# ADS, Inc. Drainage Handbook Hydraulics 3-1

Save this PDF as:

Size: px
Start display at page:

## Transcription

1 ADS, Inc. Drainage Handbook Hydraulics HYDRAULICS TABLE OF CONTENTS 3-1 Overview of Hydraulic Considerations Design Manning s Value Discharge Curves The Conveyance Method Minimum Velocity Considerations Maximum Velocity Considerations Long Term Pressure Considerations Culvert Considerations Example Problems Footnotes Figures Tables 3-1 Discharge Rates for ADS Corrugated Pipe with Smooth Interior Liner Discharge Rates for ADS Single Wall Heavy Duty and Highway Pipe Discharge Rates for ADS Triplewall and Smoothwall Sewer & Drain Pipe Conveyance Factors (Standard Units) Conveyance Factors (Metric Units) Entrance Loss Coefficients BUYER/USER IS RESPONSIBLE FOR SERVICEABILITY OF THE PRODUCT IN ANY GIVEN APPLICATION. SELLER IS NOT RESPONSIBLE FOR INJURY OR DAMAGE RESULTING FROM IMPROPER INSTALLATION, NONCOMPLIANCE WITH THESE GUIDELINES FOR INSTALLATION OF PRODUCT, OR USE OUTSIDE THE GUIDELINES SET FORTH HEREIN.

2 ADS, Inc. Drainage Handbook Hydraulics OVERVIEW OF HYDRAULIC CONSIDERATIONS The Manning s equation is the most widely recognized means of determining pipe capacity for gravity flow installations. As such, it provides the basis of the hydraulic design consideration for corrugated high density polyethylene (HDPE) and polypropylene (PP) pipe. Discharge curves allow pipe sizing through use of graphs once the design capacity requirements and slope have been established. Each product will have its own discharge curve based on its Manning s n value. This section provides flow capacities based on recommended design "n" values for ADS products. It should be noted that factors such as bends, manhole connections, debris and sediment result in hydraulic losses that will affect actual flow capacity and should be considered in final pipe selection. By reducing all of the coefficients and constants in the Manning equation down to a single factor, called the conveyance factor (K), another method of pipe sizing can be utilized. By knowing the Manning s n value for various pipe materials, the use of conveyance factor charts will allow the designer to develop comparative product options easily. Use of this method frequently results in more than one satisfactory pipe type and size for a given drainage need, thereby allowing the designer to compare product options in order to determine the most cost-effective solution. Final pipe selection should also include a review of the velocity conditions. Higher flow velocities help keep sediment contained in stormwater from settling along the bottom of the pipe. A reduction in sediment can also reduce the frequency of maintenance and help ensure that the hydraulic function of the pipe will continue throughout its design life. These velocities, however, must be kept within the maximum performance limits of the pipe and the associated facility. 3-2 DESIGN MANNING S VALUE Within the pipe industry, there is a wide range of Manning s n values, or roughness coefficients, for various types of pipe. Several items should be considered prior to selecting an n value for a given pipe material when designing any gravity flow system. 1. Manning s n values developed for any given pipe material will depend on depth of flow for partially full pipe and flow velocity for full flow conditions. Manning s n values are commonly provided for full flow conditions, but should not be assumed unless specifically noted. For most calculations, n is assumed to be constant; however, it shall be the discretion of the individual designer to use a constant or varying n value.

