1 Loss Prevention Standard LPS 1014: Issue 5.3 This Loss Prevention Standard is the property of BRE Global Ltd. and is made publicly available for information purposes only. Its use for testing, assessment, certification or approval must be in accordance with LPCB internal procedures and requires interpretation by BRE Global Ltd, LPCB and BRE experts. Any party wishing to use or reproduce this Loss Prevention Standard to offer testing, assessment, certification or approval must apply to BRE Global Ltd for training, assessment and a licence; a fee will normally be charged. BRE Global Ltd. will not un-reasonably refuse such applications. BRE Global Ltd accepts no responsibility for any un-authorised use or distribution by others of this Loss Prevention Standard and may take legal action to prevent such un-authorised use or distribution
3 Page 1 of 14 CONTENTS PAGE PARTICIPATING ORGANISATIONS 2 REVISION OF LOSS PREVENTION STANDARDS 2 FOREWORD 3 1 SCOPE 4 2 DEFINITIONS 4 3 REQUIREMENTS FOR CERTIFICATED FIRMS 5 4 OPERATIONAL REQUIREMENTS 8 5 PROVISIONAL APPROVAL 10 APPENDIX A SAMPLE CERTIFICATE OF CONFORMITY 12 APPENDIX B PUBLICATIONS REFERRED TO 13 Table of amendments issued since publication 14
4 Page 2 of 14 PARTICIPATING ORGANISATIONS This standard was approved by the LPC Fire and Security Board and Expert Group A. The following organisations participated in the preparation of this standard:- Association of British Insurers Association of Building Engineers Association of Chief Police Officers Association for Specialist Fire Protection British Automatic Fire Sprinkler Association British Security Industry Association BT Redcare Chief Fire Officers Association Door & Hardware Federation Electrical Contractors Association European Fire Sprinkler Network Fire Industry Association Health & Safety Executive Metronet Risk Engineering Data Exchange Group Royal and Sun Alliance Royal Institution of Chartered Surveyors REVISION OF LOSS PREVENTION STANDARDS Loss Prevention Standards will be revised by issue of revised editions or amendments. Details will be posted on our website at Technical or other changes which affect the requirements for the approval or certification of the product or service will result in a new issue. Minor or administrative changes (e.g. corrections of spelling and typographical errors, changes to address and copyright details, the addition of notes for clarification etc.) may be made as amendments (see amendments table on page 14) The issue number will be given in decimal format with the integer part giving the issue number and the fractional part giving the number of amendments (e.g. Issue 3.2 indicates that the document is at Issue 3 with 2 amendments). USERS OF LOSS PREVENTION STANDARDS SHOULD ENSURE THAT THEY POSSESS THE LATEST ISSUE AND ALL AMENDMENTS.
5 Page 3 of 14 FOREWORD This Standard identifies the evaluation and / or testing practices undertaken by LPCB for the purposes of approval and listing of products and services. LPCB listing and approval of products and services is based on evidence acceptable to LPCB:- and on:- that the product or service meets the standard; that the manufacturer or service provider has staff, processes and systems in place to ensure that the product or service delivered meets the standard periodic audits of the manufacturer or service provider including testing as appropriate; compliance with the contract for LPCB listing and approval including agreement to rectify faults as appropriate; The responsibility for ensuring compliance with the technical and managerial process and requirements for the product or service lies with the manufacturer, service provider or supplier. NOTES Compliance with this LPS does not of itself confer immunity from legal obligations. Users of LPSs should ensure that they possess the latest issue and all amendments. LPCB welcomes comments of a technical or editorial nature and these should be addressed to the Technical Director at The BRE Trust, a registered charity, owns BRE and BRE Global. BRE Global and LPCB (part of BRE Global) test, assess, certificate and list products and services within the fire and security sectors. For further information on our services please contact BRE Global, Watford, Herts. WD25 9XX or to Listed products and services appear in the LPCB List of Approved Products and Services which may be viewed on our website: or by downloading the LPCB Red Book App from the App Store (for iphone and ipad), from Google Play (for Android devices) or from the Windows Store (for Windows 8 Phones and Tablets from 2014).
