# 17. Pipe flow V ( )

Save this PDF as:

Size: px
Start display at page:

Download "17. Pipe flow V ( )"

## Transcription

1 17. Pipe flow V ( ) Pump types Pump systems Pumps in series and in parallel Exercises: D35-36, and D38

2 Pump types centrifugal pump VVR 120 Fluid Mechanics

3 Pump types axial flow pumps VVR 120 Fluid Mechanics

4 Rotating movement by centrifugal impeller or propeller Pressure increases over the pump Pressure increases over pump: (p out p in ) / ρg = H p = pump head Specific energy consumption pump = (w Q H p )/(3600 Q η) kwh/m 3 Efficiency η = power output/power input

5 Energy line H valve Energy line H p = function(q p )

6 A pump is characterized by a so-called pump curve η = power output/power input

7 Calculation of flowrate and pressure in a pump system Water is pumped from reservoir A to reservoir B What will the flowrate, Q p, be if the pipe characteristics, L, D, k s are known as well as static head, Δz, and pump curve? The pressure increase over pump (energy supply from pump to water) should achieve two things with respect to lifting water from reservoir A to B: 1) overcome geometric height, Δz 2) overcome head losses h f1 + h f2

8 The hydraulic characteristics for the pipe system, H syst, is obtained from the energy equation L Q 2 H syst = Δz +Σh = Δz + f losses D 2gA 2 (local losses neglected in this case) H syst states how much energy that is needed to transport 1 kg of water from A to B H p states how much energy the pump can provide to the water When the pump is introduced in the pipe system the flowrate and pump head will adjust so that H syst = H p Pressure increase over pump Q p in pipe

9 D36 Water is pumped between two reservoirs with the same water surface elevation z o. Total pipe length is L = 2500 m, diameter D = 0.1 m and equivalent sand roughness k = m. The pump characteristics is given by the figure. What is the maximum permissible distance x from the upstream reservoir to the suction side of the pump, if the pressure must not be less than atmospheric. The local losses may be neglected. The temperature is 20 C

10

11 PARALLEL PUMPING Pumps operating in parallel are replaced by a fictive equivalent pump with a pump curve obtained by horizontal addition of the single pumps pump curves Equivalent pump 2 pumps in parallel

12 PUMPS IN SERIES Pumps operating in series are replaced by a fictive equivalent pump with a pump curve obtained by vertical addition of the single pumps pump curves 2 pumps 1 pump

13 EXAMPLES OF SYSTEM CURVES 1) Two pumps operating in parallel System curve (independent of number of pumps) If one pump runs If two pumps run

14 2) Heat pump systems Heat pump system

15 3) Increase of natural flow rate 2 2 L Q L Q Without pump: Δz = f H = Δz + f = 0 2 syst 2 D 2gA D 2gA with pump H pump without pump H syst Q without Q with

16 4) Flow control using a valve H syst = Δz + ( Kvalve + f L D ) 2 Q 2gA 2 h valve Increasing K valve (choking) Valve

17 5) Time-varying reservoir surface H syst = Δz + f L D 2 Q 2gA 2 (Δz varies)

18 6) Flow regulation using speed-adjustable pumps Pump curves Speedadjustable pump (rotation per min)

19 D35 Water is to be pumped by two centrifugal pumps through a pipeline connecting two reservoirs. The pumps can be operated in parallel or one at a time. The pipeline is 2000 m long, diameter 250 mm and equivalent sand roughness is 0.2 mm. The static lift is 25.0 m. Calculate the specific energy consumption (kwh/m 3 ) both for single pump operation and when both pumps operate. The pump characteristics are Discharge Q (m 3 /s) Head (m) Total efficiency (%)

20

21 D38 Water (20 C) is pumped between two reservoirs through two identical, parallel pipes each with a diameter of 0.2 m, length 1000 m, and equivalent sand roughness of m. a) What flow is expected through the pump? b) How much energy (kwh) is needed to pump 1 m 3 of water? The efficiency of the pump η = 0.75

22

### Pumps: Convert mechanical energy (often developed from electrical source) into hydraulic energy (position, pressure and kinetic energy).

