2 Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety Guidelines for the Application, Installation and Maintenance of Solid State Controls (publication SGI-1.1 available from your local Rockwell Automation sales office or online at describes some important differences between solid state equipment and hard-wired electromechanical devices. Because of this difference, and also because of the wide variety of uses for solid state equipment, all persons responsible for applying this equipment must satisfy themselves that each intended application of this equipment is acceptable. In no event will Rockwell Automation, Inc. be responsible or liable for indirect or consequential damages resulting from the use or application of this equipment. The examples and diagrams in this manual are included solely for illustrative purposes. Because of the many variables and requirements associated with any particular installation, Rockwell Automation, Inc. cannot assume responsibility or liability for actual use based on the examples and diagrams. No patent liability is assumed by Rockwell Automation, Inc. with respect to use of information, circuits, equipment, or software described in this manual. Reproduction of the contents of this manual, in whole or in part, without written permission of Rockwell Automation, Inc., is prohibited. Throughout this manual, when necessary, we use notes to make you aware of safety considerations. WARNING Identifies information about practices or circumstances that can cause an explosion in a hazardous environment, which may lead to personal injury or death, property damage, or economic loss. IMPORTANT Identifies information that is critical for successful application and understanding of the product. ATTENTION Identifies information about practices or circumstances that can lead to: personal injury or death, property damage, or economic loss. Attentions help you identify a hazard, avoid a hazard, and recognize the consequence. SHOCK HAZARD Labels may be on or inside the equipment, such as a drive or motor, to alert people that dangerous voltage may be present. BURN HAZARD Labels may be on or inside the equipment, such as a drive or motor, to alert people that surfaces may reach dangerous temperatures. Allen-Bradley, Rockwell Automation, POINT I/O, POINT Guard I/O, POINTBus, GuardLogix,, RSLogix 5000, DeviceLogix, and TechConnect are trademarks of Rockwell Automation, Inc. Trademarks not belonging to Rockwell Automation are property of their respective companies.
3 Table of Contents Chapter 1 POINT I/O Family Overview The POINT I/O System POINT I/O Features Specify a POINT I/O System Select POINT I/O Communication Interfaces Chapter 2 Overview NetLinx Open Network Architecture Select a Network EtherNet I/P Network ControlNet Network Memory Requirements DeviceNet Network PROFIBUS DP Network Communication Adapter Environmental Specifications Chapter 3 Select POINT I/O Modules Select POINT I/O Modules Digital I/O Modules Digital AC Input Modules Digital AC Output Modules Digital DC Input Modules Digital DC Output Modules Digital Contact Modules Digital I/O Modules Environmental Specifications Self-Configurable Modules Self-Configurable Modules Environmental Specifications Analog and Temperature I/O Modules Analog Input Modules Temperature Input Modules Analog Output Modules Analog and Temperature I/O Modules Environmental Specifications Specialty I/O Modules ASC and ASC Serial Interface Modules SSI Synchronous Serial Interface Module with Absolute Encoder ARM Address Reserve Module CTM Common Terminal and 1734-VTM Voltage Terminal Modules Specialty I/O Modules Environmental Specifications Counter Modules Counter Modules Environmental Specifications Safety I/O Modules POINT I/O Accessories
4 4 Table of Contents Chapter 4 Select a Terminal Base Assembly Terminal Base Assembly One-piece Terminal Bases Chapter 5 Select a Power Supply Unit POINT I/O Communication Adapters Expansion Power Supplies Field Power Distributor Chapter 6 Mounting Requirements Power Supply Distance Rating Mount the POINT I/O System Approximate Mounting Dimensions Chapter 7 Related Documentation
5 Chapter 1 POINT I/O Family Overview The POINT I/O family has modular I/O modules that are ideal for applications where flexibility and low-cost of ownership are key for successful control system design and operation. As a key element in the Rockwell Automation Integrated Architecture, its comprehensive diagnostics and configurable features allow the product to be easily applied to any automation system and reduce engineering costs through standardization. It can be used in remote device panels, local control panels, and can be accessed from many locations including the Internet. This product has just-what-you-need granularity in 1 to 8 points to reduce system cost and size. Available features include Channel Level Diagnostics for quick troubleshooting, multiple termination options and flexibility to save money, cabinet space and commissioning/troubleshooting time, the ability to mix/match Safety I/O on the same bus, and available DeviceLogix for local control, fast response time. Self-Configuring modules are also available to reduce/simplify your design and your inventory. 5
6 6 POINT I/O Family The POINT I/O System B B A A C TOP or 1734-TOPS One-piece Terminal Base with Screw or Spring Clamp The base (A) mounts onto the DIN rail and provides the backplane. The POINT I/O module (B) snaps into the base. The removable terminal block (C) also snaps into the base and provides the wiring and terminations for field-side connections, as well as system power for the backplane. POINT I/O has 4 major components: I/O modules provide the field interface and system-interface circuitry Communication interface modules provide the network-interface circuitry Terminal base units provide the wiring and signal termination for field-side connections and system power for the backplane Power distribution modules provide the expandability of the POINT I/O system and the flexibility to mix a variety of signal types 1734 POINT I/O modules offer 1 to 8 points per module. The I/O modules are interfaced to a network through a communication interface, which includes a built-in power supply that converts incoming 24V DC power to 5V DC backplane power. Each type of communication interface (Network Adaptor) supports a maximum of 13 to 17 I/O modules, with a maximum of 10 A field power. The I/O modules receive power from the power supply through the backplane. With an external power supply, you can expand a POINT I/O assembly up to a maximum of 63 I/O modules or 504 channels.
