1 Well and Water System Disinfection For Private Wells Minnesota Department of Health 625 North Robert Street, P.O. Box Environmental Health Division St. Paul, Minnesota or This fact sheet contains a step-by-step procedure for performing a simple disinfection of private wells and water (plumbing) systems using chlorine bleach (sodium hypochlorite). Please read the entire fact sheet before starting any well disinfection. If you are not comfortable with this procedure, or for complex water systems or severe contamination problems, a licensed well contractor or pump installer can disinfect your well and water system for you. What is Disinfection? Contaminated drinking water may contain harmful bacteria, viruses, or other microorganisms that can make you sick. Disinfection is one process of killing or inactivating microorganisms to make water safe for drinking. Disinfection can also eliminate nuisance bacteria that can cause unpleasant tastes and odors. What Causes Well and Water System Contamination? A well or water system may become contaminated with harmful bacteria and other organisms when the well or plumbing is open to the environment during construction, repair, or routine maintenance. A well may also become contaminated if the well casing is deteriorated or damaged, or if the well is flooded. Contamination problems can also be caused by improper plumbing connections between water treatment devices and wastewater piping, between the potable water plumbing and heating/cooling systems, or other cross connections. How Often Should a Well be Tested? Typically, a well should be tested once a year for coliform bacteria, or whenever there are changes in the water s taste, odor, or appearance. The coliform bacteria test analyzes for a number of bacterial species. Most of these are not harmful, but a few are. Their presence indicates that surface contamination has found its way into the well, and disease organisms may also be present. The presence of E. coli or fecal coliform represents a more serious health risk and any water use should be strictly limited to nonpotable uses (not used for drinking, cooking, or human contact). Water samples should be analyzed for coliform bacteria by a laboratory that has been certified by the Minnesota Department of Health (MDH). A list of these labs can be found through the MDH s website at: or by contacting the MDH at or Check with the water testing laboratory about the procedure for collecting water samples and how long the samples are accepted for testing. Chlorine must be absent prior to taking a water sample for bacterial testing. Be aware that any amount of chlorine left in the system may erroneously result in a negative coliform bacteria test.
2 Minnesota Department of Health 2 Procedure for collecting a water sample: Collect a water sample from a regularly used cold water faucet. If possible, collect the sample from a solid faucet rather than a swing faucet or a pull out type of faucet. Remove the screen aerator from the end of the faucet and let the cold water run at medium force for at least five minutes prior to filling the bottle. Have the water sample tested for coliform bacteria by a MDH-certified lab. Follow the instructions provided by the lab for collection of the water sample. If the water sample shows the presence of coliform bacteria, the well and water system needs to be disinfected and the water should not be used for drinking, food preparation, making ice, brushing teeth, or dishwashing until the bacteria are eliminated. When Should a Well Be Disinfected? Well disinfection should be performed: When water testing indicates the presence of coliform bacteria. When the well has been near flood waters. See the MDH fact sheet Disinfecting Flooded Wells. After installation or repair of plumbing pipes and fixtures, e.g., softeners, faucets, and filters. After well or pump repairs. When iron or sulfur bacteria reduce the water supply capacity of the well or cause taste and odor problems. During startup of seasonal wells where plumbing, wells, or pumps have been disconnected, or the water system has otherwise been drained or opened. Well disinfection will not solve the following problems: When contamination is originating from a continuous source such as a septic system or an animal feedlot. When a well or plumbing system is improperly constructed, located, or damaged and in need of repair (disinfection should follow repair work). If the contaminant is nitrate, arsenic, fuel, pesticides, or other chemicals. Safety Precautions ELECTRICAL SAFETY EXTREME CAUTION is advised when disinfecting a well, as you often will be working with electricity and water. Electricity can kill you. If you are not acquainted with working with electricity, seek professional advice. Your safety precautions should include: Turn off the pump circuit breaker before removing the well cap and while working on the well. While the breaker is off, examine for chafed wire insulation or missing wire nuts and repair as necessary. Wear rubber soled shoes or boots, preferably waterproof.
