1 Ground Source Heat Pumps The Fundamentals Southington, Connecticut John F. Sima III P.E. Winter/Spring 2010
2 Ground Source Heat Pumps The Fundamentals TOPICS: Heat Pump Terminology Basic Physics of Heat Pumps Processes of Ground Source Heating and Cooling What Happens to the Heat Underground Measuring Efficiency The Differences From Traditional Systems What to Look For
3 Geothermal Heat Pump Ground Source Heat Pumps (Geothermal) are self-contained, and fit inside a cabinet that is about the same size as a conventional warm-air furnace.
4 Inside a Geothermal Heat Pump A high-efficiency blower draws air from the building across a large heat exchanger A refrigeration system extracts heat from (or rejects it to) water circulating through underground pipes.
5 How Do You Get Heat From Cold Water? There is some heat in every object (fluid) on earth. Cold water has a lot of heat in it, even though it feels cold to us. To extract heat from cold water, we pass it through a heat exchanger containing refrigerant that is colder than the water. Heat naturally flows to cold objects (the refrigerant) from warmer ones (the water). To make this low-grade heat useable for heating our buildings, geothermal heat pumps extract the heat at low temperature, then boost that heat to a temperature that is warmer than the air in our buildings. It s that simple!
6 Heat Pump Terms Geothermal really refers to hot water, or steam that can be extracted directly from the earth. It occurs in the western US, and other places. But the term is now commonly used when referring to heat pump systems that extract low-grade heat from the earth. Geoexchange, ground-source, and ground-coupled all refer to these same geothermal heat pump systems that we are looking at today.
7 Heat Pump Terms Four terms are commonly used, when describing heat pump capacity and efficiency. BTU s and Tons describe heating and cooling capacities. COP and EER describe heating and cooling efficiencies.
8 BTU s vs. Tons BTU s per hour are units for measuring the heating capacities of heat pump systems. Tons are usually used to measure cooling capacities. Both describe units of heat, and each can be converted to the other.
9 BTU = British Thermal Unit One BTU will raise the temperature of one pound of water by one degree Fahrenheit Brewing a pint of coffee (one pound of water) requires about 130 BTU s (180 deg. 50 deg.)
10 British Thermal Unit A hot bath requires about 13,750 BTU s. The math is simple: 30 gallons, weighing 8.33 pounds per gallon are warmed by 55 degrees.
11 British Thermal Unit Keeping an average home warm on a very cold night requires about 360,000 BTU s BTU = unit of heat BTU/hr = Rate of producing or removing heat
12 Measuring Heat Pump Capacity BTU/hr A heat pump s capacity is the rate at which it produces or removes heat. For heating, units are usually expressed as BTU/hr. For example, if a typical 36,000-BTU/hr heat pump runs constantly for ten hours, it will produce 360,000 BTU s
13 Measuring Heat Pump Capacity - Ton In the cooling mode, heat pump capacity can be expressed in Tons of refrigeration capacity. A Ton of refrigeration is the cooling capacity which will freeze one Ton (2,000 pounds) of water in 24 hours at 32 degrees F. Looking at it another way, a one-ton heat pump can provide as much cooling in 24 hours as a 2,000-pound block of ice.
14 Converting Tons to BTU/hr One Ton of cooling capacity is equivalent to 12,000 BTU s per hour. Remember, a 12,000- BTU/hr. heat pump can freeze (or melt) one ton of ice in 24 hours. We use the terms interchangeably. A one-ton air conditioner cools the air at the rate of 12,000 BTU/hr.
15 The Basic Physics How Do Heat Pumps Pump Heat? First, look at water s heat vs. phase diagram. Water, like other substances, absorbs a lot more heat when changing phases than when it is warmed within a phase.
16 Water Changing Phase to Ice It is relatively easy to warm a pound of water, and even easier to warm a pound of ice, but converting a pound of ice into a pound of water requires a lot of energy. Converting a pound of liquid to a pound of vapor requires even more energy. - -
17 Water Changing Phase to Steam Add 1 BTU of heat to a pound of liquid water, and its temp. rises by 1 degree F. But the pound of water absorbs 970 BTU as it evaporates at 212 deg. These are the numbers at atmospheric pressure.
