2 Getting Started Guide Is for quick commissioning with SDP and BOP. Part Number 6SE6400-5D00-1P0 Start-Up Guide Gives basic information necessary for mechanical installation, quick commissioning, nalog and Digital I/O settings, common applications with examples and troubleshooting specific for the MICROMSTER 440 Part Number Operating Instructions Gives information about features of the MICROMSTER 440, Installation, Commissioning, Control modes, System Parameter structure, Troubleshooting, Specifications and available options of the MICROMSTER 440. Part Number 6SE6400-5W00-0BP0 Parameter List The Parameter List contains the description of all Parameters structured in functional order and a detailed description. The Parameter list also includes a series of function plans. Part Number 6SE6400-5BB00-0BP0 Catalogs In the catalog you will find all the necessary information to select an appropriate inverter, as well as filters, chokes, operator panels and communication options. Part Number E86086-K Quick Start Guide MICROMSTER 440
3 Mechanical Installation 1 MICROMSTER 440 1/6 HP 350 HP Wiring Guidelines / Electrical Installation 50Hz / 60Hz Switch 3 2 Control Wiring Information 4 Quick Start Guide User Documentation Parameter Settings 5 Troubleshooting 6 Valid for Issue 05/04 Inverter Type Software Version MICROMSTER x 1/6 HP 350 HP MICROMSTER 440 Quick Start Guide 3
4 IMPORTNT NOTICE ll MM440s are UL approved UL listing can be determined by examining the inverter s Rating Label. For UL listed products the following UL mark is used: Operation with 1-ph 230V C line With the SW 2.08 and higher it is possible to supply the inverter 3 C 200 V- 240V also by an single-phase 230V line. The following restrictions have to be considered: - The devices can only operate with maximum 50% of the rated output current (VT). - The resulting output current is also possible in CT-operation. - n overload capability is not possible in both duty types. - In both of these cases, there is no longer an overload capability available. If the output current exceeds this limit, the drive unit shuts down,depending on the magnitude of the output current, in seconds with Fault "F0020" (phase failure). When utilizing the 50 % limit of the VT output current, the following input voltage range should be maintained: For Frame Sizes D and E: 230 V 15% -5% For Frame Size F: 230 V 15% -10% Further information can be obtained from Internet website: pproved Siemens Quality for Software and Training is to ISO 9001, Reg. No The reproduction, transmission or use of this document, or its contents is not permitted unless authorized in writing. Offenders will be liable for damages. ll rights including rights created by patent grant or registration of a utility model or design are reserved. Siemens G 2001, 2002, ll Rights Reserved. MICROMSTER is a registered trademark of Siemens Other functions not described in this document may be available. However, this fact shall not constitute an obligation to supply such functions with a new control, or when servicing. We have checked that the contents of this document correspond to the hardware and software described. There may be discrepancies nevertheless, and no guarantee can be given that they are completely identical. The information contained in this document is reviewed regularly and any necessary changes will be included in the next edition. We welcome suggestions for improvement. Siemens handbooks are printed on chlorine-free paper that has been produced from managed sustainable forests. No solvents have been used in the printing or binding process. Document subject to change without prior notice. User Documentation WRNING Before installing and commissioning the inverter, you must read all safety instructions and warnings carefully including all the warning labels attached to the equipment. Make sure that the warning labels are kept in a legible condition and replace missing or damaged labels. 4 Quick Start Guide MICROMSTER 440
5 Definitions and Warnings DNGER indicates an imminently hazardous situation which, if not avoided, will result in death or serious injury. WRNING indicates a potentially hazardous situation which, if not avoided, could result in death or serious injury CUTION used with the safety alert symbol indicates a potentially hazardous situation which, if not avoided, may result in minor or moderate injury. CUTION used without safety alert symbol indicates a potentially hazardous situation which, if not avoided, may result in a property damage. NOTICE indicates a potential situation which, if not avoided, may result in an undesirable result or state. For the purpose of this documentation, "" indicates important information relating to the product or highlights part of the documentation for special attention. Qualified personnel For the purpose of this Instruction Manual and product labels, a "Qualified person" is someone who is familiar with the installation, mounting, start-up and operation of the equipment and the hazards involved. He or she must have the following qualifications: 1. Trained and authorized to energize, de-energize, clear, ground and tag circuits and equipment in accordance with established safety procedures. 