1 ABLOY DA60 SWING DOOR OPERATOR Installation and commissioning manual Abloy Oy An ASSA ABLOY Group company
2 APPROVALS / STANDARDS Low Voltage directive 7//EEC as amended by the directive 9/68/EEC EMC directive 89/6/EEC Statement of fire doors by Technical Research Centre of Finland Warning! Warning! THIS MANUAL CONTAINS IMPORTANT SAFETY INSTRUCTIONS Warning - IT IS IMPORTANT FOR SAFETY OF PERSONS TO FOLLOW THESE INSTRUCTIONS SAVE THESE INSTRUCTIONS Do not allow children to play with fixed controls. Frequently examine the installation for imbalance and signs of wear or damage to cables, springs and mountings. Do not use if repair or adjustment is necessary. Disconnect the supply when cleaning or other maintenance is being carried out. Before installing the operator, check that the door is in good mechanical condition and it opens and closes properly. Ensure that entrapment between door and the surroundings is avoided. Ensure that the operator is suited for installation. Check temperature, humidity, door weights, etc. restriction, what is mentioned in this manual or other Abloy Oy material. Note! Instructions, design specifications and illustrations which are contained in this manual are not binding. Rights reserved for changes without previous notice.
3 CONTENTS Approvals... Revision... Content of delivery... General information...6 Operation... 7 Main switch and mode switch...7 Door weight...8 Installation...9 Internal connections... Commissioning... A safe door... 8 External connections... 9 Connection examples... Self diagnostic...8 Maintenance... 9 Spare parts...0
4 REVISION Following pages has been revised: Page Revision As at..006.
5 CONTENT OF DELIVERY DA60 Swing door operator - screws pcs M8x DA0 Mounting plate - screws 6 pcs,x DA7 Standard arm - screws pcs,x and pcs M8x0 DA8 Extended arm - screws pcs,x and pcs M8x0 DA9 Sliding arm - screws pcs,x0 and pcs M8x0 DA0 Extension piece - 0 mm + M8x - 0 mm + M8x + M8x - 60 mm + M8x90
6 GENERAL INFORMATION Technical data Measures 9 (L) x 8 (H) x 07 (W) mm Weight 6, kg Supply voltage 90-6 VAC, 7-6 Hz Rated output 70 W Enclosure class IP0 Temperature range Storage C (in dry premises) Operation: C (in dry premises) The automatic swing door operator must not be installed in applications where it is subjected to water or snow. Interfaces Voltage output VDC, stabilized, output current 00 ma Voltage output VDC, stabilized, output current,0 A The total load must not exceed W Potential free relay output, preset to operate seconds 0 VDC resistive load Features Usage for heavy density of pedestrian traffic Push&Go as a standard feature Normal and delayed Adjustable hold open time s or sequential use Fire detector connection Free Swing operation Door hold force Prepull before opening Secondary DC inlet for power back up ( VDC (± %), A) Maximum opening angles: With standard arm 00 degrees With sliding arm on the opening side 00 degrees With sliding arm on the closing side 90 degrees 6
7 OPERATION Abloy DA60 is an electromechanical swing door operator for heavy use. The door operator includes new free swing function: when using the door manually it operates lightly without motor s resistance and the door can be left in open position when required. It can be used on both single and double, internal and external, fire and emergency exit doors. Safety features Opening cycle: If the door is obstructed in opening cycle. The door is set free and hold open time is started. After second, new trial is done to open the door. Maximum amount for trials is. If this is exceeded or hold open time is end, the door is closed. Closing cycle: If the door is obstructed in closing cycle. The door is set free and new trials are done to close the door. If the closing is still obstructed, the operator tries to close the door at one minute intervals. MAIN SWITCH AND MODE SWITCH AUTO MAN OPEN Main switch Mode switch When the power is switched on, the mains switch lights up. = on 0= off Functions of mode switch AUTO: The operator opens the door for the duration of the hold open time. MAN: Manual use. OPEN: The door is held permanetly open. NOTE! There is seconds constant delay when mode switch is changed from position OPEN to AUTO or MAN. 7
8 DOOR WEIGHT Standard arm Door weight [kg] Door width [cm] Sliding arm Door weight [kg] Door width [cm] 8
