# Tech Tip # 61. Why 400 CFM per Ton is used for Determining Standard Air Conditions Air Volumes

Save this PDF as:

Size: px
Start display at page:

Download "Tech Tip # 61. Why 400 CFM per Ton is used for Determining Standard Air Conditions Air Volumes"

## Transcription

1 Tech Tip # 61 One of a series of dealer contractor Technical advisories prepared by HARDI Wholesalers as a customer service. Why 400 CFM per Ton is used for Determining Standard Air Conditions Air Volumes Equations that explain relationship between temperature and air quantities show why CFM requirements for summer air conditioning change with varying heat loads. The conditioned air quantity for air conditioning should be about 400 CFM per ton of cooling capacity. Does this rule-of-thumb strike a familiar note? Although many dealer-contractors may say, Sure, we've known that for a long time, how many can explain the relationship? Those who can know that they have a broader base from which to seek solutions to air conditioning problems than do those who cannot. Rules-of-thumb are useful guide posts, but only the most simple air conditioning problems can be solved with such rules alone. In an air conditioning system, the circulating air serves as a carrier of heat and moisture either to or from the conditioned space. Let us first consider air as a carrier of heat. We are not so much interested in the total amount of heat the circulating air carries as we are in the change in heat between the point where it enters the conditioned space and the point where it leaves. The difference is the amount of heat which the air has either added to or removed from the space. By careful measurement it has been found that it takes 0.24 Btu to raise one pound of air one degree Fahrenheit. This is known as the specific heat of air. Since we normally deal with cubic feet, not pounds, of air in air conditioning work, we must know another fundamental value, the number of cubic feet which one pound of air will occupy. Because this value varies considerably with the temperature and pressure, calculations are generally based upon air at so called standard conditions (dry air at 70 F and 14.7 lb/sq in.) which has a volume of cu ft/lb. The actual volume occupied by a pound of air at almost any condition may be read from a psychrometric chart. Published by the Independent Study Institute, a division of the Heating, Airconditioning & Refrigeration Distributors International. The Institute offers accredited, industry training courses in HVAC/R technology. Direct inquiries to HARDI 3455 Mill Run Drive, Ste. 820, Columbus, OH Phone 888/ (toll free) 614/ Fax 614/

2 Temperature and its Relation to Quantity We are now prepared to relate air to heat. Suppose we are supplying 300 CFM to a heater. The air enters at 70 F and leaves at 120 F. How much heat has the air picked up in passing through the heater? We use the relationship: Qs = CFM x 60 x 0.24 x 1/13.34 x (T 2 - T 1 ) where: Q is sensible heat in Btuh 60 is min/hr is Btu/lb/deg F is cu ft/lb T 2 - T 1 is temperature change, deg F. Simplifying: Qs = CFM x 1.08 x (T 2 - T 1 ) The simplified equation above is most important and is used both in cooling and heating problems where it is necessary to determine the relationship of air quantity and temperature difference to heat. Notice that in using the factor 1.08 it is assumed that the CFM value is adjusted to standard conditions. Most equipment is cataloged for standard air. Field measured flow can be adjusted to standard conditions by simple proportions of temperature and pressure (using absolute values). The preceding equation shows that the same amount of heat may be conveyed using a large air flow and a small temperature difference or a small air flow and a large temperature difference. Thus, instead of 300 CFM and a 50 F range, we could use 150 CFM with 100 F range or 600 CFM with a 25 F range. Although in each case the total amount of heat is the same, there are practical limitations in each direction. Larger air flows require larger air handling equipment and larger ductwork. Higher temperatures create fire and burn hazards and problems of distribution. As noted previously, air carries moisture as well as heat. Since evaluation of its moisture carrying capacity is more of a problem with cooling than with heating, we shall consider it in this connection. The cooling load is more complex than the heating load, and for that reason the relationship of air quantity to load is not as apparent for the former as it is for the latter. Normally the cooling load is broken down into the following categories: internal sensible, internal total, total sensible and grand total. Internal sensible includes all sources of heat which tend to cause a temperature rise in the conditioned space. These would include heat conducted through walls, floor and roof, solar energy entering through glass, heat from lights, people, appliances, etc., and heat from air which might infiltrate directly. Internal total heat includes internal sensible heat plus latent heat represented by the moisture originating in the conditioned space from people, appliances and direct infiltration.