2. Trained in the proper care and use of protective equipment in accordance with established safety procedures Trained in rendering first aid. PE Protective Earth uses circuit protective conductors sized for short circuits where the voltage will not rise in excess of 50 Volts. This connection is normally used to ground the inverter. Is the ground connection where the reference voltage can be the same as the Earth voltage. This connection is normally used to ground the motor. Use for intended purpose only The equipment may be used only for the application stated in the manual and only in conjunction with devices and components recommended and authorized by Siemens. MICROMSTER 440 Quick Start Guide 5
6 Safety Instructions General The following Warnings, Cautions and Notes are provided for your safety and as a means of preventing damage to the product or components in the machines connected. This section lists Warnings, Cautions and Notes, which apply generally when handling MICROMSTER 440 Inverters, classified as General, Transport & Storage, Commissioning, Operation, Repair and Dismantling & Disposal. Specific Warnings, Cautions and Notes that apply to particular activities are listed at the beginning of the relevant chapters and are repeated or supplemented at critical points throughout these sections. Please read the information carefully, since it is provided for your personal safety and will also help prolong the service life of your MICROMSTER 440 Inverter and the equipment you connect to it. WRNING This equipment contains dangerous voltages and controls potentially dangerous rotating mechanical parts. Non-compliance with Warnings or failure to follow the instructions contained in this manual can result in loss of life, severe personal injury or serious damage to property. Only suitable qualified personnel should work on this equipment, and only after becoming familiar with all safety notices, installation, operation and maintenance procedures contained in this manual. The successful and safe operation of this equipment is dependent upon its proper handling, installation, operation and maintenance. Risk of electric shock. The DC link capacitors remain charged for five minutes after power has been removed. It is not permissible to open the equipment until 5 minutes after the power has been removed. The following terminals can carry dangerous voltages even if the inverter is inoperative: The power supply L/L1, N/L2, L3 resp. U1/L1, V1/L2, W1/L3 the motor terminals U, V, W resp. U2/T1, V2/T2, W2/T3 and depending on the frame size the terminals DC/B, DC-, B-, DC/R resp. C/L, D/L- HP ratings are based on the Siemens 1L motors and are given for guidance only; they do not necessarily comply with UL or NEM HP ratings. CUTION Children and the general public must be prevented from accessing or approaching the equipment! This equipment may only be used for the purpose specified by the manufacturer. Unauthorized modifications and the use of spare parts and accessories that are not sold or recommended by the manufacturer of the equipment can cause fires, electric shocks and injuries. 6 Quick Start Guide MICROMSTER 440
7 NOTICE Transport & Storage Keep these operating instructions within easy reach of the equipment and make them available to all users Whenever measuring or testing has to be performed on live equipment, the regulations of Safety Code BGV 2 must be observed, in particular 8 Permissible Deviations when Working on Live Parts. Suitable electronic tools should be used. Before installing and commissioning, please read these safety instructions and warnings carefully and all the warning labels attached to the equipment. Make sure that the warning labels are kept in a legible condition and replace missing or damaged labels. WRNING Correct transport, storage, erection and mounting, as well as careful operation and maintenance are essential for proper and safe operation of the equipment. CUTION Protect the inverter against physical shocks and vibration during transport and storage. lso be sure to protect it against water (rainfall) and excessive temperatures (see Table 4-1). Commissioning WRNING Work on the device/system by unqualified personnel or failure to comply with warnings can result in severe personal injury or serious damage to material. Only suitably qualified personnel trained in the setup, installation, commissioning and operation of the product should carry out work on the device/system. Only permanently-wired input power connections are allowed. This equipment must be