9 INSTALLATION Tools required Drill Set of ball ended allen wrenches # Phillips head screwdriver Flat blade screwdrivers, pcs Steps of installation - Preparing installation - Installing the mounting plate - Mounting the operator and the arm - Connecting the operator to mains - Commissioning - Testing - Connecting devices Preparing installation - Check the proper function of the door - hinges - door clearance - Check the proper function of the lock - lock case - striker plate Removal of housing Note! Remove the protective earth wire from cover and connect it back after installation. Keep the mains disconnected when removing or mounting cover. 9
10 Installing the mounting plate Operator is to be installed on the transom, with the main switch located towards the hinge. Use the mounting plate DA0 with the door operator ensuring the installation base is level and securely fixed to a flat surface. Hinge line 9, 6 96, 0 9 o 0 0 o 0 o 0 o 0 8, 8, 70 8, Installation measurements for standard arm and for sliding arm DA9 to the closing side installation. When installing operator to the opening side of the door, refer to page. 0
11 Assembly of the operator and the standard arm to the closing side Hinge line Mounting of the operator M8x and washer Min. 0 Y Y (mm) Length of extension piece 0 No extension piece 0 0 mm (DA0/0) 0 0 mm (DA0/0) 0 0 mm (DA0/0, DA0/0) 0 0 mm (DA0/0 * pcs) mm (DA0/06) 90 Frame depth DA7 DA8 Frame depth 0-0 mm 0-0 mm - After installation, ensure that the arm and door are properly adjusted. - Mount a door stop to the door open position so that wind will not drive the door against the wall, resulting in damage. - Tighten the holding screw.
12 Assembly of the operator and the sliding arm DA9 to the closing side Hinge line Mounting of the operator M8x and washer * From the mounting plate to the mounting hole of the sliding rail, without extension piece. Y L 6* 97 M Y (mm) Length of extension piece 0 0 mm (DA0/0) 0 0 mm (DA0/0) 0 0 mm (DA0/0, DA0/0) 0 0 mm (DA0/0 pcs) 0 60 mm (DA0/06) DA9 Frame depth Frame depth H/mm Arm distance L/mm Minimum door width M/mm After installation, ensure that the arm and door are properly adjusted. - Mount a door stop to the door open position so that wind will not drive the door against the wall, resulting in damage. - Tighten the holding screw.
13 Assembly of the operator and the sliding arm DA9 to the opening side Mounting of the operator M8x and washer Hinge line max. M LY Y (mm) Length of extension piece 0 No extension piece 0 0 mm (DA0/0) 0 0 mm (DA0/0) 0 0 mm (DA0/0, DA0/0) 60 0 mm (DA0/0 * pcs) mm (DA0/06) DA9 Frame depth Frame depth H/mm Arm distance L/mm Minimum door width M/mm After installation, ensure that the arm and door are properly adjusted. - Mount a door stop to the door open position so that wind will not drive the door against the wall, resulting in damage. - Tighten the holding screw.
14 INTERNAL CONNECTIONS - Electrical connections should be made by a qualified electrician. - The power plug must have an easy access. - If a permanent connection is made unit must be equipped with an external switch providing all pole disconnection. - Keep the mains disconnected during installation. External power supply unit +VDC, min A X X black To motor red + V backup + V in black white X X6 DC X Option interface white brown AC PE AUTO: red & black MAN: NC OPEN: blue & black Position sensor blue black red Mode switch AUTO MAN OPEN I 0 Main switch white brown brown white N L DC supply back-up When not mains operated, or for back-up supply, the external VDC (min. A) supply can be connected to X connectors and. Connect + from DC supply back-up to X connector and to X connector. No battery charging or maintenance is provided by DA60.
15 COMMISSIONING Check the free movement of the door. Turn mode switch to MAN. The mode switch is located in the head panel. Plug in the mains and turn main switch on. The main switch is located in the head panel. Choose the type of the arm Main switch Mode switch standard sliding ARM The jumpers are located on the control board. Jumper is connected Jumper is disconnected Check the DOOR sealed hold closed Push&Go DOOR "Sealed" enables motorized closing pull before opening and final pull when closing. Select this to ensure the proper function of the lock when prepull and final pull are needed. Final pull will be activated 0-0 mm before the doors closed position. Final pull is activated second, when door is closed position. sealed hold closed Push&Go When hold closed jumper is selected, operator pushes the door against the frame. DOOR sealed hold closed Push&Go DOOR Push&Go is in operation, when mode switch is in AUTO position. When door is pushed or pulled manually operator opens the door. Operator opens the door to adjusted opening angle and closes the door after second hold open time. Note! It is not possble to use Push&Go and free swing options at the same time.
