). See also "How can I synchronize the strobes on the fire alarm system...?". Q: What do I need for elevator recall? A: ANSI A17.1 is the national elevator code, but local codes may be different. You should always refer to the proper codes for your area for exact requirements. Typically you will need the following: a smoke detector located in each elevator lobby; a smoke and/or heat detector in the elevator machine room (the heat if there are sprinklers); a heat detector located at the top of the elevator shaft (if there is a sprinkler at the top); a smoke detector located at the top of shaft (if there is a sprinkler anywhere in the hoist way); a set of relays located in the elevator machine room to control the elevators (primary, alternate, shunt); a visual warning ("firefighter's hat") indicating if elevators are unsafe to use; and a control panel (the panel can be the building's fire alarm panel or a dedicated panel if there is no FA panel).

2 Q: How many signals can I connect to the fire alarm panel's NAC (Notification Appliance Circuit)? A: The number of devices you can connect to a signal circuit (NAC) is based on the current rating of the circuit and the current rating of the devices connected to the circuit. You must add up the current draw of all the devices and make sure the total does not exceed the rating of the circuit you want to connect them to (it's also a good idea not to exceed 80% of the circuit's rating to give some margin for error and/or room for expansion). To find the current draw for a particular device, you should refer to the device's installation sheet or the device's U.L. product label. A fire alarm device will have a FWR (Full Wave Rectified) and DC current draw rating. Be sure to use the correct current based on the type of power supply. Also be aware that multi-candela strobe devices will have a different current rating for the different candela settings (the higher the candela, the more current). Use the current rating for the candela you are setting the strobe to (some jurisdictions, however, require you to use the worst case value, regardless of how bright the strobe is set; check with your local AHJ). Q: How far can I run the signal circuit (NAC) wire on my fire alarm panel? Q: How far can I run the IDC (Initiating Device Circuit) wire on my fire alarm panel? Q: How far can I run my addressable loop wire? Q: How loud do my signals need to be? A: You must do a voltage drop calculation for each circuit. The method for doing this should be included with the manual that comes with the fire alarm panel or booster power supply. You will need to know the following information to do the calculation: 1) The minimum operating voltage of the signaling device (for a UL regulated 24 volt device, this would be 16 volts). 2) The maximum operating current of each device (and therefore the total current draw of all devices connected to the circuit). 3) The minimum circuit voltage rating of the NAC (typically 85% of nominal 24v or 20.4 volts, but refer to panel's manual for correct value). 4) The resistance of the wire used for the signal circuit. A: Panel installation manuals should include this information (it is not the same for all panels). Typically it is based on the circuit's maximum allowable resistance. A: The distance you can run the wire on an addressable loop is determined by the size and type of wire used and the number of devices. You should refer to the fire alarm panel's manual for this information. A: NFPA 72 National Fire Alarm Code sets the standards for what's required. For public mode, signals must produce a sound level of at least 15dB above the average ambient sound level or 5dB above the maximum sound level having a duration of at least 60 seconds, whichever is greater, measured at 5 feet above the floor throughout the covered area. Q: What size batteries does the fire alarm panel need? A: Fire alarm systems must have a secondary means of power in case of AC power failure. Battery calculations will determine what size batteries are needed, and should be included with the panel or booster power supply manual. You will need to know the following information to do the calculation: 1) The required standby time (typically 24 hours). 2) The required alarm time (typically 5 minutes). 3) The panel's total supervisory current draw. 4) The panel's total alarm current draw (including signal load). Q: What type of device should I install in a kitchen, a smoke detector or heat detector? A: It is generally recommended that fixed temperature heat detectors be installed in kitchens. Every day cooking activities can cause smoke detectors to alarm, and rate of rise type heat detectors can be set off by the sudden temperature increase due to an oven door opening. If the ambient temperature in the kitchen does not exceed 100 degrees F, then you can use a 135F detector. Otherwise you would have to use one with a higher temperature rating (like 194F).

5 Q: What does the DACT (Digital Alarm Communicator Transmitter) do? Q: Can I mount the remote annunciator outdoors? Q: What type and size wire should I use for remote annunciators? Q: Do the phone lines for the DACT have to be dedicated? Q: How should the DACT be wired? Q: What format does the DACT use? A: The DACT is installed in a fire alarm panel and is used to connect to a Central Monitoring Service (CMS) that monitors the status of the system. This is a service you would have to subscribe to and pay a monthly fee. During a system event, such as an alarm, the DACT would send a signal to the CMS who would then notify the proper authorities. The DACT does not (usually) connect directly to the fire department. There must be a DACR (Digital Alarm Communicator Receiver) on the other end that "understands" the digital signals sent by the DACT. You cannot use a DACT to call someone's phone, for example, to say "there's an alarm". A: The remote annunctiators for Edwards fire alarm panels cannot be mounted outdoors. They are U.L. listed for indoor use only. A: You should always follow the manufacturer's recommendation for wire type. For the Edwards Signaling FireShield, E-FSC and E-FSA panels, you will need 1 pair of 18 awg twisted/shielded wire for the data and a second pair (does not need to be twisted/shielded) for the 24Vdc power. A: The DACT must be the first device connected to the building's incoming phone lines. Although in many cases it's recommended the lines (at least one of them) be dedicated, they do not have to be. You can have devices wired down stream as long as you use RJ31X style jacks and follow the manufacturer's instructions. This is to ensure that the dialer can capture the line in the event of an alarm. Because of this, be aware that if someone is on the phone or there's a fax machine running, it will get cut off if the dialer needs to dial out. A: The DACT must be the first device on the building's incoming phone lines using an RJ31X style jack. You can refer to the fire alarm panel's manual or dialer's installation sheet for more details. Edwards' F-DACT and SA-DACT dialers are designed to work on POTS (Plain Old Telephone Service) copper lines connected to a PSTN (Public Switched Telephone Network). The use of DSL (Digital Subscriber Lines) or VoIP (Voice over Internet Protocol) may cause problems. A: With the Edwards FireShield and E-FSC series panels, you can choose between 4/2 SIA or contact ID. The E-FSA addressable panels uses contact ID only. Q: What is the difference between an alarm, supervisory, and trouble condition? Q: What is Alarm Verification? A: An alarm condition has the highest priority on a fire alarm system. This occurs when a smoke detector, heat detector, pull station, waterflow, or some other alarm initiating device activates, and usually sounds the signaling devices to evacuate the building. A supervisory condition occurs when a device like a sprinkler tamper switch activates. This would give an indication at the fire alarm panel that something is off normal, but would not sound any alarm signals to evacuate the building. A trouble condition means something is wrong, but not in alarm or supervisory, and would also not sound the alarm signals. Some examples would include a circuit with a broken wire, a bad battery, or a ground fault. A: Alarm verification is used with smoke detectors to help prevent false alarms. When a smoke detector senses smoke, it will delay activation by a predetermined amount of time (typically less than 1 minute). If there is still smoke present after that time period has expired, then the detector will alarm the system. If the smoke has cleared before the time expires, the detector will reset and the system will not alarm.