HYDRAULIC MACHINES Used to convert between hydraulic and mechanical energies. Pumps: Convert mechanical energy (often developed from electrical source) into hydraulic energy (position, pressure and kinetic

### CENTRIFUGAL PUMP OVERVIEW Presented by Matt Prosoli Of Pumps Plus Inc.

CENTRIFUGAL PUMP OVERVIEW Presented by Matt Prosoli Of Pumps Plus Inc. 1 Centrifugal Pump- Definition Centrifugal Pump can be defined as a mechanical device used to transfer liquid of various types. As

### Practice Problems on Pumps. Answer(s): Q 2 = 1850 gpm H 2 = 41.7 ft W = 24.1 hp. C. Wassgren, Purdue University Page 1 of 16 Last Updated: 2010 Oct 29

_02 A centrifugal with a 12 in. diameter impeller requires a power input of 60 hp when the flowrate is 3200 gpm against a 60 ft head. The impeller is changed to one with a 10 in. diameter. Determine the

### Applied Fluid Mechanics

Applied Fluid Mechanics 1. The Nature of Fluid and the Study of Fluid Mechanics 2. Viscosity of Fluid 3. Pressure Measurement 4. Forces Due to Static Fluid 5. Buoyancy and Stability 6. Flow of Fluid and

### EXPERIMENT NUMBER 7 PERFORMANCE TEST OF A CENTRIFUGAL PUMP

EXPERIMENT NUMBER 7 PERFORMANCE TEST OF A CENTRIFUGAL PUMP OBJECTIVE The primary objectives of this experiment is to measure the performance of a centrifugal pump and compare the results to the manufacturers

### Vertical selfpriming Side-Channel Pumps Type WPV

Vertical selfpriming Side-Channel Pumps Type WPV FIELD OF APPLICATION The side-channel pumps are selfpriming and operate more economically (better efficiency) than normal centrifugal pumps when handling

### Minor losses include head losses through/past hydrants, couplers, valves,

Lecture 10 Minor Losses & Pressure Requirements I. Minor Losses Minor (or fitting, or local ) hydraulic losses along pipes can often be estimated as a function of the velocity head of the water within

### HYDRAULIC ANALYSIS OF PIPE LINED WITH MADISON S 100% SOLIDS STRUCTURAL POLYURETHANE COATINGS

HYDRAULIC ANALYSIS OF PIPE LINED WITH MADISON S 100% SOLIDS STRUCTURAL POLYURETHANE COATINGS Shiwei William Guan, Ph.D. Vice President, R&D and International Business Madison Chemical Industries Inc. 490

### CENTRIFUGAL PUMP SELECTION, SIZING, AND INTERPRETATION OF PERFORMANCE CURVES

CENTRIFUGAL PUMP SELECTION, SIZING, AND INTERPRETATION OF PERFORMANCE CURVES 4.0 PUMP CLASSES Pumps may be classified in two general types, dynamic and positive displacement. Positive displacement pumps

### Module 9: Basics of Pumps and Hydraulics Instructor Guide

Module 9: Basics of Pumps and Hydraulics Instructor Guide Activities for Unit 1 Basic Hydraulics Activity 1.1: Convert 45 psi to feet of head. 45 psis x 1 ft. = 103.8 ft 0.433 psi Activity 1.2: Determine

### Pump Selection and Sizing (ENGINEERING DESIGN GUIDELINE)

Guidelines for Processing Plant Page : 1 of 51 Rev 01 Feb 2007 Rev 02 Feb 2009 Rev 03 KLM Technology #03-12 Block Aronia, Jalan Sri Perkasa 2 Taman Tampoi Utama 81200 Johor Bahru. (ENGINEERING DESIGN GUIDELINE)

### Applied Fluid Mechanics

Applied Fluid Mechanics Sixth Edition Robert L. Mott University of Dayton PEARSON Prentkv Pearson Education International CHAPTER 1 THE NATURE OF FLUIDS AND THE STUDY OF FLUID MECHANICS 1.1 The Big Picture

### Calculating Horsepower Requirements and Sizing Irrigation Supply Pipelines

B-6011 Calculating Horsepower Requirements and Sizing Irrigation Supply Pipelines Guy Fipps* Pumping costs are often one of the largest single expenses in irrigated agriculture. Table 1 shows typical fuel

### MFP14, MFP14S and MFP14SS Automatic Pumps

Page 1 of 6 TI-P136-02 ST Issue 12 Cert. No. LRQ 0963008 ISO 9001, S and SS utomatic Pumps Description The Spirax Sarco automatic pump is a displacement receiver operated by steam or compressed air. It

### Selection Of Centrifugal Pumping Equipment 1

Circular 1048 Selection Of Centrifugal Pumping Equipment 1 Dorota Z. Haman, Fedro S. Zazueta, Forrest T. Izuno 2 INTRODUCTION The pump is an essential component of an irrigation system. Proper selection

