2 Introduction - Please be sure to read and understand Precautions and Introductions in CX-One Setup Manual, CX-Programmer Operation Manual and CX-Integrator Operation Manual before using the product. - This Guide describes the basic operation procedure of CX-Programmer. Refer to the Help or the Operation Manual of the PDF file for detailed descriptions. - Acrobat Reader 5.0 or later is required to read the PDF files. - You can display the PDF files from the [Start] menu on your desktop after installing the CX-Programmer. - The screen views used in this guide may be different from the actual view, and be subject to change without notice. - The product names, service names, function names, and logos described in this guide are trademarks or registered trademarks of their respective companies. - The symbols (R) and TM are not marked with trademarks and registered trademarks in this guide respectively - The product names of the other companies may be abbreviated in this guide.
3 Table of Contents Chapter 1 Overview and Installation of CX-One 1. What is CX-One? 2. Features of CX-One 3. Integrated Simulation 4. CX-One Installation Procedure Chapter 2 Example of PLC Construction by CX-One Workflow in This Chapter 1. Design 1-1. Starting CX-Programmer 1-2. Creating Unit Configuration 1-3. Setting CPU Bus Units and Special I/O Units 1-4. Checking I/O Assignment 1-5. Programming 1-6. Offline Debug 1-7. Saving a Project 2. Online Debug on a Machine 2-1. Reading a Project 2-2. Online Connection to PLC 2-3. Transferring to a Machine 2-4. Program Debug 3. / Adjustment On-site 3-1. Program Modification 3-2. Unit Parameter Change Chapter 3 Example of PLC Network Construction by CX-One Workflow in This Chapter 1. PLC Network PLC DeviceNet NT CompoWay/F Saving Configuration Adjustment On-site 2-1. Configuration Verification Diagnosis Checking CompoNet Network Servo/Inverter Settings 3-1. DeviceNet Connection RS232C Connection
6 1. What is CX-One? CX-One is an FA Integrated Tool Package that integrates Support Software for OMRON's PLC and other Components. To construct an FA based mainly on PLC, traditionally it was necessary to purchase and install individual Support Software compatible with each Unit, start the software individually, and then connect to PLC and individual Components. Installation of this FA Integrated Tool Package "CX-One" on a personal computer allows integrated operation from setup of OMRON's CPU Bus Units and Special I/O Units (SIOU) and Components to network start-up/monitoring and improving efficiency of PLC start-up. 2. Features of CX-One CX-One allows integrated management of Support Software for OMRON's PLC/Components. Installation on only one personal computer allows a user to handle Support Software for OMRON's products. Only one licensing key is required to install all Support Software. It allows integrated management of one save location for files created by Support Software. Support Software dedicated to CPU Bus Units and Special I/O Units can be started on the I/O Table. The appropriate dedicated Support Software can be automatically started by specifying a registered Unit in the I/O Table (Unit configuration table attached to a PLC). In addition, setup information such as PLC model can be passed to the dedicated Support Software at start-up, allowing easier switching between Support Software. The following functions are available by the introduction of the ID information file (CPS) for OMRON Components. Setup of CPU Bus Units and Special I/O Units without manual setting and address recognition. (Parameter and selection item names as well as available range of setup are automatically displayed) CPU Bus Units and Special I/O Units setting on personal computer and data on actual PLC (CPU Unit ) can be verified online, and unmatched item/readout data is displayed graphically. Unit configuration is displayed on the I/O Table based on Unit model. Device type on the network can be checked for its Unit model, allowing exact verification of network configuration. What is CPS? CPS (Component and network Profile Sheet) is definition information of CS/CJ series Unit/Components in CX-One. It is provided as a CPS file (XML format file). CX-One recognizes CS/CJ series Unit by information in this CPS file. CPU Bus Units and Special I/O Units setting is created based on this CPS file.
7 3. Integrated Simulation Integrated Simulation Overview: Integrated Simulation is a function of CX-One (version 2.0 or higher) that simultaneously tests interoperability between the ladder program and PT (touch panel) and checks screen operation on the computer. Earlier Versions: Operation checks had to be performed separately on the ladder program and PT (touch panel) screens. In addition, the program had to be downloaded to the devices. Using Integrated Simulation: Provides an interoperability check between the ladder program and touch panel screens. Operation can be verified before actual devices such as the PLC and PT (touch panel) are installed and wired, so software quality can be improved in the design stage. Time can be saved by eliminating the tasks up to downloading the screen data from the computer to the PT. The operation of both the PLC and PT (touch panel) can be verified simultaneously in the computer, which greatly reduces the time required for debugging and equipment downtime during improvements. Simulation of the PLC PT (touch panel) system can be started easily, with one click of an icon. Ladder program Touch panel screen One click CX-Programmer CX-Designer ed and simulation started.
