1 Increasing Cooling Tower Water Efficiency Chang Sub Kim Mentor: Melany Hunt Co-Mentors: Jim Cowell, John Onderdonk, Matthew Berbee Abstract In 2008, California Institute of Technology used 764,064,005 liters of water. Cooling towers at the central and satellite plants consumed 319,951,956 liters of water through evaporation and blowdown, contributing to over forty per cent of overall water usage on campus. In this Water Efficiency Project, the amount of water loss due to evaporation and blowdown each month has been studied and has demonstrated that on average, 83 per cent of water loss is due to evaporation and the rest due to blowdown. This project aims to improve overall water efficiency of cooling towers by examining two applicable systems that can recover vapor and reduce blowdown. An ozone treatment reduces the use of chemicals and thus decreases the blowdown rate. A vapor recovery system consisting of a circular fiber filter on top of cooling towers absorbs and condenses water vapor coming out of the cooling towers. A feasibility experiment showed that approximately 10 per cent of evaporated water could be recovered using this method. Further research should be carried out to study corrosion problems from the ozone treatment, and the type of the fiber filter that should be installed to optimize water vapor absorption without obstructing airflow. Introduction Water is one of the most vital resources on the Earth, but is becoming increasingly scarce. Numerous attempts to conserve water and reduce water pollution have been made by all kinds of organizations, from the federal government of the United States to research universities such as California Institute of Technology. Caltech currently employs various water-efficient technologies in an attempt to reduce its water consumption level through its Water Efficiency Project. In 2008, Caltech used 764,064,004 liters of water. Over half of the water was consumed through Caltech s own central and satellite utility plants. Each plant Figure 1 Satellite Plant Cooling Towers operates induced draft cooling towers with four cells. The cooling towers are used to lower the temperature of the water from condensers. A large fan pulls up cool and dry ambient air from below, and warm water sprayed near the top (Fig. 2) cools from evaporation and heat transfer to the cooler air. Warm, saturated air comes out of the cooling tower into the atmosphere (Fig. 1).
2 Eighty per cent of water used by Caltech s central and satellite plants is lost from the cooling towers. One factor of the water loss from cooling towers is evaporation. Concentration of chemicals (ions, acids, and so on) that are either originally present in water or added to increase cooling efficiency and reduce microbes increases after each cycle due to evaporation. As the concentration increases, ions might cluster together and form solids, the number of bacteria may increase significantly, thus decreasing overall cooling efficiency. Therefore, the concentration of solids should be maintained below a certain limit. Blowdown is used to adjust the concentration by bleeding and refilling cooling water. This process results significant water loss in cooling towers and also results water pollution. Increasing water efficiency of Caltech s cooling towers can lower overall water consumption significantly. Facilities employees currently attempt to decrease blowdown rate by controlling ph setup point cooling water ph at which blowdown valve opens. The ph level of cooling water increases as water evaporates and the chemical concentration increases. Setting higher ph tolerance level up to a point at which cooling Figure 2a Cooling Tower Mechanism Figure 2b Warm water spray inside the central plant cooling tower efficiency of cooling towers does not decrease significantly increases the number of cycles of cooling water per blowdown. Ozone treatment of cooling water is another possible solution to reduce blowdown. Ozone, a relatively unstable molecule composed of three oxygen atoms, acts as a strong biocide by oxidizing living organisms. Traditional chemical treatment to control microbes and prevent scaling requires frequent bleedoff of cooling water because of increase in concentration of chemicals due to evaporation. This further requires frequent refill of treatment chemicals. An alternative to the traditional chemical treatment is ozone treatment. As an effective microbial controller, ozone can replace chemicals to control microbes.