### BASIC HYDRONIC SYSTEM DESIGN

Hydronic Systems BASIC HYDRONIC SYSTEM DESIGN FCU FCU FCU FCU FCU FCU Terminal Units Fan Coils, Chilled Beams, Finned Tube, Radiant, etc. Distribution Piping AS-1 Primary Pumps P-1 & P-2 P-1 P-2 ET-1 P-B-1

### Open Cycle Refrigeration System

Chapter 9 Open Cycle Refrigeration System Copy Right By: Thomas T.S. Wan 温 到 祥 著 Sept. 3, 2008 All rights reserved An open cycle refrigeration system is that the system is without a traditional evaporator.

### Waste Collection Systems

Waste Collection Systems Lift Stations Lift Stations Training Objectives To gain an understanding of: Lift Station vocabulary Lift Station components and their function Lift Station operational requirements

### Variable Vane Pump, Direct Controlled PV7...A Series 1X / 2X

Variable Vane Pump, Direct Controlled PV7...A Series 1X / X RE 1 Issue: 1.1 Replaces: 8.8 Sizes 1 to Maximum pressure 1 bar Displacement volume 1 to cm Features Very short control times Low noise Mounting

### = water horsepower WHP brake horsepower QH WHP = (222) ( 33,000 ft-lbs/min-hp)( 7.481 gal/ft ) 1 HP=0.746 kw

Lecture 11 Pumps & System Curves I. Pump Efficiency and Power Pump efficiency, E pump E pump = water horsepower WHP brake horsepower = BHP (221) where brake horsepower refers to the input power needed

### TOPIC: 191004 KNOWLEDGE: K1.01 [3.3/3.5] Which one of the following contains indications of cavitation in an operating centrifugal pump?

KNOWLEDGE: K1.01 [3.3/3.5] P21 Which one of the following contains indications of cavitation in an operating centrifugal pump? A. Low flow rate with low discharge pressure. B. Low flow rate with high discharge

### A Spreadsheet Program for the Calculation of Piping Systems and the Selection of Pumps

Session 1633 A Spreadsheet Program for the Calculation of Piping Systems and the Selection of Pumps Craig W. Somerton Department of Mechanical Engineering, Michigan State University I. Introduction An

### Chapter 3.5: Fans and Blowers

Part I: Objective type questions and answers Chapter 3.5: Fans and Blowers 1. The parameter used by ASME to define fans, blowers and compressors is a) Fan ration b) Specific ratio c) Blade ratio d) Twist

### VARIABLE VANE PUMPS V3

VARIABLE VANE PUMPS V3 (series 30 and 40) Nominal sizes 12; 25; 40; 63 up to p n 100 bar V g 8.5; 19; 32; 47 cm 3 /rev KE 1015 11/02 replaces 07/97 easy commissioning due to automatic bleed facility low

### Water Supply. Simulation of Water Distribution Networks. Mohammad N. Almasri. Optimal Design of Water Distribution Networks Mohammad N.

Water Supply Simulation of Water Distribution Networks The Use of EPANET Mohammad N. Almasri 1 Introduction This presentation focuses on two issues: The simulation of water distribution networks (WDNs)

### SERIES ASM NEOPRENE/EPMD FLANGED SINGLE SPHERE CONNECTOR CONNECTORS. Pressures to 225 PSIG (15.51 barg) Temperatures to 230ºF (110ºC)

APPLICATIONS Process Industry Weak Acids Alkalies Compressed Air Pulp & Paper MODELS ASM - Flanged Connection OPTIONS Control Rods Oil & Gas Water & Waste Pump suction & discharge Sea water Chemical lines

### ME 305 Fluid Mechanics I. Part 8 Viscous Flow in Pipes and Ducts

ME 305 Fluid Mechanics I Part 8 Viscous Flow in Pipes and Ducts These presentations are prepared by Dr. Cüneyt Sert Mechanical Engineering Department Middle East Technical University Ankara, Turkey csert@metu.edu.tr

### Pacific Pump and Power

Pacific Pump and Power 91-503 Nukuawa Street Kapolei, Hawaii 96707 Phone: (808) 672-8198 or (800) 975-5112 Fax: (866) 424-0953 Email: sales@pacificpumpandpower.com Web: www.pacificpumpandpower.com Pumps

### INTERNATIONAL FIRE TRAINING CENTRE FIREFIGHTER INITIAL PUMPS AND PRIMERS. Throughout this note he means he/she and his means his/hers.