3 Total sensible heat includes internal sensible heat required to reduce the ventilation air from design outside temperature to room temperature. Grand total heat is the sum of all sensible and latent heat sources represented by the space load calculation and the ventilation load calculation. Since the internal sensible portion of the load includes all heat sources which tend to cause a temperature rise in the conditioned space, it is this heat value which is used in our equation to determine air quantity. As was the case for heating, we can theoretically use any convenient combination of flow and temperature difference that will balance the equation. The temperature difference in this case tells us how much the selected air quantity must be cooled below room temperature in order to remove the unwanted heat. Requirements for dehumidification Just as the internal sensible load is used in determining the amount of air needed to cool a given space, so the internal latent load is used in determining the amount of air needed to dehumidify a given space. If the two problems (heat and moisture) were independent, they could be solved with independent air quantities. Moisture in a conditioned space is in the form of vapor. A pound of dry air at a given temperature can contain variable amounts of vapor up to a maximum. At 70 F, for example, a pound of dry air can have associated with it a maximum of lb of vapor. The air is said to be saturated at this condition and the relative humidity is said to be 100%. If the pounds were only half of maximum, the relative humidity would be only 50%. Because the amount of moisture per pound of dry air is small when expressed in pounds, it is more convenient to express it in grains, there being 7,000 grains to the pound. The weight of vapor for saturated air at 70 F is grains. Vapor is removed from air by chilling it until it condenses to water. For each pound of vapor condensed, approximately 1,050 Btu must be removed by the cooling coil. This is the heat of vaporization. Its removal takes place at constant temperature just as its addition, in the boiling process for example, takes place at constant temperature. The amount of moisture in air is determined most easily from a psychrometric chart using measured values of the dry and wet bulb temperatures. Let us assume that 300 CFM enters a room at 52 F DB, 50 F WB. The chart shows that the air carries 50 grains of moisture per pound of dry air. A corresponding measurement of air leaving the room shows 76 grains per pound. The latent heat which this air carries from the room is calculated as follows: Q L = CFM x 60 x 1/13.34 x 1/7000 x 1050 x (G 2 - G 1 ) where: Q L is latent heat in Btuh 60 is min/hr is cu ft/lb 7,000 is grains/lb 1,050 is heat of vaporization (nominal value) in Btu/lb water (G 2 - G 1 ) is moisture change, grains/lb dry air.

4 Simplifying: Q L = CFM x 0.68 x (G 2 - G 1 ) Q L = 300 x 0.68 x (76-50) = 5,300 Btuh Notice that the equation for Q L can be satisfied by having a small air quantity and large difference in moisture levels or a large air quantity and small difference in moisture levels. The relationship is similar to that described between air quantity and temperature difference in the equation for sensible heat, Q S. Supply Air Varied for Load Requirements We have seen how air is used to carry both sensible and latent heat and how each form of heat, considered independently, can be the basis for calculating the air needed to carry it. We can now proceed to the solution of practical air conditioning problems which generally require that both types of heat be carried simultaneously with the same air quantity. This requires the designer to: first, establish the air quantity; second, create the temperature difference needed for the selected air CFM to convey the sensible heat; third, create the difference in grains needed for the selected air CFM to convey the latent heat. In order to see how supply air conditions are "tailored" to meet a load requirement, let us assume that a certain room is to be maintained at 78 F DB, 50% RH. The room loads are as follows: Internal sensible heat 8,000 Btuh, internal latent heat 1,430 Btuh. The air quantity would be approximated by assuming that the air would be introduced into the room at about 58 F which is 20 degrees below room temperature. Using the equation Q S = CFM x 1.08 x (T 2 - T 1 ) and solving for CFM, we have: CFM = 8,000/1.08 x 20 = 370. If the temperature difference we choose is much larger than 20 degrees, we should have difficulty mixing the cold supply air with room air in a way that would avoid drafts. We might also approach a condition where moisture would freeze on the coil surface. On the other band, if it were much less than 20 degrees, ducts, fans, etc. would become larger and more costly due to the increased CFM. The now established 370 CFM must pick up the internal latent heat of 1,430 Btuh. Using the equation Q L = CFM x 0.68 x (G 2 - G 1 ) and solving for the change in grains of moisture per pound, we have (G 2 - G 1 ) = 1,430/0.68 x 370 = 5.7. In other words, if we introduce air into the room at the rate of 370 CFM which has a moisture level 5.7 grains/lb below the desired room level, we can remove moisture at the rate indicated by the load (1,430 Btuh). From the psychrometric chart, we find the room level of moisture at 78 F DB, 50% RH is 71 gr/lb. The supply air must, therefore, be at = 65.3 gr/lb as well as at 58 F. These two conditions establish the supply air wet bulb temperature as 56.5 F. Summarizing then, 370 CFM at 58 F DB, 56.5 F WB will remove 8,000 Btuh sensible heat and 1,430 Btuh latent heat from a room and hold it at 78 F DB, 50% RH. The final step in the simple problem above would be to select a cooling coil from cataloged values which could cool the required amount of air between the two points. In trying to make a selection, we may find that practical limitations make it advisable for us to revise our original assumption of 20 degrees of cooling to a slightly lower or higher value. This would, of course, change the CFM and the other related values.

