# Data Centers. Datacom Airflow Patterns

Save this PDF as:

Size: px
Start display at page:

## Transcription

2 The most important design criterion in a data center is the inlet air condition to the datacom equipment, as most manufacturers base their environmental specifications on the air that must be drawn through their equipment for cooling. the range of 40% RH to 55% RH. This recommended envelope is a subset of a larger allowable envelope, with an inlet temperature range of 59 F to 90 F (15 C to 32 C) and a humidity range of 20% to 80%. Most manufacturers have equipment operating specifications similar to the allowable range. While the conditions listed in Thermal Guidelines represent the consensus of a number of datacom manufacturers, individual equipment environmental requirements may be different and always should be checked. An interesting consideration with regard to the design conditions relates to the ramifications of mixed air, which are not always detrimental. Notice that the recommended inlet temperature range stated previously is 68 F to 77 F (20 C to 25 C). Air generally is supplied by the air-handling units at a temperature in the range of 52 F to 60 F (11 C to 16 C). This cold air can be mixed inside the data center with the (hot) air from other sources to provide cooling air at the inlet to the equipment in the recommended inlet temperature range. The (hot) air from other sources that is mixed with the cold supply air can be referred to as bypass air since it re-enters the equipment without passing through the air-handling units. The adiabatic mixing of two or more airstreams, providing a mixed air condition, is common in commercial HVAC systems. The equation used to calculate a mixed air temperature (T 3 ) is: T 3 = [(T 1 Q 1 ) + (T 2 Q 2 )]/ (Q 1 + Q 2 ) When applied to a particular server installed in a datacom facility, the equation for the mixed air temperature (T 3 ) that occurs at the inlet grille of the server could be represented as: T 3 = 72.5 F = [(55 F 400 cfm) + (90 F 400 cfm)]/(400 cfm cfm) Where: T 3 = the temperature of mixed air that actually enters the server, T 1 = the temperature of the air in the cold aisle (55 F in this example), T 2 = the temperature of the bypass air drawn into the server from other sources (90 F in this example), Q 1 = the quantity of air drawn from the cold aisle by the server (400 cfm [189 L/s] in this example), and Q 2 = the quantity of air drawn from the other sources by the server (400 cfm in this example). In this example, the temperatures of the air drawn from the cold aisle and the bypass air are well outside of the recommended inlet temperature range (these temperatures are not uncommon in datacom facilities). When they are mixed together, however, they are able to provide a temperature inside the recommended range. Rules of Thumb to Minimize Inlet Air Temperature Excursions Several parameters can affect the extent of rack inlet air temperature excursions. These parameters can be placed into the following general categories: Space dimensional parameters; Equipment placement parameters; Temperature and humidity; Addition of localized cooling; Addition of baffles; and VAV (variable air volume) considerations. Note that the discussions of the parameters in this article can best be characterized as rules of thumb. They are intended to stimulate a thought process leading to a base case that represents a reasonable approach to overall data center design. This should be followed by a parametric analysis with a CFD program or other analytic techniques to achieve optimal results. Space Dimensional Parameters Space dimensional parameters that can affect airflow and help to maintain cool inlet air conditions include: Larger cooling aisle widths allow for increased floor plenum flow of cold air in the direct vicinity of high-density datacom equipment at a reasonable velocity. Limiting the velocity of the air supplied by the perforated floor tiles provides two benefits. High velocity air tends to blow by the inlet grilles of the servers installed closest to the floor, starving these units of cooling air. Also, high velocity air in the center of cold aisles has a tendency to bypass all of the servers that face that cold aisle and blow out of the top of the aisle without providing any initial benefit. Reference 4 provides additional information. A deeper floor plenum allows for a much more even distribution of cooling air through floor tiles. It also allows the A p r i l A S H R A E J o u r n a l 5 1