16 COMMISSIONING 6 Check the OPTION single master corridor fire n.c free swing Select "single" for a stand alone door. "Master" and "Corridor", not yet available. OPTION single master corridor fire n.c free swing OPTION single master corridor fire n.c free swing OPTION If the jumper is connected then operator requires N.C. output from the fire detector. If the jumper is disconnected then operator requires N.O. output from the fire detector. When jumper is connected the door can opened and closed manually. When opening comes, the door is opened to fully open position and closed after adjusted hold open time. Free swing is in operation when mode switch is in AUTO position. Note! It is not possble to use Push&Go and free swing options at the same time. 7 Teach door open and closed position TEACH CLOSED TEACH OPEN POWER ON TEACH - Push TEACH-button to enter learning mode. - Teach the door closed position Yellow led blinks: close the door and push TEACH-button. - Teach the door open position Green led blinks: Open the door to the desired angle and push TEACH-button. - Yellow "TEACH CLOSED" led blinks: Close the door manually. 8 Operators force, opening speed and hold open time Force FORCE The operator's force requires adjustment to suit door weight. Use lowest possible value to ensure the smooth function of safety feature. Start the adjustment by putting the force potentiometer to middle position (= 0%) and fine-tune it after opening speed adjustment. Note! Important: as less force as possible 6
17 COMMISSIONING Adjust the opening speed. min max SPEED Time (sec) Door width (mm) Door weight (kg) ,7,,,9 000,,0,,8 00,,7,,8 00,,,8 6, Minimum safe opening and closing times for door of various widths and weights are summarized in the table. Hold open times Adjust first hold open time for delayed and then hold open time for normal 0 HOLD OPEN seq 60 Adjusting the hold open time for delayed Entering the mode: - Turn mode switch to AUTO position. - Press TEACH button at least seconds. - In the programming mode green led is lit, yellow led is flashing times, pause, times, pause... - Adjust the hold open time for delayed ( sec). Time starts when the door is in open position. Full right position (seq) of the potentiometer means that every other either opens or closes the door. Back to normal mode: - Press TEACH button at least seconds or wait minutes. - Turn mode switch to MAN position. 0 HOLD OPEN seq 60 Adjusting hold open time for normal - Adjust the hold open time ( s). Time starts when the door is in open position. Full right position (seq) of the potentiometer means that every other either opens or closes the door. Note! For safe operation, always use low force, speed and long hold open time. 9 Test the operation - Turn mode switch to AUTO. - Test the operation. - If the function is not desired, repeat steps to 9. 7
18 A SAFE DOOR The safety of the door operator is controlled by basic adjustments; operator force, speeds, and hold open times. - The operator force is an important adjustment. A high value affects to the safety feature and also to its sensitivity. - High speeds increases the energy transferred in the door causing it not stop correctly. - With hold open times the distance from device to door is preset.. Adjust low speeds.. Adjust the operator force to a low setting ensuring the safety feature activates on door moving.. Adjust the hold open times. By following these basic procedures the operator is safe in operation. Note!!! High speeds and safety is only possible by fitting of Safety sensors. A safe door environment needs ALWAYS a safety sensor. It is recommended to use safety sensor when possible, not only with high speeds. 8