8 Integrated Simulation Procedure Use the following procedure to execute an integrated simulation of the ladder program and PT (touch panel) screen. For details, refer to the CX-Designer Operation Manual and CX- Programmer Operation Manual. 1. Create the screen data in the CX-Designer. 2. the Icon or select Tools Integrated Simulation. The PLC-PT Integrated Simulation Dialog Box will be displayed. 3. the Browse Button and select the desired ladder program (CXP) file. 4. the Start Button. The PLC-PT Integrated Simulation will start automatically. 5. The test window will be displayed. The Test Tool Window will list all of the communications addresses being used in the displayed screen. For example, when Host SERIAL A is connected to the CX-Simulator, the CX- Simulator value is reflected in the SERIAL A communications address. (The values can also be changed.) Test Tool Test Window
9 4. CX-One Installation Procedure Before installing the CX-One, you must: Terminate all Windows programs Uninstall previous versions of of Support Software (such as CX-Programmer) if if already installed. Installation takes about 10 to to 40 minutes depending on your personal computer. (10 minutes for a personal computer with CPU: Celeron 2.2GHz, main memory: 512MB, and CD-ROM drive: 48x) To change/modify/delete CX-One after installation, refer to to the PDF manual CX-One Setup Manual, Chapter 2 Installation and Uninstallation. Installing CX-One In case of the installing procedure by CD-ROM: Insert CX-One installation disk 1 (CD-ROM) into your personal computer s CD-ROM drive. [Choose Setup Language] dialog box is displayed. By default the OS language installed on your personal computer is automatically selected. Check if the language is appropriate, then click the [OK] button. [OK] The CX-One splash screen is displayed and CX-One installation starts. Uninstall older version of tools such as PLC Tools (PLC setting and I/O Table), CX-Server, and CX-Programmer if they have been installed. Always click [OK] Uninstalling CX-Programmer Uninstalling CX-Server
10 CX-One setup wizard starts. [Next] The [License Agreement] dialog box is displayed. Read the software license agreement carefully. If you agree with all items, select the [I accept the terms of the license agreement] radio button and click the [Next] button. Select the radio button [Next] The [User information] dialog box is displayed. Enter [User], [Company], [License] (product serial number of CX-One) [Next]
11 Select an installation folder, then click [Next] Select the radio button [Complete] The [Installation Folder Selection] dialog box and [Setup Type] dialog box are displayed. By selecting [Custom], you can individually select and install Support Software from the CD-ROM. [Next] Read the message and click [Next] The [Program Folder Selection], [Choose Destination Location of OMRON FB Library], [Select Program Folder], and [Ready to Install the Program] dialog boxes are displayed. Insert CX-One Disks 2 and 3 then click the [OK] button. [Install] CX-One installation is starts. A dialog box (right) is displayed. the [Finish] button to finish the installation wizard. Installation is complete. (When it is necessary to restart the personal computer, a restart confirmation dialog box appears.) [Finish]
12 Online Registration If the personal computer that the software has been installed on has an Internet connection, you can proceed to online user registration. After installation has been completed the [Online Registration] dialog box is displayed. If you click the [Register] button, your Web browser connects to OMRON s CX-One Web site.(*1) (*2) *1: If you click the [Exit] button to cancel online registration, the [Online Registration] dialog box is displayed every time the CX-One Support Software is started. *2: If you do not have an Internet connection, or you do not want to register online, fill out and send the user registration card that comes with the product.
14 Example of PLC Construction by CX-One Workflow in This Chapter This chapter describes an example of PLC construction from design, online debugging on the actual machine, and start-up/adjustment on-site as shown below. CX-Programmer is used for ladder program creation and CPU Bus Units and Special I/O Units (SIOU) setting, while CX-Designer is used for indicator screen generation. Also, a program simulation Support Software CX- Simulator is used as a debugging example. Starting CX- Programmer Creating Unit Configuration Setting CPU Bus Units/SIOU Checking I/O Assignment Programming Offline Debug Saving Project Design Online Debug of the Machine /Adjustment On-Site Reading Project Online Connection to PLC Transferring to Machine Program Debug Program Modification Unit Parameter Change CX-One Configuration Connection Cable CS1W-CN226(2m) PLC1 CJ Series PLC CJ1M CJ1W-ID211 4 ~ 20mA Connection Cable XW2Z-200T(2m) NS Series PT Sensor NS8-TV00B-V1 Version 6.0 or later CJ1W-OC211 CJ1W-AD081-V1 Unit No.= 21 CJ1W-NCF71 (CJ1W-MCH71) Unit No.= 2Hex CJ1W-DRM21 Unit No.= 0Hex Node Address= 01 CJ1W-SCU41-V1 Unit No.= 3Hex CJ1W-CLK21-V1 Unit No.= 1Hex Node Address= 01 Termination Resistance Setting= ON Servo Driver R88D-WN01L-ML2 Unit Name Power Unit CPU Unit DC Input Unit Transistor Output Unit Analog Input Unit Position Control Unit Motion Control Unit DeviceNet Master Unit Unit Serial Communications Unit Servo Driver NS Series PT Model CJ1W-PA202 CJ1M-CPU13 CJ1W-ID211 CJ1W-OC211 CJ1W-AD081-V1 CJ1W-NCF71 CJ1W-MCH71 CJ1W-DRM21 CJ1W-CLK21 CJ1W-SCU41-V1 R88D-WN01L-ML2 NS8-TV00B-V1 Specifications 640 points, 20K steps 4 analog inputs (Each point selectable from 1~5V, 0~5V, 0~10V, -10~10V, 4~20mA) Maximum control: 16 axis Maximum control: 30 axis 8 inches TFT Below is an example of a that has CJ1M CPU Unit with basic input/output Unit as well as analog input Unit and NCF Unit to perform the following functions: 4~20mA input from a sensor Configure a servo driver connected to the NFC Unit.