3 % 60% Summer Sensible Heating Line For Max. Allowable Temp. Range Acceptable Human Occupancy Conditions, Winter Clothing (For Reference Only) 3 Winter Sensible Heating Line For Max. Allowable Temp. Range % Existing ASHRAE Recommended Envelope For Data Centers (per 2003 ASHRAE Handbook Applications, Chapter 17) Class 1 Data Center Recommended Operating Environment (2004 Thermal Guidelines for Data Processing Environments) 20% Humidity Ratio, Pounds Moisture Per Pound of Dry Air 40 Class 1 Data Center Allowable Operating Environment (2004 Thermal Guidelines) Dry-Bulb Temperature, F Figure 1: Comparison of Class 1 data center recommended and allowable operating conditions with existing ASHRAE Handbook envelope and Standard acceptable human occupancy conditions with winter clothing. static pressure to exceed the velocity pressure at all locations with perforated tiles or other openings in the raised floor. The usage and layout of underfloor plenum distribution systems, such as cabling and piping, the impact of blockages and the type of discharge from the computer room air-conditioning (CRAC) units (if used) should also be considered. Reference 5 provides a detailed review of the physics of underfloor plenum airflow. A high ceiling allows the hot and buoyant exhaust air to stratify above the datacom equipment, so that it can be returned back to the air-conditioning units rather than recycled back to equipment intakes. A ceiling level too close to the top of the racks is a major concern. Similarly, CRAC or other airconditioning equipment returns also should be located near the ceiling whenever possible. If the hot exhaust air from equipment and cabinets can be directed upward into a ceiling return plenum, this may be superior to simply having a high ceiling. The ceiling partition can then prevent recycling of the hottest air, and allow for a mixed air temperature at the inlet to the datacom equipment near the top of the racks, which is lower than it would have been without the ceiling partition. Unfortunately, in retrofit cases there may be little that can be done to increase space dimensional parameters, and other strategies must be used. Equipment Placement Parameters Placing equipment (the air handlers and/or CRAC units, the perforated tiles, and the datacom equipment) in certain configurations can be advantageous in terms of optimizing airflow patterns. Chapter 4 of Thermal Guidelines 2 deals exclusively with equipment placement. The following should be considered: The hot-aisle/cold-aisle approach as a means to segregate hot exhaust air from the inlets of datacom equipment has been addressed many places, including Reference 2. Figure 2 shows a schematic of a hot-aisle/cold-aisle configuration. Unfortunately, a hot-aisle/cold-aisle approach does not preclude recirculation, as datacom equipment fans pull air from the most convenient location. If flexibility exists in the orientation of rows of equipment, a layout that allows hot air unobstructed access to the return of the CRAC units (or other cooling system returns) should be superior to a layout with rows perpendicular to the CRAC 5 2 A S H R A E J o u r n a l a s h r a e. o r g A p r i l

4 units. Enhancing the natural flow of exhaust air from Point A to Point B should reduce the potential for the warmest air to recycle through equipment along its return path. If flexibility exists in the placement of CRAC units, place them facing hot aisles rather than cold aisles, as the underfloor velocity pressure should be minimized in cold aisles. Low velocity pressure and high static pressure are desired to maximize flow from the perforated tiles (or other air outlets) to the data center. Placement of high-density datacom equipment at floor locations that have high static pressure allows the highest possible airflow in the cold aisle adjacent to the equipment. Typically, the highest static pressures are further away from the CRAC units, or where the flow from two or more CRAC units collides. Another strategy in the placement of high-density datacom equipment is load spreading. 4 Load spreading can reduce the impact of recirculation by allowing the mixing of hot exhaust with lower temperature exhaust from nearby equipment, creating a lower overall mixed air temperature. The strategy for placement of perforated floor tiles and the percentage opening of these tiles should be considered. While tiles primarily are placed in a cold aisle, the percentage open area of the tile affects the airflow above the floor, and also affects the pressurization below the floor. Too high of a flow rate adjacent to datacom equipment inlets could create a Bernoulli effect that impedes cooling. There also may be an advantage to placing a limited number of perforated tiles in a hot aisle near a hot spot to encourage thermal dilution mixing if there are unavoidable recirculation patterns. Location of cables and cable penetrations through the raised floor and racks should be carefully considered and limited. Unused cable openings should be closed since they allow supply air to go where it is not needed. If these openings are large or frequent enough, they also allow the static pressure to bleed from the raised floor plenum. If individual racks are removed from a row, these holes will create a short-circuit path that should be blocked. Flow near the end of an aisle should be considered in detail, as recirculation can occur both around the sides and the top of a rack or cabinet in this location. Temperature and Humidity Considerations To maintain proper inlet temperature and humidity conditions, the cooling system must have adequate capacity (tonnage) and airflow capability, with discharge conditions most conducive to Rear Front Front Rear Rear Front Front Rear Cold Cold Aisle Aisle Aisle Aisle Aisle Figure 2: Schematic of hot-aisle/cold-aisle airflow. meeting datacom equipment conditions over the full height of the cabinet or rack. The following should be considered: All available information regarding the datacom equipment should be reviewed. This includes design values for heat release and airflow. This information is available from many datacom manufacturers in the form of an equipment thermal report as delineated in Thermal Guidelines. 2 With heat release and airflow information known, an average temperature rise across the equipment racks can be calculated. An understanding of thermal control systems for the installed datacom equipment is also important. For instance, a manufacturer may use a tachometer to determine if an internal fan failure has occurred in its server. If a fan on this server fails, but the server is installed in a cabinet with fans in series with the server, this external pressure source could cause the server fan to rotate at sufficient speed to keep the server s internal fan failure alarm from being generated. Generally, it is recommended that the design differential temperature across the air-handling units be no more than 80% of the design temperature difference across the datacom equipment. For instance, if the datacom equipment has an average temperature rise of 25 F (14 C), the cooling system should be designed with a temperature drop of no more than 25 F 0.8 = 20 F (14 C 0.8 = 11 C). Since this recommendation results in 20% less energy extraction for the air handlers per unit volume of airflow, the air handlers clearly have to circulate 20% more airflow than the datacom equipment for an energy balance. Unfortunately, having a cooling system flow rate greater than a datacom equipment flow rate does not guarantee that recirculation will not occur. Ideally, temperature and humidity conditions as measured at the inlets to all datacom equipment in a data center will be controlled at recommended levels (68 F 77 F [20 C 25 C] and 40% 55% RH). One methodology for achieving this is to design for a 68 F (20 C) cold aisle. 6 This approach, however, may not be the best where very high-density loads are present and colder air is needed to help maintain conditions within the allowable range. By estimating or measuring the expected temperature distribution across the rack face, a supply condition can be chosen to provide recommended (best) or allowable (acceptable) inlet conditions across the entire face of the datacom equipment. Per Figure 1, a 59 F (15 C) and 56% 80% RH discharge air condition allows for sensible heating up to 90 F (32 C) while staying within the allowable relative humidity range. A p r i l A S H R A E J o u r n a l 5 3