18 Raise the pressure, and the properties remain similar, except that the phase change occurs at increasingly higher temperature. Heat pumps use refrigerants that shift phase at convenient temperatures and pressures. Changing Phase to Steam at Higher Pressures
19 Refrigerants Pressure vs. Heat Content
20 Refrigerants Pressure vs. Heat Content At 120 psi, Refrigerant 410-A changes state from liquid to vapor at about 30 deg. F. At 300 psi, it changes state at about 90 deg. F. These are convenient temperatures and pressures for absorbing heat from ground water, and for releasing heat to our homes.
21 How Do Heat Pumps Pump Heat? In a typical heating cycle, most of the heat is added to the refrigerant in the cold evaporator when it changes state from liquid to vapor. The compressor adds some heat, but its primary job is to raise the pressure so heat can be released in the warm condenser.
23 Review the Process: Low pressure liquid refrigerant evaporates at about 30 deg. F, within a water heat exchanger, and absorbs heat from the water (or antifreeze solution). The cool refrigerant vapor is then compressed, typically from 120 psi to 300 psi. The heat of compression warms the gas to about 90 deg. F. The warm vapor gives its heat to the house in an air heat exchanger, as the vapor condenses to a liquid. The refrigerant passes through an expansion valve, where the pressure is reduced back to 120 psi.
24 The Heat Pump Heating Process
25 The cycle is reversed for cooling The compressed, warm vapor goes to the water heat exchanger first, where it releases heat to the water and condenses to a liquid. The refrigerant pressure is reduced at the expansion valve, as for heating. The refrigerant now vaporizes in the air heat exchanger, absorbing heat from the air in the living space.
26 The Heat Pump Cooling Process
27 What Happens to the Heat Underground Most of the heat, removed from the ground by the heat pumps during the winter, is replaced by natural heat flow underground. Some heat is also replaced during the summer, when the heat pumps run in the air conditioning mode.
28 What Happens to the Heat Underground Several software applications are available, which calculate the ground loop temperature for closed loop systems. These temperature calculations require: The design (peak) heating and cooling loads Annual weather data for the site The design layout for geoexchange loops Heat conductance and heat storage capacities of the soil (bedrock)
30 Designing The Water Supply Side Each BTU removed from a pound of water lowers its temperature by one degree Fahrenheit. Each gallon of water weighs 8.33 pounds. Removing 8.33 BTU s from a gallon of water lowers its temperature by one degree Fahrenheit.
31 Designing The Water Supply Side The three-ton heat pump, which delivers 33,300 Btu/hr to the house, needs to extract 25,500 Btu/hr from the water. If the design-temperature drop, for water passing through the heat exchanger, is 6 degrees F, then the heat pump needs: 25,500 Btu/hr / ( 8.33 Btu/gal deg x 6 deg) = 510 gal/hr or 8.5 gal/minute If the heat pump runs for 8 hours in one day, it will need 4,080 gallons of water pumped through it that day.
32 Designing the Water Supply Side 25,500 Btu/hr are extracted from the water, but 33,300 Btu/hr are delivered to the house. The additional 7,800 Btu/hr, comes from the electricity purchased to run the heat pump. This is the heat generated in motor windings within the blower and compressor. An important point - no heat is wasted.
33 Measuring Heating Efficiency - COP In the heating mode, efficiency is expressed as Coefficient of Performance, or COP. COP = Total heating capacity in BTU/hr, divided by the electric power input in BTU/hr. Example: 33,300 / 7,800 = 4.27 COP By minimizing power input, the COP is maximized. That means minimizing compressor, fan and circulator running watts.
34 Measuring Cooling Efficiency - EER In the cooling mode, efficiency is expressed as Energy Efficiency Ratio = EER. EER = Total cooling capacity, in BTU/hr, divided by the electric power input in watts. Example: 39,700 / 1,670 = 23.8 EER. The same rules for maximizing efficiency by minimizing running watts hold true here too.
35 Differences From Traditional Systems Heat pumps do not burn fossil fuel. There is no air emission. ¾ of the heat comes from the earth, and is renewable. The antifreeze used in closed loop systems is propylene glycol, the non-toxic type used in recreational vehicles. The water used by open loop systems is returned to the earth unchanged, except for heat.