grounded (IEC 536 Class 1, NEC and other applicable standards). Only type B ELCBs should be used with Frame Size to Frame Size F. Machines with a three phase power supply, fitted with EMC filters, must not be connected to a supply via an ELCB (Earth Leakage Circuit-Breaker - see VDE 0160, section and EN50178 section ). The following terminals can carry dangerous voltages even if the inverter is inoperative: The power supply L/L1, N/L2, L3 resp. U1/L1, V1/L2, W1/L3. the motor terminals U, V, W resp. U2/T1, V2/T2, W2/T3. and depending on the frame size the terminals DC/B, DC-, B-, DC/R resp. C/L, D/L- This equipment must not be used as an emergency stop mechanism (see EN 60204, ) CUTION The connection of power, motor and control cables to the inverter must be carried out as shown in Figure 2-6 Motor and Power Connections on page 21, to prevent inductive and capacitive interference from affecting the correct functioning of the inverter. MICROMSTER 440 Quick Start Guide 7
8 Operation Repair WRNING MICROMSTERS operate at high voltages. When operating electrical devices, it is impossible to avoid applying hazardous voltages to certain parts of the equipment. Emergency Stop facilities according to EN IEC 204 (VDE 0113) must remain operative in all operating modes of the control equipment. ny disengagement of the Emergency Stop facility must not lead to uncontrolled or undefined restart. Certain parameter settings may cause the inverter to restart automatically after an input power failure (e.g. automatic restart). Wherever faults occurring in the control equipment can lead to substantial material damage or even grievous bodily injury (i.e. potentially dangerous faults), additional external precautions must be taken or facilities provided to ensure or enforce safe operation, even when a fault occurs (e.g. independent limit switches, mechanical interlocks, etc.). Motor parameters must be accurately configured for motor overload protection to operate correctly. This equipment is capable of providing internal motor overload protection in accordance with UL508C section 42. Refer to P0610 and P0335, i2t is ON by default. Motor overload protection can also be provided using an external PTC (disabled by default P0601). This equipment is suitable for use in a circuit capable of delivering not more than 10,000 symmetrical amperes (rms), for a maximum voltage of 230V / 460V / 575V when protected by an H, K, or J type fuse, a circuit breaker or self-protected combination motor controller. The devices listed in this manual are provided to serve as a guide. Other devices which meet the requirements of the NEC (such as fuses, circuit breakers or combination motor controllers) with similar trip characteristics may be used in order to meet local or national electrical codes. This equipment must not be used as an emergency stop mechanism (see EN 60204, ) WRNING Repairs on equipment may only be carried out by Siemens Service Centers. ny defective parts or components must be replaced using parts contained in the relevant spare parts list. Disconnect the power supply before opening the equipment for access Dismantling & Disposal CUTION The inverter s packaging is re-usable. Retain the packaging for future use. Easy-to-release screw and snap connectors allow you to break the unit down into its component parts. You can then re-cycle these component parts, dispose of them in accordance with local requirements or return them to the manufacturer. 8 Quick Start Guide MICROMSTER 440
9 Table of Contents 1 Mechanical Installation Drilling Patterns and Dimensions Environment, Heat Loss and ir Flow Wiring Guidelines / Electrical Installation Power Terminal Layouts daptation of Fan Voltage (Only Frame Size FX and GX) Motor and Power Connections Recommended Power Supplies for 3ph Connection Removal of Y Capacitor Wiring Diagrams for Motors When to Use Line Reactors (Input Chokes) When to Use Load Reactors (Output Chokes) Fuses, Circuit Breakers, Line Reactors, Output Reactors Power Cable Dimensions Hz / 60Hz Switch How to Remove I/O Card to Get t Switches Control Wiring Control Block Diagram, Control Wiring Examples Setting Parameters Introduction to Basic Operator Panel (BOP) Factory Reset Commissioning an MM Reading Motor Name Plates Level 3 Quick Commissioning Checking Direction of Motor Rotation Parameter Filter Function Setting up Inputs and Outputs, Other Commonly Used Features Troubleshooting Troubleshooting Using the Status Display Panel (SDP) Faults and larms (Warnings) Where to Get dditional Technical Information MICROMSTER 440 Quick Start Guide 9
17 2 Wiring Guidelines / Electrical Installation 2.1 Power Terminal Layouts Frame Sizes to Frame Size F Frame Size Frame Sizes B & C Frame Sizes D & E Frame Size F Figure 2-1 Power Terminal Layouts Frame Size to Frame Size F MICROMSTER 440 Quick Start Guide 17