### Benefits of. Air Flow Management. Data Center

Benefits of Passive Air Flow Management in the Data Center Learning Objectives At the end of this program, participants will be able to: Readily identify if opportunities i where networking equipment

### Data center upgrade proposal. (phase one)

Data center upgrade proposal (phase one) Executive Summary Great Lakes began a recent dialogue with a customer regarding current operations and the potential for performance improvement within the The

### Element D Services Heating, Ventilating, and Air Conditioning

PART 1 - GENERAL 1.01 OVERVIEW A. This section supplements Design Guideline Element D3041 on air handling distribution with specific criteria for projects involving design of a Data Center spaces B. Refer

### Power and Cooling for Ultra-High Density Racks and Blade Servers

Power and Cooling for Ultra-High Density Racks and Blade Servers White Paper #46 Introduction The Problem Average rack in a typical data center is under 2 kw Dense deployment of blade servers (10-20 kw

### Verizon SMARTS Data Center Design Phase 1 Conceptual Study Report Ms. Leah Zabarenko Verizon Business 2606A Carsins Run Road Aberdeen, MD 21001

Verizon SMARTS Data Center Design Phase 1 Conceptual Study Report Ms. Leah Zabarenko Verizon Business 2606A Carsins Run Road Aberdeen, MD 21001 Presented by: Liberty Engineering, LLP 1609 Connecticut Avenue

### CURBING THE COST OF DATA CENTER COOLING. Charles B. Kensky, PE, LEED AP BD+C, CEA Executive Vice President Bala Consulting Engineers

CURBING THE COST OF DATA CENTER COOLING Charles B. Kensky, PE, LEED AP BD+C, CEA Executive Vice President Bala Consulting Engineers OVERVIEW Compare Cooling Strategies in Free- Standing and In-Building

### Optimizing Network Performance through PASSIVE AIR FLOW MANAGEMENT IN THE DATA CENTER

Optimizing Network Performance through PASSIVE AIR FLOW MANAGEMENT IN THE DATA CENTER Lylette Macdonald, RCDD Legrand Ortronics BICSI Baltimore 2011 Agenda: Discuss passive thermal management at the Rack

### White Paper. Data Center Containment Cooling Strategies. Abstract WHITE PAPER EC9001. Geist Updated August 2010

White Paper Data Center Containment Cooling Strategies WHITE PAPER EC9001 Geist Updated August 2010 Abstract Deployment of high density IT equipment into data center infrastructure is now a common occurrence

### AisleLok Modular Containment vs. Legacy Containment: A Comparative CFD Study of IT Inlet Temperatures and Fan Energy Savings

WH I TE PAPE R AisleLok Modular Containment vs. : A Comparative CFD Study of IT Inlet Temperatures and Fan Energy Savings By Bruce Long, Upsite Technologies, Inc. Lars Strong, P.E., Upsite Technologies,

### Data Center Operating Cost Savings Realized by Air Flow Management and Increased Rack Inlet Temperatures

Data Center Operating Cost Savings Realized by Air Flow Management and Increased Rack Inlet Temperatures William Seeber Stephen Seeber Mid Atlantic Infrared Services, Inc. 5309 Mohican Road Bethesda, MD

### Using CFD for optimal thermal management and cooling design in data centers

www.siemens.com/datacenters Using CFD for optimal thermal management and cooling design in data centers Introduction As the power density of IT equipment within a rack increases and energy costs rise,

### Education Evolution: Scalable Server Rooms George Lantouris Client Relationship Manager (Education) May 2009

Education Evolution: Scalable Server Rooms George Lantouris Client Relationship Manager (Education) May 2009 Agenda Overview - Network Critical Physical Infrastructure Cooling issues in the Server Room

### Integrated Cabinets and Thermal Systems May 15, 2014 Panduit Korea Technical System Engineer Chester Ki

1 Integrated Cabinets and Thermal Systems May 15, 2014 Panduit Korea Technical System Engineer Chester Ki 4/10/2014 2 Agenda Market Trends Thermal Architectures Data Centre Cabinet Systems Net-Access Cabinet