36 Differences From Traditional Systems A good Air-Source Air Conditioner runs at a SEER rating of 13. Compare geothermal equipment that runs at EER ratings near 20. The difference is not because of magic. Geothermal systems reject heat to a 50-degree earth, while air-source equipment rejects heat to 80 or 90 degree air.
37 Differences From Traditional Systems Search the internet for sources that calculate the comparative operating costs for various heating and cooling systems. Try: comparison_calculator/ For heat pump, use electric heat at 427% (for COP = 4.27) Google Fuel Cost Comparison Sites
38 Piping Example Vertical Closed Loop Heating
39 What to Look For Vertical Closed Loop In southern New England, we usually design for 150 feet of borehole per ton of heat pump capacity. Boreholes should be kept at least 15 feet apart. Each borehole is filled with clay grout after the loops are installed. Casings are cut off below surface to allow lateral connections to be made. Loops are filled with a solution of propylene glycol and water. (usually 20%) Lateral runs into the house should be buried at least four feet below surface.
40 What to Look For Closed Loop Systems Clay grout is non-setting, so it is possible that the clay will migrate. Keep the loop wells separated from the potable well, especially where the bedrock is highly fractured. Well casings are cut off below grade, or removed entirely, so a good grouting job is important. A mound of chipsized bentonite should also be placed over the top of each well.
41 Operating Costs Operating cost for heating and cooling a 3,200 square foot house, with a closed loop vertical system, at current electric prices, should average about $1, per year. Average monthly heating costs can vary from $36.00 / month to $ / month.
42 Compare Operating Costs Closed-Loop Geothermal heat pump, at 17 cents / KWH, costs about $1, per year to heat and cool the 3,200 sq. ft. house. Straight electric heat, at 17 cents / KWH, would cost over $6, per year for the same house. Fuel oil at $3.00 / gallon, burned in an 80%-efficient furnace, with a 12-SEER air conditioner, could cost over $3, per year.
43 Importance of Good Design One of the most important factors, in designing a geothermal system, is to give the evaporator as much heat as you can. This means plenty of borehole and flow-rate in a closed-loop system. If you skimp on water or loops, the evaporator runs cold, the condenser will also be cooler, and the heat pump will need to run longer to warm the house. Similarly, if you skimp on duct sizes, the condenser runs hot, and the compressor consumes more electricity than needs to.
45 Importance of Good Design The geothermal system designer (installer) needs to design the air ducts and geoexchange loops conservatively, for economical operation of the system. On a typical heating day our 3-ton heat pump system might cost $3.62 to operate for the day. If the ducts are undersized, capacity and efficiency are compromised, and the same machine might cost $4.11/day. Similarly, if the geoexchange loops are undersized, operating cost might be $4.00/day. If both are under-designed, operating cost might be $4.54.
46 New Incentives The Connecticut Clean Energy Fund has money available from the American Recovery and Reinvestment Act. Retrofit customers must participate in their Utility s audit/upgrade program and show evidence of their building s energy efficiency. New Construction homes must be Energy Star rated. All recommended upgrades must be made before installing the geothermal system. Residential retrofits are eligible for $2,000/ton, and new construction installations are eligible for $1,200/ton. Check at for more information.
47 Other Incentives Connecticut Light & Power and United Illuminating are offering rebates of $ per ton of heat pump capacity, for new heat pump installations. (Up to $1, per site) The heat pumps must be Energy Star rated. The operating performance, as installed, must be within 15% of the factory ARI rating. The IRS allows a 30% tax credit for the installation cost of a geothermal heat pump system. (no performance test req.) Homeowners and businesses should check with their accountants before committing to buying geothermal.
48 More Information - Websites
49 Information on Regulations In Connecticut, check at: for information on General Permits In June Pump and Discharge systems under 250,000 gpd need not file, but must meter flow and keep daily records. No DEP regulations for closed loop systems. New Connecticut Well Drilling Regulations are being developed. They will provide for smaller separating distances to septic system and underground drains for closed loop wells than for water supply wells (open loop systems), because the closed loop wells are filled with clay grout.