6 Page 4 of 14 1 SCOPE This standard specifies the requirements of the Loss Prevention Certification Board (LPCB) for Firms engaged in system design, installation, commissioning and servicing of fire detection and alarm systems. The requirements for the issuing of LPS 1014 Certificates of Conformity against the Installation Rules are also specified. 2 DEFINITIONS 2.1 Firm An individual, body corporate or body incorporate, applying for or holding LPCB Certificates for the services detailed in Clause Installation rules For the purposes of this document, Installation Rules typically comprise at least BS , but may in addition, or alternatively, include any of the following:- 2.3 Contract a) BS 5839 all other relevant parts b) BS 6266 c) BS 7273 all relevant parts d) Health Technical Memorandum 05 all relevant parts e) NFPA 72 f) IS3218 (Ireland) A written undertaking by a certificated Firm to perform work or supply certain articles for a specified consideration. 2.4 Handover The point in a contract where commissioning and certification of the installation have been satisfactorily completed to the contract specification so enabling the installation to be formally handed over to a responsible person nominated by the user. 2.5 Maintenance Work of inspection, servicing and repair necessary in order to maintain the efficient operation of the installed system. 2.6 Repair Non-routine work necessary to restore the efficient operation of the installed system. 2.7 Servicing Routine process of work on the system (including cleaning, re-alignment, adjustment and replacement) carried out at pre-determined intervals.
7 Page 5 of 14 3 REQUIREMENTS FOR CERTIFICATED FIRMS 3.1 Capability Certificated Firms shall have the capability to undertake system design, installation, commissioning and servicing, although installation or servicing may be sub-contracted provided contractual responsibility for these services is retained by the certificated Firm. 3.2 Continuity of involvement The Firm will provide evidence of design, installation, commissioning and servicing of fire alarm installations, in accordance with Installation Rules (see 2.2), over a continuous period of not less than two years. 3.3 LPCB pre-certification site inspections Prior to Certification the Firm will provide a list of at least 8 installations for which handover has been completed:- a) within the last 12 months where the Firm does not have the service contract, or b) within the last 2 years where the Firm does have the service contract. The LPCB will choose installations from this list for inspection to the Installation Rules applied. A sufficient number of installations will be inspected to determine whether the Firm has the capability to design, install, commission and service Fire Detection and Alarm systems in accordance with Installation Rules. The number of installations to be inspected will be at the discretion of the LPCB. 3.4 Management system In order to ensure that Fire Detection and Alarm systems meet, and continue to meet, the requirements of this scheme, the Firm is required to maintain full control of their design, installation, commissioning and servicing processes through a management system approved by LPCB. The management system shall comply with ISO Full details of the LPCB ISO 9001 certification process are set out in publication SD003 Quality Management Systems Certification Scheme. The duration and frequency of Management System assessment and surveillance visits is typically one day twice per year. However the actual frequency and duration depends on a number of factors including the size of firm and scope of activities. Firms that apply to join the LPS 1014 scheme that already have ISO 9001 certification with the required scope, or wish to gain ISO 9001 certification with another UKAS accredited certification body, will be
8 Page 6 of 14 subject to an audit of their quality management system during LPS 1014 assessment and surveillance audits by LPCB. Details of the conditions for accepting ISO 9001 certification from another UKAS accredited certification body can be found in LPCB document PN004: LPS 1014 Application process non-lpcb ISO 9001 certification The Firm's management system will, in addition to meeting the requirements of clause 3.4.1, comply with the following:- (a) (b) (c) Authorisation The Firm will specify who is authorised to sign LPS 1014 Certificates of Conformity. Power supply design Battery capacity and rating of chargers used in standby supplies will be calculated from appropriate formulae. The formulae used and the reasoning behind their use will be documented. Inspection and test records Records will be generated for each installation to:- i. Confirm the correct operation of all manual call points and automatic fire detectors. ii. iii. iv. Confirm the functional integrity of detection and alarm circuits, the verification of power supplies, including mains powers supplies, and the correct operation of any facilities for remote transmission of alarm (and, where relevant, fault) signals. Confirm that the alarm sound level meets specified requirements. Confirm that connection of the Fire Alarm System to the mains power supplies is in accordance with specified requirements. v. Confirm that the system cause and effect (including, where relevant, display of addressable information) is in accordance with the specification. vi. vii. Confirm that there are no obvious sources of false alarms. Confirm that the Category of system or extent of protection is as specified.