15 Design Starting CX- Programmer Creating Unit Configuration Setting CPU Bus Units/SIOU Checking I/O Assignment Programming Offline Debug Saving a Project Starting CX-Programmer Starting CX-Programmer From the [Start] menu, select [Programs] > [OMRON] > [CX-One] > [CX-Programmer] > [CX- Programmer] to start CX-Programmer. (Or select [All Programs] > [OMRON] > [CX-One] > [CX-Programmer] > [CX-Programmer]) Creating a New Project this button to create a new CX-Programmer project.. Dedicated Support Software for each Unit can be started, succeeding communications settings from CX-Programmer. You will not have to set up communications using dedicated Support Software if you set up communications here. and select PLC model. Left-click and select CPU type. Select a PLC model from the following to use Function Blocks. CJ2H, CS1G-H, CS1H-H, CJ1G-H, CJ1H-H, CJ1M [OK] and determine CPU type.
16 Design Starting CX- Programmer Creating Unit Configuration Setting CPU Bus Units/SIOU Checking I/O Assignment Programming Offline Debug Saving a Project Double-click [ I/O Table and Unit Setup] Creating Unit Configuration Start the I/O Table/Unit setup function. When you select [Option] > [Consumption(mA)] from the menu, you can check the width and current consumption after PLC Unit configuration. (Width indication is available only for SYSMAC CJ Series) Double-click [ I/O Table and Unit Setup]. Right-click Empty Slot, select [Add Unit] and determine CPU type. Then select [General Purpose Analog I/O] from Unit selection window. Right-click Select [Add Unit] + symbol on analog I/O
17 Design Starting CX- Programmer Creating Unit Configuration Setting CPU Bus Units/SIOU Checking I/O Assignment Programming Offline Debug Saving a Project Select Unit Type. Select Unit and Number. Enter Unit number.
18 Design Starting CX- Programmer Creating Unit Configuration Setting CPU Bus Units/SIOU Checking I/O Assignment Programming Offline Debug Saving a Project The Analog Unit is registered to the I/O Table as shown below. Set up the next analog Unit s parameter. Double-click the analog Unit The Analog Unit Setup Screen is displayed. CPU Bus Units and Special I/O Units Setting Function Traditionally, initial CPU Bus Unit and Special I/O Unit settings were made by referring to documentation to calculate DM address from the Unit number and entering a hexadecimal number. Now you can set it using the pull-down menu in the CX-Programmer s I/O Table. Easy setup/transfer/verification operations are available from the integrated parameter settings screen as shown below, without recognizing addresses (this function uses CPS function of CX-One previously described). Setting CPU Bus Units and Special I/O Units For example, specify input number designation and range. Unit parameter setting Select [Enable] for input No.1 usage designation. Select [1~5V/4~20mA] for input No.1 range setting. the [OK] button.
19 Design Starting CX- Programmer Creating Unit Configuration Setting CPU Bus Units/SIOU Checking I/O Assignment Programming Offline Debug Saving a Project NCF Unit and Servo Driver Connected to the NCF Unit Setup As with Analog Unit registration, register the NCF Unit (CJ1W-NCF71). The NCF Unit resides within a position control Unit. Nest, start CX-Motion-NCF using [Start with Settings Inherited]. When opening a stored project file after starting the dedicated tool, select [Start Only]. If [Start with Setting Inherited] is selected, a new project is created. Right-click NCF Unit Point [Start Special Application] [Start with Settings Inherited] Double-click NCF Unit Register a servo driver. Displayed with NCF Unit registered. Double-click NCF Unit. Select OMRON W series (with communications function). Select R88D-WN01L-ML2.
20 Design Starting CX- Programmer Creating Unit Configuration Setting CPU Bus Units/SIOU Checking I/O Assignment Programming Offline Debug Saving a Project Edit NCF Unit parameters. Double-click NCF Unit Double-click NCF Unit. Set output relay area to CIO100 and input relay area to CIO500. Select [Axis 01]. Select [Communications Setting] Set axis parameters for axis 01. Edit servo parameters. Double-click the servo driver Set servo parameters for axis 01 as shown below. Pn50A(input signal selection 1): 2881 Pn50B(input signal selection 2): 8883 Pn511(input signal selection 5): 6541 Save the project Refer to Page 2-13 Saving Project for details.
21 Design Starting CX- Programmer Creating Unit Configuration Setting CPU Bus Units/SIOU Checking I/O Assignment Programming Offline Debug Saving a Project Using the MCH Unit When using the MCH Unit (CJ1W-MCH71) instead of the NCF Unit, use the following settings. As with Analog Unit, register the MC Unit to the I/O table. The MCH resides within the Motion. Then start CX-Motion-MCH using [Start with Settings Inherited]. When opening a stored project file after starting the dedicated tool, select [Start Only]. If [Start with Setting Inherited] is selected, a new project is created. Right-click MCH Unit Point [Start Special Application] Select [Start with Setting Inherited] Start the MCH Unit as registered. Add task, axis, program, and CAM data program, and CAM data. to add task, axis, Edit position data, parameters, program, and CAM data Open the editing screen to edit data by double-clicking position data, parameter, program, or CAM data on the project tree. Save the project and save the project to file.
22 Design Starting CX- Programmer Creating Unit Configuration Setting CPU Bus Units/SIOU Checking I/O Assignment Programming Offline Debug Saving a Project Checking I/O Assignment As with Analog Unit registration, register the IN and OUT Units. Register basic I/O Unit In this example, CJ1W-ID211 and CJ1W-OD211 are selected as IN and OUT Units respectively. By registering Units to the I/O Table, you can check I/O assignment status. Check I/O assignment In addition, you can check addresses assigned to actual I/O with a print out. This I/O assignment information can also be checked by IQ indication (IN:I, OUT:Q) during ladder programming.