GEOTHERMAL HEATING AND COOLING INTRODUCTION Geothermal Heating and Cooling Systems provide space conditioning -- heating, cooling, and humidity control. They may also provide water heating -- either to
Heating & Cooling Efficiency Advantages of Geothermal HVAC Efficiency Keith Swilley Gulf Power Company Why Gulf Power Promotes Energy Efficiency? Customer Satisfaction Education Help Customers Make Smart
GEOTHERMAL HEAT PUMPS - TRENDS AND COMPARISONS - John W. Lund Geo-Heat Center Heat pumps are used where geothermal water or ground temperatures are only slightly above normal, generally 50 to 90 o F. Conventional
How Ground/Water Source s Work Steve Kavanaugh, Professor Emeritus of Mechanical Engineering, University of Alabama Ground Source s (a.k.a. Geothermal s) are becoming more common as the costs of energy
Creating Efficient HVAC Systems Heating and Cooling Fundamentals for Commercial Buildings Heating, ventilating, and air conditioning (HVAC) systems account for nearly half of the energy used in a typical
WaterFurnace Explains GEOTHERMAL HEATING & COOLING GEOTHERMAL HEATING AND COOLING AN INTRODUCTION WaterFurnace geothermal heating and cooling systems use the clean, renewable energy in your back yard to
Geothermal Energy Using Water-Source Heat Pumps By VIRSTAR Corporation Geothermal Expertise Since 1978 All information contained herein is the exclusive property of VIRSTAR Corporation, all rights reserved.
AE-1483 Ground-source Heat Pumps Carl Pedersen Energy Educator A heat pump can be an efficient alternative to a standard home heating system. Moreover, during the cooling season, its function can be reversed,
Refrigeration Basics 101 By: Eric Nelson Basics Refrigeration is the removal of heat from a material or space, so that it s temperature is lower than that of it s surroundings. When refrigerant absorbs
Glossary of Heating, Ventilation and Air Conditioning Terms Air Change: Unlike re-circulated air, this is the total air required to completely replace the air in a room or building. Air Conditioner: Equipment
Geothermal Comfort Systems The Bryant Geothermal Advantage Throughout Bryant's historic 100-year legacy, the company has provided millions of homeowners with the finest comfort systems available. Offering
Comparing Fuel Costs of Heating and Cooling Systems June 2003 Introduction One of the most common questions posed to energy specialists at Engineering Extension asks for a comparison between costs to operate
Geothermal Energy The Ocean Pines Association Board of Directors asked the OPA Environment and Natural Assets Advisory Committee (ENAAC) to provide information about how geothermal energy could be useful
Energy Efficiency Energy Efficient Home Cooling: Choosing an air conditioning system is an important decision. A poor choice may be costly to purchase and operate and yet fail to provide the desired cooling
Heating Your Home or Business in Vermont with a Geothermal System A publication of the Northeast Vermont Development Association Created by Ben Luce, Ph.D., with support from the Vermont Clean Energy Development
Serenbe Green Geothermal Solutions with Bosch Thermotechnology Geothermal Heating and Cooling boschheatingandcooling.com C1 Residential Geothermal Heat Pumps The Bosch Complete Solution The Serenbe Community,
1 1. What percent of a commercial business s energy usage comes from their HVAC system? A. 13% B. 23% C. 33% D. 43% E. 53% 2. How much money do commercial facilities spend per square foot on energy costs
The efficient heat pump KCP&L has worked hard to build one of the best reliability records in the industry and we want to help you make the most of the energy we provide. That s why we offer information
Geothermal Heat Pump Systems GeoExchange Technology Curtis J. Klaassen, P.E. Iowa Energy Center Energy Resource Station Geothermal Heat Pump Technology Introduction What is Geothermal Energy? Geothermal
Sea Water Heat Pump Project Alaska SeaLife Center, Seward, AK Presenter: Andy Baker, PE, YourCleanEnergy LLC Also Present is ASLC Operations Manager: Darryl Schaefermeyer ACEP Rural Energy Conference Forum
Presentation Outline Common Terms / Concepts HVAC Building Blocks Plant Level Building Blocks Description / Application Data Green opportunities Selection Criteria Air Distribution Building Blocks same
Objectives MAE 320 - Chapter 6 The Second Law of Thermodynamics The content and the pictures are from the text book: Çengel, Y. A. and Boles, M. A., Thermodynamics: An Engineering Approach, McGraw-Hill,
Fuel and Energy Conversion and Equivalence Chart Please note, the fuel economy estimates within this document are examples only. Maine Public Service does not consult with customers regarding fuel source
How a Ground Source Heat Pump Works for a School or College Vertical System Image courtesy of Climate Master 1 Geothermal avoids the need for outdoor equipment..reducing vandalism and liability Image courtesy
HOT & COLD Basic Thermodynamics and Large Building Heating and Cooling What is Thermodynamics? It s the study of energy conversion using heat and other forms of energy based on temperature, volume, and
SECTION 5 COMMERCIAL REFRIGERATION UNIT 21 EVAPORATORS AND THE REFRIGERATION SYSTEM UNIT OBJECTIVES After studying this unit, the reader should be able to Define high-, medium-, and low-temperature refrigeration.