3 Ozone treatment, an alternative to traditional chemical treatments, can improve water efficiency substantially according to R.J. Strittmatter, et al 1. Ozone treatment for cooling water has several advantages over traditional controls: less or no use of chemicals (toxic and non-toxic), water conservation due to less blowdown (as less or no chemicals are used, the concentration level is much lower). However, there are several concerns about ozone treatment, including the impact on corrosion, effectiveness, and lack of general guidelines. The experiments by Strittmatter, et al show that ozone has a negligible impact on corrosion at typical use levels, does not increase mineral scales, controls fouling, and is excellent for microbial controls. Caltech had previously examined applicability of ozone treatment in its cooling towers, but did not introduce the treatment due to corrosion problems. Besides reducing blow, the amount of water used on campus can be reduced by reducing the amount of evaporative losses. Attempts to recover evaporation loss can be found in two Korean patents. Kyung Seok Kang uses hollow fiber membrane filter modules to recapture cooling water vapor 2 and Hoogeun Lee uses honeycomb, pleated or web-like fiber filters to absorb water vapor coming out of cooling towers 3. However, the amount of vapor that can be recovered from such systems is not indicated The ultimate goal of the Water Efficiency Project is to find applicable mechanisms which improve overall water efficiency of cooling towers. For this summer, a cooling tower prototype a humidifier and two different types of filters were installed and tested how much vapor dismissed from the humidifier can be absorbed by each filter. Results 1. Water Usage Data Analysis Data analysis on cooling tower water usage and its relation with cooling degree days was performed. Central cooling tower and satellite cooling tower s monthly make-up and blowdown levels are recorded in Utility Plant s monthly reports. The reports show that the cooling water make-up and blowdown levels are low during winter and increase during the summer (Fig. 3).
4 Figure 3 Central and satellite plants cooling tower water make-up and blowdown each month from January 2008 to May Note that the Satellite plant consumed noticeably more water before September Central plant s cooling towers did not operate as much as Satellite plant s as old chillers were being replaced by new ones. CT: Central Plant Cooling Tower. ST: Satellite Plant Cooling Tower A quantitative measure of how much cooling is needed each month is obtained in a form of monthly Cooling degree days (CDD) data from the weather station ID KCAPASAD5 (North Wilson Avenue, Pasadena, CA). Total cooling water make-up (central and satellite) correlates with cooling degree days each month (Fig. 4).
5 Total MU (L) Total BD (L) Tot Evap Loss (L) Evap Loss (%) ,681,702 3,326,936 12,354, ,855,822 2,798,660 12,057, ,661,875 3,733,099 11,928, ,863,949 4,283,935 17,580, ,068,764 5,368,045 20,700, ,981,472 3,100,954 27,880, ,708,885 7,476,796 27,232, ,378,625 6,009,274 33,369, ,802,806 6,060,792 35,742, ,020,676 5,407,563 31,613, ,162,689 3,682,414 21,480, ,764,691 2,264,479 14,500, ,689,875 2,837,459 16,852, ,335,177 1,759,709 9,575, ,027,879 1,602,960 15,424, ,111,629 3,468,847 19,642, ,247,090 3,743,130 22,503, Table 1 Total water make-up (MU), blowdown (BD) and evaporation loss by central and satellite cooling towers from January 2008 to May The percentage of evaporation loss is quite significant between 76 and 91 per cent each month.
6 Figure 4 Total water make-up (MU), blowdown (BD) and evaporation loss by central and satellite Cooling Towers and Cooling Degree Days (CDD). Water consumption by the cooling towers generally follows the trend of CDD as expected. However, it is noticeable that the water consumption during the summer break (June, July and August) does not increase as sharply as the CDD do. Figures 3 and 4 show that cooling water is lost more through evaporation than through blowdown. Numerical data of total make-up, blowdown and evaporative loss show that only 9 to 24 per cent of make-up water is lost through blowdown (Table 1). 2. Vapor Recovery Experiment In order to estimate how much vapor can be absorbed by different filters and parameters, a simple experiment was designed using an ultrasonic humidifier (Fig. 5) as a cooling tower prototype. Supply rate of vapor from the humidifier was calculated by dividing the difference of water remaining in the tank of the humidifier by amount of time passed. Time Passed Water Initial (ml) Water After (ml) Difference (ml) Rate (ml/min) 137 min min 20 sec min 1 sec Table 2 Amount of water emitted by the ultrasonic humidifier over different periods of time
7 Table 2 shows that 1.9 to 2.2 g of vapor was emitted by the humidifier per minute. This variation, with changing temperature and humidity levels in the laboratory, the source of error is estimated to be around 15 per cent. Two different types of filters fiber filter (Fig. 6) and pleated air filter (Figs. 7,8,9) are installed on top of a humidifier and the amount of time passed and according amount water (in grams) absorbed by each filter is measured. For fiber filter pad, variations in thickness and area were imposed. For pleated air filter, different orientations were used. Temperature of vapor coming out of the humidifier 23.5 C on average was measured in order to compare with the temperature of vapor from cooling towers estimated to be between 24 C and 30 C from cooling water temperature going into and coming out of Caltech s cooling towers. Figure 5 VICKS Ultrasonic Humidifier Attempts to measure air flow on top of the humidifier and after going through each filter was not successful as the flow was not constant without a Figure 6 Clockwise from left upper corner: fiber filter 1, 2, 3, and 4. Filters 1, 2, 3 are of same size. Filters 1 and 2 are about 1 cm thick. Filters 3 and 4 are of same thickness, about 2 cm thick Figure 7 Pleated air filter in horizontal orientation filter on top, and filters in horizontal orientation obstruct most of the air flow. Figure 10 shows a relationship between the amount of time and the amount of vapor absorbed by fiber filter 1. Vapor absorption is linear with time before saturation and concaves down afterwards.