3 Minnesota Department of Health 3 CHEMICAL SAFETY Severe eye damage may result from contact with bleach or chlorine solution. Always follow the manufacturer s use and safety directions. Avoid eye and skin contact. Wear protective goggles or a face shield and rubber gloves when working with the bleach or chlorine solution. Handle and dispose of chlorine with care. Do not mix chlorine with other chemicals, as mixing chemicals may form harmful gases. Do not leave bleach bottles lying around ingestion of bleach is the most common cause of poisoning of children in the U.S. RESPIRATORY SAFETY Underground well pits pose an extreme hazard, as they frequently contain a build-up of toxic gases or simply lack enough oxygen to sustain life. Access is limited, making quick escape difficult. If your well is located in an underground well pit, DO NOT ENTER IT. Death can occur even in a shallow well pit. Leave disinfection of wells in pits to professional, licensed well contractors, or pump installers. Harmful gases may be generated during disinfection. Avoid inhalation of fumes and make certain that enclosed spaces such as well rooms have adequate ventilation before starting disinfection. Procedure for Disinfection of the Well and Water System The following procedure is for a well that has a submersible pump with either a removable well cap or a well seal with a threaded plug in it. See STEP 4 to determine whether you have a well cap or a well seal. If the well has a sanitary seal, this procedure can only be attempted if a removable threaded plug in the sanitary seal allows access into the well. If your well has a type of pump other than a submersible pump, is located in a well pit, is a flowing well, or has a sanitary seal without a threaded plug, you should contact the MDH for advice or have your well disinfected by a licensed well contractor or licensed pump installer. STEP 1 - Isolate critical water system components Bypass water softeners and other water system components, such as the dishwasher and the washing machine, that may be damaged by chlorine prior to initiating this well disinfection procedure. Since water softeners, water filters, and other water treatment or water using devices may harbor organisms, it will be necessary to separately disinfect the softener and other devices. Water treatment devices should be disinfected separately according to the information provided by the manufacturer or water conditioning contractor. If this information is not available, see the section on disinfecting water treatment equipment and water using devices at the end of this fact sheet. Turn off and drain the water heater. Use caution to avoid scalds or burns. Follow procedures as described by the manufacturer or plumber.
4 STEP 2 - Mixing a chlorine solution Minnesota Department of Health 4 Sodium hypochlorite is the disinfectant found in laundry bleach and is the recommended product for well disinfection. Since bleach loses its disinfecting capacity over time it is important that a fresh container be used. Do not use laundry bleach that contains any fragrance or other additive. Place a large clean bucket near the well. Add 1 gallon of water and the amount of bleach indicated in the table to the left and mix thoroughly. Diameter of Well Depth of Well in Feet in Inches or less 1/8 1/4 1/ /2 1 2 s s 1 quart This table indicates the amount of laundry bleach (6.0 percent sodium hypochlorite or 5.7 percent available chlorine) that should be used for well disinfection. For wells greater than 100 feet deep or with well casing diameters greater than 6 inches, mix the bleach with 2 gallons of water. For wells greater than 200 feet deep or with well casing diameters greater than 6 inches, increase the amount of bleach proportionately. After this solution is poured into the well, it will provide a chlorine concentration of at least 50 parts per million. WARNING: If your well has not been disinfected for many years, it may have considerable scale built up. Disinfecting with a strong chlorine solution can dislodge this scale and plug or damage your pump, and/or cause problems elsewhere in the plumbing system. You may wish to begin with a weaker solution of chlorine. If the water runs red or brown, pump it out on the ground surface without recirculating it back into the well as described in STEP 6. Once the color gets lighter, mix a new chlorine solution batch as described in STEP 2 and begin the process again. In situations where an initial disinfection has not worked, where there is considerable iron or other solids in the well, or where there is a significant nuisance bacteria problem, a more concentrated chlorine solution may be used. Multiply the quantities of chlorine listed in the table above by four and mix with 4 gallons of water (for example, a 4-inch diameter well that is feet deep would need 4 s of bleach mixed with 4 gallons of water). This will provide a chlorine concentration of at least 200 parts per million in the well and water system. NOTE: Too strong a chlorine solution will reduce the effectiveness of disinfection. If the chlorine concentration greatly exceeds 200 parts per million, it can actually make the water too alkaline and reduce the effectiveness of the disinfection process.