### Reducing Room-Level Bypass Airflow Creates Opportunities to Improve Cooling Capacity and Operating Costs

WHITE PAPER Reducing Room-Level Bypass Airflow Creates Opportunities to Improve Cooling Capacity and Operating Costs By Lars Strong, P.E., Upsite Technologies, Inc. 505.798.000 upsite.com Reducing Room-Level

### Unified Physical Infrastructure (UPI) Strategies for Thermal Management

Unified Physical Infrastructure (UPI) Strategies for Thermal Management The Importance of Air Sealing Grommets to Improving Smart www.panduit.com WP-04 August 2008 Introduction One of the core issues affecting

### Driving Data Center Efficiency Through the Adoption of Best Practices

Data Center Solutions 2008 Driving Data Center Efficiency Through the Adoption of Best Practices Data Center Solutions Driving Data Center Efficiency Through the Adoption of Best Practices Executive Summary

### Combining Cold Aisle Containment with Intelligent Control to Optimize Data Center Cooling Efficiency

A White Paper from the Experts in Business-Critical Continuity TM Combining Cold Aisle Containment with Intelligent Control to Optimize Data Center Cooling Efficiency Executive Summary Energy efficiency

### Air, Fluid Flow, and Thermal Simulation of Data Centers with Autodesk Revit 2013 and Autodesk BIM 360

Autodesk Revit 2013 Autodesk BIM 360 Air, Fluid Flow, and Thermal Simulation of Data Centers with Autodesk Revit 2013 and Autodesk BIM 360 Data centers consume approximately 200 terawatt hours of energy

### GUIDE TO ICT SERVER ROOM ENERGY EFFICIENCY. Public Sector ICT Special Working Group

GUIDE TO ICT SERVER ROOM ENERGY EFFICIENCY Public Sector ICT Special Working Group SERVER ROOM ENERGY EFFICIENCY This guide is one of a suite of documents that aims to provide guidance on ICT energy efficiency.

### Liquid Cooling Solutions for DATA CENTERS - R.M.IYENGAR BLUESTAR LIMITED.

Liquid Cooling Solutions for DATA CENTERS - R.M.IYENGAR BLUESTAR LIMITED. Presentation Goals & Outline Power Density Where we have been- where we are now - where we are going Limitations of Air Cooling

### Dealing with Thermal Issues in Data Center Universal Aisle Containment

Dealing with Thermal Issues in Data Center Universal Aisle Containment Daniele Tordin BICSI RCDD Technical System Engineer - Panduit Europe Daniele.Tordin@Panduit.com AGENDA Business Drivers Challenges

### Environmental Data Center Management and Monitoring

2013 Raritan Inc. Table of Contents Introduction Page 3 Sensor Design Considerations Page 3 Temperature and Humidity Sensors Page 4 Airflow Sensor Page 6 Differential Air Pressure Sensor Page 6 Water Sensor

### - White Paper - Data Centre Cooling. Best Practice

- White Paper - Data Centre Cooling Best Practice Release 2, April 2008 Contents INTRODUCTION... 3 1. AIR FLOW LEAKAGE... 3 2. PERFORATED TILES: NUMBER AND OPENING FACTOR... 4 3. PERFORATED TILES: WITH

### Improving Data Center Energy Efficiency Through Environmental Optimization

Improving Data Center Energy Efficiency Through Environmental Optimization How Fine-Tuning Humidity, Airflows, and Temperature Dramatically Cuts Cooling Costs William Seeber Stephen Seeber Mid Atlantic

### APC APPLICATION NOTE #92

#92 Best Practices for Designing Data Centers with the InfraStruXure InRow RC By John Niemann Abstract The InfraStruXure InRow RC is designed to provide cooling at the row and rack level of a data center

### Cooling Audit for Identifying Potential Cooling Problems in Data Centers

Cooling Audit for Identifying Potential Cooling Problems in Data Centers By Kevin Dunlap White Paper #40 Revision 2 Executive Summary The compaction of information technology equipment and simultaneous

### Benefits of Cold Aisle Containment During Cooling Failure

Benefits of Cold Aisle Containment During Cooling Failure Introduction Data centers are mission-critical facilities that require constant operation because they are at the core of the customer-business

### How Row-based Data Center Cooling Works

How Row-based Data Center Cooling Works White Paper 208 Revision 0 by Paul Lin and Victor Avelar Executive summary Row-based data center cooling is normally regarded as a cold air supply architecture that

### Sealing Gaps Under IT Racks: CFD Analysis Reveals Significant Savings Potential

TECHNICAL REPORT Sealing Gaps Under IT Racks: CFD Analysis Reveals Significant Savings Potential By Lars Strong, P.E., Upsite Technologies, Inc. Bruce Long, Upsite Technologies, Inc. +1.888.982.7800 upsite.com

### Data Center Power Consumption

Data Center Power Consumption A new look at a growing problem Fact - Data center power density up 10x in the last 10 years 2.1 kw/rack (1992); 14 kw/rack (2007) Racks are not fully populated due to power/cooling

### Ten Steps to Solving Cooling Problems Caused by High- Density Server Deployment

Ten Steps to Solving Cooling Problems Caused by High- Density Server Deployment By Peter Hannaford White Paper #42 Revision 1 Executive Summary High-density servers present a significant cooling challenge.