INTERNATIONAL FIRE TRAINING CENTRE FIREFIGHTER INITIAL PUMPS AND PRIMERS Throughout this note he means he/she and his means his/hers. Areas of bold type are considered to be of prime importance. INTRODUCTION

### www.klmtechgroup.com TABLE OF CONTENT

Page : 1 of 26 Project Engineering Standard www.klmtechgroup.com KLM Technology #03-12 Block Aronia, Jalan Sri Perkasa 2 Taman Tampoi Utama 81200 Johor Bahru Malaysia TABLE OF CONTENT SCOPE 2 REFERENCES

### Selecting a Vertical Turbine Pump (Information required from client)

Selecting a Vertical Turbine Pump (Information required from client) 1. Liquid to be pumped: (Note: If liquid is not clear water, the following must also be ascertained). a. Foreign material present in

### oe4625 Dredge Pumps and Slurry Transport Vaclav Matousek October 13, 2004

oe4625 Vaclav Matousek October 13, 2004 1 Dredge Vermelding Pumps onderdeel and Slurry organisatie Transport 8. OPERATION LIMITS OF PUMP-PIPELINE SYSTEM REQUIRED MANOMETRIC PRESSURE MAXIMUM VELOCITY INITIAL

### CDX. EBARA PUMPS EUROPE S.p.A. CENTRIFUGAL PUMPS. Page - CONTENTS 100

CONTENTS Page - CONTENTS 100 - SPECIFICATIONS 200 SELECTION CHARTS 201 PERFORMANCE CHART 70 202 PERFORMANCE CHART 90 203 PERFORMANCE CHART 120 204 PERFORMANCE CHART 200 205 - CONSTRUCTIONS 300 SECTIONAL

### Optimizing the hydraulic designing of pressurized irrigation network on the lands of village Era by using the computerized model WaterGems

Optimizing the hydraulic designing of pressurized irrigation network on the lands of village Era by using the computerized model WaterGems Ali Ghadami Firouzabadi 1 and Majid Arabfard 2 1. Ali Ghadami

### A. ASME Compliance: Fabricate and install hydronic piping in accordance with ASME B31.9 "Building Services Piping.

PART 1: GENERAL 1.01 Purpose: A. This standard is intended to provide useful information to the Professional Service Provider (PSP) to establish a basis of design. The responsibility of the engineer is

### h b b h Q u da u 1 1 dy dz u 1 dy 1 dz u b h b h

P3.18 An incompressible fluid flows steadily through the rectangular duct in the figure. The exit velocity profile is given by u umax(1 y /b )(1 z /h ). (a) Does this profile satisfy the correct boundary

### Effect of the Submerged Vortex Cavitation Occurred in Pump Suction Intake on Hydraulic Forces of Mixed Flow Pump Impeller

CA2001:sessionB8.006 1 Effect of the Submerged ortex Cavitation Occurred in Pump Suction Intake on Hydraulic Forces of Mixed Flow Pump Impeller Takahide NAGAHARA, Tadashi SATO and Tomoyoshi OKAMURA Tsuchiura

### Pump Formulas Imperial and SI Units

Pump Formulas Imperial and Pressure to Head H = head, ft P = pressure, psi H = head, m P = pressure, bar Mass Flow to Volumetric Flow ṁ = mass flow, lbm/h ρ = fluid density, lbm/ft 3 ṁ = mass flow, kg/h

### 4" SUBMERSIBLE PUMPS

4" SUBMERSIBLE PUMPS 4" SUBMERSIBLE PUMPS 50/60 HZ Multi-stage centrifugal submersible pumps for clean water in 4" wells. The 4" VSP pump series is carefully designed and manufactured for maximum resistant

### VAL-MATIC VALVE AND MANUFACTURING CORP. 905 RIVERSIDE DRIVE, ELMHURST, IL 60126 TEL. (630) 941-7600 FAX.

Cavitation in Valves VAL-MATIC VALVE AND MANUFACTURING CORP. 905 RIVERSIDE DRIVE, ELMHURST, IL 60126 TEL. (630) 941-7600 FAX. (630) 941-8042 www.valmatic.com CAVITATION IN VALVES INTRODUCTION Cavitation