5 Minnesota Department of Health 5 STEP 3 - Electrical safety Turn off electrical power to the pump by turning off the circuit breaker or unscrewing the fuse. If the breaker or fuse box has a lockout hasp to prevent someone from accidentally turning on the water pump circuit breaker, use it. Power should not be turned back on until STEP 6 or after the chlorine solution has been placed in the well. STEP 4 Opening the well Do not place well components directly on the ground. Determine whether your well has a well cap or a well seal. A well cap overlaps the top of the well casing and is held in place with bolts or set screws. A sanitary seal fits tightly within the very top of the well casing. Only a professional should remove a sanitary seal. If a well has a well cap, the discharge pipe from the well is usually underground. If the well has a well seal, the discharge pipe from the well is usually through the top of the well. If you are unsure as to whether your well has a well cap or a well seal, you should seek professional advice. With electrical power off, open the well. If your well has a well cap, remove the bolts along the outside edge of the top of the well cap for newer models, or loosen the set screws on the side of the cap for older models and lift off the cap. Gently lift the wires/wire nuts out and pull to the side. Do not pull on the release cable or pull the pipe for the pitless adapter and pump. Check for damaged wires/wire nuts. Be careful not to loosen any connections. If your well has a well seal with a threaded plug, you can remove the plug and pour the chlorine solution through the hole. If there is no threaded plug in the well seal, you should have the well disinfected by a licensed well contractor or licensed pump installer. The well seal has bolts that compress the seal. Loosening the bolts too far may cause a portion of the seal or the pump to fall into the well. Do not remove or loosen the bolts. Do not remove the well seal. STEP 5 - Adding chlorine to the well Pour the mixture into the well and avoid spilling on any wire connections. A funnel should be used for pouring the chlorine solution into small openings. Be careful not to splash/spill the concentrated solution. Wear gloves and goggles. Do not use a siphon.
6 STEP 6 - Recirculating chlorinated water Minnesota Department of Health 6 Recirculating the chlorinated water mixes the water column thoroughly and distributes the chlorine. It helps to wash down the inside sidewalls of the well casing, pump wires, and drop pipe. Turn on the power to the pump. Connect a clean garden hose to a nearby yard hydrant or an outside faucet. Run the water out of the hose in an area away from the well for approximately 10 minutes until the water runs clear. You may notice that the water coming from the garden hose turns red, yellow, or brown. This is due to the chlorinated water precipitating iron from the water. The chlorinated water may also dislodge scale or rust from the sides of the well casing. Scale, iron, manganese, or other precipitated minerals may form when the chlorine is added to the system. These solids can cause clogging of faucet aerators, valves, water solenoids, and equipment using filters. Run the water out on the ground until the water runs clear. Additional chlorine solution may need to be added to the well. Do not run discolored water through the household plumbing, and do not run it into a septic system. Since a strong chlorine solution may harm vegetation, dispose of the chlorinated water away from sensitive plants. Do not discharge water into a lake or stream as this may harm aquatic life. When the water coming from the garden hose is relatively clear, turn the water off, place the garden hose into the top of the well casing and run water into the well. After the chlorine smell is first detected from the garden hose, recirculate the water back into the well for about two hours. You can use chlorine test papers, such as those commonly used to check the chlorine in swimming pools, to provide a visual indication that chlorine is present. Turn off the power to the pump. Remove the garden hose from the well casing and replace the well cap or threaded plug in the well seal.
7 STEP 7 - Bringing chlorinated water to each faucet Minnesota Department of Health 7 Turn on the power to the pump. Run chlorinated water through the entire plumbing system by running water to each fixture* one at a time until you smell bleach (or use chlorine test papers available at pool supply businesses) and then close the fixture. Do this for each fixture, including: Cold and hot water faucets. Toilets and shower/bath fixtures. Any outside faucets or yard hydrants. *Faucet aerators may need to be removed if clogging occurs from precipitated iron or loosened scale. Leave the chlorinated water in the system a minimum of two hours and preferably at least six hours or overnight. WARNING: Chlorine can cause eye damage and skin irritation. In addition to not using the water for consumptive purposes, all potential water users need to be warned that a potentially dangerous concentration of chlorine is in the water system. Do not shower/bathe with water containing high levels of chlorine. You may wish to place a pail or bag over each faucet as a reminder. STEP 8 - Removing the chlorinated water Run a garden hose from an outside faucet or yard hydrant to flush the chlorine out of the system. It can take 30 minutes to 24 hours or more to flush all of the chlorine from the well. Do not run the chlorinated water into your septic system as this can kill many of the beneficial bacteria in the system. Also, the amount of water required to flush the well may hydraulically overload and damage the septic system. Since a strong chlorine solution may harm vegetation, dispose of the chlorinated water away from sensitive plants. Do not discharge water into a lake or stream as this may harm aquatic life. Once the chlorine is gone from the well, open up each fixture one at a time until the chlorine smell is no longer present. This will purge the remaining chlorine from the water system. It should take just a few minutes to flush out the chlorine from the cold water lines. The hot water faucets will have to be run longer. In some cases, it may be quicker to drain the water heater(s) again. The small amount of chlorinated water flushed from the water pipes can be run into a septic tank.