### Fundamentals of CFD and Data Center Cooling Amir Radmehr, Ph.D. Innovative Research, Inc. radmehr@inres.com

Minneapolis Symposium September 30 th, 2015 Fundamentals of CFD and Data Center Cooling Amir Radmehr, Ph.D. Innovative Research, Inc. radmehr@inres.com Learning Objectives 1. Gain familiarity with Computational

### Supporting Cisco Switches In Hot Aisle/Cold Aisle Data Centers

CABINETS: ENCLOSED THERMAL MOUNTING MANAGEMENT SYSTEMS WHITE PAPER Supporting Cisco Switches In Hot Aisle/Cold Aisle Data Centers 800-834-4969 techsupport@chatsworth.com www.chatsworth.com All products

### Best Practices in HVAC Design/Retrofit

Best Practices in HVAC Design/Retrofit Little Server Room BIG \$AVINGS Justin Lewis, P.E., LEED AP, DCEP Sr Energy Project Manager C:530.400.6042 O:530.754.4870 jlewis@ucdavis.edu 1 What s the problem here?

### Data Center Components Overview

Data Center Components Overview Power Power Outside Transformer Takes grid power and transforms it from 113KV to 480V Utility (grid) power Supply of high voltage power to the Data Center Electrical Room

### Thermal Mass Availability for Cooling Data Centers during Power Shutdown

2010 American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. (www.ashrae.org). Published in ASHRAE Transactions (2010, vol 116, part 2). For personal use only. Additional reproduction,

### A White Paper from the Experts in Business-Critical Continuity TM. Data Center Cooling Assessments What They Can Do for You

A White Paper from the Experts in Business-Critical Continuity TM Data Center Cooling Assessments What They Can Do for You Executive Summary Managing data centers and IT facilities is becoming increasingly

### Enclosure and Airflow Management Solution

Enclosure and Airflow Management Solution CFD Analysis Report Des Plaines, Illinois December 22, 2013 Matt Koukl- DECP Mission Critical Systems Affiliated Engineers, Inc. Contents Executive Summary...

### Managing Data Centre Heat Issues

Managing Data Centre Heat Issues Victor Banuelos Field Applications Engineer Chatsworth Products, Inc. 2010 Managing Data Centre Heat Issues Thermal trends in the data centre Hot Aisle / Cold Aisle design

### Creating Data Center Efficiencies Using Closed-Loop Design Brent Goren, Data Center Consultant

RESEARCH UNDERWRITER WHITE PAPER LEAN, CLEAN & GREEN Wright Line Creating Data Center Efficiencies Using Closed-Loop Design Brent Goren, Data Center Consultant Currently 60 percent of the cool air that

### Impacts of Perforated Tile Open Areas on Airflow Uniformity and Air Management Performance in a Modular Data Center

Impacts of Perforated Tile Open Areas on Airflow Uniformity and Air Management Performance in a Modular Data Center Sang-Woo Ham 1, Hye-Won Dong 1, Jae-Weon Jeong 1,* 1 Division of Architectural Engineering,

### Data Centre Cooling Air Performance Metrics

Data Centre Cooling Air Performance Metrics Sophia Flucker CEng MIMechE Ing Dr Robert Tozer MSc MBA PhD CEng MCIBSE MASHRAE Operational Intelligence Ltd. info@dc-oi.com Abstract Data centre energy consumption

### BRUNS-PAK Presents MARK S. EVANKO, Principal

BRUNS-PAK Presents MARK S. EVANKO, Principal Data Centers of the Future and the Impact of High Density Computing on Facility Infrastructures - Trends, Air-Flow, Green/LEED, Cost, and Schedule Considerations

### Hot Air Isolation Cools High-Density Data Centers By: Ian Seaton, Technology Marketing Manager, Chatsworth Products, Inc.

Business Management Magazine Winter 2008 Hot Air Isolation Cools High-Density Data Centers By: Ian Seaton, Technology Marketing Manager, Chatsworth Products, Inc. Contrary to some beliefs, air is quite

### The New Data Center Cooling Paradigm The Tiered Approach

Product Footprint - Heat Density Trends The New Data Center Cooling Paradigm The Tiered Approach Lennart Ståhl Amdahl, Cisco, Compaq, Cray, Dell, EMC, HP, IBM, Intel, Lucent, Motorola, Nokia, Nortel, Sun,

### Cooling Capacity Factor (CCF) Reveals Stranded Capacity and Data Center Cost Savings

WHITE PAPER Cooling Capacity Factor (CCF) Reveals Stranded Capacity and Data Center Cost Savings By Lars Strong, P.E., Upsite Technologies, Inc. Kenneth G. Brill, Upsite Technologies, Inc. 505.798.0200

### A Comparative Study of Various High Density Data Center Cooling Technologies. A Thesis Presented. Kwok Wu. The Graduate School