8 Figure 8 Single walled pleated air filter in vertical orientation Figure 9 Multiple walled pleated air filter in vertical orientation Figure 10 Vapor absorption versus time of fiber filter 1. The relationship is linear (solid line) before saturation and concave down (dotted line) as the filter gets saturated.
9 Figure 11 Vapor absorption versus time of thin and thick fiber filters Figure 11 shows that the vapor absorption by thin and thick filters is almost identical before saturation. The slope of both curves is approximately 0.2 g/min in the linear region. However, vapor absorption of thick filter concaves down more slowly than that of thin filter, indicating higher saturation level. The thin filter seems to begin deviating from the linear relation around 10 grams of water while the thick filter seems to deviate around 20 grams of water. Hence, the filters may become saturation when they have absorbed 10 g of water per 1 cm of filter. Figure 12 Vapor absorption versus time of large and small filters
10 There is no significant difference in vapor absorption between small and large filters before saturation. Figure 12 shows that vapor absorption of large filters concaves down more slowly than that of small filters, indicating higher saturation level. Figure 13 Vapor absorption versus time of horizontal and vertical pleated air filters There is no significant difference in vapor absorption between vertical and horizontal filters before saturation. Although there is not enough data points no points between 4 hours and 14 hours to draw a conclusion, vapor absorption of horizontal filter concaves down more slowly than that of thin filter, indicating higher saturation level. Since both horizontal and vertical filters have same filter size, differing saturation levels seem to be due to filters orientations.
11 Figure 14 Vapor absorption versus time of single and multiple concentric vertical pleated air filters The data presented in figure 14 demonstrate that the results are similar for the single walled and multiple walled filters before saturation. Vapor absorption of multiple walled filter concaves down more slowly than that of single walled filter, indicating higher saturation level. Figures 10, 11, 12, 13, and 14 show that vapor absorption is linear with time until saturation, thickness and area do not scale proportionally with vapor absorption, vertical orientation results lower saturation than horizontal orientation, and multiple walled filter absorbs much faster than singled walled one. From the data points, around 10 per cent of vapor emitted from the humidifier was captured by the fiber filters and between 3 and 6 per cent by pleated air filter before getting saturated. Applying to Caltech s cooling towers, such filters can save around 16 million liters per year. Discussion Caltech cannot use seawater for cooling purposes due to its location over thirty miles from the ocean and fresh water is becoming scarcer every year. Cooling towers recycles their cooling water while keeping high cooling efficiency, yet takes up forty two per cent of Caltech s total water consumption. Recovering a small amount of vapor dismissed from Caltech s cooling towers by use of fiber filters can improve overall water efficiency significantly. Further research should be carried on to find optimal thickness, area, and orientation of filter extensive parameter study. Efficient ways to extract condensed vapor from saturated filters and practical application to cooling towers should be studied thereafter. Methods Acquisition of Cooling Water Data. Daily readings of central utility plant (cooling) tower and satellite plant (cooling) tower blowdown, water softners, central plant s condensate tank make up, chilled water, chilled water expansion tank, and demineralizers are recorded at between 23:00
12 and 24:00 in Central Utility Plant Operation Log. The amount of water make up for SP cooling tower is same as the amount of water softeners produced from SP, and the amount of water make up for CUP cooling tower is the amount of condensate tank make up, chilled water, water going into chilled water expansion tank and amount of demineralizers subtracted from water softeners produced from CP. Acquisition of Cooling Water Data. Central Utility Plant WaterLab provided Monthly Chemical Usage Report. Each report shows the amount of chemicals (inhibitor, dispersant/surfactant, biocides, antifoam and bromine) used for CUP, SUP, and IMSS cooling towers. Acquisition of Cooling Fan Speed and Temperature Data. The speeds of four cooling fans of CUP, supply temperature (supplying to condensers from cooling towers) of CUP, and supply and return (returning from cooling towers to condensers) temperatures of SP are recorded every minute by computer. Averaging into hourly, daily, weekly, and monthly data was performed by Matlab 2009a. Daily, weekly, and monthly Cooling degree days (CDD) data of weather station ID KCAPASAD5 (North Wilson Avenue, Pasadena, CA) are obtained from Experiment tools. VICKS Ultrasonic Humidifier V5100NS (cooling tower prototype), Marineland Rite-Size Bonded Filter Pad (fiber filter), Flanders extended surface area Pleated Air Filter (pleated air filter), OHAUS PRECISION Standard Model TS120S (scale), Dwyer Model 471 Digital Thermo Anemometer. References 1. Strittmatter, R. J., B. Yang, et al. (1992). "Application of Ozone in Cooling Water Systems." Homel Co., Ltd. Kang, K.S, inventor; Recovery System for Cooling Water at Cooling Tower, Capable of Reducing Water Consumption by Improving Recovery Ratio of Vapor and Mist. Korea Patent Aug. 31, Lee, Hoogeun. Cooling Water Recovery System Using Fiber Filter and its Operating Methods. Korea Patent Feb. 16, 2005.