9 Page 7 of Competence of staff a) Competence of staff The Firm will provide evidence that the relevant staff on each contract are competent, and where appropriate, supervised in respect of the equipment installed. b) Number of staff The Firm will employ an adequate number of staff (at least two) experienced in design in accordance with BS and all other Installation Rules applied. 3.6 Customer training The Firm will show adequate organisation to provide training for customers with regard to their responsibilities. Evidence will be provided that customers have been made aware of their responsibilities and have been offered training in the use of the system. 3.7 Maintenance capability The Firm will show adequate organisation of:- a) A call-out facility, which will result in an 8 hour on site response for, contracted customers with reasonable remedial action being taken on site within a period of 24 hours. The Firm will also have access to an adequate range of stock to resolve such an emergency. b) Provision of assistance for customers with regard to their responsibilities, including written instructions as necessary. c) Identification of changes in the layout, configuration or use of a building that result in variations from the Installation Rules. d) The provision of a call-out facility 24 hours per day, 365 days per year. 3.8 Equipment The following equipment/components shall be third party approved to appropriate standards:- Control panels Detectors Manual call points Alarm devices Line modules Cables Equipment/components not listed above need not be third party approved but shall conform to appropriate standards. Refer to clause for the issue of the LPS 1014 Certificate of Conformity.
10 Page 8 of 14 4 OPERATIONAL REQUIREMENTS 4.1 Installation rules All installation contracts undertaken within the Certification Scheme will be in accordance with the Installation Rules, except for those systems involving innovative designs (see clause 3.4). In such cases, the Firm must demonstrate the criteria used in the design of the installation. 4.2 Installations with variations from the Installations Rules Any variations from the Installation Rules must be brought to the attention of the client or their representative prior to certification being issued. During surveillance visits, the Firm will be asked by LPCB to provide documentary evidence that this has been done. 4.3 Certificate of conformity A major value of the LPS 1014 scheme to users, enforcing authorities and property insurers is that, by entering into a contract with a certificated Firm for the installation and commissioning of a Fire Detection and Alarm System, the purchaser is guaranteed that a single Certificate of Conformity will be issued by the Firm, certifying that the design, installation and commissioning of each system complies with the Installation Rules specified The Certificate of Conformity shall be issued at handover and shall indicate any agreed variations from the Installation Rules. The LPS 1014 Certificate of Conformity does not become valid until it has been signed by the authorised representative of the client, demonstrating the client s acceptance of any listed variations. The scope of the certification shall include all aspects of the installation addressed by the relevant contract requirements and the Installation Rules (including, for example, mains power supplies and fire stopping of cable penetrations), regardless of whether such aspects are the contractual responsibility of the Firm or of others It should be noted that a certificated Firm must issue a numbered Certificate of Conformity for every installation that the Firm is contracted to install and commission, regardless of whether responsibility for design of the installation rests with the Firm or a third party (e.g. consulting engineers). If the certificated Firm sub-contracts the installation work, the Firm remains responsible for the installation work (which should be adequately supervised and inspected by the Firm), and remains responsible for the issue of the Certificate of Conformity. The selection of installation sub-contractors should be based on their ability to carry the work out satisfactorily. It could take the form of approval to a recognised scheme, for example, the EIILC industry scheme for work category A3 fire alarm installation.