A Comparative Study of Various High Density Data Center Cooling Technologies A Thesis Presented by Kwok Wu to The Graduate School in Partial Fulfillment of the Requirements for the Degree of Master of

### Data Center Cooling & Air Flow Management. Arnold Murphy, CDCEP, CDCAP March 3, 2015

Data Center Cooling & Air Flow Management Arnold Murphy, CDCEP, CDCAP March 3, 2015 Strategic Clean Technology Inc Focus on improving cooling and air flow management to achieve energy cost savings and

### APC APPLICATION NOTE #112

#112 Best Practices for Deploying the InfraStruXure InRow SC By David Roden Abstract The InfraStruXure InRow SC (ACSC100 and ACSC101) is a self-contained air conditioner for server rooms and wiring closets.

### HPPR Data Center Improvements Projects Towards Energy Efficiency (CFD Analysis, Monitoring, etc.)

HPPR Data Center Improvements Projects Towards Energy Efficiency (CFD Analysis, Monitoring, etc.) Felipe Visbal / March 27, 2013 HPPR Data Center Technologies Team Services Data Centers: Thermal Assessments

### POWER USAGE EFFECTIVENESS. Developing Best Practices Manual for Indian Data Centers. Presentation by HVAC Core Group

POWER USAGE EFFECTIVENESS Developing Best Practices Manual for Indian Data Centers PUE - Power usage effectiveness is Total incoming power( IT equipment + electrical And mechanical support system ) / Presentation

### RAISED-FLOOR DATA CENTER: PERFORATED TILE FLOW RATES FOR VARIOUS TILE LAYOUTS

Paper Presented at ITHERM 2004 Ninth Intersociety Conference on Thermal and Thermomechanical Phenomena in Electronic Systems June 1-4, Las Vegas, NV RAISED-FLOOR DATA CENTER: PERFORATED TILE FLOW RATES

### Rack Hygiene. Data Center White Paper. Executive Summary

Data Center White Paper Rack Hygiene April 14, 2011 Ed Eacueo Data Center Manager Executive Summary This paper describes the concept of Rack Hygiene, which positions the rack as an airflow management device,

### Great Lakes Data Room Case Study

Great Lakes Data Room Case Study WeRackYourWorld.com Problem: During a warm summer period in 2008, Great Lakes experienced a network outage due to a switch failure in the network enclosure. After an equipment

### DataCenter 2020: hot aisle and cold aisle containment efficiencies reveal no significant differences

DataCenter 2020: hot aisle and cold aisle containment efficiencies reveal no significant differences November 2011 Powered by DataCenter 2020: hot aisle and cold aisle containment efficiencies reveal no

### Energy Efficiency Opportunities in Federal High Performance Computing Data Centers

Energy Efficiency Opportunities in Federal High Performance Computing Data Centers Prepared for the U.S. Department of Energy Federal Energy Management Program By Lawrence Berkeley National Laboratory

### Analysis of the UNH Data Center Using CFD Modeling

Applied Math Modeling White Paper Analysis of the UNH Data Center Using CFD Modeling By Jamie Bemis, Dana Etherington, and Mike Osienski, Department of Mechanical Engineering, University of New Hampshire,

### Best Practices for Wire-free Environmental Monitoring in the Data Center

White Paper Best Practices for Wire-free Environmental Monitoring in the Data Center April 2012 Introduction Monitoring for environmental threats in the data center is not a new concept. Since the beginning

### Virtual Data Centre Design A blueprint for success

Virtual Data Centre Design A blueprint for success IT has become the back bone of every business. Advances in computing have resulted in economies of scale, allowing large companies to integrate business

### IMPROVING DATA CENTER EFFICIENCY AND CAPACITY WITH AISLE CONTAINMENT

DATA CENTER RESOURCES WHITE PAPER IMPROVING DATA CENTER EFFICIENCY AND CAPACITY WITH AISLE CONTAINMENT BY: STEVE HAMBRUCH EXECUTIVE SUMMARY Data centers have experienced explosive growth in the last decade.

### Prediction Is Better Than Cure CFD Simulation For Data Center Operation.

Prediction Is Better Than Cure CFD Simulation For Data Center Operation. This paper was written to support/reflect a seminar presented at ASHRAE Winter meeting 2014, January 21 st, by, Future Facilities.