6 Q: Can I use another manufacturer's smoke detector on an Edwards fire alarm panel (or an Edwards smoke on another manufacturer's panel)? A: To ensure proper operation, a 2 wire smoke detector must be U.L. cross listed with the panel you wish to connect it to. Each fire alarm panel should include a U.L. compatibility list that will show all detectors that can be used with a particular panel. You cannot assume that just because a smoke detector is 24 volts, and the panel is 24 volts, that they will both work together (this is especially true with addressable detectors, because the communication protocols are usually different). You must refer to the U.L. compatibility sheet. Q: Can I use another manufacturer's signaling device on an Edwards fire alarm panel (or an Edwards device on another manufacturer's panel)? Q: Can I use another manufacturer's heat detector or pull station on an Edwards fire alarm panel (or an Edwards device on another manufacturer's panel)? A: To ensure proper operation, signaling devices must be U.L. compatible with the panel or booster power supply they are being connected to. Each panel should include a U.L. compatibility sheet that will show which signals will work with a particular panel. If a panel or device is U.L. listed as Special Applications, the device must be on the panel's compatibility sheet. If both the panel and device are U.L. listed as Regulated, then they are considered compatible, and may not be on the compatibility sheet. Note: Compatibility does not necessarily mean you will have strobe synchronization (see question "How can I synchronize the strobes on the fire alarm system...? "). A: Heat detectors and pull stations are usually just normally open, dry contact devices that close when they activate. If this is the case, there is no U.L. compatibility requirement, and you can use anyone's device on any panel's IDC (Initiating Device Circuit) that accepts normally open contact inputs. If it's an addressable system, however, you must use a device that is designed to work (communicate) with the panel. Q: Can I connect speakers to the fire alarm panel? A: Unlike horns which just produce a sound when voltage is applied, speakers are used to provide tones, pre-recorded voice messages and/or live paging in the event of an alarm. The fire alarm system must have the supporting audio amplifiers and audio source to connect to the speakers. You cannot connect speakers to a 24Vdc signal circuit like you would with a horn or strobe. Q: What is a Walk Test? Q: Why does my panel show a ground fault? Q: What size sampling tube do I need for my duct detector? A: Walk Test is used to test a fire alarm system to ensure everything works properly. By putting a panel into Walk Test mode, a technician can activate a device, which then gives an indication at the fire alarm panel and may or may not (depending on the set up) momentarily sound the signals. After the device activates, it will automatically restore, then the technician can go on to the next device to test. This allows for one person to test a system without someone else being at the control panel to reset it each time. A: A ground fault occurs when a circuit wire touches ground. This could be an input circuit, signal circuit, data wires, or most any other wiring that connects to the panel. To find the fault, remove each circuit one at a time until the ground fault restores. When you find the circuit with the ground fault, reconnect it, then begin breaking the circuit into sections (typically starting somewhere near the middle). If you break the circuit in the middle and the ground fault does not clear, then you know it's between your break and the panel. If it does clear, then you know it's after your break. If you end up removing all external wiring from the panel and the ground fault still does not restore, then there may be something wrong with the panel itself. A: The sampling tube must protrude into the duct at least two thirds of the way across. You cannot use a sampling tube that is longer than the duct is wide and just cut it to length. You must select the correct size tube for the duct it's being installed in. Refer to the manufacturer's instructions provided with the duct detector for proper installation.

