Ground Fault Current Distribution on Overhead Transmission Lines


 Felix Palmer
 2 years ago
 Views:
Transcription
1 FACTA UNIVERSITATIS (NIŠ) SER.: ELEC. ENERG. vol. 19, April 2006, Ground Fault Currnt Distribution on Ovrhad Transmission Lins Maria Vintan and Adrian Buta Abstract: Whn a ground fault occurs on an ovrhad transmission lin in a powr ntwork with groundd nutral, th fault currnt rturns to th groundd nutral through th towr structurs, ground rturn paths and ground wirs. This papr prsnts an analytical mthod in ordr to valuat th ground fault currnt distribution in an ffctivly groundd powr ntwork. Th ffct of soil rsistivity, ground rsistanc of towrs and powr lin configuration, on th magnitud of rturn currnts, has bn xamind. Kywords: Ovrhad transmission lin, fault currnt distribution, powr ntwork. 1 Introduction Highvoltag systms hav an ffctivly groundd nutral. Whn a ground fault occurs on an ovrhad transmission lin, in a powr ntwork with groundd nutral, th fault currnt rturns to th groundd nutral through th towr structurs, ground rturn paths and ground wirs [1],[2]. In this papr, basd on Kirchhoff s thorms, an analytical mthod in ordr to dtrmin th ground fault currnt distribution in ffctivly groundd powr ntwork is prsntd. It is possibl to find th valus of th currnts in towrs, ground wir and th currnts that rturn to th stations [3],[4],[5],[6]. Th approach usd in this papr, basd on mthod prsntd by Rudnbrg [7] and Vrma [8], can b applid to short lins, rspctivly in cas whr ar only fw spans btwn th fding station and th faultd towr. Manuscript rcivd April 14, M. Vintan is with Univrsity Lucian Blaga of Sibiu, Dpartmnt of Elctrical Enginring, E. Cioran Str. No. 4, Sibiu, , Romania (mail: A. Buta is with Univrsity Polithnica of Timisoara, Dpartmnt of Elctrical Powr Systm, Bdul V. Parvan, no. 2, Timisoara, Romania (mail: 71
2 72 M. Vintan and A. Buta: A phastoground fault that appars on a phas of a transmission lin, divids th lin into two sctions, ach xtnding from th fault towards on nd of th lin. Dpnding on th numbr of towrs btwn th faultd towr and th stations, rspctivly of th distanc btwn th towrs, ths two sctions of th lin may b considrd infinit, in which cas th ground fault currnt distribution is indpndnt from th trmination of th ntwork, othrwis, thy must b rgardd as finit, in which cas th ground fault currnt distribution may dpnd gratly on th trmination of th ntwork [5],[6]. In this papr w will b considr th cas whn th fault appars to th last towr of th transmission lin. Thn, it will b considrd th fault that appars at any towr of th transmission lin, th two sctions of th lin ar finit and it is assumd that th fault is fd from both dirctions [9],[10]. Th calculation mthod is basd on th following assumptions: impdancs ar considrd as lumpd paramtrs in ach span of th transmission lin, lin capacitancs ar nglctd; th contact rsistanc btwn th towr and th ground wir, and th towr rsistanc btwn th ground wir and th faultd phas ar nglctd; th ntwork is considrd linar in th sinusoidal stadystat and only th powr frquncy is considrd. 2 Ground Fault Currnt Distribution W prsntd two cass: th first cas is th fault at th trminal towr of th lin and th scond cas th fault at any towr of th lin. Cas 1. Figur 1 prsnts th connction of a ground wir connctd to arth through transmission towrs, ach transmission towr having its own grounding lctrod or grid,. It is assumd that all th transmission towrs hav th sam ground impdanc and th distanc btwn towrs is long nough to avoid th influnc btwn thr grounding lctrods. Th slfimpdanc of th ground wir connctd btwn two groundd towrs, calld th slfimpdanc pr span, is. Considring th sam distanc I d btwn two conscutiv towrs and that is th sam for vry span, thn Z cp = I d, whr th slfimpdanc of th ground wir is rprsntd in Ω/km. Z cpm rprsnts th mutualimpdanc btwn th ground wir and th faultd phas conductor, pr span. Whn a fault appars, a part of th ground fault currnt will gt to th ground through th faultd towr, and th rst of th fault currnt will gt divrtd to th ground wir and othr towrs. Th currnt I n flowing to ground through th nth towr, countd from th trminal towr whr th fault is assumd to tak plac, is
3 Ground Fault Currnt Distribution on Ovrhad Transmission Lins 73 qual with th diffrnc btwn th currnts i n and i n+1 [7],[8] I n = i n i n+1 (1) Fig. 1. Fault currnt distribution, cas 1. Th nxt rlation givs th loop quation for th nth msh I n I n 1 + i n νi d = 0 (2) In quation (2) ν = Z cpm / rprsnts th coupling factor btwn th ovrhad phas and ground wir and I d rprsnts th fault currnt. Th quation (2) could b writtn in th following form and similarly i n = (I n 1 I n ) + νi d (3) i n+1 = (I n I n+1 ) + νi d (4) Substituting quations (3) and (4) in quation (1), for th currnt in th faultd towr th following quation will b obtaind, which is a scond ordr diffrnc quation According to [7], th solution of this quation is I n = I n+1 2I n + I n 1 (5) I n = A αn + B αn (6) In accordanc with th solution (6) that contains th arbitrary paramtrs A and B, th currnt flowing to ground through th succssiv towrs, has an xponntial variation. Th arbitrary paramtrs A and B will b obtaind latr, from th boundary conditions.