### Managing Cooling Capacity & Redundancy In Data Centers Today

Managing Cooling Capacity & Redundancy In Data Centers Today About AdaptivCOOL 15+ Years Thermal & Airflow Expertise Global Presence U.S., India, Japan, China Standards & Compliances: ISO 9001:2008 RoHS

### Increasing Energ y Efficiency In Data Centers

The following article was published in ASHRAE Journal, December 2007. Copyright 2007 American Society of Heating, Refrigerating and Air- Conditioning Engineers, Inc. It is presented for educational purposes

### Measure Server delta- T using AUDIT- BUDDY

Measure Server delta- T using AUDIT- BUDDY The ideal tool to facilitate data driven airflow management Executive Summary : In many of today s data centers, a significant amount of cold air is wasted because

### Improving Rack Cooling Performance Using Airflow Management Blanking Panels

Improving Rack Cooling Performance Using Airflow Management Blanking Panels By Neil Rasmussen White Paper #44 Revision 3 Executive Summary Unused vertical space in open frame racks and rack enclosures

### How to Meet 24 by Forever Cooling Demands of your Data Center

W h i t e P a p e r How to Meet 24 by Forever Cooling Demands of your Data Center Three critical aspects that are important to the operation of computer facilities are matching IT expectations with the

### Choosing Close-Coupled IT Cooling Solutions

W H I T E P A P E R Choosing Close-Coupled IT Cooling Solutions Smart Strategies for Small to Mid-Size Data Centers Executive Summary As high-density IT equipment becomes the new normal, the amount of

### Energy Performance Optimization of Server Room HVAC System

International Journal of Thermal Technologies E-ISSN 2277 4114 2 INPRESSCO, All Rights Reserved Available at http://inpressco.com/category/ijtt/ Research Article Manoj Jadhav * and Pramod Chaudhari Department

### Cooling Capacity Factor (CCF) Reveals Stranded Capacity and Data Center Cost Savings

WHITE PAPER Cooling Capacity Factor (CCF) Reveals Stranded Capacity and Data Center Cost Savings By Kenneth G. Brill, Upsite Technologies, Inc. Lars Strong, P.E., Upsite Technologies, Inc. 505.798.0200

### Energy and Cost Analysis of Rittal Corporation Liquid Cooled Package

Energy and Cost Analysis of Rittal Corporation Liquid Cooled Package Munther Salim, Ph.D. Yury Lui, PE, CEM, LEED AP eyp mission critical facilities, 200 west adams street, suite 2750, Chicago, il 60606

### Airflow and Cooling Performance of Data Centers: Two Performance Metrics

2008, American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. (www.ashrae.org). Published in ASHRAE Transactions, Vol. 114, Part 2. For personal use only. Additional reproduction,

### Great Lakes Product Solutions for Cisco Catalyst and Catalyst Switches: ESSAB14 Baffle for Cisco Catalyst 6509 Switch

Great Lakes Product Solutions for Cisco Catalyst and Catalyst Switches: ESSAB14 Baffle for Cisco Catalyst 6509 Switch Great Lakes Product Solutions for Cisco Catalyst and Catalyst Switches Table of Contents

### 11 Top Tips for Energy-Efficient Data Center Design and Operation

11 Top Tips for Energy-Efficient Data Center Design and Operation A High-Level How To Guide M e c h a n i c a l a n a l y s i s W h i t e P a p e r w w w. m e n t o r. c o m When is Data Center Thermal

### Free Cooling in Data Centers. John Speck, RCDD, DCDC JFC Solutions

Free Cooling in Data Centers John Speck, RCDD, DCDC JFC Solutions Why this topic Many data center projects or retrofits do not have a comprehensive analyses of systems power consumption completed in the

### IPACK2005-73273 DISTRIBUTED LEAKAGE FLOW IN RAISED-FLOOR DATA CENTERS

Proceedings of IPACK5 ASME InterPACK '5 July 17-, San Francisco, California, USA IPACK5-7373 DISTRIBUTED LEAKAGE FLOW IN RAISED-FLOOR DATA CENTERS Amir Radmehr Innovative Research, Inc. Plymouth, MN, USA

### High Density Data Centers Fraught with Peril. Richard A. Greco, Principal EYP Mission Critical Facilities, Inc.

High Density Data Centers Fraught with Peril Richard A. Greco, Principal EYP Mission Critical Facilities, Inc. Microprocessors Trends Reprinted with the permission of The Uptime Institute from a white

### How to Build a Data Centre Cooling Budget. Ian Cathcart

How to Build a Data Centre Cooling Budget Ian Cathcart Chatsworth Products Topics We ll Cover Availability objectives Space and Load planning Equipment and design options Using CFD to evaluate options

### Overview and Design of Data Center Cabinets

Overview and Design of Data Center Cabinets In today s technology-dependent world, a reliably operating data center is a core necessity for small and large businesses alike. Without properly running network

### Airflow Simulation Solves Data Centre Cooling Problem

Airflow Simulation Solves Data Centre Cooling Problem The owner s initial design for a data centre in China utilized 40 equipment racks filled with blade servers spread out in three rows along the length

### Data Centers: How Does It Affect My Building s Energy Use and What Can I Do?

Data Centers: How Does It Affect My Building s Energy Use and What Can I Do? 1 Thank you for attending today s session! Please let us know your name and/or location when you sign in We ask everyone to

### Case Study: Innovative Energy Efficiency Approaches in NOAA s Environmental Security Computing Center in Fairmont, West Virginia

Case Study: Innovative Energy Efficiency Approaches in NOAA s Environmental Security Computing Center in Fairmont, West Virginia Prepared for the U.S. Department of Energy s Federal Energy Management Program