23 Design Starting CX- Programmer Creating Unit Configuration Setting CPU Bus Units/SIOU Checking I/O Assignment Programming Offline Debug Saving a Project Programming This section describes programming with Library (OMRON Standard Libraries) that allows easier connection to OMRON s Components. OMRON Standard Libraries is a group of Components provided by OMRON, which can be categorized into two types; FB Components (OMRON FB Library) to be used for a ladder program and SAP Components (Smart Active Parts Library) to be used for an indicator. NCF Unit Programming with OMRON FB Library Servo motor (axis 1) connected to Unit number 0 NCF is moved to position 2000 (command Unit) with speed of 2000 (command Unit/s) by relative move command. CPU &0 NCF Unit No.: 0 Servo Motor (Axis 1) Servo Motor No.1 (Axis 1) W10.00 W10.01 W10.03 W10.04 W10.05 W10.02 Start Trigger W10.02 (ENO) Done Command Aborted Error Start No.2 Start No.2 P_On (Normally ON) Unit No. &0 Axis No. Axis 1 &1 Start No.2 W10.02 Position Command 2000 Command Unit &2000 Velocity Command 2000 Command Unit/s &2000 _NCF021_MoveRelative_DINT EN (BOOL) (BOOL) ENO UnitNo (BOOL) (INT) Done Axis (BOOL) (INT) Command Aborted Execute (BOOL) (BOOL) Error Position (WORD) (DINT) ErrorID Velocity (DINT) ENO Positioning is completed W10.03 Command is aborted W10.04 Error Flag W10.05 (Omitted) Right-click from Function Blocks Select a folder from [Omronlib] > [Position ] > [NCF] Select OMRON FB Library "_NCF021_MoveRelative_ DINT11.cxf" Paste the selected OMRON FB Library on the ladder, then enter its name (instance name) (in this example, MoveRelative ). Then create a ladder program as shown below. Enter MoveRelative for instance name. Then create a ladder program OMRON FB Library is a collection of Components that OMRON provides as a Function Block to use functions of OMRON s Units for PLC and FA Components much easier on a PLC program. * For details, see FunctionBlock StructuredText Introduction Guide, Chapter 1.
24 Design Starting CX- Programmer Creating Unit Configuration Setting CPU Bus Units/SIOU Checking I/O Assignment Programming Offline Debug Saving a Project How to use Smart Active Parts See Library This section describes how to use Smart Active Parts. In this example, NCF Smart Active Parts Adjust Operation is used. From [Start] menu, select [Programs] > [OMRON] > [CX-One] > [CX-Designer] > [CX-Designer Ver. ] to start CX-Designer. (Or select [All Programs] > [OMRON] > [CX-One] > [CX-Designer] > [CX-Designer Ver. ].) Select [NS8-TV0-V1] and [ Version 6.0] or later. Select [Library] from the [Tools] menu Place Smart Active Parts on the screen. 1. Select SmartActiveParts_E -Motion - NCF - OutCIO_InCIO folder 2. Select _NCF001_xx _Adjust Operation (Check the Title) Setup Smart Active Parts 4. The selected Smart Active Parts are displayed on the screen. 3. Drag & drop it on the screen. 1. Double-click 2. Set 4 to the Destination Unit No. 3. [OK] Smart Active Parts Setting is is complete Setup is completed at 100% Save the Project. Refer to Page 2-13 Saving Project for details. 4. Communication address is automatically calculated according to the corresponding Unit.
25 Design Starting CX- Programmer Creating Unit Configuration Setting CPU Bus Units/SIOU Checking I/O Assignment Programming Offline Debug Saving a Project Offline Debug This section describes how to debug a program using CX-Simulator, a ladder simulation tool, without the PLC. Additionally, Switch Box Utility is used as a virtual input tool. (Simulator connection button) [OK] Program transfer starts. [OK] Screen when online CX-Simulator debug console is starts Starting Switch Box Utility Select [Tools] > [SwitchBox Utility] Run PLC Switch Box Utility It is useful not only for virtual input by simulator but also for debugging while checking the PLC s wiring or setting the DM and other initial values.
26 Design Starting CX- Programmer Creating Unit Configuration Setting CPU Bus Units/SIOU Checking I/O Assignment Programming Offline Debug Saving a Project Saving a Project Saving a CX-Programmer file Unit setting, Unit parameter setting, and programs using the CX-Programmer can be saved all at once. From the [File] menu, select [Save As ] Save it with a name. In this example save as Sample1. Saving CX-Designer and CX-Motion-NCF/MCH files Created data can be saved for CX-Designer and CX-Motion-NCF/MCH. Save CX-Motion-NCF as Sample2.mnf (CX-Motion-MCH as Sample5.mnh ), and CX- Designer as Sample3.ipp. Saving screen for CX-Motion-NCF Saving screen for CX-Designer If If you run a dedicated Support Software such as CX-Motion-NCF or or CX-Designer when CX- Programmer is is started, the same default folder location as that of of CX-Programmer is is used for reading and saving files. It It allows easier CX-One Support Software file management.