8 Minnesota Department of Health 8 STEP 9 Reconnecting water softeners and other water treatment devices STEP 10 Testing your water Return bypass valves to on or service position after following the manufacturer s directions to disinfect these devices. Refill the water heater if applicable. Start the water heater. Make sure the chlorine has been removed from the water system. It is recommended that a sample be collected a couple days after the well is disinfected. Do not use the water for drinking, cooking, or food preparation until it tests free of coliform bacteria. Follow the procedure for collecting a water sample given on the first page of this fact sheet. Procedure for Disinfection of Water Softeners, Water Treatment Equipment, and Water Using Devices Water softeners, water treatment equipment, and water using devices, such as dishwashers and washing machines, may be damaged by excessive amounts of chlorine. However, the softener and other devices should be disinfected when there are bacteria problems in the plumbing. After step 8, follow the manufacturer s instructions for disinfecting the particular unit you have. If the disinfection information is unavailable, the following steps can be used, as recommended by the Water Quality Association, a notfor-profit international trade organization representing the household, commercial, industrial, and small community water treatment industry. For further questions regarding this section, contact the association at or visit the website at: 1. Water Softeners Keep unit on bypass until chlorine is flushed out of the system. To thoroughly disinfect the softener after all the chlorine is flushed from the system, add one-half bleach to the softener s brine tank and run the unit through a regeneration cycle immediately. 2. Water Filters For carbon filters and other cartridge water filters, remove and discard the old filter cartridge. Wash the sump and head with laundry detergent and bleach and rinse. Insert a new cartridge filter. For whole-house carbon tank filters or a water softener that contains carbon, empty the entire media bed. Thoroughly clean the empty unit inside and out with a laundry bleach and water solution. Re-bed the unit using new carbon or other media/carbon mix.
9 Minnesota Department of Health 9 3. Reverse Osmosis (RO) Systems Turn off the water supply to the RO unit and open the RO faucet to relieve pressure and drain the RO storage tank. Remove and discard the pre- and postfilters and remove the RO membrane element. Clean and disinfect the filter sumps, the filter heads, and the RO membrane housing and end caps. Fill the first prefilter sump with water to within about 2 inches from the top and add 1 ounce (2 tablespoonfuls or 6 teaspoonfuls) of unscented laundry bleach (6.0 percent sodium hypochlorite or 5.7 percent available chlorine); carefully reassemble this first prefilter with the chlorine/water mixture but without its filter cartridge element in place. Reassemble all the remaining housings without their membrane element and filter cartridge elements in place. Open the water supply to the RO. Open the RO faucet and allow water to run until you can begin to smell the chlorine bleach. (If no chlorine bleach smell can be obtained, go back to bullet point three and increase the amount of laundry bleach added until a residual can be maintained throughout the system.) Close the RO faucet and allow the storage tank to fill and then remain full for minutes. Open the RO faucet again and leave it open until the entire chlorine bleach smell is gone. Let the accumulated water in the RO storage tank drain completely. Turn off the water supply to the RO. Close the RO faucet after all the pressure has been relieved and the water flow stops. Install all new pre- and postfilter elements, using careful aseptic techniques so as to not recontaminate the RO system. Reinstall the RO membrane element in its housing. Fill the membrane element housing with water and 1 milliliter (20 drops) of laundry bleach. Reassemble this membrane element, chlorinated water, and housing unit.* Continue on page 10. *CAUTION: High levels of chlorine over an extended period of time can degrade polyamide thin film composite (TFC) RO membranes, although significant degradations should not occur in these specified few minutes of chlorine contact time.