### VAV Reheat Box Control

3. For all except very noise sensitive applications, select VAV boxes for a total (static plus velocity) pressure drop of 0.5 H2O. For most applications, this provides the optimum energy balance (see the

### Ten Cooling Solutions to Support High- Density Server Deployment

Ten Cooling Solutions to Support High- Density Server Deployment By Peter Hannaford White Paper #42 Revision 3 Executive Summary High-density servers offer a significant performance per watt benefit. However,

### How Does Your Data Center Measure Up? Energy Efficiency Metrics and Benchmarks for Data Center Infrastructure Systems

How Does Your Data Center Measure Up? Energy Efficiency Metrics and Benchmarks for Data Center Infrastructure Systems Paul Mathew, Ph.D., Staff Scientist Steve Greenberg, P.E., Energy Management Engineer

### Avoidable Mistakes that Compromise Cooling Performance in Data Centers and Network Rooms

Avoidable Mistakes that Compromise Cooling Performance in Data Centers and Network Rooms By Neil Rasmussen White Paper #49 Executive Summary Avoidable mistakes that are routinely made when installing cooling

### Prompt Engineering applies successfully CFD analysis on large Server Room for a simulation driven Energy saving approach.

Prompt Engineering applies successfully CFD analysis on large Server Room for a simulation driven Energy saving approach.. ABSTRACT The Energy Saving approach is the target of this case story. The problem

### Improving Rack Cooling Performance Using Airflow Management Blanking Panels

Improving Rack Cooling Performance Using Airflow Management Blanking Panels White Paper 44 Revision 4 by Neil Rasmussen > Executive summary Unused vertical space in open frame racks and rack enclosures

### Elements of Energy Efficiency in Data Centre Cooling Architecture

Elements of Energy Efficiency in Data Centre Cooling Architecture Energy Efficient Data Center Cooling 1 STULZ Group of Companies Turnover 2006 Plastics Technology 400 Mio A/C Technology 200 Mio Total

### Case Study - Husky Energy Green High-Density Computing. A 40-Billion Dollar Energy Provider Knows How To Keep Pace In A Rapidly Changing IT World

Case Study - Husky Energy Green High-Density Computing A 40-Billion Dollar Energy Provider Knows How To Keep Pace In A Rapidly Changing IT World CASE STUDY EC8001A Published August 2010 Thermal Model Illustrates

### Access Server Rack Cabinet Compatibility Guide

Access Server Rack Cabinet Compatibility Guide A Guide to the Selection and Evaluation of Access Server Rack Cabinets for Compatibility and Use with Third Party Server Chassis Kalkenstraat 91-93 B-8800

### Rack Blanking Panels To Fill or Not to Fill

Rack Blanking Panels To Fill or Not to Fill A Dell Technical White Paper Dell Data Center Infrastructure David L. Moss Joyce F. Ruff Learn more at Dell.com/PowerEdge/Rack THIS WHITE PAPER IS FOR INFORMATIONAL

### Specialty Environment Design Mission Critical Facilities

Brian M. Medina PE Associate Brett M. Griffin PE, LEED AP Vice President Environmental Systems Design, Inc. Mission Critical Facilities Specialty Environment Design Mission Critical Facilities March 25,

### GREEN FIELD DATA CENTER DESIGN WATER COOLING FOR MAXIMUM EFFICIENCY. Shlomo Novotny, Vice President and Chief Technology Officer, Vette Corp.

GREEN FIELD DATA CENTER DESIGN WATER COOLING FOR MAXIMUM EFFICIENCY Shlomo Novotny, Vice President and Chief Technology Officer, Vette Corp. Overview Data centers are an ever growing part of our economy.

### Second Place: Industrial Facilities or Processes, Existing

Second Place: Industrial Facilities or Processes, Existing The TCS data center makes use of white cabinets and reflective surfaces as one method to reduce power for its lights and cooling. Data Center

### Saving energy in the Brookhaven National Laboratory Computing Center: Cold aisle containment implementation and computational fluid dynamics modeling

Saving energy in the Brookhaven National Laboratory Computing Center: Cold aisle containment implementation and computational fluid dynamics modeling Student Intern Earth and Environmental Engineering,

### Unified Physical Infrastructure SM (UPI) Strategies for Smart Data Centers

Unified Physical Infrastructure SM (UPI) Strategies for Smart Data Centers Deploying a Vertical Exhaust System www.panduit.com WP-09 September 2009 Introduction Business management applications and rich

### Energy Efficient Data Center Design. Can Ozcan Ozen Engineering Emre Türköz Ozen Engineering

Energy Efficient Data Center Design Can Ozcan Ozen Engineering Emre Türköz Ozen Engineering 1 Bio Can Ozcan received his Master of Science in Mechanical Engineering from Bogazici University of Turkey in

### Thermal Monitoring Best Practices Benefits gained through proper deployment and utilizing sensors that work with evolving monitoring systems

NER Data Corporation White Paper Thermal Monitoring Best Practices Benefits gained through proper deployment and utilizing sensors that work with evolving monitoring systems Introduction Data centers are