27 Online Debug on a Machine Reading a Project Online Connection to PLC Transferring to a Machine Program Debug This section describes connection to the machine, transfer of programs, creating Unit settings offline, and how to debug. From [File] > [Open], select the file name Sample1 Reading a Project Use CX-Programmer to read the project Sample1 saved in the previous section. or Ladder program Sample1 is retrieved. In I/O Table Unit setting function, the Unit parameter setting configured in the previous section is also retrieved. Double-click the I/O Table Unit setting
28 Online Debug on a Machine Reading a Project Online Connection to PLC Transferring to a Machine Program Debug Online Connection to PLC Verify that PLC model and communications setting created offline and the actual PLC are correct. Double-click PLC Check PLC model. Check communications setting. Confirm that automatic communication speed recognition is checked. (Online connection button) If If a connection cannot be established with the PLC, you can use the automatic online connection function. Save your current project data before using this function because it it clears project data being edited. When USB conversion cable (CS1W-CIF31) is used for connection, specify the COM port number of the USB port used. (Automatic online connection button)
29 Online Debug on a Machine Reading a Project Online Connection to PLC Transferring to a Machine Program Debug Transferring to the Machine Transfer programs and Unit setting parameters created by offline project to the PLC. In this example, data is sent at the same time to various Units using the batch transfer function. [Data to be sent] CPU Unit: Ladder program and PLC setting data, I/O Table data CPU Bus Units and Special I/O Units: AD Unit: Range setting of inputs (1~5v / 4~20mA mode) Select [PLC] > [Transfer] > [To PLC] [Transfer All] [Yes]. Program transfer starts. [OK]. Next Page CX-One CJ1W-OC211 CJ1W-AD081-V1 Unit No.= 21 Connection Cable CS1W-CN226(2m) CJ1W-NCF71 (CJ1W-MCH71) Unit No.= 2Hex Program and configuration data are are transferred at at the the same time to to CPU Bus Units and Special I/O I/O Units. PLC1 CJ Series PLC CJ1M CJ1W-DRM21 Unit No.= 0Hex Node Address= 01 CJ1W-SCU41-V1 Unit No.= 3Hex CJ1W-ID211 4 ~ 20mA Connection Cable XW2Z-200T(2m) NS Series PT Sensor NS8-TV00B-V1 Version 6.0 or later CJ1W-CLK21-V1 Unit No.= 1Hex Node Address= 01 Termination Resistance Setting= ON Servo Driver R88D-WN01L-ML2
30 Online Debug on a Machine Reading Project Online Connection to PLC Transferring to a Machine Program Debug Then data is sent at the same time to NCF Unit and the servo driver connected to NCF Unit. [Data to be sent] NCF Unit: Common parameters, axis parameters Servo Driver: Servo parameters From CX-Programmer, display the I/O Table, then start CX-Motion-NCF by [Start Only]. Right-click NCF Unit Point [Start Special Application] [Start Only] Open a saved project and transfer all NCF Unit and servo driver parameters. To prevent a servo driver operation using a ladder program, you must set the PLC to PROGRAM mode. Select Sample2.mnf If it does not go online, click and check the communications setting between the personal computer and PLC. Double-click NCF Unit Double-click NCF Unit.
31 Online Debug on a Machine Reading Project Online Connection to PLC Transferring to a Machine Program Debug The Unit restart confirmation screen will be displayed during data transfer. the [OK] button after confirming safety. Also, in the case of communication was not established between the NCF Unit and the servo driver, confirm the axis number and restore power to the NCF Unit and servo driver. When parameter transfer is completed, confirm that communications is performed normally and has not resulted in an error. Monitor the NCF Unit. Confirm consistent scan list (axis configuration) and communications status and that no axis or common Unit error has resulted. Terminate Unit monitoring. Next, perform jog operation. Carefully read the displayed cautions, then perform the operation. To perform jog operation, it is required to establish a connection, servo lock, and jog setting. [Online] > [Test Run]
32 Online Debug on a Machine Reading Project Online Connection to PLC Transferring to a Machine Program Debug When using the MCH Unit, transfer data from the CX-Motion-MCH to the MCH Unit and servo driver connected to the MCH Unit. [Data to be transferred] MCH Unit: parameter, position data, program, CAM data. Servo driver: servo parameter Display the I/O table from CX-Programmer and start CX-Motion-MCH with [Start Only]. (Refer to NCF Unit for starting from the I/O table.) Open the saved project and transfer Unit parameter, position data, program, CAM data, and servo driver parameters to the MCH Unit. To prevent a servo driver operation using a ladder program, you must set the PLC to PROGRAM mode. Select file.mnh [Open] If it does not go online, doubleclick PLC in the project tree and check the communication settings between the personal computer and PLC. Select [All Data] Select [With Servo Parameter] [OK] The Unit restart confirmation screen will be displayed during data transfer. the [OK] button after confirming safety. Also, in the case of communication was not established between the MCH Unit and the servo driver, confirm the axis number and restore power to the MCH Unit and servo driver.