Data Center Design Guide featuring Water-Side Economizer Solutions with Dynamic Economizer Cooling Presenter: Jason Koo, P.Eng Sr. Field Applications Engineer STULZ Air Technology Systems jkoo@stulz ats.com
Data Realty Colocation Data Center Ignition Park, South Bend, IN Owner: Data Realty Engineer: ESD Architect: BSA LifeStructures Project Overview Data Realty is a data center service provider for middle
how to use a simplified psychrometric chart Air Properties Temperature and Relative Humidity This NebGuide describes how to use a simplified psychrometric chart to better understand the relationships between
COMMERCIAL HVAC EQUIPMENT Condensers and Cooling Towers Technical Development Programs (TDP) are modules of technical training on HVAC theory, system design, equipment selection and application topics.
CONDENSERS AND CONDENSER COOLING SYSTEMS INTRODUCTION Conventional cooling methods of thermal power plants are extremely water intensive processes. Once-through cooling needs large natural bodies of water
What factors determine the energy efficiency of a data centre? Where is the energy used? Local Climate Data Hall Temperatures Chiller / DX Energy Condenser / Dry Cooler / Cooling Tower Energy Pump Energy
Reuse of Alternative Water Sources for Cooling Tower Systems Two Case Studies Using Non-Traditional Water Sources Matthew L. Haikalis Veolia Water Solutions & Technologies April 24, 2013 Operational Priorities
White paper: Direct heat recovery from refrigeration and cooling systems vs geoscart ground coupling Dr A. Leiper, N. Rivers and D. Zaynulin August 2014 Greeneld Energy Limited 1-2 St Andrews Hill London
Atmosphere SECTION 11.1 Atmospheric Basics In your textbook, read about the composition of the atmosphere. Circle the letter of the choice that best completes the statement. 1. Most of Earth s atmosphere
Chapter 3.4: HVAC & Refrigeration System Part I: Objective type questions and answers 1. One ton of refrigeration (TR) is equal to. a) Kcal/h b) 3.51 kw c) 120oo BTU/h d) all 2. The driving force for refrigeration
AIR WASHER PROGRAMS THE BASIC SECTIONS OF AN AIR WASHER: The basic components of an air washer system are a chamber that contain a series of spray nozzles, an eliminator section that removes water from
_ENNTEC WATER TREATMENT SOlUTioNS Industrial Water Supply Water is widely used in industry, whether it is encountered as raw water, process water or waste water. Very often make-up water must be treated
Water Efficiency Water Management Options Boilers for Commercial, Industrial and Institutional Facilities Boiler Water Impurities All boiler make-up water contains impurities. As clean steam is released
GAS TURBINE EFFICIENCY IMPROVEMENT BY INLET AIR-COOLING IN SUSTAINABLE ENERGY SYSTEM Omid Zainali 1* and Saeed Karimi Alavijeh 2 National Iranian Gas Company (NIGC), Assaluyeh, Bushehr, Iran 1* National
MEBS6006 Environmental Services I http://www.hku.hk/bse/mebs6006 Condensation and Heat Rejection Dr. Benjamin P.L. Ho Department of Mechanical Engineering The University of Hong Kong E-mail: firstname.lastname@example.org
Vocabulary #1 Independent Variable Dependent Variable Control Group Matter Boiling Point Melting Point Freezing Point Evaporation Condensation Mass A variable that is intentionally changed to observe its
International Telecommunication Union ITU-T TELECOMMUNICATION STANDARDIZATION SECTOR OF ITU Technical Paper (13 December 2013) SERIES L: CONSTRUCTION, INSTALLATION AND PROTECTION OF TELECOMMUNICATION CABLES
SECTION 5 COMMERCIAL REFRIGERATION UNIT 22 CONDENSERS UNIT OBJECTIVES After studying this unit, the reader should be able to explain the purpose of the condenser in a refrigeration system. describe differences
FINDINGS OF A DETAILED ENERGY AUDIT AT A CHEMICAL PLANT IN SINGAPORE Main Energy Consuming Systems Process chiller system Brine chiller system Process cooling tower water system Air Compressors Boilers