### SIGMA GROUP a. s. Divize průmyslová čerpadla

SIGMA GROUP a. s. Divize průmyslová čerpadla SIGMA GROUP a. s. INDUSTRIAL PUMP DIVISION Jana Sigmunda 79, 783 50 LUTÍN SEWAGE PUMPS NFPH, NFVH, NFJH, NFRH, NFPV, NFVV, NFJV, NFRV, NFPW NFVW Tel.: +420

### MATHEMATICS FOR WATER OPERATORS

MATHEMATICS FOR WATER OPERATORS Chapter 16: Mathematics The understanding of the mathematics of water hydraulics (flows, pressures, volumes, horsepower, velocities) and water treatment (detention time,

### CO 2 41.2 MPa (abs) 20 C

comp_02 A CO 2 cartridge is used to propel a small rocket cart. Compressed CO 2, stored at a pressure of 41.2 MPa (abs) and a temperature of 20 C, is expanded through a smoothly contoured converging nozzle

### Pumps SELECTION OF A PUMP

Pumps SELECTION OF A PUMP A water system needs to move the water produced from the source to its customers. In almost all cases in Minnesota, the source is at a lower elevation than the user so the water

### Centrifugal Fans and Pumps are sized to meet the maximum

Fans and Pumps are sized to meet the maximum flow rate required by the system. System conditions frequently require reducing the flow rate. Throttling and bypass devices dampers and valves are installed

### OIL SEPARATORS. 112

OIL SEPARATORS 111 OIL SEPARATORS APPLICATIONS The oil separators, shown in this chapter, are classified Pressure vessels in the sense of the Pressure Equipment Directive 97/23/EC, Article 1, Section 2.1.1

### Experiment (13): Flow channel

Introduction: An open channel is a duct in which the liquid flows with a free surface exposed to atmospheric pressure. Along the length of the duct, the pressure at the surface is therefore constant and

### APSP-15 Standard for Energy Efficiency for Residential Inground Swimming Pools, and Spas

APSP-15 Standard for Energy Efficiency for Residential Inground Swimming Pools, and Spas 1. Scope 1.1. Energy efficiency requirement for residential swimming pool filtration and heating systems used for

### THE HUMBLE CHECK VALVE

THE HUMBLE CHECK VALVE Selection of Check Valves for Pumped Systems By Geoffrey D Stone C.Eng FIMechE; CP Eng FIEAust Design Detail & Development Why do we need check valves? To prevent reverse flow To

### Investigations of a Long-Distance 1000 MW Heat Transport System with APROS Simulation Software

th International Conference on Structural Mechanics in Reactor Technology (SMiRT ) Espoo, Finland, August 9-4, 9 SMiRT -Division 3, Paper 56 Investigations of a Long-Distance MW Heat Transport System with

### BLADDER SURGE CONTROL SYSTEM

PART I GENERAL 1.01 Description BLADDER SURGE CONTROL SYSTEM This specification describes the requirements for a Bladder Surge Control System. The purpose of the system is to minimize transient pressures

### 2-Port Self-acting Temperature Control Valve Selection for Heating and Cooling Applications

Page 1 of 12 TI-S21-07 CH Issue 1 Cert. No. LRQ 0963008 ISO 9001 2-Port Self-acting Temperature Control Valve Selection How to select a system Valve selection: 1. Is the application for heating or cooling?

### EXAMPLES (OPEN-CHANNEL FLOW) AUTUMN 2015

EXAMPLES (OPEN-CHANNEL FLOW) AUTUMN 2015 Normal and Critical Depths Q1. If the discharge in a channel of width 5 m is 20 m 3 s 1 and Manning s n is 0.02 m 1/3 s, find: (a) the normal depth and Froude number

### oil liquid water water liquid Answer, Key Homework 2 David McIntyre 1

Answer, Key Homework 2 David McIntyre 1 This print-out should have 14 questions, check that it is complete. Multiple-choice questions may continue on the next column or page: find all choices before making

### Variable Frequency Drives for Water/Wastewater. Discussion on Pump Optimization Principles and Need to Know Drive Technology

Variable Frequency Drives for Water/Wastewater Discussion on Pump Optimization Principles and Need to Know Drive Technology Pumps in Water Wastewater 2 WWW Challenges: Drivers/Trends Demand for WWW Age

### HOW TO ALIGN THE UNIT

First check that the pump has not been damaged during trasport. Place the fondation bolts loosely in the holes of the base plate and align the plate by using shims. Check alignment with a spirit level.