10 Minnesota Department of Health 10 Immediately reopen the water supply to the RO system and reopen the RO faucet. Let water drip from the RO faucet until the chlorine bleach smell has dissipated. Finally, close the RO faucet, let the storage tank completely refill, and discard the first full tank of water following the completion of this procedure. Follow-up It is a good idea to double check that the water is safe. After receiving the results of a satisfactory sample analysis, take another water sample approximately 30 days after the first sample and have the water retested. If coliform bacteria are detected again, redisinfect the well using the same procedure. If the well and water system have not been disinfected for many years, they may need to be disinfected more than once. If multiple disinfections are unsuccessful, and coliform bacteria persist, contact a licensed well contractor or pump installer who can utilize special techniques and equipment to disinfect the well. The well may have to be physically cleaned or treated with other chemicals. The homeowner, well contractor, or pump installer should also inspect the well for any damage. Well casings can be cracked or well caps loosened if struck by vehicles or by garden or farming equipment. It is essential that any plumbing or well defects that could allow surface water or other contaminants to enter the well be corrected. If the well cannot be successfully disinfected, the source of the contamination should be determined if possible. If the source cannot be corrected or removed, the well may need to be sealed and a new well drilled. For more information on your well and water system see the Well Owner s Handbook, a publication available at no cost from the MDH. To obtain a copy, go to the MDH website at: or contact the MDH as indicated below. For further information, contact the Minnesota Department of Health: 625 North Robert Street P.O. Box St. Paul, Minnesota or Visit the MDH website at: To request this document in another format, call origs\brochures\well and Water System Disinfection for Private Wells 1/22/2015R Printed on recycled paper.
Indiana Department of Environmental Management www.in.gov/idem Well Disinfection Why Disinfect? Well disinfection can eliminate or reduce many different kinds harmful bacteria and viruses as well as harmless
What To Do When Your Well is Flooded Common Sense Steps To Take If Your Well Is Covered by Flood Water Courtesy of CleanWaterStore.com 2016 Contents 1. What To Do If Your Well Is Covered by Flood Water...
Procedure for Flushing Water Systems AFTER a Precautionary Drinking Water Advisory The flushing and cleaning steps contained in this document should be completed by all users of the City of Weyburn water
Sometimes hot water will have a sour smell, similar to that of an old damp rag. This smell often develops when the thermostat has been lowered to save energy or reduce the potential for scalding. Odor-causing
HOW TO DISINFECT YOUR WELL Whitman County Environmental Health Public Service Building N. 310 Main Street Colfax, WA 99111-1848 509.397.6280 INSTRUCTIONS FOR CHLORINATING WELLS The Whitman County Department
Drinking water and your health Water Storage Tanks (Cisterns) This fact sheet is intended to be a general reference for cistern users. For detailed information on cistern construction and material standards,
TCEQ GENERAL INFORMATION Water Supply Division GI-432 August 2013 Disinfecting Your Private Well Is Your Well Flooded? Disinfect It Before You Drink It! If your private well is flooded, do not use water
PUBLICATION 442-663 Virginia Household Water Quality Program: Shock Chlorination: Disinfecting Private Household Water Supply Systems Brian Benham, Associate Professor and Extension Specialist, Biological
Homeowner s GUIDE to living with a well and septic system Northeast Colorado Health Department Replacement System Leach Field Septic Tank Well Congratulations on the purchase of your new home. Living in
8 90 2010 PulteGroup, Inc. All Rights Reserved. drains All the water you use leaves the home through a drain. Maintaining drains prevents clogging, overflows, water damage, and other problems. care and
Clean Water Made Easy www.cleanwaterstore.com Stenner Pump Chlorinator Installation & Start Up Guide Thank you for purchasing a Clean Water System! With proper installation and a little routine maintenance
FLOODING EMERGENCIES WHEN THERE S A FLOOD WHAT TO KNOW AND DO Before You Evacuate If there is time, move important papers, television sets, computers, stereo equipment and easily moveable appliances such
FLORIDA DEPARTMENT OF HEALTH FLOOD INFORMATION FACT SHEET HEALTH DANGERS OF MOLD IN WATER-DAMAGED BUILDINGS Take precautionary measures to avoid indoor air quality problems in homes and buildings. Moisture