Practical Environmental Measurement Methods Trace Gas Exchange Measurements with Standard Infrared Analyzers Last change of document: February 23, 2007 Supervisor: Charles Robert Room no: S 4381 ph: 4352
DIRECT EVAPORATIVE COOLING PAD The only evaporative media with a saturation efﬁciency over 90% using less than 50% of the volume. Modular Plug & Play design. PRODUCT DATA SHEET DESCRIPTION The OXYVAP Pad
Project No TREN/FP7EN/218952 ALONE small scale solar cooling device Collaborative Project Small or Medium-scale Focused Research Project DELIVERABLE D5.2 Start date of the project: October 2008, Duration:
How does solar air conditioning work? In a conventional air conditioning system; The working fluid arrives at the compressor as a cool, low-pressure gas. The compressor is powered by electricity to squeeze
AIT Partnership Group Ltd White Paper: Free Cooling and the Efficiency of your Data Centre Using free cooling methods to increase environmental sustainability and reduce operational cost. Contents 1. Summary...
A discussion of condensate removal systems for clarifier and thickener drives for water and wastewater facilities. Richard L. Dornfeld, BSME, P.E. Staff Engineer September 25, 2014 Moisture can be a problem
Condensing Economizers Workshop Enbridge Gas, Toronto MENEX Boiler Plant Heat Recovery Technologies Prepared by: Jozo Martinovic, M A Sc, P Eng MENEX Innovative Solutions May 15, 2008 MENEX INC. 683 Louis
Analysis of data centre cooling energy efficiency An analysis of the distribution of energy overheads in the data centre and the relationship between economiser hours and chiller efficiency Liam Newcombe
CHAPTER 6: WEATHER FOR SOARING Weather patterns on Earth are complicated and chaotic. Weather is a result of the atmosphere s constant attempt to reach equilibrium. This equilibrium is continually upset
Since its founding in 1976, EVAPCO, Incorporated has become an industry leader in the engineering and manufacturing of quality heat transfer products around the world. EVAPCO s mission is to provide first
Total Heat Versus Sensible Heat Evaporator Selection Methods & Application Scope The purpose of this paper is to provide specifying engineers, purchasers and users of evaporators in industrial refrigeration
Green Walls Green walls are self-sufficient vertical gardens that are attached to the exterior or interior wall of a building. The plants receive all the water and nutrients they require from within the
International Journal of Engineering Research and Development e-issn: 2278-067X, p-issn : 2278-800X, www.ijerd.com Volume 5, Issue 3 (December 2012), PP. 87-92 Waste Heat Recovery through Air Conditioning
Wet Scrubbers for Gasifier Gas Cleaning Paper # 49 Andrew C. Bartocci Envitech, Inc. 2924 Emerson Street- Suite 320 San Diego, CA 92106 Ph: 619-223-9925, ext. 203 ABSTRACT Concern for global climate change
Page 1 of 64 1.0 PURPOSE BOILER SYSTEMS Two utility boilers are designed to supply 125,000 lbs/hr each of superheated steam to maintain the Super High Pressure Steam Header at 1500 psig. They are to be
Opening Throttled Discharge Valves This 21-story building, constructed in 1997, is located in Oregon and contains 589,000 gross square feet of mostly office occupancy. The HVAC system includes six large
CURBING THE COST OF DATA CENTER COOLING Charles B. Kensky, PE, LEED AP BD+C, CEA Executive Vice President Bala Consulting Engineers OVERVIEW Compare Cooling Strategies in Free- Standing and In-Building
Absolute and Relative Gas Concentration: Understanding Oxygen in Air Bruce Bugbee and Mark Blonquist Absolute and Relative Gas Concentration Gas concentration is described in two ways, absolute and relative