18 Issue 08/ Frame Size FX Power Terminals Hoisting eyes Shield connection Mains cable PE Cable opening for mains conection U1/L1, V1/L2, W1/L3 Cable opening C/L D/Lfor connection of an external braking unit Mains cable Phase U1/L1, V1/L2, W1/L3 Connection to Y-Capacitor Connection C/L D/Lfor external braking unit Top adjustment rail Top retaining screw Status Display Panel Electronic box Bottom adjustment rail Bottom retaining screw Fan screws Fan Shield connection control leads Fan fuses Transformer adaption Motor cable Phase U2/T1, V2/T2, W2/T3 Motor cable PE Shield connection Figure 2-2 Layout of Frame Size FX 18 Quick Start Guide MICROMSTER 440
19 Issue 08/ Frame Size GX Power Terminals Hoisting eyes Shield connection Mains cable PE Cable opening for mains conection U1/L1, V1/L2, W1/L3 Cable opening C/L D/Lfor connection of an external braking unit Mains cable Phase U1/L1, V1/L2, W1/L3 Connection to Y-Capacitor Connection C/L D/Lfor external braking unit Top adjustment rail Top retaining screw Status Display Panel Electronic Box Bottom adjustment rail Bottom retaining screw Fan screws Fan Shield connection control leads Fan fuses Transformer adaption Motor cable Phase U2/T1, V2/T2, W2/T3 Motor cable PE Shield connection Figure 2-3 Power Terminals Frame Size GX MICROMSTER 440 Quick Start Guide 19
20 2.2 daptation of Fan Voltage (Only Frame Size FX and GX) transformer is installed to adapt the cooling fan to the line voltage. It may be necessary to reconnect the transformer terminals on the primary side to match up with the line voltage. Figure 2-4 Frame Size FX, Frame Size GX Fan daptation Terminals You will most likely connect to the 480V terminals in the US however you should check to see what your actual line supply voltage is. CUTION If the terminals are not correctly connected according to the line voltage, the fan fuses can blow. Replacement for fan fuses Frame size Fuses (2 each) Recommended fuses Part Number for spare fuse FX (125HP CT) 1 / 600 V / slow-acting Cooper-Bussmann FNQ-R-1, 600 V or comparable fuse 6SL3352-7BE32-11 FX (150 HP CT) 2,5 / 600 V / slow-acting Ferraz Gould Shawmut TDR2-1/2, 600 V or comparable fuse 6SY7000-0C46 GX ( HP CT) 4 / 600 V / slow-acting Ferraz Gould Shawmut TDR4, 600 V or comparable fuse 6SY7000-0C48 Table 2-5 Replacement Fuses for Frame Size FX, Frame Size GX Fans 20 Quick Start Guide MICROMSTER 440
21 2.3 Motor and Power Connections MICROMSTER 440 drives and options should always be connected up in accordance with the diagram below: L3 L2 L1 N Fuse Optional Contactor Single Phase (Frame Sizes to C) Optional line choke Optional Filter MICROMSTER L/L1 U Motor V N/L2 PE W PE PE PE You should ensure that you have a common grounding point for all options and drives and motors - as shown L3 L2 L1 Fuse Optional Contactor Three Phase (Frame Sizes to F) Optional line choke Optional Filter MICROMSTER Motor L3 U L2 V L1 PE W PE PE PE You should ensure that you have a common grounding point for all options and drives and motors - as shown L3 L2 L1 Three Phase (Frame Sizes FX and GX) Fuse Optional Contactor Optional Filter Optional line choke MICROMSTER L3 U Motor L2 V L1 W PE PE PE You should ensure that you have a common grounding point for all options and drives and motors - as shown Figure 2-6 Motor and Power Connections MICROMSTER 440 Quick Start Guide 21
22 2.4 Recommended Power Supplies for 3ph Connection Wye Connection Neutral referred to ground Wye Connection With Station Ground L1 L2 L3 PE 3ph Drive L1 L2 L3 PE 3ph Drive Remove Y Capacitor Station Ground Wye Connection High resistance to ground Delta Connection One phase grounded L1 L2 L3 PE 3ph Drive L1 L2 L3 3ph Drive PE Remove Y Capacitor Remove Y Capacitor Station Ground Delta Connection One phase with high resistance to ground Delta Connection One phase grounded L1 L2 L3 PE 3ph Drive L1 L2 L3 PE 3ph Drive Remove Y Capacitor Remove Y Capacitor Figure Recommended Power Supplies For LL other line configurations an isolation transformer should be used with a grounded Wye secondary. 22 Quick Start Guide MICROMSTER 440
23 2.5 Removal of Y Capacitor On ungrounded power supplies, it will be necessary to disconnect the 'Y' capacitor from the inside of the unit and fit an output choke. For instructions on the removal of the Y Capacitor please see the operating instructions. The purpose of the choke is to limit high frequency circulating currents that can flow during ground faults. These would cause high currents in the output devices, leading to excessive dissipation and possible damage. Further Considerations: 1. Operation on ungrounded power supplies is only possible with unfiltered units. Filtered units (or units which do not have their 'Y' capacitors disconnected) will be damaged after running for a short time. 2. n output choke is recommended to limit the fault current during a ground fault. ll qualification tests have been carried out using an output choke. 3. It is often the case that ungrounded power supplies have high levels of transients and interference. Supplies should be checked for damaging transients before fitting MM4. If in doubt, an input choke should be installed. Supply arrangements: n ungrounded supply is one where the ground is not electrically connected to the inverter input (see section 2.4). This arrangement is sometimes used in industrial installations because, in the event of an ground fault occurring, the equipment may continue to run. CUTION Ungrounded does not mean there is no ground connection at all. ll Siemens drives must always be grounded. This is important for safety reasons. MICROMSTER 440 Quick Start Guide 23