4 74 M. Vintan and A. Buta: Paramtr α in th solution (6) could b obtaind by substituting th solution (6) in quation (5). For this purpos, n is substituting with (n + 1), rspctivly with (n 1) in quation (6) Th quation (5) bcam I n+1 = A α(n+1) + B α(n+1) (7) I n 1 = A α(n 1) + B α(n 1) (8) Bcaus, it can b writtn = α + α 2 = 2(sinh a 2 )2 (9) α = Zcpd (10) By applying quation (1) to th (n 1) towr, th following xprssion will b obtaind I n 1 = i n 1 i n (11) By substituting th quations (1) and (11) in (2), th following quation with a constant trm will b obtaind i n = i n+1 2i n + i n 1 + νi d (12) Similar with quation (5), th currnt in th ground conductor is givn by th nxt solution i n = a αn + b αn + νi d (13) a, b rprsnts th arbitrary paramtrs. Bcaus of th link btwn currnts i n and I n, th arbitrary paramtrs A, B and a, b ar not indpndnt. By substituting th solutions (6) and (13) in quation (1), it will b obtaind A αn + B αn = a αn (1 α )+b αn (1 α ) (14) Bcaus ths rlations ar th sam for vry valu of n, th following xprssions will b obtaind A = a(1 α ) (15) B = b(1 α ) (16)
5 Ground Fault Currnt Distribution on Ovrhad Transmission Lins 75 Th currnt in th ground wir will b thn givn by th following xprssion ( ) ( ) αn αn i n = A 1 α + B 1 α + νi d (17) Th boundary condition (condition for n = 0) at th trminal towr of Figur 1, which mans that th fault currnt is givn by th sum btwn th currnt in th faultd towr and th currnt in th first span of th ground wir, is I d = I 0 + i 1 (18) Long Lin. If th lin is sufficintly long so that, aftr som distanc, th varying portion of th currnt xponntially dcays to zro, A 0, and according to (6) and (17) I n = B αn (19) ( ) αn i n = B 1 α +νi d (20) Substituting ths xprssions in (18), with n = 0 for I n and n = 1 for i n, it will b obtaind ( ) ( ) α B I d = B+B 1 α + νi d = 1 α + νi d (21) For B th following xprssion will b obtaind B = (1 ν)(1 α )I d = (1 ν)(2tanh α 2 ) (1+tanh α 2 ))I d (22) Th currnt in th faultd towr will gt th xprssion I 0 = B = (1 ν)(2tanh α 2 ) (1+tanh α 2 ))I d (23) Th currnt in th first span, countd from th faultd towr, will b Th voltag ris at th trminal towr is i 1 = I d I 0 = I d [ α + ν(1 α )] (24) U 0 = I 0 = (1 ν)(1 α )I d = (1 ν)(2tanh α 2 ) (1+tanh α 2 ) I d (25) =(1 ν)zi d
6 76 M. Vintan and A. Buta: whr Z rprsnts th quivalnt impdanc of th ntwork looking back from th fault. Usually, th trminal towr is connctd, through an xtra span Z cp d, to th stationgrounding grid (Figur 2). Consquntly, a rsistanc rprsnting th grounding systm of th station rsistanc must clos th laddr ntwork rprsnting such a lin. In this cas, a part of th total ground fault currnt will flow through th station ground rsistanc R p. In ordr to us th prvious rsults, it is nough to rplac th currnt I d with I d = I d I p, and thus th valu of th currnt in th faultd towr will b [8] I 0 = (1 ν)(1 α )I d (26) Noting th sum btwn Z cp d and R p with Z p = R p + Z cp d, th currnt I p through th station grounding grid rsistanc is givn by th following xprssion I p = I dz Z p + Z (27) I d Fig. 2. Fault currnt distributions. In cas th valus of Z p and Z ar known, I p can b found out from (27) abov. is givn by th nxt xprssion I d = I d I p = I 0 + i 1 (28) Now, it will b found th nth towr, as countd from th trminal towr, whr th currnt gts rducd to 1% thn that travrsing th trminal towr. From quation (19) B αn = 1 100B n = 1 α ln100 4,6 (29) For / = 0.03, will gt n = 26.5, so it taks at last 26 towrs from th fault to gt a currnt rducd to 1% thn that travrsing th trminal towr. Taking into account this considration, it is possibl to s if on could considr A = 0
7 Ground Fault Currnt Distribution on Ovrhad Transmission Lins 77 in th xprssions of th currnts in ground wir and towrs. Th numbr of th towrs should b at last qual with th numbr givn by xprssion (29). Short lin. If th lin cannot b considrd long nough rgarding to th xprssion (29), thn paramtrs A and B will b found from th boundary conditions. With R p, rspctivly R p, ar notd th rsistancs of th grounding systms of th two stations (Figur 3), which dos not includ th grounding ffcts of th ground wir of th considrd lin. Th stations ar connctd to th trminal towrs, at both sids, through an xtra span Z cp d, and th sum btwn Z cp d and grounding systm of th stations rsistancs was notd with Z p = R p + Z cp d, rspctivly Z p = R p + Z cp d. Th boundary condition at th rciving nd of th lin is I d = I p + I 0 + i 1 = i 1 + I 0 + I 0 Z p (30) At th snding nd of th lin w hav I d = I p + i N+1 (31) I N + I p R p i N+1 Z cp d + νi d Z cp d = 0 (32) Substituting I p from (32) to (31), w will ( ) I d 1+ν Z cp d = i N+1 (1+Z cp R d R p )+ I N (33) p R p Fig. 3. Fault currnt distributions. Substituting I 0, I N, i N+1 and i 1 into (30) and (33), according to (6) and (17), a systm with two linar quations will b obtaind ] [ ] I d (1 ν) = A[ Z α st 1 + B Z 1 + Z p α st Z p [ I d (1 ν) = A αn α 1 (1+ Z α cp d R p ] [ ) R p + B αn α 1 (1+ Z α cp d R p ] ) R p (34)
8 78 M. Vintan and A. Buta: (34) givs whr: A 1, B 1, A 2, B 2 ar B 2 B 1 A 1 A 2 A = I d (1 ν),b = I d (1 ν) (35) A 1 B 2 B 1 A 2 A 1 B 2 B 1 A 2 A 1 = 1 1 α + 1,B Z 1 = p 1 α + Z p [ ( ) A 2 = αn α 1 α 1+ Z cp d Z [ ( ) st ],B 2 = αn α R p R p 1 α 1+ Z cp d Z ] st R p R p Th currnt in th faultd towr (obtaind for n = 0 in all xprssions, including A 2, B 2 ) will b [ B 2 B 1 I 0 = A+B = I d (1 ν) (1 α )+ A ] 1 A 2 (1 α ) (36) A 1 B 2 B 1 A 2 A 1 B 2 B 1 A 2 Th voltag ris of th trminal towr in this cas is U 0 = I 0 [ B 2 B 1 = I d (1 ν) (1 α )+ A ] 1 A 2 (1 α ) A 1 B 2 B 1 A 2 A 1 B 2 B 1 A 2 (37) = (1 ν)i d Z N With Z N was notd th quivalnt impdanc of th ntwork looking back from th fault in this cas [ B 2 B 1 Z N = (1 α )+ A ] 1 A 2 (1 α ) (38) A 1 B 2 B 1 A 2 A 1 B 2 B 1 A 2 Cas 2. In Figur 4 th fault occurs at th towr numbr 0. Thr ar N towrs btwn this towr and th lft station and rspctivly M towrs btwn towr numbr 0 and th right station. Th rsistancs of th grounding systms of th lft and right stations (Figur 4) ar R p, rspctivly R p. Th impdanc of th sction of ground wir btwn on station and th first towr (towr N or M) is Z cp d, and Z p = R p + Z cp d, rspctivly Z p = R p + Z cp d. Th total fault currnt I d is givn by th sum btwn th currnt I d from on sid, and I d from th othr sid of th transmission lin. In this cas, considring first th lft part from th faultd towr, th situation is idntically with that prsntd in Figur 1. So th sam quations could b writtn