7 Q: Which is better, an ionization type smoke, or photoelectric? A: Ionization type smoke detectors are good for faster burning fires that do not produce a lot of large smoke particles. Photoelectric smokes are good for slower, smoldering type fires that produce larger smoke particles. Photoelectric smokes also tend to be more stable and less susceptible to air movement and higher altitudes. In most installations a photoelectric smoke should work fine, because most places will contain items such as furniture, drapes, carpeting, and other products that generate a lot of smoke. Q: Where do I get power for my door holders? Q: Does Edwards Signaling sell explosion proof horn strobe combination signals? Q: Can I connect a "general purpose" horn or bell to my fire alarm panel? Q: How large a building will your fire alarm panels cover? Q: How many heat detectors and pull stations can I connect to a conventional fire alarm panel? Q: What do I do if the fire alarm panel does not have enough power for the signals? A: The Edwards Signaling 15**-AQN5 series door holders can be powered from 24Vac, 24Vdc, or 120Vac, so you can use a transformer with a 24Vac output, a DC power supply, or local 120Vac. In a fire alarm application you could use the aux 24Vdc supply built into most fire alarm panels, but this would put a drain on the batteries during an AC power failure (unless otherwise specified, door holders do not have to be battery backed up because loss of power would release the doors in a fail safe manor). With the Edwards Signaling EPBS series booster power supplies, you can configure the aux power to drop out during an AC failure. A: Edwards Signaling does not sell a combination explosion proof horn with strobe. The cost and size of such a device would be prohibitive. Edwards does offer, however, separate horn and strobe devices, such as the 889D-AW and 116DEGEX-FJ. A: You cannot connect a signaling device that is not listed for fire alarm use to a panel's NAC (Notification Appliance Circuit). Fire alarm signals are designed to connect to supervised fire alarm circuits. Using a non-fire alarm signal on a supervised circuit will cause a trouble on that circuit. A: The Edwards Signaling E-FSC and E-FSA panels are good for small office buildings, stores, churches, theaters, strip malls, and the like. Generally, buildings up to about 100,000 sq ft (but may accommodate larger depending on the actual number of devices needed). These panels are not designed for high rises or campus type installations. A: Most conventional heat detectors and pull stations are normally open, dry contact devices that do not draw power from the circuit they are connected to under normal (supervisory) conditions. Because of this, there is no limit to the number you can put on an Edwards conventional fire alarm panel. A: If the signal load for your system exceeds the power supply rating of the fire alarm panel, you can add booster power supplies. Edwards offers a 6 amp (EBPS6A) and 10 amp (EBPS10A) version. You can add as many booster supplies as the job needs. Q: How often do I have to replace the smoke and heat detectors (how long do they last)? Q: How often do I have to replace the batteries in the fire alarm panel? A: Per NFPA 72 (2007 edition), residential type smoke alarms (single/multi-station) must be replaced every 10 years. Commercial type smoke detectors (connected to fire alarm panel) do not have a defined replacement period (unless specified by the manufacturer), but must be tested periodically and replaced if they fail. Self restoring heat detectors also do not have a defined replacement period, but must be tested periodically as well. Fixed temperature, non restoring heats must be replaced every 15 years, or have 2 per every 100 installed laboratory tested. Refer to NFPA 72 and the manufacturer's installation instructions for more detailed descriptions of testing methods and frequency. A: A general rule of thumb is that batteries should be replaced every 4 years, or so. If a fire alarm panel indicates a battery trouble, then you may need to replace sooner. Even if a battery voltage seems normal, a bad cell may cause a fault during a load test.

8 Q: Where else can I go to learn about fire alarm systems in general, and the requirements needed to work on them? A: There are several publications relating to fire alarm codes and standards, some of which include the following: NFPA 72 National Fire Alarm Code, NFPA 101 Life Safety Code, NFPA 70 National Electrical Code, Fire Protection Handbook, and Fire Alarm Signaling Systems, to name just a few. NICET (National Institute for Certification of Engineering Technologies) provides national certification on fire alarm systems. There are also several web sites, including: nfpa.org, nicet.org, firemarshals.org, and reedconstructiondata.com/building-codes, where you can find information on a national and local level. If you are just getting into the fire alarm business, a good place to start is the local fire marshal or AHJ (Authority Having Jurisdiction). They should be able to tell you what is required to work on fire alarm systems in your area. Q: How do I know if I should be using horns or speakers on my fire alarm system? A: You should always refer to your local codes, but in general, areas with an occupancy of 300 or more people, theaters with more than one viewing room, or buildings where an occupied floor is higher than 75 feet above the exit level will require notification by means of either pre-recorded voice messages and/or live announcements, which means you need speakers and a fire alarm panel with the amplifiers and audio source to support them. This can include places like churches, auditoriums, theaters, and high rises.

### TAMARAC FIRE RESCUE INSTRUCTIONS FOR FIRE ALARM PRE-SUBMITTAL CHECKLIST

TAMARAC FIRE RESCUE INSTRUCTIONS FOR FIRE ALARM PRE-SUBMITTAL CHECKLIST In order to provide a comprehensive plan review in a timely manner, and to insure the design and installation of fire alarm systems

### CLARK COUNTY FIRE DEPARTMENT Fire Hazard & Prevention Services

CLARK COUNTY FIRE DEPARTMENT Fire Hazard & Prevention Services 575 E. Flamingo Road, Las Vegas, NV 89119 (702) 455-7316 FAX (702) 455-7347 105.8a-6.1 TITLE: FIRE ALARM SYSTEM REQUIREMENTS SCOPE: This guideline

### FIRE ALARM SYSTEM RECORD OF COMPLETION

FUNDAMENTALS OF FIRE ALARM SYSTEMS 72 33 FIRE ALARM SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. 1. PROTECTED PROPERTY

### FIRE ALARM SYSTEM RECORD OF COMPLETION

FIRE ALARM SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. 1. Protected Property Information Name of property: Description

### FLORIDA ATLANTIC UNIVERSITY FIRE ALARM SYSTEM INSTALLATION MANUAL

FLORIDA ATLANTIC UNIVERSITY FIRE ALARM SYSTEM INSTALLATION MANUAL January, 2003 Environmental Health and Safety Florida Atlantic University 777 Glades Rd. Boca Raton, FL 33431 Phone: 561-297-3129 Fax:

### FIRE ALARM SYSTEM. A. Shop drawings shall be submitted as follows: 1. Manufacturer's published literature. for aspproval.