7 POINT I/O Family 7 POINT I/O Features Adapters I/O Types Module Density Specialty Modules Module Features Network Connectivity Environmental Style Modules per Node, max ControlNet DeviceNet EtherNet I/P Profibus Digital Analog AC/DC Thermocouple RTD Specialty 1 8 points Encoder 1 MHz Counter In Counter In with Outputs Serial RS232 RS485 RS422 Channel Isolated Thermocouple RTD Serial Synchronous Interface (SSI) Address Reserve Channel-level diagnostics (LED indicator and electronic) Channel-level alarm and annunciation (electronic) Channel-level open-wire detection with electronic feedback Channel-level short-circuit detection with electronic feedback Parameter-level explicit messaging Removal and insertion under power (RIUP) Horizontal or vertical mounting without derating Automatic Device Replacement Add-On-Profiles in RSLogix 5000 DeviceNet (including SubNet connectivity) ControlNet (Logix controller only) EtherNet/IP (Logix controller only) PROFIBUS DP OPC/DDE Data Monitoring Class I, Division 2/Zone 2, Marine Certification, European ATEX Zone 2 3G Up to 63
8 8 POINT I/O Family Specify a POINT I/O System Follow these steps as you specify your POINT I/O system: Step 1 Select a communication interface Choose the interface module for your operating system. 2 Select I/O devices based on field devices location of the device number of points needed appropriate catalog number number of points available per module number of modules 3 Select a wiring base assembly Choose the appropriate wiring base assembly 4 Select optional power components Choose optional components to extend backplane power or change the field power distribution source. 5 Determine mounting requirements Determine needed dimensions based on the communication interface chosen. Remember to select the appropriate interface module a communication interface that meets the power requirements of your system I/O modules some have diagnostic features, electronic fusing, isolated inputs/outputs, and unique configurable features the appropriate wiring base assembly: Single piece screw, single piece spring, or RTB (Removable Terminal Base) additional power components as necessary adequate power capacity to meet I/O module backplane current requirements the appropriate number of DIN rails based on the number of modules and the physical locations of those modules horizontal or vertical mounting with no thermal derating
9 Chapter 2 Select POINT I/O Communication Interfaces Step 1 - Select: a communication interface module NetLinx Open Network Architecture... page 9 EtherNet I/P Network... page 11 ControlNet Network... page 12 DeviceNet Network... page 15 PROFIBUS DP Network... page 17 Overview Separate communication interface adapters are available for different networks. Install adapters into the POINTBus backplane to allow POINT I/O modules to communicate with a controller. NetLinx Open Network Architecture NetLinx Open Network Architecture is the Rockwell Automation strategy of using open networking technology for seamless, top-floor to shop-floor integration. The NetLinx-based networks DeviceNet, ControlNet, and EtherNet/IP all use the Common Industrial Protocol (CIP), so they speak a common language and share a universal set of communication services. NetLinx architecture, part of the Integrated Architecture platform, seamlessly integrates all the components in an automation system from a few devices on one network to multiple devices on multiple networks including access to the Internet helping you to improve flexibility, reduce installation costs, and increase productivity. The EtherNet/IP network is an open industrial-networking standard that supports implicit and explicit messaging and uses commercial, off-the-shelf Ethernet equipment and physical media. The ControlNet network allows intelligent, high-speed control devices to share the information required for supervisory control, work-cell coordination, operator interface, remote device configuration, programming, and troubleshooting. 9
10 10 Select POINT I/O Communication Interfaces The DeviceNet network offers low-cost, high-speed access to plant-floor data from a broad range of plant-floor devices and a significant reduction in wiring. Select a Network You can configure your system for information exchange between a range of devices and computing platforms and operating systems. Application requirements Network Select Plant management (material handling) Configuration, data collection, and control on a single, high-speed network EtherNet/IP 1734-AENT 1734-AENTR Time-critical applications with no established schedule Data sent regularly Internet/Intranet connection Close IT & Manufacturing Integration Built-in switch, or high availability requirement (2-port AENTR) High-speed transfer of time-critical data between controllers and I/O devices ControlNet 1734-ACNR Deterministic and repeatable data delivery Media redundancy Controller redundancy Intrinsic safety Connections of low-level devices directly to plant-floor controllers, without interfacing them Data sent as needed More diagnostics for improved data collection and fault detection Less wiring and reduced start-up time than a traditional, hard-wired system High noise resistance, and power over network DeviceNet 1734-ADN 1734-ADN(X) 1734-PDN Connecting to an existing PROFIBUS DP 5 m (16.4 ft) bus, 12 MB network PROFIBUS 1734-APB