E-MAIL US! WaterLab.email@example.com City of Houston Health Department Laboratory Water & Dairy Section 2250 Holcombe Blvd. Houston, TX 77030 CALL US! 832.393.3939 DRINKING WATER INFORMATION & TESTING
Precautionary Boil Water Notices: Frequently Asked Questions QUICK TIPS: Boil Water For: Drinking Brushing Teeth Washing fruits & vegetables Preparing food Mixing baby formula Making ice Giving water to
Homeowners and Home Buyers Guide to Wells and Private Sewage Systems What every homeowner should know about living with a well and a private sewage system. YOUR ENVIRONMENTAL SYSTEMS Out of sight out of
BASEMENT FLOODING Prevention Guide for Homeowners 1 Did You Know? Floods are the most common hazards in Canada. Water damage is a common cause of loss for homeowner insurance. A heavy rainfall can result
Boil Water Advisory Factsheet #3 Boil Water Advisory For Commercial/Public Facilities How to operate a commercial/ public facility under a boil water advisory Boil water advisories are issued when a municipal,
Emergency Guideline for Food Facilities during Boil Water Advisory or Other Public Notices Water supply warnings are generally required when water suppliers need to provide consumers with immediate and
KODAK Developer System Cleaner and Neutralizer TECHNICAL DATA / CHEMICAL March 2010 TI-2000 GENERAL INFORMATION KODAK Developer System Cleaner and Neutralizer is designed to remove the buildup of silver
L-5451 2-04 Drinking Water Problems: Iron and Manganese Mark L. McFarland, Associate Professor and Extension Soil Fertility Specialist Monty C. Dozier, Assistant Professor and Extension Water Resources
A Guideline for Cleaning Up After Flood or Sewer Back-up Revised 2010-03 INDEX PAGE Index 2 Personal Protection 3 Procedure for Cleaning Up 3 Safety 4 Initial Clean-up 5 Clean-up and Disinfection 5 Disinfectants
ALL YOU NEED TO KNOW... What do you know about your septic tank system? For the purposes of this booklet, a septic tank system refers to any kind of on-site sewage management system including traditional
Homeowner s Guide for Maintenance and Care of On-Site Sewage Systems It s Your Septic System Here s How to Take Care of It Properly maintaining your septic system will help reduce the possibility of health
St. Joseph, Missouri Water Protection Homeowners Guide to Your Sewer Out of Sight, Out of Mind: Don t wait until you have a problem to maintain your private lateral sewer line. Keeping Excess Water Out
How to Use Water Safely in Your Food Establishment During a Boil Water Advisory Food service establishments are allowed to operate during the boil water advisory as long as the conditions outlined below
Be prepared Being prepared before an emergency strikes will benefit you greatly in: Reducing your stress and protecting your health. Minimizing possible exposure to health hazards. Minimizing loss to personal
Watts Pure Water Systems WM-120-PT Installation and Operation Manual Premier Water Systems Do not use with water that is microbiologically unsafe or of unknown quality without adequate disinfection before
DC Water household water quality guide dcwater.com district of columbia water and sewer authority George S. Hawkins, General Manager Ensuring quality tap water is a shared responsibility of DC Water and
Improving your water quality and answering questions about your water Developed and Prepared by 2013 Reynolds Water Conditioning Co. Water Filtration & Purification Guide Including answers to common water
SANITARY SEWER BACKUP Causes & Prevention A. PURPOSE The purpose of this publication is twofold: 1. It provides homeowners with basic information on the causes of sanitary sewer backups. 2. It provides
SunMaxx Solar Filling Operating Instructions Content 1. Declaration of conformity... 2 2. Introduction... 2 3. Transportation and unpacking... 4 4. Mounting and commissioning... 5 5. End of operation...
Better Taste Better Quality Better For Your Health BETTER ON YOUR BUDGET! WATER QUALITY Are you dealing with hard water problems? DAMAGE TO EXPENSIVE APPLIANCES FROM CALCIUM SCALE BUILD-UP. EMBARRASSING
Septic Tank Maintenance Information This section has been adapted from materials developed by the Rouge RAP Advisory Council On-site Septic Subcommittee, which included representatives from Oakland, Wayne
Flood Recovery for your Home or Business Be prepared What you need to know Flood recovery for your home or business Table of Contents New Brunswick Emergency Measures Organization (nb emo)... 1 Flood Recovery
Preventing Sewer Backups To safeguard your home against flooding from sewer backups, you should understand your home's basic plumbing and the preventative techniques discussed in this brochure. Basement