33 Online Debug on a Machine Reading Project Online Connection to PLC Transferring to a Machine Program Debug Transferring NS screen data Start NS transfer program This section describes how to transfer screen data to the NS through PLC without changing cables. From [Start] menu, select [Programs] > [OMRON] > [CX-One] > [CX-Designer] > [CX-Designer Ver. ] to start CX-Designer. (Or select [All Programs] > [OMRON] > [CX-One] > [CX-Designer] > [CX-Designer Ver. ].) Open a project saved in the previous section. Select [Transfer]-[Transfer[To PT ]] from the [PT] menu. on Setup communication route Check Pass thru PLC in the Comm. Method window *Communication between the NS and the PLC must be established before transferring screen data through PLC without changing cables. If Connecting is displayed at the right bottom of the screen, use Auto Connection (See Chapter Setup NT ) to connect the NS and the PLC before starting the following procedure. If the communication between the NS and the PLC has already been established, you do not need to perform the operation described above. Check Pass thru PLC to activate the PC PLC NS route setting. Select PC PLC NS. Select Serial(Toolbus) Setup Data transfer to the NS through PLC. Set the serial port COM No. for PC PLC connection. Then, press OK. Select NT Press each setting button. Transfer screen data Enter NS Unit No. Then, press OK. OK to start transfer Screen data transfer is is complete at at 100%.
34 Online Debug on a Machine Reading Project Online Connection to PLC Transferring to a Machine Program Debug Program Debug Transfer programs and Unit setting parameters created by an offline project to the PLC. In this example, data is sent at the same time to various Units using the batch transfer function. Monitoring Monitor ON/OFF status of contacts and coils. [Yes]... ON/OFF of monitoring Frame color changes to to a specified color during Function Block execution. Current parameter value is is displayed.
35 Online Debug on a Machine Reading Project Online Connection to PLC Transferring to a Machine Program Debug Monitoring -2 Changing the Current Parameter Value Change the current value of contact or channel through conductive monitoring. Move the cursor to D100 of input parameters Right-click, then select [Set/Reset (S)] > [Value (V)] from the pull-down menu or Double-click Or ENT Change current value of the input parameter. Ensure to add "#" (hexadecimal/bcd) or "&" (decimal) to the left of the value.
Introduction - Please be sure to read and understand Precautions and Introductions in CX-Simulator Operation Manual and CX-Programmer Operation Manual before using the product. - This guide describes the
Temperature Controller Support Software CX-Thermo Ver.4.0 Online Help Contents Chapter 1 Introduction 1.1 What is CX-Thermo? 1.2 Compatible Device Models and Computers 1.3 Hardware Setups 1.4 Basic Use
How to read this guide The following shows the symbols used in this Quick start guide with descriptions and examples. Symbol Description Example P oint Reference Caution [ ] This symbol explains information
Colorfly Tablet Upgrade Guide (PhoenixSuit) 1. Downloading the Firmware and Upgrade Tool 1. Visit the official website http://www.colorful.cn/, choose 产 品 > 数 码 类 > 平 板 电 脑, and click the product to be
QUICK START GUIDE SG2 Client - Programming Software SG2 Series Programmable Logic Relay SG2 Client Programming Software T he SG2 Client software is the program editor for the SG2 Series Programmable Logic
Software User Guide For the safe use of your camera, be sure to read the Safety Precautions thoroughly before use. Types of software installed on your computer varies depending on the method of installation
B-1159(3) WindO/I-NV2 Utility Pass-Through Tool Instruction Manual Introduction This instruction manual explains the operation and handling of the WindO/I-NV2 Utility Pass-Through Tool. Before using the
Features Reference About Unified Communication System Before Using This Machine Starting a Meeting What You Can Do During the Meeting Leaving a Meeting Managing Address Book Changing Network Configuration
1 Purpose This Technical Note describes how to set up a remote collaboration. A remote collaboration consists in configuring, programming or monitoring a PLC from a remote location, without the need of
Quick Start Using DASYLab with your Measurement Computing USB device Thank you for purchasing a USB data acquisition device from Measurement Computing Corporation (MCC). This Quick Start document contains
Guide to Installing BBL Crystal MIND on Windows 7 Introduction The BBL Crystal MIND software can not be directly installed on the Microsoft Windows 7 platform, however it can be installed and run via XP
Safety Precautions Read and understand this specifications, instruction manual, installation manual and catalog to make proper use of the product. WARNING If critical situations that could lead to user
User s Manual DTAP3000 DTSX3000 Control Visualization Software LAS2.0 Data Conversion Guide 1st Edition Blank Page < Introduction > i Introduction About this Manual Thank you for purchasing the DTSX3000
LCD MONITOR TOUCH PANEL DRIVER 2 OPERATION MANUAL for Mac Version 1.0 Applicable models PN-L703A/PN-70TA3/PN-L703B/PN-70TB3/PN-L603A/PN-60TA3/PN-L603B/PN-60TB3 Contents Introduction...3 System Requirements...3
Work Off-Line Set up a new database or modify a previously saved database (without being connected to the telephone system). This helps minimize on-site programming time. Work On-Line (connected directly
How to update or recover the system program Ver.8.0 Introduction CDROM includes system program installation program to update or to recover your Programmable Terminal (PT). Please follow the instruction
Important Please read this User s Manual carefully to familiarize yourself with safe and effective usage. About This Manual This manual describes how to install and configure RadiNET Pro Gateway and RadiCS
32 Transferring Projects and Data This Chapter explains how to transfer GP-Pro EX project files to the GP and how to transfer the project files stored on the GP to your PC. Please start by reading 32.1