11 Page 9 of A certificated Firm may be required, under a contract, to supply and commission a Fire Detection and Alarm System, or to design, supply and commission the system. In such cases, since the Firm is not the installer of the system, it is not mandatory to issue a Certificate of Conformity. The Firm may issue its own certificate of commissioning (e.g. Set to work), provided this certificate does not purport to certify compliance of the installation with the Installation Rules. The Fire Detection and Alarm System will, however, remain outside the scope of the LPS 1014 certification scheme. However, the certificated Firm may certificate the installation against the installation rules (if for example this is a requirement under the contract). In this case, an LPS 1014 Certificate of Conformity must also be issued. By carrying out this additional service, which shall include full inspection of the installation against the relevant installation rules, the certificated Firm effectively brings the Fire Detection and Alarm System within the scope of the LPS 1014 certification scheme. Such systems may then be inspected by the LPCB during the course of surveillance visits, even though the certificated Firm is not the installer of the system Compliance with the above requirements for the issue of Certificates of Conformity is a prerequisite for the continued certification of a Firm, and will be verified in the course of surveillance and quality assurance audits carried out by the LPCB An LPS 1014 Certificate of Conformity shall not be issued unless the equipment/components used in the system comply with clause Certification of extensions and alterations An LPS 1014 Certificate of Conformity for the work must be issued if a valid LPS 1014 certificate exists in respect of the original installation. LPS 1014 Certificates of Conformity may be issued for extensions and alterations to existing installations which are not covered by an LPS 1014 Certificate of Conformity, provided the scope of the work covered by LPS 1014 certificate is clearly defined. If the Firm, in addition, wish to certificate retrospectively the entire installation (i.e. the original installation plus the work carried out) an LPS 1014 Certificate of Conformity may be issued, providing the Firm carry out a full design review and site inspection of the system, including full re-commissioning, against the installation rules and obtain agreement for any variations from the client. If an extension can be considered to 'stand alone' (e.g. an independent system to protect a computer suite within a building), an LPS 1014 Certificate of Conformity must be issued.
12 Page 10 of LPCB Surveillance Prior to each surveillance audit, the Firm shall provide LPCB with a list of contracts they have completed since the previous audit using LPCB form F353, from which LPCB will select one or more suitable contracts to review. The number of contracts selected for review by LPCB will depend on the size and complexity of the contracts made available for audit. Where possible, the audit will involve the inspection of two sites, alternatively, where it is not possible to visit two sites, the audit will consist of a review of a number of project files and the inspection of at least one site. 4.6 Regional offices Where the Firm wishes to design and commission under the Certification Scheme in regional offices, then these offices shall meet the requirements of this standard to be eligible for Certification. 4.7 Maintenance Maintenance of Certificated installations shall only be carried out by LPCB Certificated Fire Detection and Alarm System Firms, or their approved subcontractor, who have demonstrated:- (a) (b) the availability of appropriate compatible replacement equipment for the maintained installation, and appropriate staff training. 5. PROVISIONAL APPROVAL 5.1 Criteria Firms wishing to join the LPS 1014 scheme that do not meet the requirements of clauses 3.2 and 3.3 may apply for provisional approval. 5.2 Pre-approval site inspections For a Firm to be eligible for provisional approval, they must have completed an adequate number of fire detection and alarm systems contracts for LPCB to sample at the assessment audit. A completed F353 shall be submitted with the application form. LPCB will review the list of completed contracts and decide whether there are adequate fire detection and alarm systems to sample. If there are not enough contracts to sample, the application will be placed on hold pending the completion of further contracts. 5.3 Approval certificate Subject to a satisfactory assessment audit, the Firm will be issued with an approval certificate which will show that the Firm has gained provisional approval in the LPS 1014 scheme. The certificate will be valid for 12 months. If
13 Page 11 of 14 by the end of the 12 months, the Firm does not meet the requirements for full certification by complying fully with clauses 3.1 and 3.2, the provisional certificate maybe re-issued for a further 12 months. However, if the Firm does not comply with the requirements of clause 3.2 within 2 years, provisional LPS 1014 approval may be withdrawn. 5.4 LPS 1014 Certificates of Conformity Any contract that will be issued with an LPS 1014 Certificates of Conformity shall be inspected by LPCB before certification. The LPS 1014 Certificate of Conformity will be raised and issued by LPCB. 5.5 Red Book listing Provisionally approved Firms will not be Red Book Listed. 5.6 List of completed contracts When the provisionally listed Firm receives a new fire detection and alarm system contract, it shall update the F353 form and send a copy to LPCB. 5.7 Other requirements The requirements of clauses 3.1, 3.4 to 3.8 and section 4 shall also apply for provisional approval.