24 2.6 Wiring Diagrams for Motors The diagrams below show the typical wiring notation found on NEM and IEC motors NEM Motor IEC Motor Figure 2-8 NEM Motor Connections Three-phase motor connection 3C 230/400 V 3C 400/690 V W2 U2 V2 W2 U2 V2 W2 U2 V2 W2 U2 V2 U1 V1 W1 U1 V1 W1 U1 V1 W1 U1 V1 W1 U1 230 V Line 400 V U1 U1 400 V Line U1 690 V V1 W1 Delta connection V1 W1 Star connection V1 W1 Delta connection V1 W1 Star connection Figure 2-9 IEC Motor Connections Refer to page 45 for information on reading the motor name plate data. 24 Quick Start Guide MICROMSTER 440
25 2.7 When to Use Line Reactors (Input Chokes) Line commutating chokes are used to smooth voltage peaks (line disturbances), or to bridge commutating dips. In addition, line commutation chokes reduce the effects of harmonics on the drive, and on the power supply. If the short circuit capability of the line supply is >100 times larger than the nominal input current of the drive then a line commutation reactor must be used. If the capability of the line supply is unknown then a line commutating reactor should also be used. Siemens offers a range of line reactors that are footprint-mountable up to Frame Size E (50HP CT, 460V), reducing enclosure space and offering a very neat solution. 2.8 When to Use Load Reactors (Output Chokes) Load reactors should be used when motor cables exceed the following lengths: For drives HP, 150 Feet (Shielded) 300 Feet (Unshielded) For drives HP, 300 Feet (Shielded), 450 Feet (Unshielded). Siemens offers a range of output chokes that are footprint-mountable up to Frame Size C (15HP CT, 460V), reducing enclosure space and offering a very neat solution. The table below shows the shielded cable lengths that can be attained using the Siemens load reactors. You can get approximately 50% more length if you use unshielded cable. Frame Size Choke Part Number ± 10% ± 10 % ± 10 % ± 10 % 6SE6400-3TC00-4D3 600 feet SE6400-3TC00-4D2 600 feet 450 feet 300 feet - B 6SE6400-3TC01-0BD3 600 feet 450 feet 300 feet - C 6SE6400-3TC03-2CD3 600 feet 600 feet 300 feet - C 6SE6400-3TC01-8CE feet Table 2-10 Cable lengths using Siemens Load Reactors For all other frame sizes, Siemens load reactors allow up to 600 feet with shielded cable or up to 900 feet with unshielded cable across the recommended voltage range. MICROMSTER 440 Quick Start Guide 25
MICROMASTER 430 7.5 kw - 250 kw Operating Instructions Issue 07/05 User Documentation 6SE6400-5AE00-0BP0 MICROMASTER 430 Documentation Getting Started Guide Is for quick commissioning with SDP and BOP-2.
Issue 03/05 Faults and Alarms 5 Faults and Alarms 5.1 Fault messages In the event of a failure, the inverter switches off and a fault code appears on the display. NOTE To reset the fault code, one of three
MICROMASTER 440 0.12 kw - 250 kw Operating Instructions Issue 10/06 User Documentation 6SE6400-5AW00-0BP0 MICROMASTER 440 Documentation Getting Started Guide Is for quick commissioning with SDP and BOP.
MTE SERIES RLW World REACTORS USER MANUAL PART NO. INSTR 030 REL. 090930 2009 MTE Corporation IMPORTANT USER INFORMATION NOTICE MTE Series RLW reactors are components designed to improve the reliability
PowerFlex 700S and 700H Frame 12 DC Bus Connector Kit Installation Instructions This document provides instructions for the installation of a DC bus connector kit for PowerFlex 700S and 700H frame 12 drives
3.2 Standard Connection Diagram 3.2 Standard Connection Diagram Connect the drive and peripheral devices as shown in Figure 3.1. It is possible to run the drive via the digital operator without connecting
GPD 506/P5 Start-up Procedure and Checklist Preparation for GPD506/P5 Drive Start-Up...2 HVAC Start-Up Procedure for GPD 506/P5 WITH Bypass Option:...4 HVAC Start-Up Procedure for GPD 506/P5 WITHOUT Bypass
Automation System TROVIS 6400 TROVIS 6493 Compact Controller For panel mounting (front frame 48 x 96 mm/1.89 x 3.78 inch) Application Digital controller to automate industrial and process plants for general
MICROMASTER 440 0.12 kw - 250 kw Operating Instructions Issue 07/05 User Documentation 6SE6400-5AW00-0BP0 MICROMASTER 440 Documentation Getting Started Guide Is for quick commissioning with SDP and BOP.