Installation and Operation Manual version version About this document This document is intended as a guide for installation, maintenance and troubleshooting of Portable Device Manager (PDM) and is relevant
Notes: STATISTICA VERSION 9 STATISTICA ENTERPRISE INSTALLATION INSTRUCTIONS FOR USE WITH TERMINAL SERVER 1. These instructions focus on installation on Windows Terminal Server (WTS), but are applicable
NEC Projector User Supportware 2 Software Utility Installation Guide Image Express Utility 2.0 Desktop Control Utility 1.0 Ulead Photo Explorer 8.0 Viewer PPT Converter 2.0 PC Control Utility 3.0 To Our
QUANTIFY INSTALLATION GUIDE Thank you for putting your trust in Avontus! This guide reviews the process of installing Quantify software. For Quantify system requirement information, please refer to the
EasyMP Monitor Operation Guide Ver.4.40 2 Notations Used in This Guide The following table shows the symbols used in this manual, along with descriptions of what they mean. Caution q s Indicates procedures
M0008487C TYPE S R ADVANCED MODEL-SETUP Setup Software Preface Thank you for selecting our AC Servo Amplifier R ADVANCED MODEL. This User s Manual is a support tool explaining the use and specifications
File Management Utility T u t o r i a l Contents System Requirements... 2 Preparing Files for Transfer to GlobalMark... 2 Application Launch... 2 Printer Setup... 2 Communication Status... 4 Communication
Instruction Manual Inverter Support Software FRENIC-HVAC/AQUA Loader Thank you for purchasing our high-performance, vector control FRENIC-HVAC/AQUA series of inverters. This manual provides all the information
NTI Backup Now EZ v2 User s Guide GMAA00423010 11/12 2 Copyright statement This guide is copyrighted by Toshiba Corporation with all rights reserved. Under the copyright laws, this guide cannot be reproduced
EasyMP Network Projection Operation Guide Contents 2 Before Use Functions of EasyMP Network Projection....................... 5 Sharing the Projector....................................................
LCD MONITOR TOUCH DISPLAY DRIVER OPERATION MANUAL for Mac Version 1.0 Applicable models PN-K322B/PN-K322BH/LL-S201A Contents Introduction...3 System Requirements...3 Setting up the Computer...4 Installing
LESSON 13 Managing Devices OBJECTIVES After completing this lesson, you will be able to: 1. Open System Properties. 2. Use Device Manager. 3. Understand hardware profiles. 4. Set performance options. Estimated
SD7000 Digital Microphone Monitor Software manual Table of Contents 1. Installing The Monitor Software 1.1 Setting Up Receivers For Monitoring 1.2 Running The Application 1.3 Shutdown 2. The Detail Monitoring
Iridium Extreme TM Satellite Phone Data Services Manual Table of Contents 1 OVERVIEW... 1 2 HOW IT WORKS... 1 3 BEFORE INSTALLING... 2 4 USB DRIVER INSTALLATION... 3 5 MODEM INSTALLATION AND CONFIGURATION...
Operating manual 42/49-27 EN Engineer IT Device configurator DRC200 R&C Process Data Management Software Impressum Device configurator DRC200 Operating manual Document No. 42/49-27 EN Date of issue: 11.02
NETWORK PRINT MONITOR User Guide Legal Notes Unauthorized reproduction of all or part of this guide is prohibited. The information in this guide is subject to change without notice. We cannot be held liable
[Issue No.] FA-A-0153-F [Page] 1/31 Thank you for your continued support of Mitsubishi integrated FA software MELSOFT series. This bulletin explains the precautions when installing the MELSOFT products
Installation Guide Manuals for This Product Manuals for this product have the following structure. Read the manual according to your purpose for using this product. Disc Guides with this symbol are PDF
ZEN-SOFT01-V3 Cat.No.W386-E1-03 ZEN-SOFT01-V3 ZEN Support Software Operation Manual Revised April 2003 iv Notice: OMRON products are manufactured for use according to proper procedures by a qualified operator
PC Configuration Requirements: Configuration Requirements for ipc Operation The hardware and operating system of the PC must comply with a list of minimum requirements for proper operation with the ipc
GE Healthcare Life Sciences UNICORN 5.31 Administration and Technical Manual Table of Contents Table of Contents 1 Network setup... 1.1 Network terms and concepts... 1.2 Network environment... 1.3 UNICORN
EasyMP Network Projection Operation Guide Contents 2 Before Use Functions of EasyMP Network Projection....................... 5 Sharing the Projector....................................................
IEEE 802.11b WLAN PC Card User s Guide Version: 1.3 August 2001 Please install the Utility/Driver first before inserting the PCMCIA Card. FCC Class B Radio Frequency Interference Statement The manufacturer
USB Driver Installation for Windows XP USB Serial Converter Driver Installation for Windows XP CAUTION: You must use the drivers on the CD-ROM supplied with your USB Device. DO NOT download drivers from
UFR II Driver Guide UFR II Driver Ver. 2.20 Please read this guide before operating this product. After you finish reading this guide, store it in a safe place for future reference. ENG 0 Ot UFR II Driver
USB DRIVER INSTALLATION GUIDE Thank you for using the Icom Download Service. Please read this installation guide before installing the USB driver into your PC that is connected to the USB (Universal Serial
Networking General networking Networking overview A network is a collection of devices such as computers, printers, Ethernet hubs, wireless access points, and routers connected together for communication
Software User Guide For the safe use of your camera, be sure to read the Safety Precautions thoroughly before use. Types of software installed on your computer varies depending on the method of installation
VERITAS Backup Exec TM 10.0 for Windows Servers Quick Installation Guide N134418 July 2004 Disclaimer The information contained in this publication is subject to change without notice. VERITAS Software
SHARP Digital Signage Software Pro PN-SS05 Version 4.1 OPERATION MANUAL Contents Introduction... 2 Precautions on Use...2 Trademarks...2 How to Read this Manual...3 Definitions...3 Installing/Launching...