Polk School District Specifications for the New Fire Alarm in the Existing Building Eastside Elementary School FIRE ALARM SYSTEM 1.01 SUBMITTALS A. Shop drawings shall be submitted as follows: 1. Manufacturer's

### SECTION 16721 FIRE ALARM AND DETECTION SYSTEMS

SECTION 16721 FIRE ALARM AND DETECTION SYSTEMS The equipment requirements of this section apply to the IUB Campus. The IUPUI Campus has a preferred vendor agreement for fire alarm systems. Contact Pat

### Fire Alarm System Plans Submittal Guidelines For New and Existing Systems

Fire Alarm System Plans Submittal Guidelines For New and Existing Systems SCOPE The Temecula Fire Prevention Bureau (TFPB) has established the following requirements for the submittal of all fire alarms,

### SECTION 16721 FIRE ALARM AND DETECTION SYSTEM

1. GENERAL 1.1. Related Documents: 1.2. Scope: 1.1.1. The general provisions of the Contract, including General and Supplementary Conditions and General Requirements apply to the work specified in this

### SECTION 16721 FIRE ALARM AND SMOKE DETECTION SYSTEMS

SECTION 16721 PART 1 - GENERAL 1.1 SECTION INCLUDES A. Fire Alarm Control Panels B. Manual Fire Alarm Stations C. Automatic Smoke D. Fire Alarm Notification Appliances E. Auxiliary Fire Alarm Equipment

### HONEYWELL COMMERCIAL FIRE/BURG PANEL UL LISTING REQUIREMENTS (Compiled from VistaFBPT Installation Instructions 800-09617V1 Rev A 11/12)

HONEYWELL COMMERCIAL FIRE/BURG PANEL UL LISTING REQUIREMENTS (Compiled from VistaFBPT Installation Instructions 800-09617V1 Rev A 11/12) UL864 (Commercial Fire) Compliance General Requirements The VISTA-128FBPT/VISTA250FBPT

### DELAWARE STATE FIRE MARSHAL FIRE ALARM SYSTEM CERTIFICATE OF INSTALLATION

Phone System Owner Phone System Engineered by: of Record Drawings: of System Manuals: of Test Reports: System Installer 1. GENERAL INFORMATION Phone Delaware License No: Certificate Holder No. System Supplier

### Fire Alarm and Detection Systems And Central Station Monitoring Plan Submittal Guidelines

Fire Alarm and Detection Systems And Central Station Monitoring Plan Submittal Guidelines Red Oak Fire Rescue Office of the Fire Marshal 547 N. Methodist Red Oak, TX 75154 Phone: 469-218-7713 Fax: 468-218-7719

### SECTION 13850 DETECTION AND ALARM

SECTION 13850 DETECTION AND ALARM PART 1 GENERAL 1.01 SUMMARY A. Section Includes 1. Control Panel 2 Associated Equipment B. Products Installed But Not Supplied Under This Section 1. Section 16140 - Wiring

### Small Building Life Safety Solutions. GE Security. Affordable FireShield Conventional Fire Alarm Control Panels. imagination at work

GE Security Small Building Life Safety Solutions Affordable FireShield Conventional Fire Alarm Control Panels imagination at work cost Location: Environment: Solution: Flower shop Finely decorated, gentle

### 1. The objective of this guideline is to provide minimum standards for design and installation of fire alarm systems for the University of Missouri.

GENERAL: 1. The objective of this guideline is to provide minimum standards for design and installation of fire alarm systems for the University of Missouri. 2. Fire alarm systems are Life Safety Systems

### INTELLIGENT FIRE ALARM CONTROL PANELS. MR-2100/MR-2200 Intelligent Fire Alarm Control Panels MEA. Features. Description

INTELLIGENT FIRE ALARM CONTROL PANELS MR-2100/MR-2200 Intelligent Fire Alarm Control Panels Description MR-2100/MR-2200 Intelligent Fire Alarm Control Panel (shown with optional LED modules) Secutron's

### FireSeeker Fire Alarm Control Panel Model FS-250 Programming Manual

FireSeeker Fire Alarm Control Panel Model FS-250 Programming Manual P/N 315-049403-1 Siemens Building Technologies Fire Safety Table Of Contents Introduction...1 The Access levels...1 User Level...1 Maintenance

### Module 4, Lesson 12 Fire Alarm Systems

Student Manual Module 4, Lesson 12 Fire Alarm Systems Performance Objectives At the conclusion of this lesson, you will be able to: Identify the components and functions of a fire alarm system and determine

### SECTION 16720 - FIRE AND SMOKE ALARM SYSTEM. City of San Diego, CWP Guidelines

PART 1 -- GENERAL 1.1 WORK OF THIS SECTION SECTION 16720 - City of San Diego, CWP Guidelines A. The WORK of this Section includes providing manual and automatic fire alarm and smoke detection systems meeting

### rpsa FIRE PROTECTION ENGINEERS

R.P. SCHIFILITI ASSOCIATES, INC. P.O. Box 297 Reading, Massachusetts 01867-0497 USA 781.944.9300 Fax / Data 781.942.7500 Telephone Sample Fire Alarm System Calculations 1. A fire alarm manufacturer specifies

### NC State University Design and Construction Guidelines Division 26 Fire Alarm Systems

NC State University Design and Construction Guidelines Division 26 Fire Alarm Systems 1.0 Purpose A. The following guideline provides the minimum standards and requirements for fire alarm systems. 2.0

### PLAN REVIEW GUIDE FOR FIRE ALARM

PLAN REVIEW GUIDE FOR FIRE ALARM PROJECT NAME: PERMIT # PROJECT ADDRESS: CONTACT PERSON: PHONE Fire alarm system installation information shall be provided on the appropriate architectural and electrical