19 EXTERNAL CONNECTIONS +V out +V out Normal Delayed Safet senso Lockin circui Fire detector y r g t + VDC, 00 ma output + VDC,,0 A output 0 Ground 7, 8, 9 Potential free relay output for lock drive 6 Normal Delayed. Door will open after,0 seconds delay. Safety sensor Ground to stop the door movement during operation Locking circuit Inhibits the opening if the lock bolt is out. Grounding this input allows the opening Fire detector Ground Note! The total load must not exceed W Fire detector Take connection loop between and away if fire detector is connected. Connect fire detector between and and check fire jumper (fire n.c.). After fire alarm, one manual opening is required to re-energise the operator to chosen program selector mode. Safety Sensor On the opening side of the door: Safety sensor is connected between terminals and. The cable loop must have KOhm resistance inside the safety sensor for cable break detection. Leave resistor connected to the terminals and, when safety sensor is not used. Always use safety sensor for maximum safety. On the closing side of the door: Safety sensor is connected to input. - Do not strip any cables for unnecessary length. Loose wires may cause unwanted contacts. 9
20 EXTERNAL CONNECTIONS Impulse inputs The closing contact drive (NO) must be potential free. The device, like a push button or motion sensor, must be installed within direct sight of the door. Maximum length of the device cable is 0 meters. The total resistance of the control switch and its wiring must not exceed 00 ohm, when switch is closed. Delayed : delay =,0 seconds. When the operator receives the opening, the lock is released immediately and door is opened after,0 seconds. Normal : Door is opened immediately. - Do not strip any cables for unnecessary length. Loose wires may cause unwanted contacts. 0
21 CONNECTION EXAMPLES Safety sensors DA00 and DA00 On the opening side + out +V out ohm 8 7 Normal Delayed Safety sensor Locking circuit Fire detector 6 Connect the 000 ohm resistor from connectors and to safety sensor connectors and 6. The resistor connection controls the condition of cable. If cable is cut or short circuit, the door will stop. When sensor detects an obstacle, the operator stops the door. On the closing side + out +V out Normal Delayed Safety sensor Locking circuit Fire detector 6 When sensor detects an obstacle, the operator opens the door for duration of the hold open time. LIGHT ON LIGHT ON (LO) Jumper settings and connection block for DA00 and DA
22 CONNECTION EXAMPLES DA06 and DA06 Microwave motion sensor + out +V out green brown yellow white Normal Delayed Safety sensor Locking circuit Fire detector DA06 Microwave motion sensor + out +V out 0 green brown 9 8 yellow blue 7 Normal Delayed 6 pink white Safety sensor Locking circuit Fire detector
23 CONNECTION EXAMPLES DA0 Elbow switch + out +V out Normal Delayed N.C N.O COM Safety sensor Locking circuit Fire detector DA09 and DA09 rotary switch X red X blue black MANUAL = no connection AUTO =... OPEN =...
24 CONNECTION EXAMPLES Electric locks EL, EL, EL red + out +V out 0 9 green Normal Delayed blue Safety sensor Locking circuit black Fire detector Motor locks EL90, EL90 red + out white 0 +V out 9 green Normal Delayed blue Safety sensor Locking circuit grey Fire detector
25 CONTROLS CONNECTION EXAMPLES Motorlocks EL0, EL0 + out Extension cable ABLOY EA8, EL9 EA8 Length 6m/0m Cable 6 x 0. mm^ +V S/N: -VDC -8VAC BACKUP+ BACKUP - AC /DC AC /DC OPEN NO WHITE BLACK+VIOL. DOOR C CLOSED NC GREEN USED NO 6 YELLOW RED HANDLE C NOT USED NC 7 8 BROWN USED NO 9 BLUE RED/GREEN CYLINDER C NOT USED NC 0 ORANGE NO BOLT IN TURQUOISE C GREY NC BOLT OUT PINK C OPENING 6 DELAY SWITCH TIME s RESERVED 7 s s s 8 6s Example s. 8s s s EA POWER V out Normal Delayed Safety sensor Locking circuit Fire detector EL0 consumes max. 600mA current. Electric lock EL0 red + out +V out 0 9 green Normal Delayed blue Safety sensor Locking circuit black Fire detector
26 CONNECTION EXAMPLES Rebated doors Impulse device ACTIVE DOOR + out +V out Normal Delayed Safety sensor Locking circuit Fire detector PASSIVE DOOR + out +V out Normal Delayed Passive door opens after constant delay,0 seconds. Adjust the hold open time for passive door - seconds shorter than active door. Safety sensor Locking circuit Fire detector 6 Note! Mechanical coordinator ensures that double doors close correctly!