This article was published in ASHRAE Journal, February 2011. Copyright 2011 American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. Posted at www.ashrae.org. This article may not
A Buyer s Guide for Residential Ground Source The aim of this publication is to help readers with the decision to purchase and install a ground source heat pump (or geoexchange) system. This document is
GEOTHERMAL HEAT PUMP SYSTEMS ARE RED HOT BUT ARE THEY REALLY GREEN? Richard C. Niess 1 Gilbert & Associates / Apogee Interactive, Inc., Gloucester Point, Virginia 23062 Phone & Fax (804) 642 0400 ABSTRACT
Renewable Heat Pumps A guide for the technically minded How do heat pumps work? A heat pump is an environmental energy technology that extracts heat from low temperature sources (air, water, ground), upgrades
SECTION 5 COMMERCIAL REFRIGERATION UNIT 22 CONDENSERS UNIT OBJECTIVES After studying this unit, the reader should be able to explain the purpose of the condenser in a refrigeration system. describe differences
Fact Sheet #6 Air Conditioning In this fact sheet you will discover: The opportunity for energy efficiency How air conditioning works Low cost actions to reduce energy usage now Investments to reduce costs
The Mean Green Cooling MachineTM www.aqua-chill.com Runs Less. Cools More. What is AquaChill? AquaChill is not a swamp cooler. Aqua Chill is a water cooled evaporative air conditioner. A water cooled system
Refrigeration Service Engineers Society 1666 Rand Road Des Plaines, Illinois 60016 UNDERSTANDING REFRIGERANT TABLES INTRODUCTION A Mollier diagram is a graphical representation of the properties of a refrigerant,
Basic Design Considerations for Geothermal Heat Pump Systems 2005 Tri-Service Infrastructure Systems Conference and Exhibition Gary Phetteplace US Army Engineer Research and Development Center Cold Regions
Chilled Water HVAC Systems By Ron Prager, Brinco Mechanical Services, Inc. Types of water based systems: There are three types of HVAC systems that utilize water as a heat transfer medium. The first system,
Geothermal Heat Pumps in Agricultural Applications Oregon Geothermal Working Group Meeting May 17, 2006 Alternative Farming Center, Johnson County, Tennessee Andrew Chiasson Geo-Heat Center Oregon Institute
HOME HEATING USING GEOTHERMAL ENERGY An introduction to using ground sourced central heating in New Zealand Introduction The purpose of this guide is to give the end user the basic information required
www.lgeaircon.com New concept Ecofriendly Highefficiency Heating solution Total heating & Hot water Solution for MULTI V LG Electronics AE Company, Commercial Air Conditioning 2 Yeouidodong, Yeongdeungpogu,
Rainwater Harvesting With climate change now a reality rather than a speculated possibility, the demand on water resources has gone up, whilst the amount of water available for supply has gone down. Forth
How does solar air conditioning work? In a conventional air conditioning system; The working fluid arrives at the compressor as a cool, low-pressure gas. The compressor is powered by electricity to squeeze
Air Conditioning 101 What is Refrigeration? Refrigeration is Cooling by the Removal of Heat Heat is Measured In BTU s A BTU is a British Thermal Unit It is the Amount of Heat to Raise One Pound of Water,
AIRAH Refrigeration (in HVAC) Back to Basics For the First Time Terms of Reference What this session is NOT about Detailed Refrigeration Design Detailed analysis of various Refrigants properties Comparison
COMMERCIAL HEATING VENTILATION & AIR CONDITIONING (HVAC) REBATE FORM Valid July 1 - December 31, 2015 Steps to Getting Your Rebate: 1. Confirm that equipment is eligible. 2. Purchase and install new eligible
A buyer s guide to heat pumps To find out more about installing a heat pump call 0300 123 1234 or visit energysavingtrust.org.uk What are heat pumps? Heat pumps extract available heat from a natural source