### City of Bettendorf Fire Alarm System Requirements

City of Bettendorf Fire Alarm System Requirements Section 907 of the 2009 Edition of the International Fire Code (IFC) and Section 10-7-3 of the Municipal Code provide fire alarm requirements. IFC Section

### EDWARDS SIGNAL SOLUTIONS www.edwards-signals.com DISTRIBUTED BY: Lee Dan Communications, Inc. www.leedan.com info@leedan.com Toll-Free: 800-231-1414

EDWARDS SIGNAL SOLUTIONS www.edwards-signals.com DISTRIBUTED BY: Lee Dan Communications, Inc. www.leedan.com info@leedan.com Toll-Free: 800-231-1414 Fire Alarm CONTROL S y s t e m s CONVENTIONAL FIRE ALARM

### SECTION 28 31 11 FIRE ALARM AND DETECTION SYSTEM

KNOXVILLE, TENNESSEE SECTION 28 31 11 PAGE 1 PART 1 - GENERAL 1.01 DESCRIPTION OF WORK SECTION 28 31 11 A. Extent of fire alarm and detection system work shall be as described in this specification, as

### FIRE ALARM APPLICATION

FIRE ALARM APPLICATION ENUMCLAW FIRE DEPARTMENT 1330 Wells St, Enumclaw, WA 98022 Phone: 360-825-5544 Fax: 360-825-9442 COMMUNITY DEVELOPMENT, BUILDING DEPARTMENT 1309 Myrtle Ave Enumclaw WA 98022 Phone:

### FIRE DETECTION AND ALARM

Scope Provide a fire alarm system, or expand the existing system, as required by Code, the requirements in the Special Instructions to Designers (SID) of the Design Guidelines, and/or as noted in the Program

### Original Document 10/16/07 Revised 01/30/09 2 nd Revision 01-23-12 3 rd Revision- 12/18/14

North Collier Fire Control & Rescue District Greater Naples Fire Rescue District Immokalee Fire Control & Rescue District 2800 North Horseshoe Drive Naples, Florida 34104 SYSTEM REHABILITATION PLAN CHECKLIST

### Fire Alarm System Plans Review Checklist Property location Date of Review

Fire Alarm System Plans Review Checklist Property location Date of Review 1. Is application completed in entirety? 2. Are the plans review fee submitted with the application? 3. Does floor plan include

### FIRE ALARM AND DETECTION SYSTEMS SECTION 16721

PART 1 - GENERAL 1.01 WORK INCLUDED FIRE ALARM AND DETECTION SYSTEMS SECTION 16721 A. Provide a complete fully addressable, power limited, fire detection and evacuation system. The system shall be connected

### Bold items are particular to the City of Euless

EULESS FIRE DEPARTMENT FIRE MARSHAL S OFFICE INFORMATION LINE: Revised 2/12 Fire Chief Wes Rhodes Fire Marshal Paul Smith EFD-FMO 3-2 2009 International Fire & Building Code as Amended NFPA Standards Adopted

### FIRE ALARM AND EMERGENCY COMMUNICATION SYSTEM RECORD OF COMPLETION

FIRE ALARM AND EMERGENCY COMMUNICATION SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. It shall be permitted to modify this

### Module 5. Fire and Emergency Alarm System Part I- Basics

Module 5 Fire and Emergency Alarm System Part I- Basics 1 This module will describe: 1. Components and the arrangements of components in fire and emergency alarm systems. 2. How these systems work. 3.

### EXHIBIT A SCOPE OF WORK

EXHIBIT A SCOPE OF WORK 1. (Contractor) shall provide fire alarm system maintenance/repair/testing services as described herein to the California Department of Veterans Affairs (hereinafter CDVA, CalVet,

### 1.0 General. Inspection, Testing, and Maintenance 1 of 8

1.0 General 1.1 Scope This specifications covers the minimum requirements for the inspection, testing, and maintenance of the existing Notifier fire alarm systems at Bergen Community College (BCC) campus

### D7050/D7050TH. Installation Instructions. Multiplex Photoelectric Smoke Detectors

D7050/D7050TH EN Installation Instructions Multiplex Photoelectric Smoke Detectors D7050/D7050TH Installation Instructions.0 Description Notices These instructions cover the installation of the D7050/D7050TH

### SECTION 13850 (28 31 00) FIRE DETECTION AND ALARM SYSTEM

SECTION 13850 (28 31 00) FIRE DETECTION AND ALARM SYSTEM ENGINEERING SPECIFICATION 25-POINT INTELLIGENT COMMUNICATING FIRE DETECTION SYSTEM PART 1 GENERAL 1.1. DESCRIPTION: A. This section of the specification

### NFPA 72. Exception No. 1: Where ambient conditions prohibit installation of automatic smoke detection, automatic heat detection shall be permitted.

NFPA 72 3.3.7.2 3.3.7.2 False Alarm. Activation or reporting of an alarm for which no such alarm condition, fire or emergency actually exists. Additionally, False Alarm is the willful and knowing initiating

### FIRE ALARM SYSTEM CHECKLIST For Addressable Systems PRIOR TO INSPECTION

Building Name/Location: Installing Company: Observation By: Date: Time: 1 Building Occupants, Authorities and Alarm Monitoring Co Have Been Notified 2 FACP Manufacturer and Panel is Approved for NCSU Campus

### Telluride Fire Protection District Fire Alarm Systems Policy Version 03/2007

Telluride Fire Protection District Fire Alarm Systems Policy Version 03/2007 FIRE ALARM SYSTEMS POLICY TELLURIDE FIRE PROTECTION DISTRICT TABLE OF CONTENTS FIRE ALARM PROTECTION POLICY PLAN REVIEW SUBMITTAL