SIMATIC S7-300 Getting Started for First Time Users Order No.: 6ZB5310-0NC02-0BA0 04/2007 A5E01094750-01 Safety Guidelines This manual contains notices you have to observe in order to ensure your personal
..OR How To Protect your 3-Phase Equipment Investment with 3-Phase Monitors from Time Mark... TIME MARK CORPORATION 11440 EAST PINE STREET TULSA, OK 74116 USA tel 918 438-1220 fax 918 437-7584 www.time-mark.com
Compact Variable Frequency Drive INSTALLATION GUIDE 62-0269 01 Honeywell Technical Support 888-516-9347 Honeywell Customer Web-site: customer.honeywell.com VFD technical data can be accessed via: customer.honeywell.com/vfd
General information The construction of is based on ABB A Line contactors. The mounting plate, including a built-in A contactor, is designed to integrate an ABB manual motor starter type MS325. Starters
Oil and Coolant Circulating Heating System Model - OCSM Installation & Operation Manual 216280-000 REV 2 Identifying Your System The HOTSTART heating system is designed to heat fluids for use in marine
Characteristics variable speed drive ATV32-7.5kW 400 V - 3P - Bluetooth built-in - w heat sink Main Range of product Altivar 32 Product or component type Product destination Product specific application
Adjustable Frequency Drive Instruction Manual VLT Series 3500 Instruction Manual 175R5237 - Document Version 5.00 This manual applies to all VLT Series 3502-3800 Adjustable Frequency Drives with software
VFD 101 Lesson 3 Parts of a Variable Frequency Drive (VFD) This lesson covers the parts that make up the Variable Frequency Drive (VFD) and describes the basic operation of each part. Here is the basics
Data sheet Measuring and monitoring relays CM-MSS (4), Thermistor motor protection relays The devices CM-MSS (4) and (5) are used to monitor the overload of motors by the wiring temperature. The motors
MICROMASTER 430 7.5 kw - 250 kw Operating Instructions Issue 10/06 User Documentation 6SE6400-5AE00-0BP0 MICROMASTER 430 Documentation Getting Started Guide Is for quick commissioning with SDP and BOP-2.
543-0032-00, 943-0032-00 User s Manual 1 Comfort Alert Diagnostics Faster Service And Improved Accuracy The Comfort Alert diagnostics module is a breakthrough innovation for troubleshooting heat pump and
782 Electric Latch Retraction Controller Installation Instructions The 782 is designed to be used with UL Listed Yale 7000P series (electric latch retraction) or Corbin Russwin ED4000/ED5000 x M94 series
Contents English Page Safety Precautions and Warnings.............................................................. 5 1. OVERVIEW................................................................................
Powered by Eaton Technology VSD Series Drives User Manual Supersedes September 2006 LIT-1201828 For more information visit: www.johnsoncontrols.com Powered by Eaton Technology VSD Series Drives User Manual
Variable Freq Drives 26 29 23 The following information shall be included in specifications prepared for use on all University of Cincinnati construction and renovation projects. This information is supplemental
MCR1900 Media Converter 19-Slot Chassis Installation Guide Part #5500304-11 Copyright Statement This document must not be reproduced in any way whatsoever, either printed or electronically, without the
Safety Requirements for Power Supplies Intended for Medical Applications Disclaimer: Emerson does not warrant the accuracy or completeness of this article, including but not limited to, the reliability
MAKING MODERN LIVING POSSIBLE Operating Instructions VLT HVAC Drive FC 102, 1.1-90 kw Safety Safety WARNING HIGH VOLTAGE! Frequency converters contain high voltage when connected to AC mains input power.
Bulletin 1365 Startup and Adjustment Only qualified electrical personnel familiar with the construction and operation of this equipment and the hazards involved should install, adjust and/or service this
MICROMASTER 440 Operating Instructions Issue B1 User Documentation MICROMASTER 440 Documentation Getting Started Guide Is for quick commissioning with SDP and BOP. Operating Instructions Gives information
Product and functional description The KNX / DALI gateway N 141/02 is a 4 MU wide, DINrail mounted KNX device with one DALI interface to which up to 64 DALI actuators (e.g. DALI ballasts) can be connected
Technical Description Transistor D.C. Chopper Controller Type GS 24 S Table of contents 1. Getting started guide 2. General information 2.1. Characteristics 2.2. Accessories 3. Information about the Machine
Installation Manual Version 7.3 IMPORTANT: READ ENTIRE MANUAL CAREFULLY, THIS PHASE CONVERTER MUST BE INSTALLED BY A INDUSTRIAL LICENSED ELECTRICIAN 230 VOLTS MODEL ONLY READ FIRST!!!!!! DANGER: HIGH VOLTAGE
Specifying a Variable Frequency Drive s Put on by Bruce Reeves and Jeremy Gonzales Dykman Electrical Covering the Western US For all of your VFD and Soft Start and Motor Needs How To Specify a Variable
VFD 101 Lesson 4 Application Terminology for a VFD This lesson covers the application terminology associated with a Variable Frequency Drive (VFD) and describes each term in detail. When applying a Variable
425 CONTROLS DATA MANAGEMENT PROCESS AUTOMATION EUROCUBE General purpose single phase thyristors and solid state relays Product data abc 425 EUROCUBE A complete range of low cost solid state relays and
LIFT CONTROL SYSTEMS CATALOGUE 2007 All Your Needs For Elevators INDEX 1. Lift Control Cards... 3 2. Speed Control Units... 7 3. Emergency Rescue Cards... 8 4. Lift Control Panels... 10 5. Photocells...