11 Select POINT I/O Communication Interfaces 11 EtherNet I/P Network The Ethernet Industrial (EtherNet/IP) network protocol is an open industrial-networking standard that supports both real-time I/O messaging and message exchange. It emerged due to the high demand for using the Ethernet network for control applications. The EtherNet/IP network uses off-the-shelf Ethernet communication chips and physical media. The EtherNet/IP network provides excellent drive and I/O control performance along with HMI information processing and many commercial technologies. EtherNet/IP Network Considerations Adapter 1734-AENT 1734-AENTR Considerations A total of 63 POINT I/O modules can be assembled on a single EtherNet/IP node. Expansion power supplies may be used to provide additional POINTBus backplane current. Refer to the User Manual to determine the ratings for direct and rack connections allowed. The 1734-AENT/1734-AENTR adapter supports direct- and rack-optimized connections. A direct connection is a real-time data transfer link between the controller and whatever module occupies the slot that the configuration data references. Direct-connection messaging occurs at a cyclic rate specified by the requested packet interval (RPI) during configuration. A rack-optimized connection is a grouping of data from more than one I/O module into a single block of data sent over a single connection at the same data rate. Rack-optimized connections reduce the total number of connections needed to transfer data when using many I/O modules in a system. Assume a system contains 8 digital I/O modules interfaced to a 1734-AENT/1734-AENTR adapter. If you used direct connections to transfer data to each of these modules, you need 8 connections one to each of the 8 I/O modules. If you use a rack-optimized connection to transfer the data, you need only a single connection the connection to the 1734-AENT/1734-AENTR adapter.
12 12 Select POINT I/O Communication Interfaces EtherNet/IP AENT/1734-AENTR 1734-AENT/1734-AENTR Technical Specifications 1734-AENT/1734-AENTR Input voltage, nom. 24V DC Input voltage range V DC Field side power requirements V DC (+20% = 28.8V DC) Inrush current 6 A for 10 ms POINTBus current (ma) 800 (1734-AENTR) 1000 (1734-AENT) Power 24V 4.5 W Power dissipation, max V Input overvoltage protection Reverse polarity protected Interruption Output voltage will stay within specifications when input drops out for 10 10V with max load. ControlNet Network The ControlNet network is an open, state-of-the-art control network that meets the demands of real-time, high-throughput applications. The ControlNet network uses the proven Common Industrial Protocol (CIP) to combine the functionality of an I/O network and a peer-to-peer network providing high-speed performance for both functions. The ControlNet
13 Select POINT I/O Communication Interfaces 13 network gives you deterministic, repeatable transfers of all mission-critical control data in addition to supporting transfers of non-time-critical data. ControlNet Network Considerations Adapter 1734-ACNR Considerations A total of 63 POINT I/O modules can be assembled on a single ControlNet node. Expansion power supplies may be used to provide additional POINTBus backplane current. Up to 25 direct connections and 5 rack connections are allowed. The 1734-ACNR ControlNet adapter provides high-speed transfer of time critical data between controllers and I/O devices. It manages data transfers between controllers on the ControlNet network and POINT I/O modules plugged into the POINTBus backplane. The ControlNet network allows the exchange of messages between ControlNet products compliant with the ControlNet International specification. The 1734-ACNR adapter features include a variety of control system solutions, local communication network access through the network access port (NAP), and redundant media. It requires Series C POINT I/O modules or later. The 1734-ACNR adapter requires a typical 24V DC power supply with a maximum of 10.2 W of power. It provides a maximum backplane current of 1.0 A at 5V DC. Backplane current can be extended beyond 1.0 A with a 1734-EP24DC backplane extension power supply. The 1734-EP24DC can supply up to an additional 1.3 A of backplane current. Multiple 1734-EP24DC power supplies can be used to reach the maximum limit of 63 POINT I/O modules if 25 or fewer of these modules are analog or specialty modules. The adapter supports 25 direct and 5 rack I/O connections to the POINT I/O modules. From a single 1734-ACNR adapter, multiple controllers establish I/O connections, up to a maximum of 5 rack I/O connections per adapter. Direct connections must be used with analog and specialty modules. Multiple rack connections permit multiple controllers to connect to I/O over a single 1734-ACNR adapter. The number of connections that can be supported on a network depends on the ControlNet parameters (NUT, RPI, and API) and the POINT I/O configuration by itself (number and types of I/O modules). The following example shows a single POINT I/O ControlNet adapter with 5 connections and 8 I/O modules. The POINT I/O modules are monitored by the 5 controllers on the ControlNet network. The POINT I/O modules in: slots 1, 3, and 5 are controlled by the first controller. slots 2 and 4 by the second controller. slot 6 by the third controller. slot 7 by the fourth controller.