### DORMA MODEL PS-406BB POWER SUPPLY INSTALLATION INSTRUCTIONS

Features: INSTALLATION Install in accordance with NFPA 70. DORMA MODEL PS-406BB POWER SUPPLY INSTALLATION INSTRUCTIONS Up to 1.95 Amps Load Capacity Class 2 Rated Outputs Overload, Over Voltage, and Short

### SFC-200 SERIES FIRE ALARM CONTROL PANELS. SFC-200 Series Fire Alarm Control Panels. Features. Description

SFC-200 SERIES FIRE ALARM CONTROL PANELS SFC-200 Series Fire Alarm Control Panels Description Summit s SFC-200 Series fire alarm control panels consist of six and twelve zone models which are equipped

### University Design Standard. Fire Alarm Systems

University Design Standard Fire Alarm Systems 1.0 Overview This document provides Virginia Tech s standards for the design and installation of fire alarm systems and equipment in new construction, retrofit

### SECTION 16721 FIRE DETECTION AND ALARM SYSTEM PART 1 - GENERAL 1.01 DESCRIPTION

SECTION 16721 FIRE DETECTION AND ALARM SYSTEM PART 1 - GENERAL 1.01 DESCRIPTION A. This section of the specifications includes the furnishing, installation, and connection of the microprocessor-controlled

### DTW Works Master Specification Version 2006

Issued 2006/08/01 Section 13852 Multiplex Fire Alarm System Page 1 of 10 PART 1 GENERAL 1.1 RELATED WORK.1 Section 01330 Submittal Procedures..2 Section 01780 Closeout Procedures..3 Section 01810 Commissioning..4

### Rancho Cucamonga Fire Protection District Prevention Bureau Standard

Rancho Cucamonga Fire Protection District Prevention Bureau Standard Title: Fire Alarm and Monitoring Systems Standard # 9-3 Effective: May 2002 Number of Pages: 7 Revised: January 2014 INTENT The intent

### Fire Alarm Systems Permit Packet. City of Greer Fire Department

Fire Alarm Systems Permit Packet City of Greer Fire Department Updated July 2004 If you have any questions or comments regarding the information contained within; or of you need assistance interpreting

### INSTRUCTIONS FOR BUILDINGS WITH FIRE PROTECTION EQUIPMENT

INSTRUCTIONS FOR BUILDINGS WITH FIRE PROTECTION EQUIPMENT FIRE EXTINGUISHERS,SPRINKLER SYSTEMS AND FIRE ALARMS Attachment #1 Inspection of Fire Extinguishers Fire Extinguishers must be tested according

### HERNANDO COUNTY FIRE ALARM GUIDELINES

HERNANDO COUNTY FIRE ALARM GUIDELINES To be used for all commercial building fire alarm system plan review. The procedures set forth in this document are the minimum requirements necessary to ensure a

### D287/D288/D292/D293A/D293E

D87/D88/D9/D9A/D9E EN Installation Guide Smoke Detector Bases D87/D88/D9/D9A/D9E Installation Guide.0 Overview.0 Overview The D87/D88/D9/D9A/D9E Smoke Detector Bases are designed for use with the D8 Ionization

### Fault Isolators. CFAA Technical Seminar. Stephen Ames October 30, 2013

Fault Isolators CFAA Technical Seminar Stephen Ames October 30, 2013 1 Field Device Fault Isolation Field Device Fault Isolators when required are detailed in CAN/ULC-S524-06 When a data loop serves more

### FVSU-33201301 REPAIR & UPGRADE FIBER OPTIC 280000-1 SECTION 280000 FIRE ALARM SYSTEM CONNECTIVITY

FVSU-33201301 REPAIR & UPGRADE FIBER OPTIC 280000-1 SECTION 280000 FIRE ALARM SYSTEM CONNECTIVITY PART 1 - GENERAL 1.1 SUMMARY A. Section Includes: 1. Fire-alarm control unit. 2. Addressable interface

### Faraday Intelligent Fire Detection Systems

Faraday Intelligent Fire Detection Systems Faster detection means better protection for buildings and the people in them. Greater safety and value for new and retrofit applications The right fit Fire safety

### SECTION 16853 ZONED (DC LOOP) FIREALARM SYSTEM

SECTION 16853 ZONED (DC LOOP) FIRE-ALARM SYSTEM PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and Division 1

### FIRE ALARM SYSTEM SUBMITTAL CHECKLIST AND APPLICATION

PERMITS AND INSPECTIONS FIRE ALARM SYSTEM SUBMITTAL CHECKLIST AND APPLICATION 911 Assigned PROJECT LOCATION Subdivision: Lot: Blk: Sec: PROJECT New Construction Addition/Remodel Demolition Other: Number

### SECTION 16721 FIRE ALARM AND DETECTION SYSTEM

SECTION 16721 FIRE ALARM AND DETECTION SYSTEM PART 1 - GENERAL 1.1 RELATED DOCUMENTS: A. Drawings and general provisions of Contract, including General and Supplementary Conditions and Division-1 Specification

### v 1.42b Conceal-Alarm Information Packet for Fire Alarm System Contractors & Installers Conceal -Alarm

v 1.42b Conceal-Alarm Information Packet for Fire Alarm System Contractors & Installers Conceal -Alarm Quick Reference Sheet Important Items to Understand > The Conceal-Alarm series product family is compatible

Using your LED Plus keypad System 238 System 2316 System 238i System 2316i Part Number 5-051-372-00 Rev B Thank you for purchasing this C&K alarm system Your system is one of the most powerful and advanced