NX Series Inverters HVAC Pocket Programming Guide HVAC Pocket Programming Guide HVAC Pocket Programming Guide / Contents This guide provides a single reference document for the user of NXL HVAC (product
Ametek, Rotron Technical Products Division 627 Lake Street Kent, Ohio 44240 User's Guide 120 Volt, 800 Watt and 240 Volt, 1200 Watt Brushless Motor Drive Electronics 5.7" (145 mm) and 7.2" (183 mm) Windjammer
Type VariFlex 2 RVCF Product Description VariFlex 2 RVCF is a simple, compact general purpose AC variable speed drive for use with AC induction motors. A full range of power rating is available from 0.4kW
This Quick Start Guide is designed to familiarize the user with the connection and configuration of the DTS-305 DIN rail mounted single / 3 phase power & energy meter with RS-485 or TCP communications.
$25.00 BDI 1100 Frequency Inverter Installation and Operating Manual 12/96 MN71100 Table of Contents Section 1 General Information............................. 1-1 Introduction....................................
Installation and Operating Instructions AC Variable Speed Drive 0.75kW - 160kW 200-480 Volt 1 & 3 Phase Easy Start Up Guide: QD:HVAC IP55 Mechanical Mounting Information can be found on page 12 HVAC Display
Data sheet Three-phase monitoring relay CM-PFE The CM-PFE is a three-phase monitoring relay that monitors the phase parameter phase sequence and phase failure in three-phase mains. 2CDC 251 005 S0012 Characteristics
Variable Air Volume (VAV) EC Motor Control G3 PWM BARD The Enviro-Tec Generation 3 PWM (G3 PWM) board provides a pulse-width modulated (PWM) signal to the EC motor to control fan speed. The board is factory
LIFT CONTROL SYSTEMS CATALOGUE 2007 All Your Needs For Elevators INDEX 1. Lift Control Cards... 3 2. Speed Control Units... 7 3. Emergency Rescue Cards... 8 4. Lift Control Panels... 10 5. Photocells...
Contents Introduction Safety...3 Safety Guidelines...3 Warnings Against Unintended Start...3 Introduction...4 About this manual...4 Assumptions...4 References...4 Trademarks...5 Programming the VLT 6000
Rectiverter Wiki The RECTIVERTER is a technology created by Eltek. The Rectiverter is a three port module with an AC input port, an AC output port, and a bidirectional DC port. It is intended for the use
RANCO INSTALLATION INSTRUCTIONS ETC TWO STAGE ELECTRONIC TEMPERATURE CONTROL Relay Electrical Ratings PRODUCT DESCRIPTION The Ranco ETC is a microprocessor-based family of electronic temperature controls,
Installation, Operation and Maintenance Manual VLT 6000 Series Adjustable Frequency Drive 12/01 23-6108-00 Revision K Rotating shafts and electrical equipment can be hazardous. Therefore, it is strongly
MAKING MODERN LIVING POSSIBLE Operating Instructions VLT Frequency Converters - Safe Torque Off www.danfoss.com/drives Contents Contents 1 Introduction 2 1.1 Purpose of the Manual 2 1.2 Additional Resources
SECTION 26 29 23 VARIABLE FREQUENCY DRIVES PART 1 GENERAL 1.01 SCOPE A. Furnish and install individual freestanding variable frequency AC drives (VFD) as shown on the Drawings and specified herein. 1.02
SINAMICS DCM DC converters from 6 kw to 2500 kw for variable-speed direct-current drives Edition 01-12/2010 SINAMICS drives SINAMICS DCM Compact User Manual Legal information Warning notice system This
The cost effective starter for all AC induction motors from 4A 2800A The choice for small to medium industrial applications The XFE Soft Starter range provides a combination of competitive prices, flexible
Form: RLW-TRM-E Rel: March 2011 Form RLW-TRM-E March 2011 Page 1 Table of Contents STANDARD DELIVERY SCHEDULE... 3 SELECTION & APPLICATION GUIDE... 4 MODEL CODE PART NUMBER CONFIGURATION... 5 RL REACTOR
Drive Technology \ Drive Automation \ System Integration \ Services Addendum to the Operating Instructions MOVIMOT with AS-Interface and AC Motor DT/DV Unit Replacement MOVIMOT MM..C -> MM..D with MLK3A
Specification Guide 1.0 General 1.01 The electronic overload relay shall be available in NEMA and IEC contactor mount configurations. 1.02 The electronic overload relay shall be capable of being applied
Important User Information Thank you for purchasing LS Variable Frequency Drives! SAFETY INSTRUCTIONS Always follow safety instructions to prevent accidents and potential hazards from occurring. In this
MAKING MODERN LIVING POSSIBLE AK-SC255 On-Site Installation Guide DANFOSS ELECTRONIC CONTROLS & SENSORS How to Use This Guide Read this Guide completely as you install and start up your new AK-SC 255 controller.