### FIGURE P8 50E FIGURE P8 62. Minor Losses

8 48 Glycerin at 40 C with r 1252 kg/m 3 and m 0.27 kg/m s is flowing through a 4-cm-diameter horizontal smooth pipe with an average velocity of 3.5 m/s. Determine the pressure drop per 10 m of the pipe.

### Radial piston pumps type R and RG

Radial piston pumps type R and RG Operating pressure p max = 700 bar Delivery flow Q max = 91.2 lpm (at 1450 rpm) Geometric displacement V g max = 64.2 cm 3 /rev. 1. General Motor pumps and hydraulic power

### Pump Maintenance - Repair

Pump Maintenance - Repair Brian Trombly Mo Droppers Cummins Bridgeway, Gaylord, Mi The basic centrifugal pump consists of two main elements: 1. The rotating element which includes an impeller and a shaft.

### Design of Lift Station and Wastewater Treatment Facility in Ascension Parish

Design of Lift Station and Wastewater Treatment Facility in Ascension Parish Christopher Banks Stephen Webster Brittany Williams Technical Advisors, MWH: Sparkle W. Noble Michael R. Johnston, P.E. Faculty

### Highly flexible couplings

Construction and operation 8.03.00 Instructions for installation 8.03.00 Types of stress 8.04.00 Diagrams for static deformation of the coupling ring 8.05.00 Coupling size 8.07.00 Examples of combinations

### CHAPTER 25 IDEAL GAS LAWS

EXERCISE 139, Page 303 CHAPTER 5 IDEAL GAS LAWS 1. The pressure of a mass of gas is increased from 150 kpa to 750 kpa at constant temperature. Determine the final volume of the gas, if its initial volume

### Experiment 3 Pipe Friction

EML 316L Experiment 3 Pipe Friction Laboratory Manual Mechanical and Materials Engineering Department College of Engineering FLORIDA INTERNATIONAL UNIVERSITY Nomenclature Symbol Description Unit A cross-sectional

### CEE 370 Fall 2015. Laboratory #3 Open Channel Flow

CEE 70 Fall 015 Laboratory # Open Channel Flow Objective: The objective of this experiment is to measure the flow of fluid through open channels using a V-notch weir and a hydraulic jump. Introduction:

### IMPORTANT SAFETY NOTICE

IMPORTANT SAFETY NOTICE To: Our Valued Customers User safety is a major focus in the design of our products. Following the precautions outlined in this manual will minimize your risk of injury. ITT Goulds

### VERTICAL TURBINE AND PROPELLER PUMPS

VERTICAL TURBINE AND PROPELLER PUMPS INTRODUCTION Vertical Turbine and Propeller Pumps Model 7000 Series Turbine Pump Model 800 Series Axial Flow Propeller Pump Model 800 Series Mixed Flow Propeller Pump

### 1 DESCRIPTION OF THE APPLIANCE

1 DESCRIPTION OF THE APPLIANCE 1.1 INTRODUCTION The cast iron SF boilers are a valid solution for the present energetic problems, since they can run with solid fuels: wood and coal. These series of boilers

### PS1800 Centrifugal Pumping Systems

PS1 Centrifugal Pumping Systems General Data and Sizing Tables The curve show the performance range of 4 models at 1Wp solar array - irradiation of 6kWh/m² on a tilted surface - ambient temperature 3 C

### Pumping System Design Seminar

Pumping System Design Seminar Hydraulic Variations for Both PC and Centrifugal Grinder Pumps Utilized in Pressure Sewer Systems Dana Mullen, Market Manager Pressure Sewer Systems COLUMBUS, OHIO A Pressure

### Introduction. The following is an outline of the contents of this paper: Definition of Artificial Lift Page 2. How an Oil Well is Produced Page 2

Introduction Canadian Oilwell Systems Company and it s subsidiaries are suppliers of oil well Electric Submersible Pumping systems (ESPs). Such pumps are used to lift oil from oil wells so that the oil

### OUTCOME 1 STATIC FLUID SYSTEMS TUTORIAL 1 - HYDROSTATICS

Unit 41: Fluid Mechanics Unit code: T/601/1445 QCF Level: 4 Credit value: 15 OUTCOME 1 STATIC FLUID SYSTEMS TUTORIAL 1 - HYDROSTATICS 1. Be able to determine the behavioural characteristics and parameters

### DATA COLLECTION AND PUMP ENERGY SAVING OPPORTUNITIES. Presented By: Rick Rumsey, P.E.

DATA COLLECTION AND PUMP ENERGY SAVING OPPORTUNITIES Presented By: Rick Rumsey, P.E. Data Collection Customer Information Pump Motor Information Pump Information Irrigation System Information Historic