### CBD-233. Fire Alarm and Detection Systems

Page 1 of 5 CBD-233. Fire Alarm and Detection Systems Originally published August 1984. R.H.L. McEwen Fire alarm systems are normally required by building codes. In the case of new buildings, this is usually

### C. Conform to requirements of Americans with Disabilities Act (ADA).

SECTION 28 31 00 - FIRE ALARM AND DETECTION SYSTEMS PART 1 - GENERAL 1.1 SECTION INCLUDES A. Fire alarm and detection systems 1.2 REFERENCES A. NFPA 70 - National Electrical Code B. NFPA 72 - National

### Attachment 9. Trouble signals. Interfaced equipment. Primary (main) power supply

FIRE DETECTION, ALARM AND MASS NOTIFICATION SYSTEMS Inspection, testing, and maintenance of fire detection, alarm and Mass Notification systems shall be performed in accordance with the manufacturer's

### PC4020CF v3.0 and higher Commercial Fire Installation Guide DLS-3 v1.3

PC4020CF v3.0 and higher Commercial Fire Installation Guide DLS-3 v1.3 Table of Contents Section 1: Introduction 1 1.1 Introduction...1 1.2 Hardware Description and Specifications...1 Section 2: Fire Zone

### Finance and Administration Department 907 Billy Mitchell Blvd. P: (210) 228-1022 Fire Alarm Permit Application

PERMIT FEE: \$ Finance and Administration Department 907 Billy Mitchell Blvd. P: (210) 228-1022 Fire Alarm Permit Application PAYMENT TYPE: Check Credit Card Charge to Job #: (Please complete all of the

### Agenda. Agenda (continued) Fundamentals of Fire Alarm Systems

Fundamentals of Fire Alarm Systems Sponsored by UL SFPE Austin/San Antonio Chapter San Marcos, Texas 7 January 2015 Agenda Introduction and Administration Historical Context of Today s NFPA 72 Fire Alarm

### INSPECTION AND TESTING OF FIRE ALARM SYSTEMS

Page 1 January 2, 2009 INSPECTION AND TESTING OF FIRE ALARM SYSTEMS Introduction Early warning plays a key role in a healthcare facility s ability to safely evacuate its residents during a fire emergency.

### Fire Wire. Genesis Series Cables for Fire-Lite Alarms

Fire Wire Genesis Series Cables for Fire-Lite Alarms We've Got a Cable for That! Genesis Series Cables for Firelite DIRECTORY ANN-BUS... 2 Signaling Line Circuits (SLC)... 3 Conventional 2&4 Wire Initiating

### Reference numbers following checklist statements represent an NFPA code section unless otherwise specified.

Fire Alarm System Plan Review Checklist 2010 OFC and 2007 NFPA 72 This checklist is for jurisdictions that permit the use of the 2007 NFPA 72 in lieu of IFC s referenced 2002 NFPA 72. Date of Review: Permit

### FIRE ALARM SYSTEM CHECK LIST

FIRE ALARM SYSTEM CHECK LIST BUILDING NAME: DESIGNER: INSPECTION BY: LOCATION: INSTALLER: DATE: Preparation for Acceptance Test Fire authorities have been notified of the system test. Also notify any location

### JULY 2013 UCB STANDARDS 16720-1

SECTION 16720 FIRE ALARM AND DETECTION SYSTEMS PART 1 GENERAL 1.01 Reference A. Related Sections 1. Section 15300 Fire Protection 2. Section 15950 Controls 3. Division 16 Electrical 4. Division 14 - Conveying

### CHANGES IN NFPA 72 NATIONAL FIRE ALARM CODE 1999 2002

CHANGES IN NFPA 72 NATIONAL FIRE ALARM CODE 1999 2002 Three new chapters were added. What was chapter 1 in 1999 was reorganized into chapters 1 (Fundamentals), 2 (Referenced Publications), and 3 (Definitions).

### SECTION 13850 (28 31 00) FIRE DETECTION AND ALARM SYSTEM

SECTION 13850 (28 31 00) FIRE DETECTION AND ALARM SYSTEM ENGINEERING SPECIFICATION INTELLIGENT REPORTING FIRE DETECTION SYSTEM PART 1 GENERAL 1.1 DESCRIPTION A. This specification includes the furnishing,

### Understanding Fire Alarm Requirements & Inspections. Presented By Bill Conroy Technical Sales For Briscoe Protective Systems Inc

Understanding Fire Alarm Requirements & Inspections Presented By Bill Conroy Technical Sales For Briscoe Protective Systems Inc Introduction Fire Alarm Requirements are structured through a system of codes.

### BELMONT FIRE DEPARTMENT FIRE ALARM SYSTEM REQUIREMENTS BFD-OFM-10-011

Fire Alarm System plan(s) MUST be reviewed and approved by the Belmont Fire Department prior to the start of construction. The design and any changes must be fully compliant with NFPA 1, NFPA 101, NFPA

### FIRE SPRINKLER SYSTEM SUPERVISORY SERVICE User s Guide (DamarNet RAR Service)

FIRE SPRINKLER SYSTEM SUPERVISORY SERVICE User s Guide (DamarNet RAR Service) The information provided in this user guide pertains to fire suppression sprinkler system monitoring service provided over

### SILENT KNIGHT MODEL 5207

SILENT KNIGHT MODEL 5207 Fire Control / Communicator Installation, Programming, and Operation Manual Part Number 150865 Rev. C, 04/03 Contents Section 1 Introduction.......................................................................1-1

### 2012 Ontario Building Code Changes Affecting Fire Alarm Systems

2012 Ontario Building Code Changes Affecting Fire Alarm Systems CFAA Annual Technical Seminar May 31, 2013 Ken Baird VP Systems www.lrifire.com LRI 2010 Developments in Life Safety Introduction Code Development