5 In the procedure described above, we were required to maintain an exact room condition of 78 F DB, 50% RH. In comfort air conditioning, we strive for exact control of temperature, but we are not so particular about summer humidity as long as it is less than the design value. It is this fact that makes the package or self-contained air conditioner practical. These units are factory engineered with psychrometric characteristics which meet most conditions of average application. In other words, the balance between the sensible and latent heat removing capacities is such that if they are selected for their sensible capacity, they will have at least enough and probably more latent capacity than is needed. If the latter is the case, the room will balance out at a slightly lower relative humidity than was intended by design. We usually do not object to this on a small job. In a large job, however, this might possibly mean more refrigeration capacity and higher operating cost than the design intended and so must be checked carefully. In our opening statement we quoted a rule-of-thumb about air conditioning requiring 400 CFM per ton. This value is usually the basis for rating self-contained air conditioners. Thus, we have a 2-ton unit handling 800 CFM, a 3-ton 1,200, a 5-ton 2,000, a 10-ton 4,000, etc. With 80 F DB 50% RH (77 gr/lb) air entering, these units usually will do about 70 percent sensible cooling and 30 percent latent cooling. On this basis, a 3-ton unit would do 36,000 Btuh total cooling, 25,200 Btuh sensible cooling and 10,800 Btuh latent cooling. With 400 CFM per ton, air would be cooled according to: T 2 - T 1 = 25,200/1,200 x 1.08 = 19.4 F and would leave the coil at 80 F F = 60.6 F. Air would be dehumidified according to: G 2 - G 1 = 10,800/1,200 x 0.68 = 13.2 grains and would leave the coil at = 63.8 grains or 57 F WB.

### THE PSYCHROMETRIC CHART AND ITS USE

Service Application Manual SAM Chapter 630-16 Section 3A THE PSYCHROMETRIC CHART AND ITS USE Psychrometry is an impressive word which is defined as the measurement of the moisture content of air. In broader

### Greenhouse Cooling. Why is Cooling Needed?

Greenhouse Cooling Why is Cooling Needed? Solar radiation is the heat input for the earth can radiate as much as 277 Btu/ft 2 /hr onto the surface of the earth on summer s day in coastal and industrial

### APPLICATION GUIDE. Comparison of Latent Cooling Performance of Various HVAC systems in a Classroom Application

APPLICATION GUIDE Comparison of Latent Cooling Performance of Various HVAC systems in a Classroom Application Section Comparison of Latent Cooling Performance of Introduction Most commercial HVAC systems

### Energy Efficient Building Design College of Architecture Illinois Institute of Technology, Chicago. Relative Humidities RH% 49.4. 0.

Psychrometrics Psychrometric Chart Relative Humidities RH% 49.4 100% 80% 0.030 Enthalpies 70% H btu/lb 46.5 0.028 85 Not to Scale 0.026 Humidity Numbers and Values 43.7 60% Ratios are approximate 0.024

### The Need for Ventilation and Moisture Control for Health, Comfort and Sustainability Nikki Kruger Industry Manager

The Need for Ventilation and Moisture Control for Health, Comfort and Sustainability Nikki Kruger Industry Manager ANTITRUST POLICY STATEMENT FOR SPRAY POLYURETHANE FOAM ALLIANCE MEETINGS It is and shall

### College & University Technicians 46 th Annual PTG Convention & Technical Institute Humidity Control in the Institutional Environment

College & University Technicians 46 th Annual PTG Convention & Technical Institute Humidity Control in the Institutional Environment Period 1 Whole Building Humidity Control Systems By Claud Kissmann,

### TECH TIP # SEER and the TEV Removing the Mystery of the Thermostatic Expansion Valve

TECH TIP # 28 One of a series of dealer contractor technical advisories prepared by HARDI wholesalers as a customer service. 13 SEER and the TEV Removing the Mystery of the Thermostatic Expansion Valve

### Comparing Air Cooler Ratings Part 1: Not All Rating Methods are Created Equal

Technical Bulletin By Bruce I. Nelson, P.E., President, Colmac Coil Manufacturing, Inc. Comparing Air Cooler Ratings Part 1: Not All Rating Methods are Created Equal SUMMARY Refrigeration air coolers (evaporators)

### HVAC Calculations and Duct Sizing

PDH Course M199 HVAC Calculations and Duct Sizing Gary D. Beckfeld, M.S.E., P.E. 2007 PDH Center 2410 Dakota Lakes Drive Herndon, VA 20171-2995 Phone: 703-478-6833 Fax: 703-481-9535 www.pdhcenter.com An

### Navigating the Cooling process on the Psychrometric Chart

Navigating the Cooling process on the Psychrometric Chart Two examples of cooling will be reviewed in the following examples. The first is an example of sensible mechanical cooling and the second is an

### Total Heat Versus Sensible Heat Evaporator Selection Methods & Application

Total Heat Versus Sensible Heat Evaporator Selection Methods & Application Scope The purpose of this paper is to provide specifying engineers, purchasers and users of evaporators in industrial refrigeration

### TECH TIP # 56 MORE ON LADDER DIAGRAMS

TECH TIP # 56 One of a series of dealer contractor technical advisories prepared by HARDI wholesalers as a customer service. MORE ON LADDER DIAGRAMS To complete an electrical circuit you need a source

### UNDERSTANDING AND USING THE HVAC DESIGN REVIEW FORM

Page 1 UNDERSTANDING AND USING THE HVAC DESIGN REVIEW FORM Each of the 38 points of requested information is discussed, and references to the supporting manual are given to substantiate the requirement.