VACUUM REFRIGERATION SYSTEMS CHILL VACTOR The Croll-Reynolds CHILL-VACTOR is a chiller that uses a vapor flashing process. Water has a pressure-temperature relationship which is its boiling point. If its
Global warming and its implications for conservation. 4. Greenhouse gasses and the lapse rate The layer model is a reasonable heuristic model, but it assumes that the atmosphere acts as a perfect blackbody
Forgotten savings: Heat recovery from surface blowdown 1. Introduction The purpose of this article is to inform thermal plant operators of the interesting fuel savings that can be obtained by recovering
Intelligent Process Cooling: Saving Money, Protecting the Environment & Curing Process Headaches Stephen Petrakis Frigel North America, Inc. 2008 All Contents Copyright Frigel Firenze & Frigel North America,
Refrigeration Basics 101 By: Eric Nelson Basics Refrigeration is the removal of heat from a material or space, so that it s temperature is lower than that of it s surroundings. When refrigerant absorbs
Q. The diagram shows two thermometers. The bulb of each thermometer is covered with a piece of wet cotton wool. One of the thermometers is placed in the draught from a fan. The graph shows how the temperature
GEO 101: PHYSICAL GEOGRAPHY Chapter 07: Water and Atmospheric Moisture Water on Earth Unique Properties of Water Humidity Atmospheric Stability Clouds and Fog Water on Earth The origin of water A scientific
Lecture 23: Terrestrial Worlds in Comparison Astronomy 141 Winter 2012 This lecture compares and contrasts the properties and evolution of the 5 main terrestrial bodies. The small terrestrial planets have
HUMIDIFICATION SYSTEMS: A COST AND EFFICIENCY COMPARISON The requirements of modern industrial processes, as well as more stringent indoor air quality (IAQ) standards, have resulted in an increased demand
UNIT 6a TEST REVIEW 1. A weather instrument is shown below. Which weather variable is measured by this instrument? 1) wind speed 3) cloud cover 2) precipitation 4) air pressure 2. Which weather station
ES 106 Laboratory # 6 MOISTURE IN THE ATMOSPHERE 6-1 Introduction By observing, recording, and analyzing weather conditions, meteorologists attempt to define the principles that control the complex interactions
Microbiological Control Strategy in Cooling Tower Systems By Dave Christophersen, CWT Originally Published: CSTR February 2006 Because evaporative cooling tower systems are open to the atmosphere and sunlight,
Unit 2: Weather Weather Lore: ways to keep track of common trends in weather patterns some have scientific facts, while others are more about coincidence weather lore may vary from place to place as different
Sci. Revs. Chem. Commun.: 3(2), 2013, 128-132 ISSN 2277-2669 SOLAR WATER PURIFICATION WITH THE HELP OF CSP TECHNOLOGY JINESH S. MACHALE *, PRACHI D. THAKUR, PIYUSH S. LALWANI and GAYATRI M. APTE Department
Overview This Unit covers the competences required to inspect complex/central air conditioning systems as defined by the CIBSE TM 44 Figure 1.1: Summary of system types and their component parts. The air
IMPROVING ENERGY EFFICIENCY IN COOLING TOWER DESIGN Environmental Impacts of Buildings > 39% of total energy use* > 70% of electricity consumption* > HVAC accounts for 40-60% of the energy used in US commercial
Atmosphere 1. Insulator maintains our T balance (500 degrees F, T changes without it) 2. Shield from meteors 3. Ocean of air dynamic, distributes heat Look at Mr. Moon: 1. Temps light side- 400 degrees
Feasibility of a Hybrid Cooling System in a Thermal Power Plant C. R. WILLIAMS AND M.G. RASUL * College of Engineering and Built Environment Faculty of Sciences, Engineering and Health, Central Queensland
- White Paper - State of the Art Energy Efficient Data Centre Air Conditioning - Dynamic Free Cooling - Release 2, April 2008 Contents ABSTRACT... 3 1. WHY DO I NEED AN ENERGY EFFICIENT COOLING SYSTEM...