14 Page 12 of 14 APPENDIX A SAMPLE CERTIFICATE OF CONFORMITY
15 Page 13 of 14 APPENDIX B PUBLICATIONS REFERRED TO For undated references please refer to the latest published issue. Standard ISO 9001 Title Quality management systems Requirements BS 5839: Part 1 Part 6 Part 8 Part 9 Fire detection and fire alarm systems for buildings Code of practice for system design, installation, commissioning and maintenance Code of practice for the design, installation and maintenance of fire detection and fire alarm systems in dwellings Code of practice for the design, installation, commissioning and maintenance of voice alarm systems Code of practice for the design, installation, commissioning and maintenance of emergency voice communication systems BS 6266: Code of practice for fire protection for electronic equipment installations BS 7273: Part 1 Part 3 Part 4 Part 5 Code of practice for the operation of fire protection measures Electrical actuation of gaseous total flooding extinguishing systems Electrical actuation of pre-action sprinkler systems Actuation of release mechanisms for doors Electrical actuation of watermist systems (except pre-action systems) HTM 05 Health Technical Memorandum for alarm and detection systems IS3218 (Ireland) Code of Practice for Fire Detection and Alarm Systems for Buildings - System Design, Installation, Servicing and Maintenance
16 Page 14 of 14 AMENDMENTS ISSUED SINCE PUBLICATION DOCUMENT NO. AMENDMENT DETAILS SIGNATURE DATE LPS LPS LPS LPS LPS LPS Issue 3 - superseded Issue 4 - not published - withdrawn Issue 5 - published - effective from Change to copyright information Change to copyright information The term deviation has been replaced by variation throughout the document Participating organisations revised Contents revised, section 5 added List of Installation Rules updated 2.5 Servicing - definition revised to align with BS Repair - definition revised to align with BS Maintenance - definition revised to align with BS Innovative Designs no longer used, therefore deleted Amended (c) ii. - Amended (c) vii. - Added Amended Amended Amended Amended Added Amended Provisional Approval added Appendix A - Certificate replaced by latest version being used Appendix B - List of publications updated 17/05/ /05/ /07/ /09/ /03/2010 LPS Change of the front cover Title added to header Table of Contents amended Revision of Loss Prevention Standards section moved to Page 2 Web address changed on page 2 Notes added to Page 3 Appendix A. Certificate replaced by latest version being used Repagination Change to copyright information Update of references to ISO standards SP Jan.2014
Loss Prevention Standard LPS 1197: Issue 4.2 Requirements for the LPCB approval and listing of companies inspecting, repairing and maintaining fire and security doors, doorsets, shutters and active. This
Loss Prevention Standard LPS 1581: Issue 2.1 Requirements and tests for LPCB approval of nonload This Loss Prevention Standard is the property of BRE Global Ltd. and is made publicly available for information
Loss Prevention Standard : ISSUE 3.0 Requirements for the LPCB Approval and Listing of Companies Undertaking the Maintenance and Repair of Doorsets, Shutters, and Active Smoke/Fire Barriers This standard
BAFE Scheme: SP203-3 Version 1: July 2008 Amendment No: 1 Fire Protection Industry Scheme, Reference SP203 Part 3 For the Design, Installation, Commissioning & Maintenance of Fixed Gaseous Fire Suppression
Automatic Fire Alarm (AFA) Automatic Fire Detection (AFD) Introduction AFD can be described as being the means or equipment used to raise an alarm, whilst AFA is actually the action of the alarm itself.