### Glossary of Heating, Ventilation and Air Conditioning Terms

Glossary of Heating, Ventilation and Air Conditioning Terms Air Change: Unlike re-circulated air, this is the total air required to completely replace the air in a room or building. Air Conditioner: Equipment

### Characteristics of Evaporators

Characteristics of Evaporators Roger D. Holder, CM, MSME 10-28-2003 Heat or Energy In this paper, we will discuss the characteristics of an evaporator coil. The variance of the operational condenses of

### Keys to Efficient Dehumidification

Keys to Efficient Dehumidification Jeff Ihnen for Engineered Systems Magazine, May 2009 p 608.785.1900 400 Main Street, Suite 200 La Crosse, WI 54601 Contents Keys to efficient dehumidification... 1 Relative

### Dr. Michael K. West, PE 1 Dr. Richard S. Combes, PE 2 Advantek Consulting / Melbourne, Florida

Optimizing 100% Outside Air Systems with Heat Pipes Dr. Michael K. West, PE 1 Dr. Richard S. Combes, PE 2 Advantek Consulting / Melbourne, Florida Introduction To meet increasingly rigorous building codes

### Hospital Application Guide. Cost-effective climate control for hospitals

Hospital Application Guide Cost-effective climate control for hospitals Munters is the world leader in dehumidification Munters is the largest manufacturer of dehumidifiers in the world. Since developing

### Moisture Control. It s The Dew Point. Stupid! Its not the humidity.

Moisture Control Its not the humidity. It s The Dew Point Stupid! Mike Schell EpiphanyTec Inc. Santa Barbara, CA mschell@epiphanytec.com 805 687-3175 Matching great technology to market need! Topics SHR

### Combination Ratio of a Variable Refrigerant Flow System

Combination Ratio of a Variable Refrigerant Flow System Introduction At first examination, Variable Refrigerant Flow (VRF) technology may seem similar to a traditional split-system. The VRF outdoor unit

### By Tom Brooke PE, CEM

Air conditioning applications can be broadly categorized as either standard or critical. The former, often called comfort cooling, traditionally just controlled to maintain a zone setpoint dry bulb temperature

### THE PSYCHROMETRIC CHART: Theory and Application. Perry Peralta NC State University

THE PSYCHROMETRIC CHART: Theory and Application Perry Peralta NC State University PSYCHROMETRIC CHART Identify parts of the chart Determine moist air properties Use chart to analyze processes involving

### Efficient Humidity Control with Heat Pipes 1

Fact Sheet EES-75 December 1991 Efficient Humidity Control with Heat Pipes 1 Roy Johannesen and Michael West 2 Building moisture is usually controlled by air conditioning (AC), but some installed systems

### air conditioners how to choose a cooling system

air conditioners how to choose a cooling system taking responsibility As an individual, your efficient use of energy brings benefits such as lower bills, improved comfort levels in your home and a reduced

### APPLICATION GUIDE. Moisture Management in Waterborne Climate Systems

APPLICATION GUIDE Moisture Management in Waterborne Climate Systems Contents Introduction 3 WBCS Concept 3 Condensation 4 Moisture Sources in the Space 4 Impact of a High Moisture Load 5 Designing to Manage

### Chapter 5. Measures of Humidity. Phases of Water. Atmospheric Moisture

Chapter 5 Atmospheric Moisture Measures of Humidity 1. Absolute humidity 2. Specific humidity 3. Actual vapor pressure 4. Saturation vapor pressure 5. Relative humidity 6. Dew point Phases of Water evaporation

### Air Conditioning Contractors of America

Air Conditioning Contractors of America WHO IS ACCA???? Industry Manuals Residential D, J, S, H, RS, T, P A manual J load calculation is a measurement of how much heating and cooling capacity a home will

### Dedicated Outdoor Air Systems (D.O.A.S.)

Commercial and Industrial Climate Control Systems Dedicated Outdoor Air Systems (D.O.A.S.) AMDOAS-1 What is it? Why use one? What are my options? Selection considerations Design steps What is it? A separate

### Presentation: The role of dehumidification in improving coating performances.

a technical presentation by Jagdeep Singh, General Manager Technical Drying Services, an associate company of Bry-Air (Asia) PVT. LTD. Abstract: Controlling the dew point at 5 degrees F below the surface

### Creating the Ideal Environment for Accelerated Drying Times on Construction and Restoration Projects

4.02.08 updated Creating the Ideal Environment for Accelerated Drying Times on Construction and Restoration Projects Moisture Removal Systems www.groundheaters.com www.wackerneuson.com Controlling moisture

### MAINTAINING SPACE TEMPERATURE AND HUMIDITY IN THE DIGITAL SWITCH ENVIRONMENT

ESL-IE-94-04-58 MAINTAINING SPACE TEMPERATURE AND HUMIDITY IN THE DIGITAL SWITCH ENVIRONMENT Namir F. Saman, Ph.D., P.E. Visiting Assistant Professor Energy Systems laboratory College Station, Texas ABSTRACT