14 14 Select POINT I/O Communication Interfaces slot 8 by the fifth controller ControlNet ACNR Memory Requirements The 1734-ACNR adapter has 586 bytes of memory available for scheduled transmit data. When developing an application, the amount of data used by an individual connection must also include a small amount of overhead (I/O bytes per connection). The following formula tracks the amount of available scheduled transmit data. Available Memory = [(Number of connections * 10) + Sum of all connection sizes] In the following example, the system uses a 1734-ACNR adapter with five ASC modules. Application Data Size (number of bytes) ASC ASC ASC ASC ASC Total Bytes Used Memory Required In this example, a sixth module could be added if it used less than 54 bytes of application data. There are 64 bytes of memory left. 64 = [(5 * 10) +472]
15 Select POINT I/O Communication Interfaces 15 For more information about the 1734-ACNR adapter, see the POINT I/O ControlNet Adapter User Manual, publication 1734-UM ACNR Technical Specifications Input voltage, nom Input voltage range 1734-ACNR 24V DC V DC Field side power requirements V DC (+20% = 28.8V DC) Inrush current 6 A for 10 ms POINTBus current 1000 ma (1) Power consumption at 24V 8.0 W Power dissipation, max V Input overvoltage protection Reverse polarity protected Interruption Output voltage will stay within specifications when input drops out for 10 ms at 10V with max load. (1) V DC ±5% ( V). DeviceNet Network The DeviceNet network is an open low-level network that provides connections between simple industrial devices (such as sensors and actuators) and higher-level devices (such as PLC controllers and computers). The DeviceNet network uses the proven Common Industrial Protocol (CIP) to provide the control, configure, and data collection capabilities for industrial devices. The POINT I/O family offers four interfaces for connecting to the DeviceNet network. DeviceNet Network Considerations Adapter 1734-ADN Consideration All POINT I/O modules count as a single node on the main network. A total of 63 POINT I/O modules can be assembled on a single DeviceNet node. Behaves as a slave device on the main network and a master on the POINTBus backplane. RSNetWorx for DeviceNet software is needed for configuration of the 1734-ADN adapter on the main network and the POINTBus backplane Expansion power supplies may be used to provide additional POINTBus backplane current.
16 16 Select POINT I/O Communication Interfaces DeviceNet Network Considerations Adapter 1734-ADNX 1734-PDN Consideration Acts like a 1734-ADN adapter, with additional capabilities. All POINT I/O modules, and some third-party field devices, count as a single node on the main network. Has a second, Phoenix-style connector that extends the subnet off the module, so that any DeviceNet-capable device could be connected to a subnet and scanned by the 1734-ADNX adapter. Network on the second connector is electrically isolated from the main network and can be used to extend the total DeviceNet trunk line distance. (1) Node numbers of the devices on the POINTBus backplane and subnet would not count against the 63 slave nodes allowed on the main network. Devices on the subnet and the main network need to be connected at different communication rates or use different sampling methods (for example, change-of-state or polled). Data from these devices would be included in the data being sent to/from the 1734-ADNX adapter on the main network. POINT I/O expansion power supplies are permitted and may be required to add more modules. Each POINT I/O module on the main network counts as a separate node. Electrically connects the main network to the I/O modules, which are connected on the POINTBus backplane. No configuration to the 1734-PDN communication interface necessary since it is transparent to the main network. Total POINTBus backplane current of I/O modules cannot exceed 1.3 A. Expansion power supplies may not be used. (1) For example: with thick round media at 125 Kbps, you could run a maximum of 500 m (1640 ft) to a 1734-ADNX adapter on the main network. You could then wire an additional 500 m (1640 ft) of cable on the subnet connector and double the distance of the network. Remember that this subnet needs terminating resistors and a 24V DC power connection, the same as any other DeviceNet network. It is important that the total amount of data coming from the subnet does not exceed the data capability of either the 1734-ADN or 1734-ADNX adapter. 250 bytes (248 data + 2 bytes command info) for output data (used as either COS, cyclic, or poll) 250 bytes (248 data + 2 bytes status info) for polled input data 250 bytes (248 data + 2 bytes status info) for COS/cyclic input data 8 bytes (6 data + 2 status info) for strobe input data The data coming through the 1734 adapter combined with the other data from the main network cannot exceed the data capability of the main network master scanner. If this occurs, you will need multiple master scanners on the main network and the I/O modules on the subnet will need to be split between multiple 1734-ADN or 1734-ADNX adapters. With the 1734-PDN communication interface, the multiple masters on the main network will be able to communicate to separate groups of modules on its subnet through the same 1734-PDN communication interface, so no additional adapter would be necessary.