### DN [mm] [m 3 /h] Characterizing disk Dimensions / Weights see «Dimensions and weights», page 3 Motorizing

Technical data sheet R5.. Characterized control valves, 3-way, with external thread for open and closed cold and warm water systems for modulating control on the water side of air-handling and heating

### Industrial Process Pump Safety Manual IMPORTANT SAFETY NOTICE

Industrial Process Pump Safety Manual IMPORTANT SAFETY NOTICE To: Our Valued Customers User safety is a major focus in the design of our products. Following the precautions outlined in this manual will

### Practice Problems on Conservation of Energy. heat loss of 50,000 kj/hr. house maintained at 22 C

COE_10 A passive solar house that is losing heat to the outdoors at an average rate of 50,000 kj/hr is maintained at 22 C at all times during a winter night for 10 hr. The house is to be heated by 50 glass

### A10VSO Nominal size 18 see RD 92712 A10VSO Nominal size 28...140 see RD 92711

A10VO Nominal size 18 see RD 92712 A10VO Nominal size 28...140 see RD 92711 The variable displacement axial piston pump A10VO in swashplate design was designed for hydrostatic drives in open circuits.

### Chapter 5 MASS, BERNOULLI AND ENERGY EQUATIONS

Fluid Mechanics: Fundamentals and Applications, 2nd Edition Yunus A. Cengel, John M. Cimbala McGraw-Hill, 2010 Chapter 5 MASS, BERNOULLI AND ENERGY EQUATIONS Lecture slides by Hasan Hacışevki Copyright

### BLOWERS EXHAUSTERS CONTINENTAL INDUSTRIE ASME PTC 10 PERFORMANCE TEST PROCEDURE. Blowers & Exhausters. Page 1 of 6 PURPOSE STANDARDS INSTRUMENTS

PURPOSE Page 1 of 6 Test purpose is the measure of the following compressor operating parameters: flow of gas handled pressure rice produced shaft power requirement efficiency surge limit STANDARDS Test

### Wet gas compressor capacity limits

Understanding Centrifugal Compressor Performance in a Connected Process System Scott Golden, Scott A. Fulton and Daryl W. Hanson Process Consulting Services Inc., Houston, Texas Wet gas compressor capacity

### ENERGY RETROFIT PROGRAM

ENERGY RETROFIT PROGRAM An innovative but simple retrofit for existing hot water and chilled water piping systems that will help you save money. REDUCE FLOW BY 50% REDUCE PUMP HEAD BY 75% REDUCE PUMP POWER

### 1.0 2.0 3.0 4.0 5.0 6.0 7.0. Q [m 3 /h] Wilo-Star Cast iron body 60 Hz. Star 30 F. Star 21. Star 17 FX. 4 8 12 16 20 24 28 Q [US gpm]

Product review: Range: Wilo-Star....... Star F Star Star Star F Star Star FX [m /h] Wilo-Star Cast iron body Hz [US gpm].......... [m /h] Wilo-Star Bronze body 9 Hz [US gpm] Star Star Star Star Star BF

### p atmospheric Statics : Pressure Hydrostatic Pressure: linear change in pressure with depth Measure depth, h, from free surface Pressure Head p gh

IVE1400: n Introduction to Fluid Mechanics Statics : Pressure : Statics r P Sleigh: P..Sleigh@leeds.ac.uk r J Noakes:.J.Noakes@leeds.ac.uk January 008 Module web site: www.efm.leeds.ac.uk/ive/fluidslevel1

### Fan Basics and Selection Criteria (How to Use)

Feature: Understanding SANYO DENKI Products from Scratch Fan Basics and Selection Criteria (How to Use) Honami Osawa 1. Introduction In recent years, the importance of cooling technology has become even

### HS-901(A) BASIC STEAM HEATING SYSTEMS

HS-901(A) BASIC HEATING SYSTEMS One-Pipe Two-Pipe Basic Steam Heating Systems One-pipe steam heating system EQUALIZER SAFETY FACTOR STATIC HEAD PRESSURE DROP 2" HEATING UNIT 15" DRIP CONNECTION In a one-pipe,

### Pump-Transfer Cooler Filtration Unit UKF

Pump-Transfer Cooler Filtration Unit UKF Symbol General The UKF unit is a compact, easy-to-install system for offline filtration cooling circuits. It consists of a low-noise feed pump, a filter and a plate