### Makeup Air For Exhaust Systems In Tight Houses. Tony Jellen Engineering Projects

Makeup Air For Exhaust Systems In Tight Houses Tony Jellen Engineering Projects PA Housing & Land Development Conference February 23, 2012 Effects of Kitchen Ventilation on Residential Dwellings Anthony

### Humid Air. Water vapor in air. Trace Glasses 1% Argon (A) Water vapor (H 2

Humid Air Water vapor in air Oxygen 21% Trace Glasses 1% Argon (A) Water vapor (H 2 O) Carbon dioxide (CO 2 ) Neon (Ne) Helium (He) Krypton (Kr) Hydrogen (H) Ozone (O 3 ) Nitrogen 78% Humid Air Water vapor

### The formula for finding CFM is: CFM = BTUH OUTPUT_ Temp Rise (ACF)* *Altitude correction factor below 1000ft = 1.08

Air Volume Requirement Air conditioning systems are engineered with a specific amount of indoor air passing across the surface of the evaporator coil. The amount of air is measured in cubic feet per minute.

### Venice Library Humidity Study. for Williams Building Diagnostics, LLC 305 15 th Street West Bradenton, FL 34205. Report April 13, 2015

for Williams Building Diagnostics, LLC 305 15 th Street West Bradenton, FL 34205 Report April 13, 2015 Moses & Associates, Inc. 2209 NW 40 th Terrace, Suite A Gainesville, FL 32605 FL License EB-0003097

### Hourly Analysis Program v.4.1 Page 1 of 1

Air System Design Load Summary for Zona 9 DESIGN COOLING DESIGN HEATING COOLING DATA AT Feb 1800 HEATING DATA AT DES HTG COOLING OA DB / WB 32.4 C / 23.1 C HEATING OA DB / WB -0.6 C / -3.2 C Sensible Latent

### EFFECTS OF INDOOR RELATIVE HUMIDITY ON REFRIGERATED DISPLAY CASE PERFORMANCE

P (5, EFFECTS OF INDOOR RELATIVE HUMIDITY ON REFRIGERATED DISPLAY CASE PERFORMANCE Ronald H. Howell, Professor Luis Rosario, Graduate Student Antonio Bula, Graduate Student Department of Mechanical Engineering

### Air Conditioning Design Psychrometrics & Coil Load Calculations

Conditioning Design - Psychrometrics & Load Calculation 1 Conditioning Design Psychrometrics & Load Calculations Conditioning Design Keith E. Elder, P.E. s s are the main devices for transferring energy

### TECH TIP # 37 SOLVING SERIES/PARALLEL CIRCUITS THREE LAWS --- SERIES CIRCUITS LAW # 1 --- THE SAME CURRENT FLOWS THROUGH ALL PARTS OF THE CIRCUIT

TECH TIP # 37 SOLVING SERIES/PARALLEL CIRCUITS Please study this Tech Tip along with assignment 4 in Basic Electricity. Parallel circuits differ from series circuits in that the current divides into a

### Refrigeration Manual. Part 3 - The Refrigeration Load

Refrigeration Manual Part 3 - The Refrigeration Load FOREWORD The practice of refrigeration undoubtedly goes back as far as the history of mankind, but for thousands of years the only cooling mediums were

### Air Water Vapor Mixtures: Psychrometrics. Leon R. Glicksman c 1996, 2010

Air Water Vapor Mixtures: Psychrometrics Leon R. Glicksman c 1996, 2010 Introduction To establish proper comfort conditions within a building space, the designer must consider the air temperature and the

### Criteria for Obtaining Specified Humidity and Temperature Conditions

Criteria for Obtaining Specified Humidity and Temperature Conditions by Clay Hile, Parameter Generation & Control, Inc. Providing a specified humidity and temperature for testing or process control can

### Air Conditioning Psychrometrics

Air Conditioning Psychrometrics Course No: M05-005 Credit: 5 PDH A. Bhatia Continuing Education and Development, Inc. 9 Greyridge Farm Court Stony Point, NY 10980 P: (877) 322-5800 F: (877) 322-4774 info@cedengineering.com

### Refrigeration and Air Conditioning with Psychrometry

Refrigeration and Air Conditioning with Psychrometry Refrigeration is a process of maintaining low temperature in comparison to surrounding temperature. Refrigeration is the process of removing heat from

### How do I measure the amount of water vapor in the air?

How do I measure the amount of water vapor in the air? Materials 2 Centigrade Thermometers Gauze Fan Rubber Band Tape Overview Water vapor is a very important gas in the atmosphere and can influence many

### Measuring The Right Thing For Humidity Control It s the Dew Point Stupid!

Page 1 of 6 Measuring The Right Thing For Humidity Control It s the Dew Point Stupid! By Mike Schell, AirTest Technologies Corp. A version of this article appeared in the June 2004 edition of Indoor Air