EE 4900: Fundamentals of Sensor Design Lecture 10 Humidity Sensing and Flow Sensing 1 2 Humidity Sensing Humidity Sensing Q: What are we measuring? A: Water vapor content in air and other gases. 3 Usually
KEY CONCEPT Most clouds form as air rises and cools. BEFORE, you learned Water vapor circulates from Earth to the atmosphere Warm air is less dense than cool air and tends to rise NOW, you will learn How
1/20/14 2014 Service Technician Training Program Closed Loop Systems Daniel S. Krack, CWT 2 Closed Loop Cooling and Heating The Closed Loop Cooling Advantages High Efficiency Chillers, Heat Exchangers,
Chapter 6 Atmospheric Aerosol and Cloud Processes Spring 2015 Cloud Physics Initiation and development of cloud droplets Special interest: Explain how droplet formation results in rain in approximately
I-STUTE Project - WP2.3 Data Centre Cooling Project Review Meeting 8, Loughborough University, 29 th June 2015 Topics to be considered 1. Progress on project tasks 2. Development of data centre test facility
A car air-conditioning system based on an absorption refrigeration cycle using energy from exhaust gas of an internal combustion engine G Vicatos J Gryzagoridis S Wang Department of Mechanical Engineering,
Common Defects in Digital Printing Paul Geldenhuys & Amir Shapira January, 2009 Overview Ambient Influences Humidity Temperature Sunlight & UV Abrasion Chemical Resistance Common Defects in Digital Printing
Name Weather Unit Test Page 1 1 The diagram below shows the flow of air over a mountain from point A to point C. Which graph best shows the approximate temperature change of the rising and descending air
Ocean and Weather Name: Period: Date: Essential Question: How does the ocean affect climate and weather on land? On the left is the Illustration of major ocean currents throughout the globe. Ocean currents
SECOND GRADE 1 WEEK LESSON PLANS AND ACTIVITIES WATER CYCLE OVERVIEW OF SECOND GRADE WATER WEEK 1. PRE: Exploring the properties of water. LAB: Experimenting with different soap mixtures. POST: Analyzing
K4. Triple Point of Nitrogen I. OBJECTIVE OF THE EXPERIMENT We will study the temperature-pressure diagram of nitrogen, in particular the triple point. II. BAKGROUND THOERY States of matter Matter is made
ENGINE REPAIR UNIT 5: LUBRICATION AND COOLING SYSTEMS DIAGNOSIS AND REPAIR LESSON 3: COOLING SYSTEM FUNCTION AND COMPONENTS I. Terms and definitions A. Coolant Fluid that carries excessive heat from the
Portable Evaporative Air Cooler OWNER S MANUAL Read and save these instructions before use Model: CL48PM Power rating: 130 Watts Voltage rating: 230 Volt, 50Hz Made in P.R.C. QUICK START GUIDE Fill with
VII. Commercial - Industrial Cooling Water Efficiency 1.0 Background Commercial and industrial (mechanical) cooling systems have become commonplace throughout the United States and the world over the last
Objectives Increase awareness of the types of economizers currently used for data centers Provide designers/owners with an overview of the benefits and challenges associated with each type Outline some
National Competency Based Skill Training Refrigeration and Air-conditioning Mechanic Logbook Trainee:... Training Provider:... Year:... Trainee Contact no:... Competency Based Skill Training Logbook Introduction
Chem 100 Section Experiment 5 Name Partner s Name Chemical Reactions: Making Table Salt Introduction During chemical reactions, substances combine with each other in a definite proportion by mass, meaning
HVAC Systems: Overview Michael J. Brandemuehl, Ph.D, P.E. University of Colorado Boulder, CO, USA Overview System Description Secondary HVAC Systems Air distribution Room diffusers and air terminals Duct
Bytes and BTUs: Holistic Approaches to Data Center Energy Efficiency NREL 1 National Renewable Energy Laboratory Presentation Road Map A Holistic Approach to Efficiency: Power, Packaging, Cooling, Integration
Lesson 36 Selection Of Air Conditioning Systems Version 1 ME, IIT Kharagpur 1 The specific objectives of this chapter are to: 1. Introduction to thermal distribution systems and their functions (Section
Lubrication System Lecture-10 Introduction In engines, frictional losses are mainly due to sliding as well as rotating parts Engine friction is expressed in terms of frictional power f p =i p -b p Frictional
COMMERCIAL HVAC CHILLER EQUIPMENT Air-Cooled Chillers Technical Development Programs (TDP) are modules of technical training on HVAC theory, system design, equipment selection and application topics. They