9 Ground Fault Currnt Distribution on Ovrhad Transmission Lins 79 Fig. 4. Ground fault currnt distributions. (117), and th solutions for th currnt in th towrs, rspctivly in th ground wir ar I n s = A s αn + B s αn (39) αn αn i n s = A s 1 α + B s 1 α + νi d (40) Th subscript s is usd for th lft part from th faultd towr. I n s rprsnts th currnt in th towr numbr n, countd from th faultd towr to th lft part of th transmission lin. In ordr to find th constants A s, B s, it is ncssary to writ th boundary conditions. For th faultd towr, th following formulas can b writtn { I0 I 1 i 1 + ν I d = 0 I 1 I 2 i 2 + ν I d = 0 (41) Also th xprssion can b writtn I 1 = i 1 i 2 (42) Substituting i 1 and i 2 from quations (41) in quation (42), it will b obtaind ( I 1 2+ Z ) cp d = I 0 + I 2 (43) For th lft trminal it can b writtn I N + i N+1 = i N (44) I N + I p R p i N+1 Z cp d + I dz m = 0 (45) (I N 1 I N ) i N + ν I d = 0 (46)
10 80 M. Vintan and A. Buta: i N+1 = I d I p (47) whr Z m rprsnts th mutual coupling btwn th ground wir and th faultd phas, in th last span. Rplacing i N+1 and i N from (45), (46) in (44), by taking into account (47), th following xprssion will b obtaind I N ( 1+ + Z cp d + R p ) ( = I N 1 + I d ν R p + Z ) m Z cp d + R p Exprssions (43) and (48) rprsnts th boundary conditions. By rplacing I 1, I 2, I N and I N 1 from th solutions (39) and (40) in (43) and (48), it will b obtaind two systm quations from which rsults A s and B s )( (2+ α Z cp d α ν R p+z m )I R p +Z d I 0 αn L s cp A s = ) d ) (49) (2+ α(n 1) Z cp d α R s (2+ α(n 1) Z cp d α L s whr B s = (48) )( I 0 αn R s (2+ α Z cp d α ν R p+z m )I R p +Z d cp ) d ) (50) (2+ α(n 1) Z cp d α R s (2+ α(n 1) Z cp d α L s L s = 1+(1 α ) +,R R p + Z s = 1+(1 α) + cp d R p + Z cp d Similar xprssions ar obtaind for th currnts from th right part of th faultd towr { In d = A d αn + B d αn i n d = A d 1 αn + B α d 1 αn + νi (51) α d Th constants A d and B d ar givn by th following xprssions A d = B d = )( (2+ α Z cp d α ν R p+z m )I R p+z d I 0 αm L d cp ) d ) (52) (2+ α(m 1) Z cp d α R d (2+ α(m 1) Z cp d α L d )( I 0 αm R d (2+ α Z cp d α ν R p+z m )I R p+z d cp ) d ) (53) (2+ α(m 1) Z cp d α R d (2+ α(m 1) Z cp d α L d
11 Ground Fault Currnt Distribution on Ovrhad Transmission Lins 81 whr L d = 1+(1 α ) +,R R p + Z d = 1+(1 α ) + cp d R p + Z cp d At th faultd towr th total ground fault is (Figur 4) Th currnt in th faultd towr I 0 bcam I 0 = I d = I 0 i 1s i 1d (54) (1 ν)i d +( Ws T s I d + W d T d I d )( ) V1 1 V α 2 1 α ( ) ( ) (55) 1 α Ls αn 1 α T s + L d αm T d + α Rs αn 1 α T s + R d αm T d whr W s = ν R p + Z m,w R p + Z d = ν R p + Z m cp d R p + Z cp d V 1 = 2+ Z cp d ( T s = α(n 1) 2+ Z cp d α ( T d = α(m 1) 2+ Z cp d α 3 Numrical Rsults α,v 2 = 2+ Z cp d α ( )R s α(n 1) 2+ Z cp d )R d α(m 1) ( 2+ Z cp d ) α L s, ) α L d In ordr to illustrat th thortical approach outlind in sction abov, w ar considring that th lin that conncts two stations is a 110 kv transmission lin with aluminiumstl 185/32 mm 2 and on aluminiumstl ground wir 95/55 mm 2 (Figur 5). Lin impdancs pr on span ar dtrmind on th bass of th following assumptions: avrag lngth of th span is 250 m; th rsistanc pr unit lngth of ground wir is 0.3 Ω/km and its diamtr is 16 mm. Ground wir impdanc pr on span and th mutual impdanc Z m btwn th ground wir and th faultd phas ar calculatd for diffrnt valus of th soil rsistivity ρ with formulas basd on Carson s thory of th ground rturn path, givn in th Appndix 1. Impdanc Z m is calculatd only in rlation to th faultd phas conductor, bcaus it could not b assumd that a lin sction of a fw spans ar transposd. Th fault was assumd to occur on th phas which is th furthst from
12 82 M. Vintan and A. Buta: Fig. 5. Disposition of lin conductors. th ground wir, bcaus th lowst coupling btwn th phas and ground wir will produc th highst towr voltag. Figur 6 shows th valus for th impdanc of finit lin in cas of a fault at th last towr of th lin, as a function of th soil rsistivity and for diffrnt valus of towrs impdancs. Th valus ar calculatd with th proposd xprssion (38). Finit lin impdanc [Ω] =50Ω =10Ω =4Ω Ground wir currnt [ka] ρ=500ωm ρ=100ωm ρ=10ωm Soil rsistivity [Ωm] Fig. 6. Impdanc of finit lin for diffrnt valus of soil rsistivity Span numbr Fig. 7. Ground wir currnt for diffrnt valus of ground wir and mutual impdanc in cas of th fault at th last towr. = 10Ω. Figur 7 shows th currnts flowing in th ground wir in cas of a fault at th last towr of th lin. It was assumd that th lin has 15 towrs. Th valus of ground wir and mutual impdanc btwn th faultd phas and th ground wir givn in Tabl 1, wr calculatd for diffrnt valus of th soil rsistivity. For thos valus and for that numbr of towrs, according to th xprssion (29), th lin should b considrd a short lin. In Tabl 1 w prsntd th valus of th ground wir impdanc and th mutual impdanc Z m, pr on span, btwn th ground wir and th faultd phas, calculatd with Carson s formulas, for diffrnt valus of th soil rsistivity.