Chapter 9: Water Heating 145 CHAPTER 9: WATER HEATING Energy costs for water heating can be as great as the costs for heating, for an energy efficient house, in a mild climate. Estimating hot water usage
AIR CONDITIONING EFFICIENCY F8 Energy eco-efficiency opportunities in Queensland Foundries Hot tips and cool ideas to save energy and money! Air conditioning units or systems are often used by foundries
Demystifying HVAC Test Your HVAC Knowledge By Ron Prager How much do you know about HVAC? Try testing yourself with the following questions and then take a look at the answers on the following page. 1)
9111 05-10 Connecticut Energy Efficiency Fund Home Performance Program Application (Tier II) This application is for energy efficiency retrofit proposals for existing residential unit(s). The application
Air-sourced 90 Hot Water Supplying Heat Pump "HEM-90A" Takahiro OUE *1, Kazuto OKADA *1 *1 Refrigeration System & Energy Dept., Compressor Div., Machinery Business Kobe Steel has developed an air-sourced
air conditioners how to choose a cooling system taking responsibility As an individual, your efficient use of energy brings benefits such as lower bills, improved comfort levels in your home and a reduced
Dehumidification Basics Why do you want to keep indoor Rh between 30-60%? ASHRAE recommends keeping the relative humidity in a home between 30-60% to limit the effects of many unwanted conditions and harmful
Energy Analysis and Comparison of Advanced Vapour Compression Heat Pump Arrangements Stuart Self 1, Marc Rosen 1, and Bale Reddy 1 1 University of Ontario Institute of Technology, Oshawa, Ontario Abstract
Chapter 3.4: HVAC & Refrigeration System Part I: Objective type questions and answers 1. One ton of refrigeration (TR) is equal to. a) Kcal/h b) 3.51 kw c) 120oo BTU/h d) all 2. The driving force for refrigeration
Study on the performance of air conditioning system combining heat pipe and vapor compression based on ground source energy-bus for commercial buildings in north China Yijun Gao, Wei Wu, Zongwei Han, Xianting
A NEW DESICCANT EVAPORATIVE COOLING CYCLE FOR SOLAR AIR CONDITIONING AND HOT WATER HEATING John Archibald American Solar Roofing Company 8703 Chippendale Court Annandale, Va. 22003 e-mail: firstname.lastname@example.org
USER S GUIDE For all Packaged Systems (Air Conditioners and Heat Pumps) WA & WL - Series Air Conditioners WH & SH - Series Air Source Heat Pumps IH - Series Air Source Heat Pumps DATE: 02-21-12 QA - Series
Energy Efficiency Tips for Businesses Top 10 Tips Lighting Tips Heating and Cooling Temperature Control Office Equipment Laundry Service Refrigeration Equipment Food Service Equipment Employee Involvement
s.doty 10-2014 White Paper #30 Hybrid (Dual Fuel) - Gas Heat and Air Source Heat Pump System Switches Fuels Automatically for Economy. What is an Air-Source Heat Pump? A heat pump is a modified air conditioning
1932 Lexington Houston, Texas 77098-4220 (713) 524-4877 The purpose for this information is to provide a better understanding of the HVAC equipment, components, designs, and installations, of HVAC system
Characteristics of Evaporators Roger D. Holder, CM, MSME 10-28-2003 Heat or Energy In this paper, we will discuss the characteristics of an evaporator coil. The variance of the operational condenses of
In the compression-refrigeration loop (air conditioning), which is likely to be warmer? 1. Condenser coil 2. Evaporator coil Answer: (1) Condenser coil See the video. A.R.E. Building Systems Study Guide
QUESTIONS TO ASK WHEN REPLACING YOUR HVAC TOGETHERWESAVE.COM TOGETHERWESAVE.COM IS IT TIME TO REPLACE YOUR HVAC SYSTEM? If your heating and cooling system is 15 to 20 years old and is experiencing problems,