FAT MEDIA QUALITY ASSURANCE STATEMENT NOTE 1: This is a CONTROLLED Document as are all quality system files on this server. Any documents appearing in paper form are not controlled and should be checked
Page: 1 of 11 For the FPC assessment of fire detection and alarm system products as specified in the harmonized standards of BS EN 54, Annex ZA, please refer to PN218. Where a product is being assessed
ELECSA and the Fire Industry Guide to Fire Protection and Fire Risk Assessment schemes www.elecsa.co.uk 80% Black 100% Black Section 1: What are the opportunities in the Fire Industry? Regulation of the
Want to exceed customer expectations and stand out from the crowd? Third party approval of management systems from BRE Global www.bre.co.uk Demonstrate your commitment to quality Quality Management Systems
Smart Meters Programme Schedule 2.5 (Security Management Plan) (CSP South version) Schedule 2.5 (Security Management Plan) (CSP South version) Amendment History Version Date Author Status v.1 Signature
WELDING FABRICATOR CERTIFICATION SCHEME DOCUMENT CS/1: SCHEME DESCRIPTION AND BENEFITS 6 th Edition July 2012 Issued under the authority of the Governing Board for Certification All correspondence should
NSF Certification UK SERVICE PROTOCOL For Certification against ISO 22000 and FSSC 22000 The purpose of this protocol is to provide existing and prospective customers with information on the way in which
OBOA 2009 Huntsville, ON Overview of ULC Standards Affecting Building Occupancy Alan Cavers Area Manager Fire & Security Systems Group Course Title: Rev Date Agenda Introduction to Underwriters Laboratories
CFP 2/4/8 ZONE CONVENTIONAL FIRE ALARM CONTROL PANEL user manual & log book Approved Document No. DFU7001020 Rev 1 CONTENTS Safety...3 Important information regarding the safe use of this fire alarm panel
Publication Reference EA IAF/ILAC-A4: 2004 EA IAF/ILAC Guidance on the Application of ISO/IEC 17020:1998 PURPOSE This guidance document is for ISO/IEC 17020: General Criteria for the operation of various
Joint Accreditation System of Australia and New Zealand Scheme (AMS Scheme) Requirements for bodies providing audit and certification of 13 April 2015 Authority to Issue Dr James Galloway Chief Executive
www.redbooklive.com Fire and Security Products and Services Making LPCB Approval work for you Not all fire and security products and services on the market can be trusted in the event of a fire or attempted
This manual is proprietary and no part thereof shall be copied without written authorisation from the company Ref: Quality Manual.ind Issue: June 2009 INDEX 1 Amendment Status 2 Controlled Distribution
The benefits of LPS 1277 - A specifier's guide Alarm transmission equipment (ATE) forms a vital part of any alarm system installation. It guarantees an alarm event is reliably and quickly transmitted to
Page: 1 of 10 Introduction 1. The requirements of this document supplement the Factory Production Control requirements given in Table 1 of PN111 by giving the specific requirements for Factory Production
Australian Transport Council National Standard for the Administration of Marine Safety SECTION 4 SURVEYS OF VESSELS Edition 1 Draft for comment issued 20 December 2005 Endorsed by the Australian Transport
Greater Manchester Fire and Rescue Service Record of Fire Safety Equipment Testing CONTENTS 1. MEANS OF ESCAPE 2. FIRE WARNING AND AUTOMATIC FIRE DETECTION 3. FIRE EXTINGUISHERS AND HOSEREELS 4. EMERGENCY
Network Certification Body Scheme rules for assessment of railway projects to requirements of the Railways Interoperability Regulations as a Notified and Designated Body 1 NCB_MS_56 Contents 1 Normative
OPERATING PROCEDURE IT CHANGE MANAGEMENT PROCEDURES MANUAL PREPARED BY: AEMO DOCUMENT NO: Enter Document ID VERSION NO: 6.6 STATUS FINAL Approvals The undersigned have approved the release of Version 6.6
Guide for Certification of Seafarer Recruitment and Placement Service Providers GUIDE FOR CERTIFICATION OF SEAFARER RECRUITMENT AND PLACEMENT SERVICE PROVIDERS AUGUST 2011 American Bureau of Shipping Incorporated
IAF MD 2:2007. International Accreditation Forum, Inc. IAF Mandatory Document IAF Mandatory Document for the Transfer of Accredited Certification of Management Systems (IAF MD 2:2007) IAF MD2:2007 International
I.S. 3218 :2013 Fire Detection & Alarm Systems Overview of significant changes 26 th March 2014 FPS Ltd Today s Programme Commencement Transition Competence & Qualifications System Certification System
Compliance Schedules and Building Warrant of Fitness Purpose of this guidance information The purpose of this guidance information is to help building owners and managers of commercial, industrial or communal
Implementation and Customer Services ( ICS") Installation Services Standard Terms and Conditions of Supply 1. General (Effective September 2013) This web page content defines the standard terms and conditions