13 Ground Fault Currnt Distribution on Ovrhad Transmission Lins 83 Tabl 1. Ground wir impdanc and mutual impdanc, pr on span for diffrnt valus of th soil rsistivity. ρ[ωm] R cpd [Ω] Z m [Ω] Ground wir currnt [ka] =500Ω =100Ω =10Ω Ground wir currnt [ka] =100Ω =50Ω =10Ω Span numbr Fig. 8. Currnt flowing in th ground wir in cas of diffrnt valus of soil rsistivity; N = M = 15 towrs btwn faultd towr and th both nds of th lin; = 10Ω Span numbr Fig. 9. Currnt flowing in th ground wir in cas of diffrnt valus for towrs impdancs; N = M = 15 towrs btwn faultd towr and th both nds of th lin. Using th sam valus of th ground wir and mutual impdanc calculatd for diffrnt valus of soil rsistivity givn in th Tabl 1, th currnts flowing in th ground wir in cas of th fault at any towr of th lin ar shown in Figur 8. Figur 9 shows th currnts flowing in th ground wir for diffrnt valus of th towrs impdancs. Th total fault currnt from both stations was assumd to b I d = 15000A and I d = I d = 7500A. Thos valus ar valid for a soil rsistivity of 100Ωm. It was assumd that th fault appars at th middl towr of th lin, so thr ar N = 15 towrs and rspctivly M = 15 towrs btwn th faultd towr and th trminals. 4 Conclusions This papr dscribs an analytical mthod in ordr to dtrmin th ground fault currnt distribution in powr ntworks, whn th fault appars at th last towr of th lin, rspctivly at any towr of th transmission lin. Th author dvlopd this modl basd on th arlir approach of Rudnbrg [7] and Vrma [8]. Rudnbrg dvlopd a modl that was valid only for long lins, without taking into account th mutual coupling btwn th faultd phas and th ground conductor. Vrma dvlopd that modl by taking into account th mutual coupling,
14 84 M. Vintan and A. Buta: but h trats only th cas of long lin to. Th authors improvd thir modl by considring th cas of a short lin, whn it has to considr th station from th nd of th lin. Rfrncs [1] A. Buta, Transmission and Distribution of Elctricity. Timisoara: Publishing Hous of Tchnical Univrsity of Timisoara, [2] E. Clark, Circuit Analysis of AC Powr Systms. Bucharst: Tchnical Publishing Hous, [3] F. Dawalibi and G. B. Nils, Masurmnts and computations of fault currnt distribution on ovrhad transmission lins, IEEE Transactions on Powr Apparatus and Systms, vol. PAS103, no. 3, pp , Mar [4] J. Endrnyi, Analysis of transmission towr potntials during ground faults, IEEE Transactions on Powr Apparatus and Systms, vol. PAS103, no. 10, pp , Oct [5] H. B. Goci and S. A. Sbo, Distribution of ground fault currnts along transmission lins  an improvd algorithm, IEEE Transactions on Powr Apparatus and Systms, vol. PAS104, no. 3, pp , Mar [6] L. M. Popović, Practical mthod for valuating ground fault currnt distribution in station, towrs and ground wir, IEEE Transactions on Powr Dlivry, vol. 13, no. 1, pp , Jan [7] R. Rudnbrg, Transint Prformanc of Elctric Powr Systms. Bucharst: Tchnical Publishing Hous, [8] R. Vrma and D. Mukhdkar, Ground fault currnt distribution in substation, towrs and ground wir, IEEE Transactions on Powr Apparatus and Systms, vol. PAS98, no. 3, pp , May/Jun [9] M. Vintan, Diffrnt factors influnc on th slf and mutual impdancs of th ovrhad wirs with ground rturn, in Procdings of Th Fourth Intrnational Powr Systms Confrnc, Timisoara, 2001, pp [10] M. Vintan and M. Bogdan, A practical mthod for valuating ground fault currnt distribution on ovrhad transmission lins, Scintific Bulltin of th Polithnica Univrsity of Timisoara, vol. Tom 48(62), pp , Nov
New Basis Functions. Section 8. Complex Fourier Series
Nw Basis Functions Sction 8 Complx Fourir Sris Th complx Fourir sris is prsntd first with priod 2, thn with gnral priod. Th connction with th ralvalud Fourir sris is xplaind and formula ar givn for convrting
More informationStatistical Machine Translation
Statistical Machin Translation Sophi Arnoult, Gidon Mailltt d Buy Wnnigr and Andra Schuch Dcmbr 7, 2010 1 Introduction All th IBM modls, and Statistical Machin Translation (SMT) in gnral, modl th problm
More informationQuestion 3: How do you find the relative extrema of a function?
ustion 3: How do you find th rlativ trma of a function? Th stratgy for tracking th sign of th drivativ is usful for mor than dtrmining whr a function is incrasing or dcrasing. It is also usful for locating
More informationLecture 20: Emitter Follower and Differential Amplifiers
Whits, EE 3 Lctur 0 Pag of 8 Lctur 0: Emittr Followr and Diffrntial Amplifirs Th nxt two amplifir circuits w will discuss ar ry important to lctrical nginring in gnral, and to th NorCal 40A spcifically.
More informationNonHomogeneous Systems, Euler s Method, and Exponential Matrix
NonHomognous Systms, Eulr s Mthod, and Exponntial Matrix W carry on nonhomognous firstordr linar systm of diffrntial quations. W will show how Eulr s mthod gnralizs to systms, giving us a numrical approach
More informationA Note on Approximating. the Normal Distribution Function
Applid Mathmatical Scincs, Vol, 00, no 9, 4549 A Not on Approimating th Normal Distribution Function K M Aludaat and M T Alodat Dpartmnt of Statistics Yarmouk Univrsity, Jordan Aludaatkm@hotmailcom and
More informationThe Matrix Exponential
Th Matrix Exponntial (with xrciss) 92.222  Linar Algbra II  Spring 2006 by D. Klain prliminary vrsion Corrctions and commnts ar wlcom! Th Matrix Exponntial For ach n n complx matrix A, dfin th xponntial
More informationCPS 220 Theory of Computation REGULAR LANGUAGES. Regular expressions
CPS 22 Thory of Computation REGULAR LANGUAGES Rgular xprssions Lik mathmatical xprssion (5+3) * 4. Rgular xprssion ar built using rgular oprations. (By th way, rgular xprssions show up in various languags:
More informationThe example is taken from Sect. 1.2 of Vol. 1 of the CPN book.
Rsourc Allocation Abstract This is a small toy xampl which is wllsuitd as a first introduction to Cnts. Th CN modl is dscribd in grat dtail, xplaining th basic concpts of Cnts. Hnc, it can b rad by popl
More informationby John Donald, Lecturer, School of Accounting, Economics and Finance, Deakin University, Australia
Studnt Nots Cost Volum Profit Analysis by John Donald, Lcturr, School of Accounting, Economics and Financ, Dakin Univrsity, Australia As mntiond in th last st of Studnt Nots, th ability to catgoris costs
More informationIncomplete 2Port Vector Network Analyzer Calibration Methods
Incomplt Port Vctor Ntwork nalyzr Calibration Mthods. Hnz, N. Tmpon, G. Monastrios, H. ilva 4 RF Mtrology Laboratory Instituto Nacional d Tcnología Industrial (INTI) Bunos irs, rgntina ahnz@inti.gov.ar
More informationLecture 3: Diffusion: Fick s first law
Lctur 3: Diffusion: Fick s first law Today s topics What is diffusion? What drivs diffusion to occur? Undrstand why diffusion can surprisingly occur against th concntration gradint? Larn how to dduc th
More information(Analytic Formula for the European Normal Black Scholes Formula)
(Analytic Formula for th Europan Normal Black Schols Formula) by Kazuhiro Iwasawa Dcmbr 2, 2001 In this short summary papr, a brif summary of Black Schols typ formula for Normal modl will b givn. Usually
More informationME 612 Metal Forming and Theory of Plasticity. 6. Strain
Mtal Forming and Thory of Plasticity mail: azsnalp@gyt.du.tr Makin Mühndisliği Bölümü Gbz Yüksk Tknoloji Enstitüsü 6.1. Uniaxial Strain Figur 6.1 Dfinition of th uniaxial strain (a) Tnsil and (b) Comprssiv.
More informationSUBATOMIC PARTICLES AND ANTIPARTICLES AS DIFFERENT STATES OF THE SAME MICROCOSM OBJECT. Eduard N. Klenov* RostovonDon. Russia
SUBATOMIC PARTICLES AND ANTIPARTICLES AS DIFFERENT STATES OF THE SAME MICROCOSM OBJECT Eduard N. Klnov* RostovonDon. Russia Th distribution law for th valus of pairs of th consrvd additiv quantum numbrs
More information[ ] These are the motor parameters that are needed: Motor voltage constant. J total (lbinsec^2)
MEASURING MOOR PARAMEERS Fil: Motor paramtrs hs ar th motor paramtrs that ar ndd: Motor voltag constant (voltssc/rad Motor torqu constant (lbin/amp Motor rsistanc R a (ohms Motor inductanc L a (Hnris
More informationVector Network Analyzer
Cours on Microwav Masurmnts Vctor Ntwork Analyzr Prof. Luca Prrgrini Dpt. of Elctrical, Computr and Biomdical Enginring Univrsity of Pavia mail: luca.prrgrini@unipv.it wb: microwav.unipv.it Microwav Masurmnts
More informationImproving Managerial Accounting and Calculation of Labor Costs in the Context of Using Standard Cost
Economy Transdisciplinarity Cognition www.ugb.ro/tc Vol. 16, Issu 1/2013 5054 Improving Managrial Accounting and Calculation of Labor Costs in th Contxt of Using Standard Cost Lucian OCNEANU, Constantin
More informationSimulation of a Solar Cell considering SingleDiode Equivalent Circuit Model
Simulation of a Solar Cll considring SinglDiod Equivalnt Circuit Modl E.M.G. Rodrigus, R. Mlício,, V.M.F. Mnds and J.P.S. Catalão, Univrsity of Bira Intrior R. Font do Lamiro,  Covilhã (Portugal) Phon:
More informationChapter 3: Capacitors, Inductors, and Complex Impedance
haptr 3: apacitors, Inductors, and omplx Impdanc In this chaptr w introduc th concpt of complx rsistanc, or impdanc, by studying two ractiv circuit lmnts, th capacitor and th inductor. W will study capacitors
More information811ISD Economic Considerations of Heat Transfer on Sheet Metal Duct
Air Handling Systms Enginring & chnical Bulltin 811ISD Economic Considrations of Hat ransfr on Sht Mtal Duct Othr bulltins hav dmonstratd th nd to add insulation to cooling/hating ducts in ordr to achiv
More informationCurrent and Resistance
Chaptr 6 Currnt and Rsistanc 6.1 Elctric Currnt...66.1.1 Currnt Dnsity...66. Ohm s Law...64 6.3 Elctrical Enrgy and Powr...67 6.4 Summary...68 6.5 Solvd Problms...69 6.5.1 Rsistivity of a Cabl...69
More informationPrinciples of Humidity Dalton s law
Principls of Humidity Dalton s law Air is a mixtur of diffrnt gass. Th main gas componnts ar: Gas componnt volum [%] wight [%] Nitrogn N 2 78,03 75,47 Oxygn O 2 20,99 23,20 Argon Ar 0,93 1,28 Carbon dioxid
More informationSection 7.4: Exponential Growth and Decay
1 Sction 7.4: Exponntial Growth and Dcay Practic HW from Stwart Txtbook (not to hand in) p. 532 # 117 odd In th nxt two ction, w xamin how population growth can b modld uing diffrntial quation. W tart
More informationTraffic Flow Analysis (2)
Traffic Flow Analysis () Statistical Proprtis. Flow rat distributions. Hadway distributions. Spd distributions by Dr. GangLn Chang, Profssor Dirctor of Traffic safty and Oprations Lab. Univrsity of Maryland,
More informationEFFECT OF GEOMETRICAL PARAMETERS ON HEAT TRANSFER PERFORMACE OF RECTANGULAR CIRCUMFERENTIAL FINS
25 Vol. 3 () JanuaryMarch, pp.375/tripathi EFFECT OF GEOMETRICAL PARAMETERS ON HEAT TRANSFER PERFORMACE OF RECTANGULAR CIRCUMFERENTIAL FINS *Shilpa Tripathi Dpartmnt of Chmical Enginring, Indor Institut
More informationMEASUREMENT AND ASSESSMENT OF IMPACT SOUND IN THE SAME ROOM. Hans G. Jonasson
MEASUREMENT AND ASSESSMENT OF IMPACT SOUND IN THE SAME ROOM Hans G. Jonasson SP Tchnical Rsarch Institut of Swdn Box 857, SE501 15 Borås, Swdn hans.jonasson@sp.s ABSTRACT Drum sound, that is th walking
More informationEcon 371: Answer Key for Problem Set 1 (Chapter 1213)
con 37: Answr Ky for Problm St (Chaptr 23) Instructor: Kanda Naknoi Sptmbr 4, 2005. (2 points) Is it possibl for a country to hav a currnt account dficit at th sam tim and has a surplus in its balanc
More informationCategory 7: Employee Commuting
7 Catgory 7: Employ Commuting Catgory dscription This catgory includs missions from th transportation of mploys 4 btwn thir homs and thir worksits. Emissions from mploy commuting may aris from: Automobil
More informationAP Calculus AB 2008 Scoring Guidelines
AP Calculus AB 8 Scoring Guidlins Th Collg Board: Conncting Studnts to Collg Succss Th Collg Board is a notforprofit mmbrship association whos mission is to connct studnts to collg succss and opportunity.
More informationCircuits with Transistors
ircuits with Transistors ontnts 1 Transistors 1 2 Amplifirs 2 2.1 h paramtrs.................................... 3 3 Bipolar Junction Transistor (BJT) 3 3.1 BJT as a switch...................................
More informationCALCULATING MARGINAL PROBABILITIES IN PROC PROBIT Guy Pascale, Memorial Health Alliance
CALCULATING MARGINAL PROBABILITIES IN PROC PROBIT Guy Pascal, Mmorial Halth Allianc Introduction Th PROBIT procdur within th SAS systm provids a simpl mthod for stimating discrt choic variabls (i.. dichotomous
More information7 Timetable test 1 The Combing Chart
7 Timtabl tst 1 Th Combing Chart 7.1 Introduction 7.2 Tachr tams two workd xampls 7.3 Th Principl of Compatibility 7.4 Choosing tachr tams workd xampl 7.5 Ruls for drawing a Combing Chart 7.6 Th Combing
More informationSIMULATION OF THE PERFECT COMPETITION AND MONOPOLY MARKET STRUCTURE IN THE COMPANY THEORY
1 SIMULATION OF THE PERFECT COMPETITION AND MONOPOLY MARKET STRUCTURE IN THE COMPANY THEORY ALEXA Vasil ABSTRACT Th prsnt papr has as targt to crat a programm in th Matlab ara, in ordr to solv, didactically
More informationLong run: Law of one price Purchasing Power Parity. Short run: Market for foreign exchange Factors affecting the market for foreign exchange
Lctur 6: Th Forign xchang Markt xchang Rats in th long run CON 34 Mony and Banking Profssor Yamin Ahmad xchang Rats in th Short Run Intrst Parity Big Concpts Long run: Law of on pric Purchasing Powr Parity
More informationIntroduction to Finite Element Modeling
Introduction to Finit Elmnt Modling Enginring analysis of mchanical systms hav bn addrssd by driving diffrntial quations rlating th variabls of through basic physical principls such as quilibrium, consrvation
More informationThe Normal Distribution: A derivation from basic principles
Th Normal Distribution: A drivation from basic principls Introduction Dan Tagu Th North Carolina School of Scinc and Mathmatics Studnts in lmntary calculus, statistics, and finit mathmatics classs oftn
More informationCIRCUITS AND ELECTRONICS. Basic Circuit Analysis Method (KVL and KCL method)
6. CIRCUITS AND ELECTRONICS Basic Circuit Analysis Mthod (KVL and KCL mthod) Cit as: Anant Agarwal and Jffry Lang, cours matrials for 6. Circuits and Elctronics, Spring 7. MIT 6. Fall Lctur Rviw Lumpd
More informationVan der Waals Forces Between Atoms
Van dr Waals Forcs twn tos Michal Fowlr /8/7 Introduction Th prfct gas quation of stat PV = NkT is anifstly incapabl of dscribing actual gass at low tpraturs, sinc thy undrgo a discontinuous chang of volu
More informationFar Field Estimations and Simulation Model Creation from Cable Bundle Scans
Far Fild Estimations and Simulation Modl Cration from Cabl Bundl Scans D. Rinas, S. Nidzwidz, S. Fri Dortmund Univrsity of Tchnology Dortmund, Grmany dnis.rinas@tudortmund.d stphan.fri@tudortmund.d Abstract
More informationThe Fourier Transform
Th Fourir Transfor Larning outcos Us th Discrt Fourir Transfor to prfor frquncy analysis on a discrt (digital) signal Eplain th significanc of th Fast Fourir Transfor algorith; Eplain why windowing is
More informationHardware Modules of the RSA Algorithm
SERBIAN JOURNAL OF ELECTRICAL ENGINEERING Vol. 11, No. 1, Fbruary 2014, 121131 UDC: 004.3`142:621.394.14 DOI: 10.2298/SJEE140114011S Hardwar Moduls of th RSA Algorithm Vlibor Škobić 1, Branko Dokić 1,
More informationThe international Internet site of the geoviticulture MCC system Le site Internet international du système CCM géoviticole
Th intrnational Intrnt sit of th goviticultur MCC systm L sit Intrnt intrnational du systèm CCM géoviticol Flávio BELLO FIALHO 1 and Jorg TONIETTO 1 1 Rsarchr, Embrapa Uva Vinho, Caixa Postal 130, 95700000
More informationForeign Exchange Markets and Exchange Rates
Microconomics Topic 1: Explain why xchang rats indicat th pric of intrnational currncis and how xchang rats ar dtrmind by supply and dmand for currncis in intrnational markts. Rfrnc: Grgory Mankiw s Principls
More informationQUANTITATIVE METHODS CLASSES WEEK SEVEN
QUANTITATIVE METHODS CLASSES WEEK SEVEN Th rgrssion modls studid in prvious classs assum that th rspons variabl is quantitativ. Oftn, howvr, w wish to study social procsss that lad to two diffrnt outcoms.
More informationVersion 1.0. General Certificate of Education (Alevel) January 2012. Mathematics MPC3. (Specification 6360) Pure Core 3. Final.
Vrsion.0 Gnral Crtificat of Education (Alvl) January 0 Mathmatics MPC (Spcification 660) Pur Cor Final Mark Schm Mark schms ar prpard by th Principal Eaminr and considrd, togthr with th rlvant qustions,
More informationInstallation Saving Spaceefficient Panel Enhanced Physical Durability Enhanced Performance Warranty The IRR Comparison
Contnts Tchnology Nwly Dvlopd Cllo Tchnology Cllo Tchnology : Improvd Absorption of Light Doublsidd Cll Structur Cllo Tchnology : Lss Powr Gnration Loss Extrmly Low LID Clls 3 3 4 4 4 Advantag Installation
More informationhttp://www.wwnorton.com/chemistry/tutorials/ch14.htm Repulsive Force
ctivation nrgis http://www.wwnorton.com/chmistry/tutorials/ch14.htm (back to collision thory...) Potntial and Kintic nrgy during a collision + + ngativly chargd lctron cloud Rpulsiv Forc ngativly chargd
More informationDept. of Materials Science and Engineering. Problem Set 8 Solutions
MSE 30/ECE 30 Elctrical Prortis Of Matrials Dt. of Matrials Scinc and Enginring Fall 0/Bill Knowlton Problm St 8 Solutions. Using th rlationshi of n i n i i that is a function of E g, rcrat th lot shown
More informationCHAPTER 4c. ROOTS OF EQUATIONS
CHAPTER c. ROOTS OF EQUATIONS A. J. Clark School o Enginring Dpartmnt o Civil and Environmntal Enginring by Dr. Ibrahim A. Aakka Spring 00 ENCE 03  Computation Mthod in Civil Enginring II Dpartmnt o Civil
More informationMathematics. Mathematics 3. hsn.uk.net. Higher HSN23000
hsn uknt Highr Mathmatics UNIT Mathmatics HSN000 This documnt was producd spcially for th HSNuknt wbsit, and w rquir that any copis or drivativ works attribut th work to Highr Still Nots For mor dtails
More informationAC Circuits ThreePhase Circuits
AC Circuits ThrPhs Circuits Contnts Wht is ThrPhs Circuit? Blnc ThrPhs oltgs Blnc ThrPhs Connction Powr in Blncd Systm Unblncd ThrPhs Systms Aliction Rsidntil Wiring Sinusoidl voltg sourcs A siml
More informationAn Adaptive Clustering MAP Algorithm to Filter Speckle in Multilook SAR Images
An Adaptiv Clustring MAP Algorithm to Filtr Spckl in Multilook SAR Imags FÁTIMA N. S. MEDEIROS 1,3 NELSON D. A. MASCARENHAS LUCIANO DA F. COSTA 1 1 Cybrntic Vision Group IFSC Univrsity of São Paulo Caia
More information5 2 index. e e. Prime numbers. Prime factors and factor trees. Powers. worked example 10. base. power
Prim numbrs W giv spcial nams to numbrs dpnding on how many factors thy hav. A prim numbr has xactly two factors: itslf and 1. A composit numbr has mor than two factors. 1 is a spcial numbr nithr prim
More informationConstraintBased Analysis of Gene Deletion in a Metabolic Network
ConstraintBasd Analysis of Gn Dltion in a Mtabolic Ntwork Abdlhalim Larhlimi and Alxandr Bockmayr DFGRsarch Cntr Mathon, FB Mathmatik und Informatik, Fri Univrsität Brlin, Arnimall, 3, 14195 Brlin, Grmany
More informationUpper Bounding the Price of Anarchy in Atomic Splittable Selfish Routing
Uppr Bounding th Pric of Anarchy in Atomic Splittabl Slfish Routing Kamyar Khodamoradi 1, Mhrdad Mahdavi, and Mohammad Ghodsi 3 1 Sharif Univrsity of Tchnology, Thran, Iran, khodamoradi@c.sharif.du Sharif
More informationSection 55 Inverse of a Square Matrix
 Invrs of a Squar Matrix 9 (D) Rank th playrs from strongst to wakst. Explain th rasoning hind your ranking. 68. Dominan Rlation. Eah mmr of a hss tam plays on math with vry othr playr. Th rsults ar givn
More informationGold versus stock investment: An econometric analysis
Intrnational Journal of Dvlopmnt and Sustainability Onlin ISSN: 2688662 www.isdsnt.com/ijds Volum Numbr, Jun 202, Pag 7 ISDS Articl ID: IJDS20300 Gold vrsus stock invstmnt: An conomtric analysis Martin
More informationSOFTWARE ENGINEERING AND APPLIED CRYPTOGRAPHY IN CLOUD COMPUTING AND BIG DATA
Intrnational Journal on Tchnical and Physical Problms of Enginring (IJTPE) Publishd by Intrnational Organization of IOTPE ISSN 077358 IJTPE Journal www.iotp.com ijtp@iotp.com Sptmbr 015 Issu 4 Volum 7
More information1754 IEEE TRANSACTIONS ON WIRELESS COMMUNICATIONS, VOL. 6, NO. 5, MAY 2007
1754 IEEE TRANSACTIONS ON WIRELESS COMMUNICATIONS, VOL. 6, NO. 5, MAY 007 On th Fasibility of Distributd Bamforming in Wirlss Ntworks R. Mudumbai, Studnt Mmbr, IEEE, G. Barriac, Mmbr, IEEE, and U. Madhow,
More informationTheoretical approach to algorithm for metrological comparison of two photothermal methods for measuring of the properties of materials
Rvista Invstigación Cintífica, ol. 4, No. 3, Nuva época, sptimbr dicimbr 8, IN 187 8196 Thortical approach to algorithm for mtrological comparison of two photothrmal mthods for masuring of th proprtis
More informationI. INTRODUCTION. Figure 1, The Input Display II. DESIGN PROCEDURE
Ballast Dsign Softwar Ptr Grn, Snior ighting Systms Enginr, Intrnational Rctifir, ighting Group, 101S Spulvda Boulvard, El Sgundo, CA, 9045438 as prsntd at PCIM Europ 0 Abstract: W hav dvlopd a Windows
More informationResearch Progress in Acoustical Application to Petroleum Logging and Seismic Exploration
Snd Ordrs of Rprints at rprints@bnthamscinc.nt Th Opn Acoustics Journal 23 6  Opn Accss Rsarch Progrss in Acoustical Application to Ptrolum Logging and Sismic Exploration Lin Fa * Li Wang Yuan Zhao 2
More information5.4 Exponential Functions: Differentiation and Integration TOOTLIFTST:
.4 Eponntial Functions: Diffrntiation an Intgration TOOTLIFTST: Eponntial functions ar of th form f ( ) Ab. W will, in this sction, look at a spcific typ of ponntial function whr th bas, b, is.78.... This
More informationCloud and Big Data Summer School, Stockholm, Aug., 2015 Jeffrey D. Ullman
Cloud and Big Data Summr Scool, Stockolm, Aug., 2015 Jffry D. Ullman Givn a st of points, wit a notion of distanc btwn points, group t points into som numbr of clustrs, so tat mmbrs of a clustr ar clos
More informationPlanning and Managing Copper Cable Maintenance through Cost Benefit Modeling
Planning and Managing Coppr Cabl Maintnanc through Cost Bnfit Modling Jason W. Rup U S WEST Advancd Tchnologis Bouldr Ky Words: Maintnanc, Managmnt Stratgy, Rhabilitation, Costbnfit Analysis, Rliability
More informationImportant Information Call Through... 8 Internet Telephony... 6 two PBX systems... 10 Internet Calls... 3 Internet Telephony... 2
Installation and Opration Intrnt Tlphony Adaptr Aurswald Box Indx C I R 884264 03 02/05 Call Duration, maximum...10 Call Through...7 Call Transportation...7 Calls Call Through...7 Intrnt Tlphony...3 two
More informationProduction Costing (Chapter 8 of W&W)
Production Costing (Chaptr 8 of W&W).0 Introduction Production costs rfr to th oprational costs associatd with producing lctric nrgy. Th most significant componnt of production costs ar th ful costs ncssary
More informationBasis risk. When speaking about forward or futures contracts, basis risk is the market
Basis risk Whn spaking about forward or futurs contracts, basis risk is th markt risk mismatch btwn a position in th spot asst and th corrsponding futurs contract. Mor broadly spaking, basis risk (also
More informationControversies about the value of the third cosmic velocity
.478/v469 A N N A L E S U N I V E R S I T A T I S A R I A E C U R I E  S K Ł O D O W S K A L U B L I N P O L O N I A VOL. LXVIII SECTIO AAA Controvrsis about th valu of th third cosic vlocity STANISŁAW
More informationAdverse Selection and Moral Hazard in a Model With 2 States of the World
Advrs Slction and Moral Hazard in a Modl With 2 Stats of th World A modl of a risky situation with two discrt stats of th world has th advantag that it can b natly rprsntd using indiffrnc curv diagrams,
More informationNUMERICAL COMPUTATION OF THE EFFECTIVENESSNUMBER OF TRANSFER UNITS FOR SEVERAL CROSSFLOW HEAT EXCHANGERS WITH DIFFERENT FLOW ARRANGEMENTS
Prodings of COBEM 2009 20th Intrnational Congrss of Mhanial Enginring Novmbr 1520, 2009, Gramado, RS, Brazil NUMERICAL COMPUTATION OF THE EFFECTIVENESSNUMBER OF TRANSFER UNITS FOR SEVERAL CROSSFLOW
More informationChapter 5 Capacitance and Dielectrics
5 5 5 Chaptr 5 Capacitanc and Dilctrics 5.1 Introduction... 53 5. Calculation of Capacitanc... 54 Exampl 5.1: ParalllPlat Capacitor... 54 Exampl 5.: Cylindrical Capacitor... 56 Exampl 5.3: Sphrical
More informationACCURACY OF DISTRIBUTION CURRENT TRANSFORMERS UNDER NONSINUSOIDEAL EXCITATION
ACCURACY OF DSTRBUTON CURRENT TRANSFORMERS UNDER NONSNUSODEAL EXCTATON Astract K. Dnath School of Enginring Univrsity of Tasmania Hoart, Australia 7000 Th accuracy of CTs usd for mtring uross ar rquird
More informationAbstract. Introduction. Statistical Approach for Analyzing Cell Phone Handoff Behavior. Volume 3, Issue 1, 2009
Volum 3, Issu 1, 29 Statistical Approach for Analyzing Cll Phon Handoff Bhavior Shalini Saxna, Florida Atlantic Univrsity, Boca Raton, FL, shalinisaxna1@gmail.com Sad A. Rajput, Farquhar Collg of Arts
More informationCPU. Rasterization. Per Vertex Operations & Primitive Assembly. Polynomial Evaluator. Frame Buffer. Per Fragment. Display List.
Elmntary Rndring Elmntary rastr algorithms for fast rndring Gomtric Primitivs Lin procssing Polygon procssing Managing OpnGL Stat OpnGL uffrs OpnGL Gomtric Primitivs ll gomtric primitivs ar spcifid by
More informationInfrared VibrationRotation Spectroscopy of HCl and DCl
Chmistry 363 JMS 1/05 Spring 010 DLC 1/10 Infrard VibrationRotation Spctroscopy of HCl and DCl Exprimnt Objctiv: to obtain th quilibrium bond lngth (r ) and vibrationrotation spctroscopic constants from
More informationPhysics 106 Lecture 12. Oscillations II. Recap: SHM using phasors (uniform circular motion) music structural and mechanical engineering waves
Physics 6 Lctur Oscillations II SJ 7 th Ed.: Chap 5.4, Rad only 5.6 & 5.7 Rcap: SHM using phasors (unifor circular otion) Physical pndulu xapl apd haronic oscillations Forcd oscillations and rsonanc. Rsonanc
More informationSimulation of the electric field generated by a brown ghost knife fish
C H A P T R 2 7 Simulation of th lctric fild gnratd by a brown ghost knif fish lctric fild CONCPTS 27.1 Th fild modl 27.2 lctric fild diagrams 27.3 Suprposition of lctric filds 27.4 lctric filds and forcs
More informationMagic Square of Squares
Intrnatinal Jurnal f Enginring and Tchnical Rsarch (IJETR) ISSN: 232869, Vlum, Issu8, Octbr 23 Magic Squar f Squars Shubhankar Paul Abstract A n n array f intgrs is calld a magic squar whn all th rws,
More informationPerformance Evaluation
Prformanc Evaluation ( ) Contnts lists availabl at ScincDirct Prformanc Evaluation journal hompag: www.lsvir.com/locat/pva Modling Baylik rputation systms: Analysis, charactrization and insuranc mchanism
More informationEffect of Design Parameter on the Performance of Lithium Ion Battery
Aadil Ahmad, Mohd. Parvz / Intrnational Journal of Enginring Rarch and Application Vol. 3, Iu 4, JulAug 2013, pp.11961201 Effct of Dign Paramtr on th Prformanc of Lithium Ion Battry Aadil Ahmad 1, Mohd.
More informationModern Portfolio Theory (MPT) Statistics
Modrn Portfolio Thory (MPT) Statistics Morningstar Mthodology Papr May 9, 009 009 Morningstar, Inc. All rights rsrvd. Th information in this documnt is th proprty of Morningstar, Inc. Rproduction or transcription
More informationThe Coverage Analysis for Low Earth Orbiting Satellites at Low Elevation
(IJACSA) Intrnational Journal of Advancd Computr Scinc and Applications, Vol. 5, No. 6, 14 Th Covrag Analysis for Low Earth Orbiting Satllits at Low Elvation Shklzn Cakaj 1, Bxht Kamo 1, Algnti Lala 1,
More informationSharp bounds for Sándor mean in terms of arithmetic, geometric and harmonic means
Qian t al. Journal of Inqualitis and Applications (015) 015:1 DOI 10.1186/s166001507411 R E S E A R C H Opn Accss Sharp bounds for Sándor man in trms of arithmtic, gomtric and harmonic mans WiMao Qian
More informationLG has introduced the NeON 2, with newly developed Cello Technology which improves performance and reliability. Up to 320W 300W
Cllo Tchnology LG has introducd th NON 2, with nwly dvlopd Cllo Tchnology which improvs prformanc and rliability. Up to 320W 300W Cllo Tchnology Cll Connction Elctrically Low Loss Low Strss Optical Absorption
More informationExamples. Epipoles. Epipolar geometry and the fundamental matrix
Epipoar gomtry and th fundamnta matrix Epipoar ins Lt b a point in P 3. Lt x and x b its mapping in two imags through th camra cntrs C and C. Th point, th camra cntrs C and C and th (3D points corrspon
More informationGriffithsMcCoy singularities in the random transversefield Ising spin chain
PHYSICAL REVIEW B VOLUME 59, NUMBER 17 1 MAY 1999I GriffithsMcCoy singularitis in th random transvrsfild Ising spin chain Frnc Iglói Rsarch Institut for Solid Stat Physics and Optics, P.O. Box 49, H1525
More informationFactorials! Stirling s formula
Author s not: This articl may us idas you havn t larnd yt, and might sm ovrly complicatd. It is not. Undrstanding Stirling s formula is not for th faint of hart, and rquirs concntrating on a sustaind mathmatical
More informationFACULTY SALARIES FALL 2004. NKU CUPA Data Compared To Published National Data
FACULTY SALARIES FALL 2004 NKU CUPA Data Compard To Publishd National Data May 2005 Fall 2004 NKU Faculty Salaris Compard To Fall 2004 Publishd CUPA Data In th fall 2004 Northrn Kntucky Univrsity was among
More informationPolicies for Simultaneous Estimation and Optimization
Policis for Simultanous Estimation and Optimization Migul Sousa Lobo Stphn Boyd Abstract Policis for th joint idntification and control of uncrtain systms ar prsntd h discussion focuss on th cas of a multipl
More informationDeveloping a Travel Route Planner Accounting for Traffic Variability
Procdings of th 009 IEEE Systms and Information Enginring Dsign Symposium, Univrsity of Virginia, Charlottsvill, VA, USA, April 4, 009 FPMisk.3 Dvloping a Travl out Plannr Accounting for Traffic Variability
More informationCapacitance and Dielectrics
Chaptr 5 Capacitanc and Dilctrics 5.1 Introduction...53 5. Calculation of Capacitanc...54 Exampl 5.1: ParalllPlat Capacitor...54 Intractiv Simulation 5.1: ParalllPlat Capacitor...56 Exampl 5.: Cylindrical
More informationHitrac Luminaire LED
indirct mission 72 2000 LED 0q p (RAL9002) LED 12W 10lm 4000K nutral whit Switchabl Vrsion 2 Product dscription Panl profil: aluminium, powdrcoatd. Uppr part: mounting plat with LED modul. 5pol trminal
More informationCHARACTERISTICS OF ELECTROMAGNETIC WAVE PROPAGATION THROUGH A MAGNETISED PLASMA SLAB WITH LINEARLY VARYING ELECTRON DEN SITY
Progrss In Elctromagntics Rsarch B, Vol. 21, 385 398, 2010 CHARACTERISTICS OF ELECTROMAGNETIC WAVE PROPAGATION THROUGH A MAGNETISED PLASMA SLAB WITH LINEARLY VARYING ELECTRON DEN SITY Ç. S. Gürl Dpartmnt
More informationAn Broad outline of Redundant Array of Inexpensive Disks Shaifali Shrivastava 1 Department of Computer Science and Engineering AITR, Indore
Intrnational Journal of mrging Tchnology and dvancd nginring Wbsit: www.ijta.com (ISSN 22502459, Volum 2, Issu 4, pril 2012) n road outlin of Rdundant rray of Inxpnsiv isks Shaifali Shrivastava 1 partmnt
More informationISO 9001 DIL UNIVERSAL CONTACTORS
GANZ KK Kft ISO 0 crtifid DIL UNIVERSAL CONTACTORS 00.0. GANZ KK Ltd. applis a Quality control systm according to th rquirmnts of th standard ENISO0 Bridg Moving magnt Coil Fixd magnt Auxiliary contactunit
More informationOXYGEN TRANSFER MEASUREMENTS AT SURFACE AERATORS IN WASTE WATER AS BASIS FOR ENERGY SAVING IN AERATION
OXYGEN TRANSFER MEASUREMENTS AT SURFACE AERATORS IN WASTE WATER AS BASIS FOR ENERGY SAVING IN AERATION Ditr Lomp Hochschu Brmrhavn Grmany Ahmt NuruBruns Achim, Grmany ABSTRACT Oxygn transfr masurmnts
More informationAnalyzing the Economic Efficiency of ebaylike Online Reputation Reporting Mechanisms
A rsarch and ducation initiativ at th MIT Sloan School of Managmnt Analyzing th Economic Efficincy of Baylik Onlin Rputation Rporting Mchanisms Papr Chrysanthos Dllarocas July For mor information, plas
More informationHigher order mode damping considerations for the SPL cavities at CERN
Highr ordr mod damping considrations for th SPL cavitis at CERN W. Wingartn Outlin Th SPL study at CERN HOM damping rquirmnts for SPL study Optimisation of cavity gomtry rlatd to HOM damping Conclusion
More information