17 Select POINT I/O Communication Interfaces DeviceNet Adapter Specifications Attribute 1734-PDN 1734-ADN/X Input voltage, nom 24V DC Input voltage range 11 25V DC DeviceNet V DC specification Field side power requirements V DC (+4% = 25V DC) V DC (+20% = 28.8V DC) Inrush current 6 A for 5 ms 6 A for 10 ms POINTBus current 1300 (1) ma 1000 ma Power 24V 8.0 W 8.1 W Power dissipation, max V V Input overvoltage protection Reverse polarity protected Interruption Output voltage will stay within specifications when input drops out for V with max load. (1) V DC ±5% ( V). PROFIBUS DP Network PROFIBUS for Decentralized Peripherals is a standard in field bus communication in automation. that helps eliminate hard wiring, and reduces costs associated with design and installation. PROFIBUS DP Network Considerations Adapter 1734-APB Considerations A total of 63 POINT I/O modules can be assembled on a single PROFIBUS DP node. Expansion power supplies may be used to provide additional POINTBus backplane current. Other considerations when using the APB adapter. Example, if needed (see EtherNet/IP section) APB Technical Specifications Attribute Input voltage, nom Input voltage range Field side power requirements Inrush current Value 24V DC V DC V DC (+20% = 28.8V DC) 6 A for 10 ms
18 18 Select POINT I/O Communication Interfaces 1734-APB Technical Specifications Attribute Value POINTBus current 1000 ma (1) Power consumption at 24V 8.0 W Power dissipation, max V Input overvoltage protection Reverse polarity protected Interruption Output voltage will stay within specifications when input drops out for 10 10V with max load. (1) V DC ±5% ( V). Communication Adapter Environmental Specifications Attribute Value Operating temperature C ( F) Nonoperating temperature C ( F) Relative humidity 5 95% noncondensing Operating shock 30 g Nonoperating shock 50 g Vibration Hz Enclosure type rating None (open-style) Mounting DIN Rail Certifications (when product is marked) c-ul-us, Ex, CE, C-Tick, CI / EtherNet/IP / DeviceNet
19 Chapter 3 Select POINT I/O Modules Step 2 - Select: I/O modules some modules have diagnostic features, electronic fusing, or individually isolated inputs/outputs Digital I/O Modules... page 20 Analog and Temperature I/O Modules... page 26 Specialty I/O Modules... page 32 Counter Modules... page 37 Safety I/O Modules... page 40 POINT I/O Accessories... page 47 Select POINT I/O Modules The POINT I/O family provides a wide range of input and output modules to span many applications, from high-speed digital to process control. POINT I/O modules support producer/consumer technology, which allows input information and output status to be shared among multiple Logix controllers. 19
20 20 Select POINT I/O Modules Each POINT I/O module mounts adjacent to the network adapter or another I/O module and removable terminal block (RTB) to connect all field-side wiring. The RTBs are part of the terminal base assembly. They are not included with the I/O modules and must be ordered separately. The POINT family of I/O modules includes: 1734 digital I/O modules analog I/O modules specialty I/O modules wiring systems network communication adapters POINT Guard I/O modules. Digital I/O Modules Choose digital I/O modules when you need: a wide variety of voltage interface capabilities isolated and non-isolated module types point-level output fault states choice of direct-connect or rack-optimized communications field-side diagnostics (on select modules) Most output modules have built-in surge suppression to reduce the effects of high-voltage transients. However, we recommend that you use an additional suppression device if an output is being used to control inductive devices, such as: relays motor starters solenoids motors Additional suppression is especially important if your inductive device is in series with or parallel to hard contacts, such as push buttons or selector switches.