GUIDANCE ON ELECTRICAL INSPECTIONS Electricity Electricity is a versatile and convenient source of energy. However, it can be potentially dangerous if the system has not been properly designed, installed,
EXHIBIT A SCOPE OF WORK 1. (Contractor) shall provide fire alarm system maintenance/repair/testing services as described herein to the California Department of Veterans Affairs (hereinafter CDVA, CalVet,
Benchmark OHS Consulting Pty Ltd Self Assessment WHS Audit Tool This WHS Auditing System Tool is to be used as a self-assessment of YOUR COMPANY compliance with AS 4801 and the Work Health and Safety Act
Materials and Qualification Procedures for Ships Approval for Thickness Measurement of Hull Structure Revision 8, 21 December 2015 Page 1 of 13 Lloyd s Register Group Limited, its subsidiaries and affiliates
HMO Information Sheet No 1 FIRE DETECTION AND ALARM SYSTEMS 1. Introduction When a property is in multiple occupation, the risk of fire breaking out is greater than in an ordinary single family home. Some
OPERATING PROCEDURE IT CHANGE MANAGEMENT PROCEDURES MANUAL PREPARED BY: AEMO DOCUMENT NO: Enter Document ID VERSION NO: 6.6 STATUS FINAL Approvals The undersigned have approved the release of Version 6.7
Information Security Policies Version 6.1 Information Security Policies Contents: 1. Information Security page 3 2. Business Continuity page 5 3. Compliance page 6 4. Outsourcing and Third Party Access
maintenance of CCTV surveillance systems code of practice Issue 3 January 2015 For other information please contact: British Security Industry Association t: 0845 389 3889 f: 0845 389 0761 e: firstname.lastname@example.org
Appendix A manual Example of a food company quality Contents Date: 13/03/95 RME-QLMN-OO Page 1 of 3 Section Title ISO 9001 reference 01 In trod uction 02 Purpose 03 Scope 04 Definitions 05 Management responsibility
DCA metrics for the approval of Auditing Firms for Certifications Scheme VERSION 1.0 2013, Data Centre Alliance Limited (www.datacentrealliance.org). All rights reserved. This publication may not be reproduced
Compliance Document for New Zealand Building Code Clause F7 Warning Systems Fourth Edition Prepared by the Department of Building and Housing This Compliance Document is prepared by the Department of Building
CFP 2/4/8 ZONE FIRE ALARM CONTROL PANEL CFP 2/4/8 ZONE FIRE ALARM PANEL user manual & log book approved document no. DFU7001000 rev 4 CFP USER MANUAL Approved Document No. DFU7001000 Rev 4 1 CONTENTS Safety...
LPCB Red Book Listed Products and Passive Fire Protection Installer Schemes Answering the needs of the market Ian Stewart Passive installer scheme manager September 2011 Introduction to BRE Global Research,
BRITISH STANDARD Quality management systems Guidelines for configuration management ICS 03.120.10 BS ISO 10007:2003 BS ISO 10007:2003 This British Standard was published under the authority of the Standards
Guidance for Electrical Contractors on Emergency Lighting Legislation Issued in the interests of safety by in conjunction with the Industry Committee for Emergency Lighting ECA / ICEL Guidance For Electrical
28 th April 2005 Version Final 1.1 CODE OF PRACTICE FOR THE AUTOMATIC FIRE ALARM SYSTEM Copyright New Zealand Fire Service Page 1 of 1 Table of Content 1 Document History 3 2 Copyright 3 3 Purpose of this
ISO 9001: 2008 Boosting quality to differentiate yourself from the competition xxxx November 2008 ISO 9001 - Periodic Review ISO 9001:2008 Periodic Review ISO 9001, like all standards is subject to periodic
1 Module 5 Software Support Services TABLE OF CONTENTS Version 3.1 1. AGREED TERMS AND INTERPRETATION... 2 2. SUPPORT PERIOD... 3 3. SCOPE OF SUPPORT SERVICES... 4 4. RESELLER PROVISION OF... 8 5. ANCILLARY
SOFTWARE MAINTENANCE AGREEMENT DATE PARTIES (1) WAY FORWARD TECHNOLOGIES LIMITED at Wellington ("the Supplier") (2) Gilbarco (NZ) on behalf of BACKGROUND The Licensee is a licensed user of the software
I.S. 3218 :2013 Fire Detection & Alarm Systems Overview of significant changes 26 th March 2014 FPS Ltd Today s Programme Commencement Transition Competence & Qualifications System Certification System
General System Guidelines for New Intruder Alarm Installations in Commercial Premises Introduction Intruder Alarm Systems installed in the UK since 1 st October 2005 are required to be designed, fitted
CONTRACT FOR THE APPOINTMENT OF AN APPROVED INSPECTOR CIC/AppInsp The Construction Industry Council - Association of Consultant Approved Inspectors contract for the appointment of an approved inspector
Health and Safety Management Standards Health and Safety Curtin University APR 2012 PAGE LEFT INTENTIONALLY BLANK Page 2 of 15 CONTENTS 1. Introduction... 4 1.1 Hierarchy of Health and Safety Documents...