Thank you... Welcome to your new world of better living with water2buy s Aquasmart Reverse Osmosis water. If this is your first experience of Aquasmart reverse osmosis water in your home, you ll be amazed
GEORGIA DEPARTMENT OF HUMAN RESOURCES ENVIRONMENTAL HEALTH SECTION A HOMEOWNERS GUIDE TO ON-SITE SEWAGE MANAGEMENT SYSTEMS March 12, 2002 WHAT IS AN ON-SITE SEWAGE MANAGEMENT SYSTEM An on-site sewage management
Florida Keys Aqueduct Authority 1100 Kennedy Drive Key West, Florida 33040 Septic Tank to Cistern Conversions Saving Water & Saving Money One of the benefits of connecting to the Central Wastewater System
NEW HAMPSHIRE DEPARTMENT OF HEALTH AND HUMAN SERVICES DIVISION OF PUBLIC HEALTH SERVICES FOOD PROTECTION SECTION EMERGENCY ACTION PLAN CONTAMINATED WATER SUPPLY (BIOLOGICAL) For the purpose of this Emergency
1 Well Records and Maintenance Guidelines If you have a home well, you alone are responsible for maintaining the safety of our drinking water supply. When your well system is suitably located, correctly
GE SmartWater Water Filtration System Icemaker Connection Kit (RVKIT) INSTALLATION INSTRUCTIONS For use with models GXRV10, GXRM10, PNRQ15, PNRQ20, PNRV12 (beginning on page 1) and PNRV18 (beginning on
Nick Fish, Commissioner David G. Shaff, Administrator 1120 SW 5 th Avenue, Room 600 Portland, Oregon 97204-1926 Information: 503-823-7404 www.portlandoregon.gov/water About the Event: BOIL WATER NOTICE
Support Cleaning Apparatus Operation, Cleaning, & Safety Manual Revision 1.1 31 May 2014 WARNING: The instructions and precautionary statements contained herein are intended for the Support Cleaning Apparatus
Southwest Florida Water Management District Septic System Your Is Your Responsibility! PIPE SEPTIC TANK DRAIN FIELD SOIL You should know that: As a homeowner you re responsible for maintaining your septic
CITY OF NORTH RIDGEVILLE 7307 AVON BELDEN ROAD NORTH RIDGEVILLE, OH 44039 (440) 353-0819 WWW.NRIDGEVILLE.ORG WHY IS THERE WATER IN MY BASEMENT? There are two major sources of water in a basement as the
Before You Evacuate WHEN THERE S A FLOOD What you NEED TO KNOW to protect your health and safety If there is time, move important papers, television sets, computers, stereo equipment and easily moveable
Preventing water damage caused by plumbing fixtures Thousands of home insurance claims are filed every year. Some losses are major, others aren t, but they re always inconvenient and usually avoidable!
What is a septic tank? Where is my septic tank located? Do septic tanks last forever? What should and should not go into my septic tank? How can I tell if my septic tank is working properly? Why should
Home Drinking Water Treatment Systems Prepared by: Glenda M. Herman Extension Housing Specialist Gregory D. Jennings Extension Water Quality Specialist Published by: North Carolina Cooperative Extension
OPERATIONS AND MAINTENANCE INFORMATION FOR: THE CANPLAS BACKWATER VALVE THE CHEMTROL BALL SHUT OFF VALVE SUMP PUMPS AND WASTEWATER EJECTOR PUMPS THE LOUISVILLE AND JEFFERSON COUNTY METROPOLITAN SEWER DISTRICT
MAINTAINING YOUR SPA WATER Tap water that is safe to drink is not always safe for a spa. Normal tap water is usually filled with minerals and microcontaminants that are not visible to the naked eye. Properly
for Holding Tank Systems The goal of a septic system is to protect human health and the environment by properly treating wastewater before returning it to the environment. Your holding tank system is designed
Sewage Back-Ups: Information for Residents Background: Severe rainstorms, floods, and even spring thaws can put a strain on sanitary sewers and septic systems. Large volumes of storm water and ground water
SEPTIC SYSTEMS Who Has A Septic System? Approximately 30 percent of Connecticut s population is served by on-site subsurface sewage disposal systems (a.k.a. septic systems). This means a large percentage
Guide to Backflow Prevention, Cross-Connection Control, Auxiliary Water Systems and Booster Pumps Why be concerned? It can be a health hazard for you, your family and others if contaminated water enters
Series 9000 Water Treatment System Owners Manual Installation Service & Parts Operation Guide The Clear Choice for Soft, Conditioned Water TABLE OF CONTENTS Page Pre-Installation Review --------------------------------------------------------------------------------
Unpackaging & Handling Be sure to carefully inspect the unit before accepting the shipment. If any damage has occurred document it with the trucking company immediately. Contact your Kellogg Distributor
What Is a Cross-Connection? A cross-connection is a direct arrangement of piping that allows the potable (safe drinking) water pipe to be connected to a pipe supply that contains a contaminant or pollutant.