### 527 CMR: BOARD OF FIRE PREVENTION REGULATIONS

527 CMR 24.00: FIRE WARNING SYSTEMS INSTALLED IN BUILDINGS WITHIN THE COMMONWEALTH OF MASSACHUSETTS Section 24.01: Purpose 24.02: Scope 24.03: Definitions 24.04: Approval of Design 24.05: Power Supply

### Commercial Fire Alarm Standards July 1, 2010 Edition Page 1 of 14

City of Mercer Island Development Services Group Fire Code Review and Inspection 9611 SE 36 th Street Mercer Island, WA 98040-3732 PHONE (206) 275-7605 FAX (206) 275-7726 www.mercergov.org Commercial Fire

### conventional system operation

conventional system operation detection line operation Conventional detection systems normally operate on a 24VDC line. In the standby condition, the detectors will draw a low current, typically less than

### TECHNICAL DATA. Scan with smart phone to access Custom Zone Description Text. Viking Technical Data may be found on 24 Hour Clock

Page 1 of 8 1. DESCRIPTION The Viking VFR400 is a microprocessor based multi-hazard releasing control panel for use on preaction, deluge, Surefire and Firecycle multicycle sprinkler systems, MX-1230 Fire

### Fire Prevention Coffee Break Training. November 2015

Fire Prevention Coffee Break Training November 2015 Agenda Changes in the Pire Prevention Bureau FM Lund Tags FM Lund System priorities for the FD FM Lund Transmission Technologies- Phelan Questions and

### Design Standards Fire Alarm Systems Division 13860 (1995 CMS); 283100 (2004 CMS) Amended Feb 2015

Design Standards Fire Alarm Systems Division 13860 (1995 CMS); 283100 (2004 CMS) Amended Feb 2015 13860 (283100) FIRE ALARM SYSTEM The following standard shall be followed for the design of University

### TESTING, INSPECTION, AND MAINTENANCE FREQUENCIES FOR FIRE DETECTION AND ALARM SYSTEMS

TESTING, INSPECTION, AND MAINTENANCE FREQUENCIES FOR FIRE DETECTION AND ALARM SYSTEMS The following information regarding testing frequencies for fire detection and alarm systems. All of the following

### BASIC FIRE ALARM TRAINING

BASIC FIRE ALARM TRAINING What is a fire alarm system? Per the defini+on in NFPA 72 A system or por+on of a combina+on system that consists of components and circuits arranged to monitor and annunciate

### Life Alarm Fire Alarm Controls

FIRE SUPERVISORY SUPV SILENCED SILENCE AC POWER RESET UL, ULC Listed FM Approved MEA Approved* Life Alarm Fire Alarm Controls Fire Alarm Controls 4005 Series Fire Alarm Control Panels Eight through Thirty-Six

### ERS-2400B. PERS-2400B Personal Emergency Reporting System

PERS-2400B Personal Emergency Reporting System ERS-2400B Durability and Versatility for Emergency Reporting Solutions Create a customized and comprehensive Personal Emergency Reporting System with the

### AETNA FIRE ALARM SERVICE CO., INC.

FIRE ALARM AND EMERGENCY COMMUNICATION SYSTEM INSPECTION AND TESTING FORM To be completed by the system inspector or tester at the inspection or test. It shall be permitted to modify this form as needed

### New and Existing Fire Alarm & Signaling Systems

ORANGE COUNTY FIRE AUTHORITY Planning & Development Services Section 1 Fire Authority Road, Building A, Irvine, CA 92602 714-573-6100 www.ocfa.org New and Existing Fire Alarm & Signaling Systems Guideline

### MODEL 5010 DUAL CHANNEL SMOKE/FIRE DETECTION MODULE

DESCRIPTION MODEL 5010 DUAL CHANNEL SMOKE/FIRE DETECTION MODULE DESCRIPTION The SST Model 5010 Two Channel Smoke/Fire Detection Module provides two independent detection input channels for the NOVA-5000

### Firmware version: 1.10 Issue: 7 AUTODIALER GD30.2. Instruction Manual

Firmware version: 1.10 Issue: 7 AUTODIALER GD30.2 Instruction Manual Firmware version: 2.0.1 Issue: 0.6 Version of the GPRS transmitters configurator: 1.3.6.3 Date of issue: 07.03.2012 TABLE OF CONTENTS

### The Benefits of ADDRESSABLE Fire Alarm Technology

The Benefits of ADDRESSABLE Fire Alarm Technology NOTICE: If you were born after 1990 or if you lived through the 60 s and can t remember what happened since, you may be surprised to learn that fire alarm

### SMOKE DETECTOR INSTALLATION PROGRAM The Burlington Ordinance Perspective

SMOKE DETECTOR INSTALLATION PROGRAM The Burlington Ordinance Perspective The National Fire Alarm Code, NFPA 72, sets the minimum requirements of performance, selection, use and location of automatic detection

### B. NICET: National Institute for Certification in Engineering Technologies.

PART 1 - GENERAL 1.01 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and Division 01 Specification Sections, apply to this Section.

### EQUIPMENT SPECIFICATIONS

EQUIPMENT SPECIFICATIONS IC-1600 Intelligent Controller The IC-1600 Intelligent Controller is a fully intelligent panel that has a complete database on board. It operates in conjunction with the Access

### INSPECTION AND TESTING FORM

INSPECTION AND TESTING FORM SERVICE ORGANIZATION PROPERTY NAME (USER) DATE: 08-04-15 TIME: 8:00 Name: Siemens Industries Inc. Name: Kcvtcs Madisonville Tech, School Bldg. Address: 2700 Stanley Gault Pkwy