SCHEDULE 25 Business Continuity 1. Scope 1.1 This schedule covers TfL s requirements in respect of: any circumstance or event which renders, or which TfL considers likely to render, it necessary or desirable
Page 1 / 9 ABSTRACT This document defines the general requirements that need to be fulfilled by a supplier applying for a NSQ- 100 certificate. NQSA Conformity Bodies Assess competence Assess conformity
GAP-ANALYSIS CROSS REFERENCE BETWEEN ISO/IEC 17020:2012 AND ISO/IEC 17020:1998 The principle standard used by International Accreditation Service (IAS) for the accreditation of Inspection Bodies is ISO/IEC
Fire Alarm System Monitoring - CAN/ULC-S561-03 Brian McBain ULC Regulatory Services May 4, 2011 Copyright 1995-2007 Underwriters' Laboratories of Canada. All rights reserved. No portion of this material
NORTHERN IRELAND SAFETY GROUP STATUTORY ELECTRICAL INSPECTIONS 26/08/2010 1 Introduction Paul Kane Commercial Operations Manager Contract Services NI Limited We welcome the opportunity to provide you with
The provisions of this Service Schedule are in addition to the Conditions for Provision of Closed Circuit Television Service (the Conditions ) and the Customer s acceptance as a user of the terms of the
BUILDING INFORMATION MODEL (BIM) PROTOCOL 2013 Standard Protocol for use in projects using Building Information Models The CIC acknowledges the technical input and leadership provided by the BIM Task Group
for Inspecting and Certifying Buildings and Works Building Control Regulations 2014 February, 2014 Table of Contents 1. Introduction 1 1.1 Status and Purpose of Code 1 1.2 Overview of Code 1 1.3 Application
Procurement Policy Note Taking Account of Suppliers Past Performance Action Note 04/15 25 th March 2015 Issue 1. To ensure good delivery of public services and value for money, it is important that suppliers
Minding Your Business BUSINESS WATCH Introduction BUSINESS WATCH At Business Watch we understand that the security of your property and business is important, but it may not be cost effective to install
FUNDAMENTALS OF FIRE ALARM SYSTEMS 72 33 FIRE ALARM SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. 1. PROTECTED PROPERTY
QSS 0: Products and Services without Bespoke Contracts. Amendment History Version Date Status v.1 Dec 2014 Updated For 2015 deployment Table of Contents 1. DEFINITIONS 3 2. INTRODUCTION 3 3. WORKING WITH
GAP.220.127.116.11 A Publication of Global Asset Protection Services LLC NATIONAL FIRE ALARM AND SIGNALING CODE INTRODUCTION National Fire Protection Association (NFPA) documents describe a level of fire protection
Frequently Asked Questions Unannounced audits for manufacturers of CE-marked medical devices 720 DM 0701-53a Rev 1 2014/10/02 What is an unannounced audit?... 6 Are unannounced audits part of a new requirement?...
FIRE ALARM SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. 1. Protected Property Information Name of property: Description
EN 4179/NAS 410 Interpretation The NANDTB has adopted NAS 410 / EN 4179 in lieu of AS 3669 as the standard for the qualification and approval of NDT technicians. Employers applying these standards sometimes