21 Select POINT I/O Modules 21 Digital AC Input Modules 1734 Digital AC Input Modules Technical Specifications 1734-IA IA IM IM4 Number of inputs 2 (1 group of 2) 2 (1 group of 4) 2 (1 group of 2) 2 (1 group of 4) Voltage, on-state input, nom 120V AC 220V AC Voltage, on-state input, min 65V AC 159V AC Voltage, on-state input, max 132V AC 264V AC Input delay time, on to off 20 ms hardware filter plus 0 65 ms digital filter programmable in increments of 1 ms (1) Current, on-state input, min V AC, 60 Hz V AC, 60 Hz Input impedance, nom 10.6 kω 22.3 kω Current, off-state input, max V AC 2.9 ma POINTBus current 75 5V DC Power dissipation, max V AC Thermal dissipation, max V AC Terminal base unit 1734-TB, 1734-TBS, 1734-TOP, or 1734-TOPS (1) Input ON-to-OFF delay time is the time from a valid input signal to recognition by the module. Digital AC Output Modules 1734 Digital AC Output Modules Technical Specifications 1734-OA OA4 Number of outputs 2 4 Voltage, on-state output, nom 120V AC; 220V AC Voltage, on-state output, min 74V AC Voltage, on-state output, max 264V AC Output current rating 1.5 A ( A each) 2.0 A (750 ma per output, 2.0 A max per module) POINTBus current 75 5V DC Power dissipation, max 2 264V AC V AC Thermal dissipation, max V AC V AC Terminal base unit 1734-TB, 1734-TBS, 1734-TOP, or 1734-TOPS
POINT I/O Modules Bulletin 1734 Selection Guide Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety Guidelines for
User Manual POINT I/O Digital and Analog Modules and POINTBlock I/O Modules atalog Numbers 74-IA, 74-IM4, 74-IB, 74-IB4, 74-IB8, 74-IB4D, 74-IM, 74-IM4, 74IV, 74-IV4, 74-IV8, 74-OA, 74-OA4, 74-OB, 74-OBEP,
Micro800 Programmable Controllers Bulletin 2080 Selection Guide Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety
User Manual DeviceNet Network Configuration Important User Information Solid-state equipment has operational characteristics differing from those of electromechanical equipment. Safety Guidelines for the
Installation Instructions USB-to-Data Highway Plus Cable Catalog Number 1784-U2DHP Topic Page Important User Information 2 Environment and Enclosure 3 Install the Cable 5 Configure the DH+ Node Address
Automation System TROVIS 6400 TROVIS 6493 Compact Controller For panel mounting (front frame 48 x 96 mm/1.89 x 3.78 inch) Application Digital controller to automate industrial and process plants for general
Preface Contents SIMATIC NET CP 243-2 AS-Interface Master Manual Technical Description and Installation Instructions Interface to the User Program 2 in the S7-200 CPU Access to the Data of the AS-i Slaves
POINT I/O EtherNet/IP Adapter Module Catalog Number 1734-AENT User Manual Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment.
FLEX I/O Isolated Analog Modules 1794-IF4I, -OF4I, IF2XOF2I, -IF4IXT, -IF4ICFXT, -OF4IXT, IF2XOF2IXT User Manual Important User Information Solid state equipment has operational characteristics differing
140 Fieldbus slave modules with I/Os, DIO 1534CF00 1534CH00 1534PF00 1534PH00 1536CH00 1536CL10 1536PH00 1536PL00 Order number 1534CF00 1534CH00 1534PF00 1534PH00 Figure Type SM 153, CANopen slave, DIO
Isolated AC Sine Wave Input 3B42 / 3B43 / 3B44 FEATURES AC averaging technique used to rectify, amplify, and filter 50 Hz to 400 Hz sine-wave signals. Accepts inputs of between 20 mv to 550 V rms to give
E031026 000823 Process modules Digital input PMI for inputs for 120 V AC inputs PMI Input E4, E5, GND L- PMI 120 V AC Input E4, E5, Common C E6, E7, GND L- E6, E7, Common C LEDs for the inputs operation
Module 1 Overview ControlLogix5000 Module Overview This module takes a fundamental approach to a ControlLogix system. It begins with an overview of the architecture and migrates into an introduction of
Smart DeviceNet Remote I/O Terminals ather and Use Information for Effective Preventive Maintenance et more useful data for preventive maintenance when you build cost-effective parallel information systems
Technical Specification Sheet Document No. 149-188P25 Rev. 6 March, 2000 Unitary Controller The Unitary Controller can operate as an independent stand-alone controller, or can be connected to the APOGEE
User Manual MicroLogix 1100 Embedded Web Server Bulletin 1763 Controllers Important User Information Solid-state equipment has operational characteristics differing from those of electromechanical equipment.