### UNDERSTANDING REFRIGERANT TABLES

Refrigeration Service Engineers Society 1666 Rand Road Des Plaines, Illinois 60016 UNDERSTANDING REFRIGERANT TABLES INTRODUCTION A Mollier diagram is a graphical representation of the properties of a refrigerant,

### Troubleshooting an Air Conditioning system. R D Holder Eng. Roger D Holder MSME

Troubleshooting an Air Conditioning system R D Holder Eng. Roger D Holder MSME Troubleshooting of an air conditioning system is a step by step procedure. I have found that a 4 step procedure is the best

### How to Read a Psychrometric Chart

130 135 35 140 145 150 155 160 165 40 35 42 125 41 175 40 610 Meters above Sea Level BAROMETRIC PRESSURE 707 mm of Mercury 115 120.98 1.00 1.02 35 39 38 37 170 165 110 36 105 35 WET BULB TEMPERATURE -

### Energy Efficient Homes: Air Conditioning 1

FCS3262 Energy Efficient Homes: Air Conditioning 1 Wendell A. Porter, Hyun-Jeong Lee, and Kathleen C. Ruppert 2 Quick Facts Heating, ventilation and air conditioning accounts for more than 40% of your

### Presentation Outline. Common Terms / Concepts HVAC Building Blocks. Links. Plant Level Building Blocks. Air Distribution Building Blocks

Presentation Outline Common Terms / Concepts HVAC Building Blocks Plant Level Building Blocks Description / Application Data Green opportunities Selection Criteria Air Distribution Building Blocks same

### Element D Services Heating, Ventilating, and Air Conditioning

Load Calculation Criteria PART 1 - GENERAL 1.01 OVERVIEW A. This section includes requirements for calculating HVAC cooling and heating loads. B. Load calculations must be performed in accordance with

### HVAC Made Easy - Overview of Psychrometrics

PDHonline Course M135 (4 PDH) HVAC Made Easy - Overview of Psychrometrics Instructor: A. Bhatia, B.E. 2012 PDH Online PDH Center 5272 Meadow Estates Drive Fairfax, VA 22030-6658 Phone & Fax: 703-988-0088

### Because here you can see a simple an elementary direct evaporative cooling system this is called as a single stage system you can see from the

Refrigeration and Air Conditioning Prof M. Ramgopal Department of Mechanical Engineering Indian Institute of Technology, Kharagpur Lecture No. # 38 Air Conditioning Systems Welcome back in the last lecture

### Humidification Strategies for Data Centers and Network Rooms

Humidification Strategies for Data Centers and Network Rooms By Tony Evans White Paper #58 Revision 1 Executive Summary The control of humidity in Information Technology environments is essential to achieving

### Glossary of HVAC Terms

Glossary of HVAC Terms Heating, Ventilation and Air Conditioning (HVAC) is a major sub- discipline of mechanical engineering. The goal of HVAC design is to balance indoor environmental comfort with other

### HVAC FORMULAS. TON OF REFRIGERATION - The amount of heat required to melt a ton (2000 lbs.) of ice at 32 F. 288,000 BTU/24 hr. 12,000 BTU/hr.

HVAC FORMULAS TON OF REFRIGERATION - The amount of heat required to melt a ton (2000 lbs.) of ice at 32 F 288,000 BTU/24 hr. 12,000 BTU/hr. APPROXIMATELY 2 inches in Hg. (mercury) = 1 psi WORK = Force

### SECTION 5 COMMERCIAL REFRIGERATION UNIT 21 EVAPORATORS AND THE REFRIGERATION SYSTEM

SECTION 5 COMMERCIAL REFRIGERATION UNIT 21 EVAPORATORS AND THE REFRIGERATION SYSTEM UNIT OBJECTIVES After studying this unit, the reader should be able to Define high-, medium-, and low-temperature refrigeration.

### Presented By: WALTER E. JOHNSTON, PE CEM, CEA, CLEP, CDSM, CPE

Presented By: WALTER E. JOHNSTON, PE CEM, CEA, CLEP, CDSM, CPE

### Application - problems. MEL 806 Thermal System Simulation (2-0-2) Dr. Prabal Talukdar Associate Professor Department of Mechanical Engineering

Application - problems MEL 806 Thermal System Simulation (2-0-2) Dr. Prabal Talukdar Associate Professor Department of Mechanical Engineering IIT Delhi Gas vapour mixture Taking 0 C as the reference temperature,

### NEW PEAK MOISTURE DESIGN DATA IN THE 1997 ASHRAE HANDBOOK OF FUNDAMENTALS

NEW PEAK MOISTURE DESIGN DATA IN THE 1997 ASHRAE HANDBOOK OF FUNDAMENTALS Lew Harriman Director of Research Mason-Grant Consulting Portsmouth, NH ABSTRACT Chapter 26 of the 1997 edition of the Handbook