27 CONNECTION EXAMPLES Fire door system red + out white 0 +V out 9 green Normal Delayed EL90 Motor lock blue grey Safet sensor Locking circuit Fire detector y LED NC C NO LED NC C NO OPERATION: When detector reacts, it s relay switches on. Then the (-) is disconnected from the operator s control unit (connector ). The operator doesn t open the door from but it have to be opened manually. The operator closes the door after manual opening. In fire door use the operator have to be connected to external battery backup (VDC, min. A). In case of fire -> the door closes After fire alarm, one manual opening is required to re-energise the operator to chosen program selector mode. 7
28 SELF DIAGNOSTICS The means of diagnostic features is to - detect malfunctions - try to take care of safety during malfunction - get the operator to recover from the defected state. In case the result of the diagnostics shows unrecoverable malfunctions, the door operator is considered as unsafe, and the door is set free for manual use. The user is informed by blinking both of the LED s in control unit. Control units LED s TEACH CLOSED TEACH OPEN POWER ON TEACH Yellow led = Y Green led = G Indication Possible Fault Corrective user interventions in defined order G not lit Y not lit No power. Faulty power supply unit. Faulty control board. ) Check the mains. ) Remove pin connector from the control board. ) Measure the voltage from pin connector, connection points and. If voltage is under VDC, change the power supply unit. ) Measure the voltage from pin connector, +V out against. If voltage is not VDC, change the control board. G lit Y lit The door close and open positions are not successfully teached. Impulse device is active all the time. Fire detector is active. ) Teach the door open and close positions. ) Check all devices and connections. ) Check fire detector connection and fire N.C. jumper. G lit Y flash Flash short...short...short...: 000 ohm resistor is missing or cable of safety sensor is cut. ) Check that 000 ohm resistor is connected in control board or in safety sensor. ) Check that cables are not damaged. Flash short...long...short...long...: Safety sensor is active or cable of safety sensor is short-circuited. ) Move obstacle from safety sensor detection area. ) Check that cables are not damaged. G flash Y flash Internal fault in the control board. Door motion is stopped. ) Switch main switch off for 0 seconds. ) Check that all applicable jumpers are in place (one of the two arms is selected, single is selected). ) Teach the door open and close positions. ) Change a spare control board. 8 G flash Y flash alternates Internal fault in the position sensor board. Door motion is stopped. ) Switch main switch off for 0 seconds. ) Check that all applicable jumpers are in place (one of the two arms is selected, single is selected) Check position sensor s cable and connector. ) Teach the door positions. ) Change a spare position sensor.
29 MAINTENANCE Requirements for trouble-free use of the operator Installation, commissioning and maintenance is made by trained and qualified technician. Door leaf is moving sensitively and locking works well. Regular annual services are made: - Under 00 openings per day; service once a year openings per day; service two times a year - Over 00 openings per day; service... times a year Inspections made in the service: - Greasing of the bevel gears - Fixing of the operator and arm - Function and adjustments of and safety devices - Programming and adjustments of the operator 9
30 DA60 SPARE PARTS Head panel 807 Compatible unit 8098 Position sensor Control unit Mode switch Rear damper Side damper 800 Transformer 8007 Main switch 8077 DA7 DA8 DA9 Cover aluminium 08 Cover white 07 0
32 Some of the materials in this product, such as electronic components, require specialist recycling techniques. Nimike Päiväys 968 /006 PRODUCT MANAGEMENT DOOR AUTOMATICS/..006/FH Abloy Oy Wahlforssinkatu 0 P.O. Box 08 FIN-8080 JOENSUU FINLAND Tel Fax ISO 900 ISO 00 CERTIFIED ORGANISATION An ASSA ABLOY Group company ABLOY Oy is one of the leading manufacturers of locks, locking systems and architectural hardware and the world s leading developer of products in the field of electromechanical locking technology. The ASSA ABLOY Group is the world s leading manufacturer and supplier of locking solutions, dedicated to satisfying end-user needs for security, safety and convenience.