Stratix 5700 Network Address Translation Quick Start Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment. Safety Guidelines
Application Technique Safety Function: Door Monitoring Products: Trojan 5 Switch, GuardLogix Controller Safety Rating: CAT. 3, PLd to ISO 13849-1: 2008 Topic Page Important User Information 2 General Safety
Telephone- and leased line modem for industrial applications TD-36 Modem for industrial PSTN- and leased line applications The TD-36 is an analogue V.34 PSTN modem as well as an industrial 2-wire leased
Rack mounted telephone- and leased line modem for industrial applications TR-6 Rack modem for industrial PSTNand /-wire leased line applications The TR-6 is an analogue V. 9 -rack PSTN modem as well as
FieldBarrier Features Assembly 8... 12 outputs Ex ia IIC, FISCO and Entity Advanced fault isolation and diagnostics at the spur FieldBarrier in Zone 1/Div. 2 Instruments in Zone 0...1/Div. 1 For FOUNDATION
Controller 5000GL Controller 5000GL provides flexible system architecture with options of GBUS and LOCAL BUS communications to field devices, to meet a wide range of site requirements. GGBUS L LOCAL BUS
Programmable Relays ZEN Series Relay, Timer, Counter, and Time Switch Functions Weekly Timer and Calendar Timer Functions Twin Timer Function (Separate ON/OFF Times) Two Analog Input Channels (DC Models
FX14 Field Controller (1/4) FX14 Field Controller The FX14 is an equipment field controller in the Facility Explorer range of products. The controller is designed specifically for commercial Heating, Ventilating,
FX07 Field Controller (1/4) FX07 Field Controller Display Model Dimensions in mm (inches) The FX07 is a terminal unit controller in the Facility Explorer range of products. The controller is designed specifically
Universal I/O EDI Distributor Control Interface Wiring and Setup Instructions EDI UNIVERSAL I/O INTERFACE MODULE The only interface needed for EDI-V5 controls Network compatible with all older EDI controls
Data sheet Electronic timer CT-AHD.12 OFF-delayed with 1 c/o (SPDT) contact The CT-AHD.12 is an electronic time relay with OFF-delay. It is from the CT-D range. With their MDRC profile and a width of only
MasterINTERFACE 39 Series - Relay interface modules Common features Space saving 6.2 mm wide Connections for 16-way jumper link Integral coil indication and protection circuit Secure retention and easy
38 Series - Relay interface modules 0.1-2 - 3-5 - 6-8 - 16 A 38 SERIES Common features Instant ejection of relay by plastic retaining clip Integral coil indication and protection circuit EMR Electromechanical
DVPPF02-H2 PROFIBUS DP Slave Communication Module Application Manual Warning Please read this instruction carefully before use and follow this instruction to operate the device in order to prevent damages
ABB Drives User s Manual Pulse Encoder Interface Module RTAC-0 Pulse Encoder Interface Module RTAC-0 User s Manual 3AFE 64486853 REV A EN EFFECTIVE:.5.00 00 ABB Oy. All Rights Reserved. Safety instructions
Unidirectional Transmitter/ Receiver Units Introduction Wireless Input/Output (I/O) connects directly to analog, discrete and pulse transducer signals. The signals are transmitted by radio and either re-created
SIMATIC ET 200S distributed I/O SIMATIC ET 200S distributed I/O 2AO I ST analog electronic module (6ES7135-4GB01-0AB0) Manual Preface Properties 1 Parameters 2 Diagnostics 3 Analog value representation
4 2 1 Cat. Number 1769-L2-QFC1 Embedded Communication Port Isolated Serial Non-Isolated Serial CompactLogix Capacity CompactLogix Configuration EtherNet/IP Connections Memory Embedded I/O (pre-configured
4 SIMATIC S7-300 Central processing units CPU 312C to CPU 317F-2 DP CPU 317F-2 DP The failsafe CPU with a large program memory and quantity framework for demanding applications For configuration of a failsaf
White Paper Converting Relays to Programmable Controllers Introduction For years now, engineers have been considering programmable controller versus relay-based control for their applications. While many
DeviceNet Communication Manual Soft-Starter Series: SSW-07/SSW-08 Language: English Document: 10000046963 / 00 03/2008 Summary ABOUT THIS MANUAL... 5 ABBREVIATIONS AND DEFINITIONS... 5 NUMERICAL REPRESENTATION...