About This Guide 3 About This Guide This user guide is intended for Photovoltaic (PV) system owners, installers, technicians, maintainers, administrators and integrators who are authorized to configure
EasyMP Monitor Operation Guide Ver.4.53 2 Notations Used in This Guide The following table shows the symbols used in this manual, along with descriptions of what they mean. q s Indicates additional information
Legal Notes Unauthorized reproduction of all or part of this guide is prohibited. The information in this guide is subject to change for improvement without notice. We cannot be held liable for any problems
MODEL: MX-M283N MX-M363N MX-M453N MX-M503N DIGITAL MULTIFUNCTIONAL SYSTEM Software Setup Guide BEFORE INSTALLING THE SOFTWARE SETUP IN A WINDOWS ENVIRONMENT SETUP IN A MACINTOSH ENVIRONMENT TROUBLESHOOTING
data analysis data mining quality improvement web-based analytics Notes STATISTICA VERSION 11 CONCURRENT NETWORK LICENSE WITH BORROWING INSTALLATION INSTRUCTIONS 1. The installation of the Concurrent network
TM SECURITY SYSTEM MANAGEMENT SOFTWARE FOR WINDOWS Quick Start Instructions Introduction WinLoad for Windows was developed to simplify and speed up the task of programming Paradox control panels. Remote
Software License Registration Guide When you have purchased new software Chapter 2 Authenticating a License When you would like to use the software on a different PC Chapter 3 Transferring a License to
Meridian 1 Meridian 1 Attendant PC LAN Interface Installation Guide Document Number: P0874391 Document Release: Standard 1.00 Date: November 1997 Year Publish FCC TM 1997 All rights reserved Printed in
Legal Notes Unauthorized reproduction of all or part of this guide is prohibited. The information in this guide is subject to change without notice. We cannot be held liable for any problems arising from
Operating Instructions (For Setting Up) Digital Imaging Systems Installation Overview Model No. DP-8060 / 8045 / 8035 Table of Contents Setting Your Machine Installation Overview General Installation Overview...
Installation Guide Sybase ETL Small Business Edition 4.2 for Windows Document ID: DC00738-01-0420-01 Last revised: April 2007 Topic Page 1. Overview 2 2. Before you begin 2 2.1 Review system requirements
i-stat TECHNICAL BULLETIN Configuring Wireless Settings in an i-stat 1 Wireless Analyzer Before configuring wireless settings, please enable the wireless functionality by referring to the Technical Bulletin
How to read this guide The following shows the symbols used in this Quick start guide with descriptions and examples. Symbol Description Example P oint Caution This symbol explains information you need
Allworx OfficeSafe Operations Guide Release 6.0 No part of this publication may be reproduced, stored in a retrieval system, or transmitted, in any form or by any means, electronic, mechanical, photocopy,
5.6.3 Lab: Registry Backup and Recovery in Windows XP Introduction Print and complete this lab. In this lab, you will back up a computer registry. You will also perform a recovery of a computer registry.
AXIS Camera Station Quick Installation Guide Copyright Axis Communications AB April 2005 Rev. 3.5 Part Number 23997 1 Table of Contents Regulatory Information.................................. 3 AXIS Camera
Installation Instruction STATISTICA Concurrent Network License with Borrowing Domain Based Registration Notes: ❶ The installation of the Concurrent network version entails two parts: a) a server installation,
April 2012 QIAsymphony Management Console User Manual For use with software version 4.0 Sample & Assay Technologies Trademarks QIAGEN, QIAsymphony, Rotor-Gene (QIAGEN Group). InstallShield (Informer Technologies,
Network Setup Guide This manual contains the setup information required to use the machine over wired LAN. If you use the machine with USB connection, refer to your setup sheet. Introduction To use the
EPSON Scan Server & EPSON TWAIN Pro Network EPSON Scan Server & EPSON TWAIN Pro Network SCANNER UTILITY PROGRAMS All rights reserved. No part of this publication may be reproduced, stored in a retrieval
PCLinq2 Hi-Speed USB Bridge-Network Cable Congratulations! Quick Network Setup Guide For Windows 98/ME/2000/XP Congratulations for installing the PCLinq2 Hi-Speed USB Bridge-Network Cable. This Quick Network
RDC-7 Windows XP Installation Guide CONTENTS 1. End User License Agreement...3 2. Important notes...4 3. Customer support...4 4. Installing the USB driver...4 I. Prior to installation...4 II. Installation
Data Management Software CL-S10w Installation Guide Safety Warning Please read this manual and the instrument and computer manual carefully beforehand and use the software properly and safely. Official
User Manual Onsight Management Suite Version 5.1 Another Innovation by Librestream Doc #: 400075-06 May 2012 Information in this document is subject to change without notice. Reproduction in any manner
Author Janice Hong Version 1.0.0 Date Mar. 2014 Page 1/56 How to use the VMware Workstation / Player to create an ISaGRAF (Ver. 3.55) development environment? Application Note The 32-bit operating system
1.1 Overview Technical Note Cameleon requires that you have a static IP address defined for the server PC the Cameleon server application runs on. Even if the server PC has a static IP address, you may