An ASSA ABLOY Group brand ABLOY DA6 SWING DOOR OPERATOR Installation and commissioning manual APPROVALS / STANDARDS Electrical safety tested and approved FI, S, N, D (according to CB-scheme) Low Voltage
ABLOY DOOR AUTOMATICS Easy access for all types of swing doors Automatic door operators bring additional convenience in situations where the doors opening manually would be inconvenient or laborious. Recommended
ABLOY EL490 AND EL590 SCANDINAVIAN RANGE MOTOR LOCKS Flexible multifunctional locking ABLOY EL490 and EL590 motor locks have been developed to further increase both the security and safety of the entire
K3 K4 www.sebury.com.cn Digital Keypad Use s Manual Contents Introduction Introduction Specifications Intramural Interface Circuit 3 Mounting 3 Wiring 5 Power UP 7 Engineer Programming Mode 7 The K3/K4
TS EMR T/PT/TDE Surface applied door closer Installation instructions: Pull side track mount door closer with smoke detector (EMR T) Push side track mount door closer with smoke detector (EMR PT) Double
Securitron Magnalock Corp. www.securitron.com ASSA ABLOY, the global leader Tel 800.624.5625 firstname.lastname@example.org in door opening solutions INSTALLATION AND OPERATING INSTRUCTIONS For Model GL1 Gate
ABLOY EL426, EL526 Europrofile multipoint motor locks New ABLOY multipoint locks are the latest extension to the wide ABLOY Europrofile electromechanical lock case range. An ASSA ABLOY Group brand FUNCTION
INSTALLATION GUIDE Card Reader & Controller with KIM Swipe Reader for Solitaire 850 / 950 / 850L Learnlok PK2930 Card Reader and Controller Model 3.5 with KIM Swipe Reader Table of Contents 1. Features..................................
ABLOY EL4, EL5 Europrofile motor locks ABLOY Europrofile locks can be installed with long plates or roses. An ASSA ABLOY Group brand Convenience, High security, High durability - Europrofile motor locks
Features: INSTALLATION Install in accordance with NFPA 70. DORMA MODEL PS-406BB POWER SUPPLY INSTALLATION INSTRUCTIONS Up to 1.95 Amps Load Capacity Class 2 Rated Outputs Overload, Over Voltage, and Short
1 VOT6506E CENTRAL BATTERY UNIT FOR EMERGENCY LIGHTING Installation and maintenance instructions TKT65XXB KEEP IN A SAFE PLACE FOR LATER USE 2 TKT65XXB product description REV.4; 20.07.2009 JAK Table of
ABLOY EL466, EL566 Europrofile handle controlled multipoint locks New ABLOY multipoint locks are the latest extension to the wide ABLOY Europrofile electromechanical lock case range. An ASSA ABLOY Group
Page 1 of 5 WD-AMX Water Detection Controllers Features: Benefit: LED Status of leak status VFC output Audible alarm Auto or manual reset alarm output Uses an isolated AC signal which prevents oxidation
HM-W536 Install Guide 9/13/2013 IMPORTANT SAFETY INSTRUCTIONS Warning - When using electrical devices, basic safety precautions should be followed to reduce the risk of fire, electrical shock or injury.
Multi-application heat tracing Control and Monitoring in commercial and residential buildings Roof & Gutter de-icing sensor module Technical Information Approvals Module IP rating Ambient operating temperature
Manual for Fire Suppression & Methane Detection System Fogmaker North America Post address: 150 Gordon Dr Exton, PA 19341 Delivery address: 150 Gordon Dr Exton, PA 19341 Tel: 610-265-3610 Fax: 610-265-8327
ABLOY DC 240 DOOR CLOSER Heavy duty door closer ABLOY DC240 heavy duty door closer offers a wide variety of functional options. ABLOY DC240 DOOR CLOSER The ABLOY DC240 have been developed to meet the exacting
Technical Overview Add-on Sensors - Smoke Alarm Get yours direct at: 01491 410913 www.theclimate.co.uk OVERVIEW This kit contains a standard smoke alarm and relay pattress. The Kidde Smoke Alarm supplied
EC8666 Statement Automatic Door Operator is a reliable and quiet door opening and closing device. This product is ideal for enabling access to areas for people with disabilities or simply for convenience
TMS TANK MANAGEMENT SYSTEM Page 1 of 9 Operating Instructions GENERAL The Tank Management System is a bespoke design to control, monitor and accommodate efficient storage and dispensing of TMS. FUNCTIONS
EC DECLARATION OF CONFORMITY FOR MACHINES (DIRECTIVE 98/37/EC) Manufacturer: Address: Declares that: FAAC S.p.A. Via Benini, 1-40069 Zola Predosa BOLOGNA - ITALY 770 mod. operator is built to be integrated
Installation and user manual for the FX range of fire panels 1, 2, 4 and 8 zone panels Contents Panel installation 3 Panel connections 3 Wiring connection drawings 4 Panel facilities 6 Installation check