Data Sheet Maximum Productivity and Versatility for Control without Compromise! Basic Bus Communication Module DESCRIPTION The Basic Bus Communication Module (BCM) is part of the MLC 9000+ DIN rail mount
Panel Meters and Controllers Modular Panel Meter Type EDM 35 Modular digital panel meter, 3 1/2-digit Indicating or controlling current, voltage, resistance, temperature, tacho or frequency. Easy programming
IntesisBox ModBus Server - KNX Gateway for integration of KNX equipment into Modbus (RTU and TCP) control systems. Integrate KNX based lighting control into your SCADA, BMS, PLC "talking" Modbus. Master
MANUFACTURER DATA SHEET High Speed Counter Manufacturer: Allen-radley/Rockwell Model Number: 1746-HSCE See www.geomartin.com for additional PDF datasheets Martin Part Number: E-014901-03 VendorPartNumber:
3500/22M Transient Data Interface Bently Nevada* Asset Condition Monitoring Description The 3500 Transient Data Interface (TDI) is the interface between the 3500 monitoring system and GE s System 1* machinery
Power-monitoring unit PowerLogic System Technical data sheet 2003 Power Meter Series 800 Function and characteristics PB100313 The PowerLogic Power Meter Series 800 offers all the high-performance measurement
NTA CPU board PROCESS INTERFACES NTA is a CPU board for STAR DualBus DCS systems. NTA provides the internal bus communication, managing all I/O boards of the STAR DualBus modular system. NTA also manages
www.maxim-ic.com FEATURES Temperature measurements require no external components Measures temperatures from -55 C to +125 C in 0.5 C increments. Fahrenheit equivalent is -67 F to 257 F in 0.9 F increments
Programmable Controller G Series The IMO G6 is a very compact modular programmable controller offering extremely high performance. It is ideal for all applications from process control to machine control
This Quick Start Guide is designed to familiarize the user with the connection and configuration of the DTS-305 DIN rail mounted single / 3 phase power & energy meter with RS-485 or TCP communications.
1769-SDN DeviceNet Scanner Module Catalog Numbers 1769-SDN User Manual Important User Information Solid state equipment has operational characteristics differing from those of electromechanical equipment.
TSI and TSI logo are registered trademarks of TSI Incorporated. SmartTune is a trademark of TSI Incorporated. THERMAL ANEMOMETRY ELECTRONICS, SOFTWARE AND ACCESSORIES IFA 300 Constant Temperature Anemometry
Ponto Series A new concept for automation Programmable Controller Remote I/O for Field Buses Special models of I/O modules Web connection Ponto Series Programmable Controller High connectivity CPUs Direct
Factory Line Switches With Standard Functions Data Sheet 05/2004 This data sheet is valid for the following products: FL SWITCH SF 8TX FL SWITCH SF 7TX/FX FL SWITCH SF 6TX/2FX FL SWITCH SF 16TX FL SWITCH
Installation Instructions Universal Serial Bus (USB) to DH-485 Interface Converter Catalog Number 1747-UIC Contents Overview..................................................3 Computer and Operating System
Model Number Single head system Features Parameterization interface for the application-specific adjustment of the sensor setting via the service program ULTRA 000 programmable switch outputs Hysteresis
55 Series - General purpose relays 7-10 A Features 55.12 55.13 55.14 Printed circuit mount, general purpose 2, 3 & 4 Pole relays 55.12-2 Pole 10 A 55.13-3 Pole 10 A 55.14-4 Pole 7 A AC coils & DC coils
Issued: April 1999 Status: Updated Version: C/26.04.2006 Data subject to change without notice Features Versatile digital disturbance recorder module for recording various phenomena in the electric power
2CDC 251 098 F0t06 a Rotary switch for the preselection of the time range of the ON time b Potentiometer with direct reading scale for the fine adjustment of the ON time c Rotary switch for the preselection
User Manual FLEX I/O High-Density Analog Modules Catalog Numbers 1794-IE8, 1794-IE8XT, 1794-OE4, 1794-OE4XT, 1794-IE12, 1794-OE12, 1794-IE4XOE2, 1794- IE4XOE2XT, 1794-IE8XOE4 Important User Information
E L E K T R O N I K Appliance Description Programmable safety center FPSC Fiessler Programmable Safety Center Flexible Hard- and Software concept Available with a safe bus system or/and two counter inputs
Product datasheet Characteristics TM7BDM8B expansion block - TM7 - IP67-8 DI/DO - 24V DC - 0.5 A - M8 connector Main Range of product Product or component type Range compatibility Enclosure material Bus
LevelOne IFE-0500 4-Port PoE + 1-Port TP Industrial Fast Ethernet Switch User Manual Ver. 1.0.0-0711 1 FCC Warning This Equipment has been tested and found to comply with the limits for a Class-A digital
MAKING MODERN LIVING POSSIBLE AK-SC255 On-Site Installation Guide DANFOSS ELECTRONIC CONTROLS & SENSORS How to Use This Guide Read this Guide completely as you install and start up your new AK-SC 255 controller.
Power Supply Unit, Primary Switched, Narrow Design MINI POWER provides: Extra narrow design with widths of 22.5 mm, 45 mm, and 67.5 mm (0.886, 1.772, and 2.657 in.) Global use due to a wide-range input