Flex Power Supply E N G / 0 5. 2 0 1 3 One solution, many applications A new way to make and use Power Supplies Yet another strong proposition by Adelsystem for power supplies and power continuity specialists.
Solid Core and Split Core Adjustable Current Status Switches CSS-O, CSS-C; CSP-O, CSP-C DESCRIPTION FEATURES PRODUCT DATA Very low operating trip points LED status indication Integral DIN rail mounting
Type: DILM115(RAC240) Article No.: 239548 Sales text Contactor,55kW/400V,AC operated Ordering information Connection technique Description Description Rated operational current Screw terminals 3 pole AC
SIMATIC ET 200S distributed I/O SIMATIC ET 200S distributed I/O 2AO I ST analog electronic module (6ES7135-4GB01-0AB0) Manual Preface Properties 1 Parameters 2 Diagnostics 3 Analog value representation
Fan and Pump AC Inverter Key Features for Fan and Pump Applications PID and Auto Energy Saving Functions. Input Phase Loss and Output Phase Loss Protection. LCD Keypad can be used to copy parameter settings
Preface Contents SIMATIC NET CP 243-2 AS-Interface Master Manual Technical Description and Installation Instructions Interface to the User Program 2 in the S7-200 CPU Access to the Data of the AS-i Slaves
Description Power Range NOTE: This product has been replaced by the AxCent family of servo drives. Please visit our website at www.a-m-c.com or contact us for replacement model information and retrofit
PowerXL DE1 Variable Speed Starter www.eaton.eu/de1 Number 1 in efficiency The easiest way of variable motor speed NEW Variation DE11 The new device category! The PowerXL DE1 Variable Speed Starter Why
DOCUMENT: ECSEQ6-0 EFFECTIVE: 09/23/10 SUPERSEDES: Operational Overview and Controls Guide Two or Three Pump IronHeart Lite with Variable Frequency Drives 6700 Best Friend Road. Norcross, GA 30071. (770)
Features: INSTALLATION Install in accordance with NFPA 70. DORMA MODEL PS-406BB POWER SUPPLY INSTALLATION INSTRUCTIONS Up to 1.95 Amps Load Capacity Class 2 Rated Outputs Overload, Over Voltage, and Short
Manual No. YEG-TOE-S616-55.1-OY VARISPEED F7 Control Frequency Inverter USER S MANUAL Table of Content Warnings... VII Safety Precautions and Instructions for Use... VIII EMC Compatibility... X Line Filters...
Keithley Instruments 28775 Aurora Road Cleveland, Ohio 44139 1-888-KEITHLEY http://www.keithley.com Model 1756 Test Lead Kit Gerneral Purpose Test Lead Information Description These test leads allow you
Mobile Data Power Model: MDP-25 Topic Section Features... 2 Operational Features Summary... 2 Back-up Battery Power Internal Charger Voltage Spike Protection RF Noise Filtering Warning of Imminent Loss
Installation Instructions This document provides you with the following information: Because of the variety of uses for the products described in this publication, those responsible for the application
The versatile inverter for low power ratings Brochure August 2008 SINAMICS The ideal introduction The more flexible an inverter, the better it is. And if it s simple to install and straightforward in operation,
E031026 000823 Process modules Digital input PMI for inputs for 120 V AC inputs PMI Input E4, E5, GND L- PMI 120 V AC Input E4, E5, Common C E6, E7, GND L- E6, E7, Common C LEDs for the inputs operation
Siemens Standard Drives Application Handbook Martin Brown Siemens Standard Drives Congleton December 1997 1. Introduction....4 1.1 What is a Variable Speed Drive?...4 1.2 The Variable Frequency Inverter...7
AC variable speed drive for use with AC induction motors V/F control + Auto-torque compensation function Input voltage ranges: 1-ph 200~240V, 3-ph 380~480V 2 frame sizes Conforms to EMC standard EN 61800-3
SAFETY PRECAUTIONS AND INSTRUCTIONS FOR USE OF TECHNICAL INFORMATION Please read and understand the product instruction manual before installing, servicing or operating Yaskawa products. Technical content
Your consent to our cookies if you continue to use this website.