Product and functional description The KNX / DALI gateway N 141/02 is a 4 MU wide, DINrail mounted KNX device with one DALI interface to which up to 64 DALI actuators (e.g. DALI ballasts) can be connected
ADI 9510-B Advantium 2 Plus Alarm INSTALLATION AND OPERATING INSTRUCTIONS Carefully Read These Instructions Before Operating Carefully Read These Controls Corporation of America 1501 Harpers Road Virginia
PSDC 08128 v.1.2 PSDC 12V/8A/8x1A Power supply for up to 8 analog cameras PTC/TOPIC. EN** Edition: 9 from 25.05.2015 Supersedes the edition: 8 from 12.12.2014 the 8x 1A/12V DC power output for powering
CMR Electrical Ltd Bolton House Five Chimneys Lane Hadlow Down East Sussex TN22 4DX Tel: 01825 733600 LD2 One & Two Zone Water Detection Alarm Installation and Operation Manual Contents 1) Operation 2)
MODEL NUMBER: ISC910-1-0-GB-XX ISC911-5-0-GB-XX IXP20 CONTROLLER SPECIFICATIONS Working Environment Plastic Housing... Power ImproX IXP20 Controller INSTALLATION MANUAL Designed to work in an indoor (dry)
PULL CHAIN SPEED CONTROL REVERSE SWITCH The Casablanca 4-Speed series of fans feature a 4-speed, pull chain fan control and a forward/reverse slide switch. XTR MOTOR PRINTED CIRCUIT BOARD LIGHT KIT PULL
EPSOLAR LS1024B / LS2024B/ LS3024B Solar Charge Controller USER MANUAL Thank you very much for selecting our product! This manual offers important information and suggestions with respect to installation,
SECTION 13850 DETECTION AND ALARM PART 1 GENERAL 1.01 SUMMARY A. Section Includes 1. Control Panel 2 Associated Equipment B. Products Installed But Not Supplied Under This Section 1. Section 16140 - Wiring
Passive Infrared Motion Detector Installation Instructions 5420/90 The 5420/90 Passive Infrared Motion Detector provides reliable, high performance detection at an affordable price. The Detector features
GB VariEco868 roller shutter/awning drive Keep these instructions in a safe place! After installation of the tubular drive attach these instructions to the cable for the electrician. Device function: Commissioning
ANTI-THEFT SYSTEM 1995 Volvo 850 1995-96 ACCESSORIES & EQUIPMENT Volvo Anti-Theft Systems 850 DESCRIPTION & OPERATION WARNING: Deactivate air bag system before performing any service operation. For 1995
68 Flexible, high specification system Choice of 1, 2, 4 or 8 zones Simple one-shot auto-reset user test facility Approved to EN54 Maintenance free poly switch circuit protection, with auto reset Class
Power Window/Power Lock Installation To begin with you will need all the parts listed below: From Donor Fiero: Fiero power window regulators Power window motors (Generic GM type part) -motors are riveted
Website: www.andico.com.au Service manual CAUTION - BEFORE SERVICING THE UNIT, READ THE SAFETY - PRECAUTIONS IN THIS MANUAL. - ONLY FOR AUTHORISED SERVICE PERSONNEL. MODELS: MPK1-09CR-QB8 MPK1-12ER-QB6
INSTALLATION INSTRUCTION SECURITY SYSTEM ADP-CAN Introduction Motorcar security system ADP-CAN is for motorcars provided with CAN net. It is for the work with the motorcar factory security systems or remote
INSTALLATION INSTRUCTIONS FOR MINI MAKE-UP AIR MODEL FER May 2012 VERSION 1.3 Please read instructions carefully before installation. This unit is a complete fresh air make-up package with an integrated
782 Electric Latch Retraction Controller Installation Instructions The 782 is designed to be used with UL Listed Yale 7000P series (electric latch retraction) or Corbin Russwin ED4000/ED5000 x M94 series
TESTING, SERVICE & REPAIR GUIDE (For SH Space Heating Models & RA Water Heating Models) WARNING - HIGH VOLTAGE AC electrical circuits are connected to this heater. Do not attempt any service work on the
Operator's manual Straight line wiper Ocean The Seematz wiper housing consists of sea water resistant aluminium Almg 3. All other metal parts are made of stainless steel or brass. All colored parts are
4 3. SEISCO PARTS & SERVICE REMOVAL AND REPAIR GUIDE A. Changing the Control Board B. Replacing a Heating Element C. Thermistor Replacement D. High Limit Switch Replacement E. Level Detector Replacement
Wespot SecNurse A NEW GENERATION TECHNICAL AIDS USER S GUIDE EN This manual is published by OPTEX, without any warranty. Improvements and changes to this manual necessitated by typographical errors, inaccuracies
DC-8706K Auto Dial Alarm System User Guide Basic Contents: 1x the host unit; 1x wireless door (window) magnet; 1x wireless infrared detector; 2x remote control; 1x siren; 1x phone core; 1x AC to DC power
0--00-0 (-0 ) R Low Energy Door Operators Wiring Instructions For 0, 0, 00, 0 REQUIREMENTS: 0 VOLT POTENTIAL PRESENT. MAKE SURE POWER INPUT TO UNIT IS TURNED OFF DURING INSTALLATION AND WIRING PROCEDURE.