### Innovent LASER Packaged Fresh Air Conditioning Units

LASER Latent And Sensible Energy Reduction Latent And Sensible Energy Reduction For Outside Air Innovent LASER Packaged Fresh Air Conditioning Units Innovent LASER units provide both sensible and latent

### SAULT COLLEGE OF APPLIED ARTS AND TECHNOLOGY SAULT STE. MARIE, ONTARIO COURSE OUTLINE

SAULT COLLEGE OF APPLIED ARTS AND TECHNOLOGY SAULT STE. MARIE, ONTARIO COURSE OUTLINE COURSE TITLE: Heating, Ventilation and Air Conditioning CODE NO. : HMI 214 SEMESTER: FOUR PROGRAM: AUTHOR: Home Inspection

### Energy-Recovery. Worth the Risk?

engineers newsletter providing insights for today s hvac system designer energy-conscious design ideas Air-to-Air Energy Recovery from the authors Energy consumption costs money, uses natural resources,

### It will be available soon as an 8.5 X 11 paperback. For easier navigation through the e book, use the table of contents.

The System Evaluation Manual and Chiller Evaluation Manual have been revised and combined into this new book; the Air Conditioning and Refrigeration System Evaluation Guide. It will be available soon as

### A Glossary of HVAC Terms:

Since 1979 TACL A537C Doctor COOL & P rofessor HEA T The Team For All Seasons TM A Glossary of HVAC Terms: Confused by the many terms and acronyms surrounding your indoor comfort system? Don t be! This

### Below are detailed instructions for using the EMS load calculator.

Introduction The EMS load calculator is designed to make load calculating as painless as possible. For sizing the equipment, only the first three tabs (Steps 1, 2 & 3) need to be completed. This process

### The Fallacies of Venting Crawl Spaces January 3, 2002 Craig DeWitt, PhD, PE

104 Vista Terrace RLC Engineering, LLC www.rlcengineering.com Clemson, SC 29631 info@rlcengineering.com 864.654.2979 The Fallacies of Venting Crawl Spaces January 3, 2002 Craig DeWitt, PhD, PE Almost 70%

### Energy Efficient Homes: Air Conditioning

Energy Efficient Homes: Air Conditioning Quick Facts The average energy bill for a typical single family home in the U.S. is \$2,200. Roughly 46 percent of the bill, or \$1,012, is spent on heating, ventilation,

### Causes of High Relative Humidity Inside Air Conditioned Buildings. Roger G.Morse AIA, Paul Haas CSP, CIH Morse Zehnter Associates

Causes of High Relative Humidity Inside Air Conditioned Buildings Roger G.Morse AIA, Paul Haas CSP, CIH Morse Zehnter Associates S. FLORIDA AVE. AMBIENT 91 F db / 78 F wb 16,000 HOURS ANNUALLY THAT wb

### Components HVAC General Standards HVAC Guidelines HVAC System Selection Life Cycle Cost Analysis

Components HVAC General System Selection Life Cycle Cost Analysis Outdoor Air Design Values Indoor Air Design Values Outdoor Air Ventilation Welding Ventilation Temperature Control Systems Ductwork HVAC

### SUPPLEMENTING COMMERCIAL HVAC SYSTEMS WITH HVLS FANS

SUPPLEMENTING COMMERCIAL HVAC SYSTEMS WITH HVLS FANS Improving Energy Efficiency and Lowering Energy Costs with HVLS Fans As the cost of energy continues to rise, building designers and engineers are constantly

### DEHUMIDIFICATION: Supermarket Humidity Control Design Guide

DEHUMIDIFICATION: Supermarket Humidity Control Design Guide The Humidity Expert Supermarket Humidity Control Design Guide A Supermarket environment is one of the most unique in the commercial arena. The

### Pressure Enthalpy Explained

Pressure Enthalpy Explained Within the new F Gas course the requirement for an understanding of Pressure Enthalpy (Ph) graphs is proving to be a large learning curve for those who have not come across

### Specific Volume of Liquid (Column 7). The volume per unit of mass in cubic feet per pound.

Steam Tables What They Are How to Use Them The heat quantities and temperature/ pressure relationships referred to in this Handbook are taken from the Properties of Saturated Steam table. Definitions of

### Pool Dehumidification Basics

Copyright 2009 Wescor. All rights reserved. Permission granted to reproduce for personal and educational use only. When energy costs were low, many pool owners considered only first cost when choosing

### Recover Heat from Boiler Blowdown Water

Prepared for California Energy Commission (CEC) Prepared By: Southern California Gas Company (A Sempra Energy Utility) E3M Inc. May 2012 i Disclaimer The CEC and its contractor, Southern California Gas

### Home Energy Evaluation Report

Home Energy Evaluation Report Nate Begeman, 1550 Saint Francis Dr San Jose, CA 95125 Air Infiltration Current Air Leakage 2,852 Current Air Changes Per Hour 0.91 Recommended Air Changes Per Hour 0.35 Percent

### > Executive summary. Explanation of Cooling and Air Conditioning Terminology for IT Professionals. White Paper 11 Revision 2. Contents.