Yellowhead County Hamlet of Cadomin Septic Tank Use & Maintenance Tips This guide gives an overview of the responsibilities for property owners in Cadomin. For Seasonal, Permanent & Vacationing Cadomin
31. ECO-INFO -- SEPTIC SAFE PROTECT YOUR HEALTH AND ENVIRONMENT YOUR SEPTIC PUMP-OUT SYSTEM with SELF ASSESSMENT TROUBLE SHOOTING GUIDE Edited 21/12/01 Wyong Shire Council has many non sewered areas that
Repair and Disinfection of Water Mains Water Protection Program fact sheet 9/2012 Every year waterborne disease outbreaks occur in the United States as a result of public water distribution system defi
Contra Costa Environmental Health 2120 Diamond Blvd., Suite 200 Concord, CA 94520 Phone: (925) 692-2500 Fax: (925) 692-2504 www.cchealth.org/eh/ RECOMMENDED PROGRAM FOR WELL AND SEPTIC SYSTEM REAL ESTATE
LAGOON SEWAGE TREATMENT SYSTEMS It s Your On-Site System Operation and Maintenance Guide for Homeowners OKLAHOMA DEPARTMENT OF ENVIRONMENTAL QUALITY ENVIRONMENTAL COMPLAINTS AND LOCAL SERVICES P.O. Box
Septic Systems Maintenance: A typical septic system consists of two basic components: a septic tank and an underground disposal field. Wastewater flows from the house to the septic tank. Effluent, after
Homeowner s Manual For: MIGHTY MAC 500 Gallon-Per-Day 600 Gallon-Per-Day 750 Gallon-Per-Day Table of Contents I. Introduction II. About Your MIGHTY MAC System III. Homeowner (System Owner) Responsibilities
Sewer Jetter GuideSM How to Unclog Drains with Your Pressure Washer Use this Guide To: Learn how a sewer jetter works Find out if a sewer jetter can help solve your plumbing problem Choose the right pressure
Understanding and Caring for Your Septic System Summit County Public Health 1867 W. Market Street Akron, Ohio 44313 330-926-5600 www.scphoh.org The purpose of a home's subsurface septic system is to dispose
WINTERIZING YOUR HOME PLUMBING AT BLUE RIDGE SHORES The following are suggestions to help you winterize your home plumbing. They are for homes where the heat is not left on during the winter months. There
WD-DWGB-3-4 2009 Corrosivity of Water Supplies What is meant by Corrosivity? Corrosive water can be defined as a condition of water quality which will dissolve metals from metallic plumbing at an excessive
Bernalillo County Office of Environmental Health A comprehensive guide to help maintain your well and keep your drinking water safe Bernalillo County Office of Environmental Health Bernalillo County Commission
ABC CIRCUITS 10 Circuit Drive Circuit Town, IN 12345 SLUG CONTROL PLAN The purpose of this plan is to provide detailed instructions for slug prevention and control. A complete copy of this plan is maintained
THE CORPORATION OF THE VILLAGE OF WARFIELD POLICY TITLE: Sanitary Sewer Operations POLICY: #5435 PURPOSE: This policy is to provide the Village of Warfield s procedures for maintaining its sanitary sewer
Page 1 of 2 Dear Occupant: You contacted the City of Lincoln Park to claim that you discovered that you had suffered property damage or personal injury as a result of a sewage disposal system event. Enclosed,
The Emergency Water Updated December 2006 1 Morgan County PWS ID# 5800412 Revision Date: December 2006 Table of Contents EMERGENCIES PAGE Power Outage 3 Water Main Break 4 Source Failure and Chlorine Failure
14 / WASTE SYSTEM The waste water system in your trailer is made up of sinks, tub, shower, toilet, plumbing drain and vent lines. Waste water from the sinks and shower is contained in a gray water holding
Plumbing Installations A homeowner guide to the City of Winnipeg plumbing requirements for a single-family dwelling February 2001 contents General Information 3 Inspection 4 New Drain and Vent Installations
Iron Air Charge 2510-SXT Installation & Start-Up Guide Thank you for purchasing a Clean Water System! With proper installation and a little routine maintenance your system will be providing iron free water
A GUIDE TO OPERATING & MAINTAINING YOUR SEPTIC SYSTEM WHAT YOU NEED TO KNOW... The way you treat your septic system will influence how long the system lasts and how well it functions. If you own or rent
On-Site Sewage Management System An owners reference guide GWINNETT COUNTY BOARD OF HEALTH ENVIRONMENTAL HEALTH SECTION "Depend on Us to Protect Gwinnett's Health" 240 OAK STREET, SUITE 101, LAWRENCEVILLE,