EL460, EL461, EL560, EL561 Europrofile handle controlled locks Europrofile locks offer intelligent solution for medium traffic doors. Locks can be installed with long plates or roses. An ASSA Group brand
Security Alarm Central Unit 3 4 Technical KNX Alarm central unit EAM 4000 ETS-product family: Alarm system Product type: Alarm central unit The alarm central unit is a modern alarm system using the KNX
Know-how makes the difference Electrical Actuators With Dansk Ventil Center as your business partner, you are always guaranteed a wide and well sorted product range and a unique technical know-how Product
Mechanism Diagram 15-1-1 GENERAL During assembly/installation, use the torque values and service products as in this section. WARNING! Torque wrench tightening specifications must be strictly adhered to.
Service Manual For the ADMIRAL 26, ADMIRAL 2832 PLUS, & ADMIRAL 35 Automatic Scrubbers For: Training Troubleshooting Adjustments Rev. OCT 2012 Contents 1 Cautions ----------------------------------------------------------------------
ATS-220 AUTOMATIC TRANSFER SWITCH CONTROL UNIT OPERATOR S MANUAL For Use in 208 to 240 Volts Single and 3 Phase ATS Systems With 110Volt AC or DC Control Motors and selenoids 4501 NW 27 ave Miami FL 33142
Operating instructions Diffuse reflection sensor OJ50xx 7096 / 0 07 / 004 Contents Preliminary note. Symbols used Function and features Installation. Installation of the supplied mounting fixture 4 4 Electrical
Model 201 Wiegand Touchpad Reader Installation Guide P/N 460353001C 15AUG11 2011 UTC Fire & Security. All rights reserved. This document may not be copied in whole or in part or otherwise reproduced without
EMF/EMR Holder/Release Devices with Integral Door Closers EMR TECHNICAL DETAILS DORMA EMR SERIESHOLDER/RELEASE DEVICE The DORMA EMR Series holder/ release device incorporates a photoelectric detector and
4/6.1/EN/3 Smoke Detector Type RM-O-VS pproved by the German Institut für Bautechnik Contents Technical Data Contents Technical Data 2 Description pplication 3 Installation Instructions 4 Circuit Diagram
TrueAlarm Systems UL, ULC, CSFM Listed; FM Approved* Network Annunciators; es Features Provides a dedicated local area network (LAN) for connection of a TrueSite workstation server to remote clients: es
EIGHT CHANNEL MIXER/EQUALISER SDV1092-8 Music Mixer / Equaliser Installation guide and user manual 1 CONTENTS CONTENTS...2 SAFETY NOTES...3 INTRODUCTION...4 USER CONTROLS...7 VOLUME CONTROL...7 MUSIC SOURCE
Instructions - Parts List Leak Detection System 311200A For detecting leaks in your diaphragm pump system. Not for use in explosive atmospheres. Part No. 234576 120 psi (0.8 MPa, 8 bar) Maximum Air Input
Pilot Operated Port Solenoid Valve for Dry Air Series VQ0/30 Compact and lightweight with large flow capacity [Option] VQ0 Weight (g) 46 80 C [dm 3 /(s bar)].5 (C8) 3.0 (C) Series Series VQ0 VCH VDW VQ
5731 Benjamin Center Drive Tampa, Florida 33634 Phone:813.349.1900 Fax:813.349.1907 Version: A Release Date: 2013-07-24 READ THIS MANUAL CAREFULLY AND KEEP IT ACCESSIBLE FOR FURTHER REFERENCE! USE AS DIRECTED: