2 Many new firefighter get confused between Standpipe vs. Sprinklers because the FDC ( Fire Department Connection) on the outside of the building look the same. Although they may have a similar purpose (getting water to a fire inside a building) their functions are completely different.
3 STANDPIPE: Is a pre-piped water supply system that allows Fire Dept hose to be connected from points inside the building. Found in structures of large area (footprint), multiple floors or structures with both. Allows us to get closer to the fire, with our hose lines, quicker and prevents us from stretching large amounts of hose throughout the building before we can even close enough to begin firefighting operations. What s happening to the fire when we have these Large stretches?
4 SRINKLERS: Is also a pre-piped water supply system but instead of feeding hose lines, they feed sprinkler heads throughout the building, as designed by an engineer. Doesn t need to be Entire building, could just Be an area of building Typically found in high fire hazard structures or one with large occupancy. They are designed to keep fire confined to a specific area and not necessarily designed to extinguish the fire. We are seeing more and more in residential applications, single or 2 family homes, to protection a truss building system or a heating system room. Village of Westbury also requires residential sprinklers when a home s attic is sheet rocked, be aware these smaller residential sprinklers systems will differ from the commercial application, typically we will not be able to supplement the water source to them, most will be fed solely by local water.
5 Connecting our F.D. Hose to a FDC Sprinkler or Standpipe The Engine will first need to gain a water source (hydrant) which will typically be in close proximity to the FDC. -Does this mean that this hydrant will operational? We need to be ready for anything! when the engine is at an operational hydrant ( water source) we want to connect to the FDC using larges diameter hose possible, Typically our 5 hose. Can we reverse lay, instead of Hydrant to FDC, can we go FDC to Hydrant? The newer FDC, we are seeing are 5 Storz and not the standard 2.5 Siamese. If this is the case, we can take our 5 Hose and make a direct connection to FDC. 5 Storz ( sexless) 2.5 Siamese
6 Connecting our F.D. Hose to a FDC Sprinkler or Standpipe If we are confronted with a Sprinkler and a Standpipe FDC, next to each other, we always want to feed the STANDPIPE first, since this is what we ll be using. Note: The multiple Standpipe or Sprinkler FDC, found around a structure will all feed the entire, common, system. Note: Sprinklers and Standpipes are independent of each other, unless marked Combo System, only these will be feeding both sprinkler & Standpipe systems at the same time. Example: Combo system Source Mall
7 Connecting 5 Fire Hose to a FDC Sprinkler or Standpipe Best 2 nd Best
8 FDC SIAMESE clapper Valve Note: In a FDC Siamese, there is a clapper valve that directs the water flow. If only connecting 5 make sure the clapper is operational otherwise you ll need to cap the side not being used. ( gate it if nec. ) Note: if found with no caps debris inside could hinder operations
9 Connecting 2.5 Hose to a FDC Sprinkler or Standpipe When we decide to connect 2.5 hose to our FDC, get that first 2.5 connected as soon a possible, get operational before doing the second one.
10 Overcoming obstacles at a FDC Siamese Break cap if unable To remove
12 Sprinkler Systems Now that we have a FD water supply into the sprinkler System, is our job now done? NO It is very important for us to gain control of the buildings sprinkler system. An active sprinkler, although it may be keeping the main body of fire in check, it is typically hindering our hose line advancement. - the water being forced downward also forces down the products of combustion the smoke and heat are not lifting, even if the roof team cut us a nice big hole. This will typically slow down us from advancing to the fire, visibility is harder, the TI camera doesn t hit on the hot room, because it s being cooled
13 Sprinkler Systems Note: A Sprinkler systems can be a wet or dry system. Wet the system is always charge with water or an extinguishing agent. Dry ( typically found in outside or in unheated areas ) example: garages These systems are charge with air at a greater pressure then the water supply s pressure. When a head is tripped, the air escaping lowers the air pressure, making the water pressure greater and allowing the water to flow in pipe.
14 Sprinkler Systems When the head is actively flowing water, This triggers a chain of events: Sensors in the pipe system will sense water movement and this activates an alarm, triggering a FD Response The moving water will activate the outside Sprinkler Alarm aka: sprinkler gong or water flow gong The outside drain will be flowing water out The more water = the more water flow inside... ( could indicate more heads tripped then 1? )
15 Active Head Flowing Water Active Fire Sprinkler Systems Sprinkler Gong Active Drain discharging water Fire alarm transmitted What is happening if the gong is ringing, stops, then ringing? Water movement Is sensed
16 Sprinkler Systems What is important to us, as we arrive on scene is: the gongs going off and water being discharged. * Listen for gong & look for that trail of water in parking lot *These items allow us to isolate the active riser, that we need to gain control of. In buildings with multiple occupancy changes or the dividing of a once larger occupancy into many smaller ones, this may not be as obvious as you may think. The gong closest to the fire building may not be the active one and the fire areas sprinklers could be getting fed from a different part of the building altogether. These signs * and a good preplan will help you isolate the active riser for that fire area. Note: it s not uncommon to have multiple risers for 1 building, in different locations.
17 Sprinkler Systems Once we ve located the Active Riser, supplemented the water source with our engine, then we need to gain control of it. Sprinkler controls valves can be found on the outside or inside of a building. Typically in newer building: They are found grouped in a Sprinkler Room. Closed Open Outside Stem & Yolk ( OS&Y)
18 Sprinkler Systems Sprinkler alarm Typically in newer building: Inside Sprinkler Room Sprinkler Siamese Sprinkler drain So when open door, what side will riser be on? Older building Attached to building: Wall Post Indicator Valve NOTE Since Open Access chain and locked In open position
19 Sprinkler Systems When the FDC is not attached to the building: in front yard, out by the street, in a parking lot Due to our climate, This entire set up will be in a outside under ground pit These risers could be in an underground pit near the FDC or a Post Indicator Valve typically between FDC and Building Pit
20 Sprinkler Systems Gaining control of the sprinkler valves will typically require forcible entry, if the valves are confined in a room or in an outside underground pit. For the Post indicators, or any sprinkler control valve with common access, you may not need to force entry to them, but the valve will be locked in the open position. Once the hose line crew has made it to the fire area, they will request the sprinkler be shut down.
21 Sprinkler Systems Fire Pumps Note: Sprinklers in large footprint buildings or especially taller buildings, the street water pressure may not be sufficient to supply enough pressure to the sprinkler systems These building the sprinkler system's water will be supplemented by a Fire Pump, boosting the pressure. Diesel pump Electric pump
22 Sprinkler Systems Fire Pumps These Fire Pumps need to be shut down: 1. When our Engine is connected to the sprinkler system and we are now augmenting the water supply OR 2. When we have orders to shut down the sprinkler system, if our engine is connected to the system or not. Provisions should always be in place to augment the system, plus restarting a pump is typically a simple few steps.
23 Sprinkler Systems Fire Pumps Controller & Pump Red Button Stop Green Button Start With Diesel may be turn key also
24 Shutting Down Sprinkler Systems All Locks should remove and the valve ready to be operated, awaiting the orders to shut down the sprinklers For the OS&Y valves you want to turn the wheel so the stem goes from exposed to inside the pipe: Exposed Stem Open Hidden Stem Closed
25 Sprinkler Systems For the Post Indicators these work just like a Hydrant Open or Closed Cut the lock freeing the crank handle Pull off handle Operate to nut as you would a Hydrant The indicator will let you know if OPEN or CLOSED
26 Sprinkler Systems Once the Sprinkler is shut down, is your job done? NO, remain at the control valve. If the fire is unable to be controlled by line(s), if there is trouble with the lines if there is a catastrophic event requiring regrouping The sprinklers can always be reactivated.
27 Standpipe System Now that we have a FD water supply into the Standpipe System, what s next? Does this mean we have water to the structure? No Once the MPO starts to flow water we ll get a better indication if our connection is effective. If they flows water and the rig is not continually flowing water, we re probably good. But If there is water flow, the rig is working hard and the hose team is not connected yet, we have to look for: broken pipe, open valve
28 Note: Standpipe System Just like a Sprinklers Systems, A Standpipe system can also be Wet Or Dry. A Wet System will be supplied by town water, and A Dry System, again typically in areas susceptible to freezing ( parking garages ), will be dry, until: (1) a valve is opened putting town water into it or (2) we put the water in with our engines. In Both systems, we ll be connecting our hose to the system, Wet supplementing the water supply Dry we may be the only water supply and system is just a piping system.
29 Standpipe System If we are unable to make a connection to a specific FDC, Alternatives to get water to the standpipe system could be: find another FDC else where around the building the closest inside Standpipe Connection: Remember will need a double female adaptor since you ll be trying to connect 2 male connections other inside connections could later be used to supplement the original connection, once man power allows, by feeding another lower, close standpipe connection. Don t only think of an inside Standpipe Connections as a discharges, The system is a grid/loop They can be fed from these points too! Adaptor Pipe Thread Our Thread
30 Standpipe System of outside Siamese don t work: FIRE FLOOR 2nd Line X X 1 st Line Connection Reversed to a 1st feed 1 st Due Connection Missing X X X X 3rdL Line X Connection Damaged Connection Reversed to a 2 nd feed 2 nd Due
31 Attaching Attack Lines to Standpipe system
32 Attaching Attack Lines to Standpipe system Hose Team s Equipment Nozzle : 2 High Rise Packs ( make sure there is a Nozzle s in bag or bring one ) Officer : Officers tool - 1 High Rise Pack, Hand light & Radio Back Up: 2 High Rise Pack Control : Standpipe Bag 1 High Rise Pack, Hand Light & Radio Rule of thumb: 1 st Line Connecting - Floor below Fire Floor 2 nd Line Connecting - 2 Floors below Fire
33 Attaching Attack Lines to Standpipe system
34 Attaching Attack Lines to Standpipe system Hose Team Equipment Control : will be making the connection to the stand pipe Nozzle and Back up: Set up hose for easy advancement to fire Officer should be accessing floor plan, of the set up floor, to gain layout and determine best means to attack. ( typically in high rise floor layout same floor to floor ) How may doors down is 504, will be same a on right or left? Maybe easier to advance the floor below hallway then go up, then to go up to fire floor and advance to fire apartment?
35 Attaching Attack Lines to Standpipe system
36 Attaching Attack Lines to Standpipe system
37 Attaching Attack Lines to Standpipe system When advancing hose line, use gravity to your advantage. Whenever possible, try to get the hose in an easily advancing position before orders are given to control to charge the line. Length of hose being used by 1 st line should be relayed to 2 nd line, They should always have more: (1) starting from further away, (2) if 1 st line does come up short 2 nd line can advance past 1 st line and make the fire.
38 Sprinkler & Standpipe Hands on portion End of Lecture Part 2 of Drill : Gear up going to Source Mall to Review: Connecting to Sprinkler System using (2) 2.5 hose Gaining access sprinkler room and OS&Y s Controlling Fire Pump Shutting down Sprinkler System Getting System back operational
39 Sprinkler & Standpipe Hands on portion Part 3 of Drill : Gear up going to Roosevelt Field Mall to Review: Connecting to Standpipe System using 5 hose Connecting to stand pipe if Siamese not operational Review Standpipe bags Connecting our hose to system Getting High Rise packs into operation Setting pressure using in line pressure gauge Hose line positioning & advancement Repacking High Rise packs
Firefighter Review Instructor Guide Session Reference: 3 Topic: Attack Line Handling Level of Instruction: Time Required: Three Hours Materials: Two Fully Equipped Pumpers Structure for Use in Advancing
S TANDPIPE O PERATIONS(1.1) NFPA 14 NFPA 13E Developed by Lieutenant Bryan Clark December 2010 T ASK S KILL DESCRIPTION AND DETAIL Firefighting in buildings equipped with standpipes is challenging, and
Fire Sprinklers 1 Topics History of Fire Sprinklers Types of Sprinkler Systems Types of Sprinkler Heads Future of Fire Sprinklers Facts about Sprinkler Systems 2 History of Fire Sprinklers Officially developed
FIRE SAFETY MANUAL INSPECTION FORMS...48 FORM F-1 AUTOMATIC SPRINKLER SYSTEMS WEEKLY INSPECTION...48 FORM F-2 AUTOMATIC SPRINKLER SYSTEMS MONTHLY INSPECTION...49 FORM F-3 AUTOMATIC SPRINKLER SYSTEMS QUARTERLY
1. The process for making the fire pump operational begins: a. En route to the emergency scene b. Immediately after receiving dispatch c. After connecting to the water source and determining proper operating
2011 NFPA 25 Standpipe Testing Excerpts 6.3 Testing Where water damage is a possibility, an air test shall be conducted on the system at 25 psi (1.7 bar) prior to introducing water to the system. Extreme
Fire Suppression Plan Review General A. Are the shop drawings on the contractor s title block? B. Do the drawings meet the engineer design documents? C. Is the applicable code (NFPA 13, 13R, 13D, 14, 20)
SECTION IV MAINTENANCE PROCEDURES FOR FIRE PROTECTION SYSTEMS SECTION IV SECTION IV MAINTENANCE PROCEDURES FOR FIRE SAFETY EQUIPMENT TABLE OF CONTENTS... Page Preface... 1 Maintenance and Inspection Schedules...
Risk Control Bulletin Inspection, Testing & Maintenance (ITM) of Water-Based Fire Protection Systems Introduction Fire protection systems are provided in or at a building to safeguard the lives of building
I. Introduction 10 minutes Introduction (1 of 2) An uninterrupted water supply is: The primary weapon for extinguishment Essential for fire fighter safety Ensuring a dependable water supply is a critical
NFPA 14 3.3.5 3.3.5 High-Rise Building. A building where the floor of an occupiable story is greater than 55 ft (17 m) 75 ft (23 m) above the lowest level of fire department vehicle access. 188.8.131.52 184.108.40.206
Fighting Fire in Sprinklered Buildings Student Guide Fighting Fire in Sprinklered Buildings Student Guide Table of Contents Purpose........................................................... 3 Instruction
PLAN REVIEW GUIDE FIRE SPRINKLER SYSTEMS PROJECT NAME: PERMIT PROJECT ADDRESS: CONTACT PERSON: CONTRACTOR PHONE Fire sprinkler system installation information shall be provided on the appropriate plans.
Important Ontario Fire Code Information for Building Owners in the City of Windsor This information is intended to be used a reference only. For a complete listing consult the Ontario Fire Code or contact
Automatic Fire Sprinkler Submittal Requirements All commercial and industrial buildings with a total floor area of 5000 sq. ft. shall have an approved automatic sprinkler system installed. The Windsor-Severance
GENERAL: 1. All fire protection systems shall be installed in accordance with the International Fire Code and applicable NFPA standards. This guideline provides additional requirements for the design and
Overview of Fire Pumps and Water Storage Tanks M. Steven Welsh, P.E. Registered FPE Koffel Associates, Inc. www.koffel.com firstname.lastname@example.org Expertly Engineering Safety From Fire Outline Introduction Water
MISSISSIPPI INSTITUTIONS OF HIGHER LEARNING OFFICE OF RISK MANAGEMENT ANNUAL BUILDING FIRE INSPECTION REPORT Date of Inspection: University: Building: Address: Contact Person: Phone number: This inspection
CHECK, TEST, INSPECT REQUIREMENTS OF THE ONTARIO FIRE CODE CHECK - Means visual observation to ensure the device or system is in place and is not obviously damaged or obstructed. TEST - Means operation
Burnsville Fire Department 100 Civic Center Pky, Burnsville, MN 55337 Fire Marshal: 952-895-4579 FAX: 952-895-4512 2016 FIRE SUPPRESSION PERMIT APPLICATION PERMIT Wet System Dry System Cooking Hood Clean
High Rise Fire Protection Standpipe and Sprinkler Systems By: Douglas Nadeau, PE President RAN Fire Protection Engineering, PC Tel: 518 275 0791 Email: email@example.com Introduction Why talk about high-rise
Report of Initial Findings Modesto Fire Department Informational Summary Report of Serious MFD Injuries, Illness, Accidents, and Near-Miss Incident Coston Incident Structure Fire 01/01/2010 $MF10000129
PDHonline Course M110 (4 PDH) Introduction to Fire Protection Systems Instructor: Lawrence J. Marchetti, P.E. 2012 PDH Online PDH Center 5272 Meadow Estates Drive Fairfax, VA 22030-6658 Phone & Fax: 703-988-0088
GAP.220.127.116.11 A Publication of Global Asset Protection Services LLC ESTIMATING FIRE PROTECTION WATER DEMANDS INTRODUCTION What constitutes an adequate water supply has generated much discussion over the
3 ENGINE COMPANY SKILLS 1 ¾ RESIDENTIAL ATTACK LINES 1. General Information The attack line of choice for a residential fire is the pre-connected 1 ¾ attack line with an Automatic Nozzle 1 ¾ attack lines
The In-Line Gauge in Standpipe Operations BY RUSS CHAPMAN Your engine company receives a report of fire in a mid-rise elderly housing complex during morning coffee at the beginning of a shift. You know
White Paper Avoiding Freeze-Ups and Malfunctions of Automatic Fire Sprinkler Systems Be knowledgeable. Be prepared. WA011-10May11 Myth: When a fire occurs every sprinkler goes off. Fact: Sprinklers are
RESIDENTS FIRE SAFETY INFORMATION PACK MARIE CURIE SCEAUX GARDENS ESTATE LONDON SE5 THE CONTENTS OF YOUR PACK Section Page No. 1. 3. Introduction Here we will explain the purpose of the Fire Safety Information
July 1, 2010 SANTA ROSA FIRE DEPARTMENT FIRE PREVENTION BUREAU PLAN REVIEW CHECKLIST RESIDENTIAL FIRE SPRINKLERS NFPA 13D Address: Permit #: Inspector: Date: Status: Inspector: Date: Status: A-Approved;
Maintaining Fire Protection Systems Fire continues to be a major threat to your business and your personal safety. Each year several thousand people are injured or killed by fires and billions of dollars
FIRE SAFETY PLAN FOR KITCHENER, ONTARIO Additional information of fire safety plans may be found at our website at www.kitchener.ca/fire.htm. Before submission, please read and change all sections to address
RESIDENTS FIRE SAFETY INFORMATION PACK PERRONET HOUSE PRINCESS STREET LONDON SE1 THE CONTENTS OF YOUR PACK Section Page No. 1. 3. Introduction Here we will explain the purpose of the Fire Safety Information
Commercial Fire Inspections Fire Department Inspection Requests and Procedures The following guidelines shall be used when calling for inspection requests: 1. All inspection requests shall be coordinated
NFPA 13R 1.1 1.1 Scope This standard covers the design and installation of automatic sprinkler systems for protection against fire hazards in residential occupancies up to and including two four stories
March 2, 2007 Dry 101a 1. DESCRIPTION A Dry Pipe Sprinkler System is a fire-protection system which utilizes water as an extinguishing agent. The system piping from the Dry Pipe Valve to the fusible sprinklers
RESIDENTS FIRE SAFETY INFORMATION PACK CASTLEMEAD CAMBERWELL ROAD LONDON SE5 THE CONTENTS OF YOUR PACK Section Page No. 1. 3. Introduction Here we will explain the purpose of the Fire Safety Information
SECTION 15400 - FIRE PROTECTION SYSTEMS SECTION DESCRIPTION 15401 GENERAL REQUIREMENTS 15402 FIRE PROTECTION DESIGN CRITERIA 15403 SPRINKLER EQUIPMENT 15404 FIRE PUMPS 15405 STANDPIPE AND FIRE HOSE EQUIPMENT
Winnipeg Fire Department Fire Prevention Branch Manitoba Fire Code Life-Safety Equipment Maintenance Requirements The Fire Prevention Branch of the Winnipeg Fire Department has prepared this document of
DFES BEB GUIDELINE No : GL 03 TITLE : SAFETY EQUIPMENT SIGNAGE Issued: March 2015 Replaces: January 2015 Valid until: March 2017 Prepared by: Built Environment Branch Authorised by: Manager, Built Environment
13D Residential Sprinkler System Plan Review Checklist 2010 OFC and 2007 NFPA 13D Date of Review: Permit Number: Business/Building Name: Address of Project: Designer Name: Designer s Phone: Contractor:
NFPA 13D 1.1 1.1 This standard shall cover the design and installation of automatic sprinkler systems for protection against the fire hazards in one- and two-family dwellings and manufactured homes. When
Fire detection, alarm, and suppression systems are installed to: Notify occupants to escape a fire Summon emergency responders Initiate suppression systems Supervise suppression systems for operational
MCKINNEY FIRE DEPARTMENT FIRE MARSHAL S OFFICE AUTOMATIC FIRE SPRINKLER SYSTEMS These guidelines are to be followed when a business, facility or organization installs an automatic fire sprinkler system
PLAN CHECK CORRECTION SHEET FOR NFPA 13 2016 This is intended to provide uniform application of the codes by the plan check staff and to help the public apply the codes correctly. Section: Mechanical Plan
Natural Gas Emergencies Purpose To protect the personnel within the department, and citizens from the hazards involved in a natural gas emergency. The Incident Commander is to use his/her best judgment
Utility Systems Electrical The electrical supply to your home begins outside, where you will see either an overhead feed and piping down the side of your home or (if you have underground service) a metal
Introduction to Sprinklers EFSN Training i Module 1 90 Minutes Topics How sprinklers work Performance of sprinkler systems Types of Sprinkler Introduction to sprinkler systems Introduction ti to sprinkler
July 1, 2010 SANTA ROSA FIRE DEPARTMENT FIRE PREVENTION BUREAU PLAN REVIEW CHECKLIST RESIDENTIAL FIRE SPRINKLERS NFPA 13R Address: Permit #: Inspector: Date: Status: Inspector: Date: Status: A-Approved;
Big Water 101 Blackwood Fire Company Engine Company Training Engine Work The job of the engine is to get water on the fire. Plain and simple. Accomplishing that can be a problem depending on the circumstances.
TOPIC: CHARACTERISTICS AND FUNCTIONS OF WILDLAND HOSE LAYS TIME FRAME: 1:00 LEVEL OF INSTRUCTION: Level II AUTHORITY: 1997 NFPA 1001 3.3-18 BEHAVIORAL OBJECTIVE: Condition: Behavior: Standard: A written
FIRE DEPARTMENT Bureau of Fire Protection and Life Safety www.cityofsanmateo.org 1900 O Farrell, Suite 140 San Mateo, CA 94403-1332 (650) 522-7940 FAX: (650) 522-7941 TDD: (650) 522-7047 MAINTENANCE AND
NFPA 14 Standpipes & Hose Valves Presented by American Fire Sprinkler Association 1 www.firesprinkler.org 2 DISCLAIMER This seminar and its content is not a formal interpretation issued pursuant to NFPA
Oxnard Fire Department Fire Protection Planning Guide 360 W Second St Oxnard, CA 93030 (805) 385-7722 Fax (805) 385-8009 Design for Fire and Life Safety The Oxnard Fire Department offers fire protection
Large Facility Fire Safety Checklists and Logs This package contains checklists to ensure that all fire and life safety equipment are properly inspected. There are also logs on which to record the inspections
Introduction Fixed fire protection in the form of automatic sprinkler protection is a critical investment in the protection of the physical property of any business or organization from loss by fire. When
Fire Safety In High Rise Building CLASSIFICATION OF BUILDINGS AS PER NATIONAL BUILDING CODE 1. GROUPING. Group A - Residential : Lodgings, Dwellings, Dormitories, Flats, Hotels. Group B Group C - Educational
FIRE SAFETY MANUAL FSF Downloaded from: www.firesafetyfirst.co.uk Contents Introduction ii Page Section 1 Practical Fire Safety Guidance 1/1 Section 2 Fire Safety Training 2/1 Section 3 Log-book 3/1 Fire
FIRE PREVENTION INSPECTION CHECKLIST For Class A Occupancy (For Assembly Buildings, Bars, Restaurants, Gyms, Churches, Arenas, Theatres or wherever people gather) Name Of Occupancy Date Physical Address
IDENTIFICATION BROCHURE FOR Gem and Star ON-OFF SPRINKLERS 1 INTRODUCTION TO THE VOLUNTARY REPLACEMENT PROGRAM This brochure provides information that will assist you in identifying whether the sprinklers
Fire Safety Plan (Single-Stage Fire Alarm System) (Small Establishment): Fire Safety Plan Single-Stage Fire Alarm System for: (Business Name) (Business Address) Submission Date - Submitted by - Signature
P a g e 1 SECTION 04 (Doc.No.A/DBR 001) FIRE-FIGHTING DESIGN BRIEF REPORT P a g e 2 1.0 SCOPE 2.0 STANDARDS AND CODES 3.0 TYPES OF SYSTEM PROPOSED 4.0 FIRE HYDRANT SYSTEM 5.0 AUTOMATIC SPRINKLER SYSTEM
21 00 00. Fire Suppression For campus projects that require a fire suppression system shut down in a campus facility, a Shut Down Procedure of Fire Safety System Sheet must be completed and filed seven
Fire Pump Layout and Sizing Victoria B. Valentine, P.E. Learning Outcomes Identify the appropriate sections of NFPA 20 that apply to sizing and layout of fire pumps. Identify the components of a fire pump
Activity Sheet 1.1 Fire hazards in the workplace Timing 15 minutes Look at the illustrations of the different workplaces. For each, try to identify: n three sources of fuel n three sources of ignition.
Fire Hose and Appliances Identify the Construction Features of Fire Hose Materials used in construction Cotton Nylon Rayon vinyl Poly-mired vinyl Polyester Identify the Construction Features of Fire Hose
Tumble Dryer Buying Guide Factors to Consider When purchasing a new Tumble Dryer With only a few weeks each year where you can be certain it won t rain, tumble dryers can be a real life saver, ensuring
KODAK VERSAMARK, INC. PREPARED BY : Gary Rowland 6/6/06 Kodak Versamark, Inc. 3000 Research Blvd. Dayton, Ohio 45420 APPROVED BY : Fire Suppression System Inspection, Testing and Maintenance SHEET 1 OF
City of South Salt Lake Fire Marshal Regulations for Water Based Fire Protection and Water Supply Systems Rev. Oct. 2012 1 Fire Flow 508.1 Required water supply. An approved water supply capable of supplying
Springdale Fire Department Backup Driver Certification Program Backup Driver Task Book I. Obtain required prerequisites 1. Performance a. Complete Probationary Program b. Complete CEVO Fire Course c. Complete
Instructions This is a tactical problem for a commercial structure fire. A PDF file has been provided with views of the fire building. You should use the file for digital slides or overhead transparencies.
SECTION 15300 FIRE PROTECTION WET PIPE FIRE SPRINKLER SYSTEM PART 1 - GENERAL 1.01 RELATED DOCUMENTS A. Drawings and general provisions of Contract including General and Supplementary Conditions, Division
CITY OF SPRING LAKE PARK Code Enforcement Department 1301 81 st Avenue NE Spring Lake Park MN 55432 Business Phone 763-784-6491 Fax 763-792-7257 INSPECTION, TESTING AND MAINTENANCE OF FIRE PROTECTION SYSTEMS
SPRINKLER SYSTEM PLANS AND CALCULATIONS CHECK LIST 1. Working plans shall be drawn to an indicated scale, on sheets of uniform size, with a plan of each floor, and shall show those items from the following
I. Introduction Inspection and Testing Program Fire Protection Equipment State of Minnesota Emergencies seldom give warning before they strike. Thus, it is essential that fire protection equipment be inspected,
TRAINING AND EQUIPMENT MANUAL HOSE PRACTICES 301.010 ANNUAL SERVICE TEST FOR FIRE HOSE EFFECTIVE: OCTOBER 2007 The Department will test all fire hose annually. The testing of fire hose determines its serviceability.
Map Symbol: Preplan Exported: 1/13/2015 5:38:43 PM Layer Category: s, Simple AD Light AD- Light AD Mini Horn AD Speaker and Horn AD Water Bell AD- Mini Horn AD- Speaker and Horn AD- Water Bell Layer Description:
St. John s University Fire Safety Plan Founder s Village Townhouses Page 1 St. John s University Fire Safety Plan Part 1-Building Information Section Founder s Village Townhouses 8000 Utopia Parkway Jamaica
COMPREHENSIVE PROPERTY INSPECTIONS Thank you for selecting CPI for your Deficiency Observation. A full home inspection was not performed on this property at the buyers request. This inspection is a limited
Checklist for Residential Care Premises Name of Premises: Address of Premises: Name of Responsible Person: What area / location does the assessment cover? Does the assessment cover the whole site YES or
BUILDING OWNERS - SERVICE RELATED ISSUES FOR FIRE ALARM SYSTEMS Owners have numerous responsibilities as it pertains to the maintenance and operation of a building s fire safety equipment. The liabilities
Joint Commission expectations for Testing Fire Alarm and Sprinkler Systems Washington Society for Healthcare Engineering October 22, 2011 Yakima, Washington Managing the Process Documentation management.
Topic: Fire Jeopardy Reference #: DG 14-10 Level of Instruction: In service personnel Time Required: 1-2 hours Instructor Preparation: This drill requires some preparation in order for it to be successfully
FIRE PRE-PLAN FACILITIES SERVICES VOLUNTEER FIRE WARDENS & EMERGENCY RESPONSE MEMBERS KEELE CAMPUS & GLENDON CAMPUS Ken Wong, P.Eng. SFPE. Mgr., Building Code / Fire Protection Code Compliance Facilities
General Inspection FIRE SAFETY SELF-INSPECTION FORM FOR CULTURAL INSTITUTIONS 1. All Floors (inspect from top floor to basement): Yes are fire exits and directional signs properly illuminated? is the emergency