### Selection and Determination of Tubing and Production Casing Sizes

CHAPTER 3 Selection and Determination of Tubing and Production Casing Sizes OUTLINE 3.1 Overview 3.2 Overview of Nodal Analysis 3.3 Selection and Determination of Tubing and Production Casing Sizes for

### European Aviation Safety Agency

European Aviation Safety Agency EASA TYPE-CERTIFICATE DATA SHEET Number: E.070 Issue: 05 Date: 16 November Type: GE Aviation Czech M601/H80 series turboprop engines Models: M601D M601D-1 M601D-2 M601D-11

### SIRIUX. SINGLE AND DOUBLE HIGH EFFICIENCY CIRCULATORS Heating Air-conditioning OPERATING LIMITS APPLICATIONS. 28 m 3 /h* Heads up to: Flows up to:

OPERATING LIMITS Flows up to: m /h* Heads up to: m C Max operating pressure: bars Temperature range: - à + C Max ambient temperature: + C ND of orifices: à * m /h: parallel operation SIRIUX SINGLE AND

### Solution of Pipe Flow Problems. Class 21 Fluid Mechanics. Types of Pipe Flow Problems 4/6/2011. Energy Equation. Tuesday, April 5.

4/6/ Class Fluid Mechanics Energy Equation Tuesday, April 5 Types of Pipe Flow Problems Single pipes Determine pressure drop or head loss Determine flow rate or average velocity Pipe diameter Multiple

### A Practical Guide to Free Energy Devices

A Practical Guide to Free Energy Devices Part PatC1: Last updated: 22nd October 2005 Author: Patrick J. Kelly Please note that this is a re-worded excerpt from this patent. If the content interests you,

### SUPPLEMENTAL TECHNICAL SPECIFICATIONS BI-DIRECTIONAL STATIC LOAD TESTING OF DRILLED SHAFTS

July 14, 2015 1.0 GENERAL BI-DIRECTIONAL STATIC LOAD TESTING OF DRILLED SHAFTS This work shall consist of furnishing all materials, equipment, labor, and incidentals necessary for conducting bi-directional

### Theory, Application, and Sizing of Air Valves

Theory, Application, and Sizing of Air Valves VAL-MATIC VALVE AND MANUFACTURING CORP. 905 RIVERSIDE DRIVE, ELMHURST, IL 60126 TEL. (630) 941-7600 FAX. (630) 941-8042 www.valmatic.com 1 THEORY, APPLICATION,

### ATEX instruction for PAHT G 2-90 in dust applications

MAKING MODERN LIVING POSSIBLE Instruction ATEX instruction for PAHT G 2-90 in dust applications danfoss.high-pressurepumps.com Table of Contents 1. Common demands for Category 2 and 3 installations...3

### TABLE OF CONTENT

Page : 1 of 21 Project Engineering Standard www.klmtechgroup.com KLM Technology #03-12 Block Aronia, Jalan Sri Perkasa 2 Taman Tampoi Utama 81200 Johor Bahru Malaysia TABLE OF CONTENT SCOPE 2 REFERENCES

### Nozzle Loads, Piping Stresses, and the Effect of Piping on Equipment

Nozzle Loads, Piping Stresses, and the Effect of Piping on Equipment By Patty Brown & Mark van Ginhoven November 13, 2009 1 CA 2009 Fluor Corporation. All Rights Reserved. Topics Covered Introduction Nozzle

### Product catalogue, pipe and sewer cleaning systems

Product catalogue, pipe and sewer cleaning systems Nozzles Rotorjet trolley Hose reels Cleaning devices www.hammelmann.com Contents (Navigation via Bookmarks) Rotorjet trolley Rotary joints, spray pipes

### Equipment Information

2070C Equipment Information INDEX: DESCRIPTION AND KEY FEATURES LAYOUT NOMINAL TECHNICAL DATA CONFIGURATION Sealed Air GmbH Customer Systems Center D4 Park 4 CH-6039 Root-Längenbold Telephone: +41 (0)

### HYDRAULICS. H91.8D/C - Computerized Open Surface Tilting Flow Channel - 10, 12.5, 15 and 20 m long

HYDRAULICS H91.8D/C - Computerized Open Surface Tilting Flow Channel - 10, 12.5, 15 and 20 m long 1. General The series of channels H91.8D has been designed by Didacta Italia to study the hydrodynamic