Explanation of Cooling and Air Conditioning Terminology for IT Professionals White Paper 11 Revision 2 by Tony Evans Click on a section to jump to it > Executive summary As power densities continue to

### Whole House Dehumidification for Occupant Comfort and Energy Savings

Downloaded from www.rsrews.com. Since 1968, RS Andrews has proudly served Atlanta's Heating, Air Conditioning & Plumbing Needs. Whole House Dehumidification for Occupant Comfort Energy Savings June 2009

### Smaller. Quieter. Smarter.

Smaller. Quieter. Smarter. Product Guide Dehumidifiers Welcome to Aprilaire Aprilaire, Your Partners in Comfort offers a complete line of dehumidifiers designed to meet the ever increasing needs of today

### Air Conditioning Clinic

Air Conditioning Clinic Cooling and Heating Load Estimation One of the Fundamental Series April 2011 TRG-TRC002-EN Cooling and Heating Load Estimation One of the Fundamental Series A publication of Trane,

### WFLO Commodity Storage Manual

Condensation Control Revised 2008 Two manifestations of condensation that must be controlled are: 1. Fogging at entrance doors to frozen food storage spaces. 2. Moisture condensation on packages brought

### Comfort Conditioning & Indoor Air Quality

This article was published in ASHRAE Journal, May 2011. Copyright 2011 American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. Reprinted here by permission from ASHRAE at www.newellinstruments.com.

### Refrigeration Basics 101. By: Eric Nelson

Refrigeration Basics 101 By: Eric Nelson Basics Refrigeration is the removal of heat from a material or space, so that it s temperature is lower than that of it s surroundings. When refrigerant absorbs

### Grain Drying Tools: Equilibrium Moisture Content Tables and Psychrometric Charts

DIVISION OF AGRICULTURE R E S E A R C H & E X T E N S I O N University of Arkansas System Agriculture and Natural Resources FSA1074 Grain Drying Tools: Equilibrium Moisture Content Tables and Psychrometric

### Walnut Drying Design and Operation. Selecting Dryer Type. Tray Drying Before 1920. Don Osias Jim Thompson

Walnut Drying Design and Operation Don Osias Jim Thompson Selecting Dryer Type Tray Drying Before 1920 1 Stack Dryer Energy efficient High capital cost Pothole For small lots High labor cost Hopper-bottom

### Humidification Strategies for Data Centers and Network Rooms

Humidification Strategies for Data Centers and Network Rooms White Paper 58 Revision 3 by Tony Evans > Executive summary The control of humidity in Information Technology environments is essential to achieving

### High Altitude HVAC. Silvertip Integrated Engineering Consultants mhaughey@earthlink.net www.silvertipconsultants.com

Presentation to: Rocky Mountain ASHRAE 2013 Tech Conference April 19, 2013 High Altitude HVAC Design Considerations by: Michael D. Haughey, PE, HBDP, CEM, LEED TM AP 2013 Silvertip Integrated Engineering

### AIR CONDITIONING EFFICIENCY F8 Energy eco-efficiency opportunities in Queensland Foundries

AIR CONDITIONING EFFICIENCY F8 Energy eco-efficiency opportunities in Queensland Foundries Hot tips and cool ideas to save energy and money! Air conditioning units or systems are often used by foundries

### Engineering White Paper UTILIZING ECONOMIZERS EFFECTIVELY IN THE DATA CENTER

Engineering White Paper UTILIZING ECONOMIZERS EFFECTIVELY IN THE DATA CENTER SUMMARY A proper balance of temperature and humidity control is essential for efficient data center operation, and integral

### FBQ. DC Duct Heat Pump or Cooling Only

FBQ DC Duct Heat Pump or Cooling Only EXPERTISE AND INNOVATION Daikin s FBQ DC Duct systems offer a powerful solution, compact in design and easily concealed in a ceiling. With both cooling only and heat

### Calculating Total Cooling Requirements for Data Centers

Calculating Total Cooling Requirements for Data Centers By Neil Rasmussen White Paper #25 Revision 2 Executive Summary This document describes how to estimate heat output from Information Technology equipment

### Energy Efficiency. Energy Efficient Home Cooling:

Energy Efficiency Energy Efficient Home Cooling: Choosing an air conditioning system is an important decision. A poor choice may be costly to purchase and operate and yet fail to provide the desired cooling

### Dehumidification in Industrial and Building Applications

PDHonline Course M227 (4 PDH) Dehumidification in Industrial and Building Applications Instructor: A. Bhatia, B.E. 2012 PDH Online PDH Center 5272 Meadow Estates Drive Fairfax, VA 22030-6658 Phone & Fax:

### CHAPTER 3. BUILDING THERMAL LOAD ESTIMATION

CHAPTER 3. BUILDING THERMAL LOAD ESTIMATION 3.1 Purpose of Thermal Load Estimation 3.2 Heating Load versus Cooling Load 3.3 Critical Conditions for Design 3.4 Manual versus Computer Calculations 3.5 Heating