Glossary of HVAC Terms Heating, Ventilation and Air Conditioning (HVAC) is a major sub- discipline of mechanical engineering. The goal of HVAC design is to balance indoor environmental comfort with other
Increasing Natural Gas Boiler Efficiency by Capturing Waste Energy from Flue Gas Mark Schiffhauer, ATSI Engineering Services Cameron Veitch, Combustion and Energy Systems Scott Larsen, New York State Energy
Nordic Heat Pump Product Guide About Maritime Geothermal Maritime Geothermal is a privately owned, Canadian based manufacturer of geothermal heat pumps. We began manufacturing the Nordic line of heat pumps
I Dave s Statement If the thermostat calls for cooling, and the furnace fan is running properly, and the coil airflow is adequate, and the condenser fan is running properly, and the condenser airflow is
Heat Recovery and Compressed Air Systems By Frank Moskowitz for the Compressed Air Challenge Having a fundamental understanding of how your plant s compressed air system works and what forces influence
Geothermal: The Clean Energy Secret May 7, 2008 Published by Dr. Patrick Moore in conjunction with the New York Affordable Reliable Electricity Alliance (New York AREA) Geothermal: The Clean Energy Secret
Kylteknik ( KYL ) Refrigeration course # 424503.0 v. 2014 8. Heat pumps, heat pipes, cold thermal energy storage Ron Zevenhoven Åbo Akademi University Thermal and Flow Engineering Laboratory / Värme- och
DOE/EE-0220 Energy Savings from Dual-Source Heat Pump Technology Dual-source heat pump technology provides added degree of energy efficiency The purpose of this Technology Installation Review is to provide
The Only GUY To Call May 2014 412.885.2356 Why are my utility bills so high? What can I do to lower my energy expenses? Did you know... that between 2007 and 2012, the average U.S. household spent more
Technical Description of the Stockton College Geothermal HVAC Retrofit Harold E. Taylor *, Lynn F. Stiles and William Hemphill December 1997 ABSTRACT The need to replace old, worn out and obsolete Heating,
APPLICATION NOTE An In-Depth Examination of an Energy Efficiency Technology Thermal Energy Storage Strategies for Commercial HVAC Systems Summary...1 How This Technology Saves Energy...2 Types of Demand
NFAT (Need for and Alternatives To) Ground Coupled Heat Pump Systems and MB Hydro Ed Lohrenz, B.E.S., CGD 204.318.2156 email@example.com 1 Ed Lohrenz - background Worked in geothermal industry since 1982
Field test of a novel combined solar thermal and system with an ice store Anja Loose Institute for Thermodynamics and Thermal Engineering (ITW), Research and Testing Centre for Thermal Solar Systems (TZS),
HEAT PUMP FREQUENTLY ASKED QUESTIONS HEAT PUMP OUTDOOR UNIT ICED-UP DURING COLD WEATHER: It is normal for a heat pump to have a build up of white frost on the outside coil during cold damp weather. The
Save money, reduce energy use and earn incentives by improving the energy efficiency of your business. Georgia Power s Commercial Energy Efficiency Program makes incorporating energy-efficient improvements
Hot Water Boilers and Controls Why Condensing Boilers are Different Presented Oct. 14, 2008 Long Island Chapter, ASHRAE H.W. Boilers and Controls Major types of boilers Advantages and disadvantages Resistance
Appendix C Minimum Equipment Efficiency Standards Appendix C: Minimum Equipment Efficiency Standards This Appendix is an overview of building and equipment standards in the State of California that have
FinAnswer Express Utah Incentive Catalog Effective as of May 19, 2012 Heating, Ventilation & Air Conditioning Equipment Rocky Mountain Power provides incentives for many types of energy-efficient technologies.
Propane Gas Underground Systems: Residential Infrastructure Requirements and Energy Benefits AIA Best Practices The Propane Education & Research Council and HanleyWood are registered providers with the