3 ADS, Inc. Drainage Handbook Hydraulics Storm sewers, culverts and sanitary sewers are typically subject to collection of debris and sediment, which adversely effect flow rates. Consideration should be given for the collection of debris and sedimentation and adjust the design n value accordingly. Pipe inside surface texture, geometry, joint opening and pipe material can also influence collection of debris and sedimentation depending on the susceptibility of the debris to either adhere to the pipe surface or be trapped and caught by other obstructions. Tests conducted at Utah State University Water Research Laboratory show minimum Manning s n values of less than for corrugated HDPE pipe with a smooth interior liner. To accommodate actual field conditions and to incorporate a safety factor, ADS recommends using a Manning s n value of for corrugated HDPE and PP products with a smooth interior liner. There is considerable justification for both HDPE and PP products to be designed with the same Manning s n value. Both smooth interior products are made using the same mold blocks and are produced on the same manufacturing equipment. From a material standpoint, both HDPE and PP are polyolefin materials, very similar in chemical makeup, that behave similarly during processing. Also, ADS performs regular internal quality checks which assure the liner roughness of polypropylene is equal to, if not better than, the liner roughness of HDPE products with an established Manning s n value of In general, it is common engineering practice to include a safety factor of 20-30% to the Manning s values determined during laboratory testing. However, it should be noted, this practice is not utilized for most Manning s n values provided for metal pipes. Recommended design Manning s n values for all ADS pipe products are listed in Table 3-1.

4 ADS, Inc. Drainage Handbook Hydraulics DISCHARGE CURVES The mathematical relationship of the terms included in the Manning s formula is often shown graphically through discharge curves. Discharge curves are one method of selecting an adequate pipe size, once the required capacity and slope have been determined. Discharge curves for ADS HDPE and PP pipe products under gravity flow steady state conditions are shown in Figures 3-1 through 3-3.

5 ADS, Inc. Drainage Handbook Hydraulics 3-5 Figure 3-1 Discharge Rates for ADS Corrugated Pipe with Smooth Interior Liner fps (12.2m/s) fps (10.7m/s) Flow capacity (cfs) % 0.10% 1.00% 10.00% 60 (1500mm) 54 (1350mm) 48 (1200mm) 42 (1050mm) 36 (900mm) 30 (750mm) 24 (600mm) 18 (450mm) 15 (375mm) 12 (300mm) 10 (250mm) 31 fps (9.4m/s) 27 fps (8.2m/s) 25 fps (7.6m/s) 23 fps (7.0m/s) 21 fps (6.4m/s) 19 fps (5.8m/s) 17 fps (5.2m/s) 15 fps (4.6m/s) 13 fps (4.0m/s) 10 fps (3.0m/s) 9 fps (2.7m/s) 8 (200mm) 7fps (2.1m/s) 6fps (1.8m/s) 5fps (1.5m/s) 8 fps (2.4m/s) 4fps (1.2m/s) (150mm) 2fps (0.6m/s) 3fps (0.9m/s) fps (0.3m/s) 4 (100mm) 0.02% 0.03% 0.04% 0.05% 0.20% 0.30% 0.40% 0.50% 2.00% 3.00% 4.00% 5.00% 1cfs = m 3 /s 1ft/s = m/s 1% = 0.01 ft/ft Slope of pipe in feet per 100ft (%slope) 1. Applicable products: N-12, MEGA GREEN, N-12 STIB, N-12 WTIB, HP STORM, SaniTIte, SaniTite HP, N- 12 Low Head Note: Based on a design Manning s n of Solid lines indicate pipe diameters. Dashed lines indicate approximate flow velocity. Redeveloped from FHWA HDS 3 Design Charts for Open-Channel Flow 2

6 ADS, Inc. Drainage Handbook Hydraulics 3-6 Figure 3-2 Discharge Rates for ADS Single Wall Heavy Duty and Highway Pipe fps (3.0m/s) (600mm) 9 fps (2.7m/s) Flow capacity (cfs) (450mm) 15 (375mm) 12 (300mm) 10 (250mm) 8 fps (2.4m/s) 7 fps (2.1m/s) (200mm) 6 fps (1.8m/s) (150mm) 4fps (1.2m/s) fps (1.5m/s) fps (0.6m/s) 3fps (0.9m/s) 4 (100mm) 1fps (0.3m/s) 3 (75mm) % 0.02% 0.03% 0.04% 0.05% 0.10% 0.20% 0.30% 0.40% 0.50% 1.00% 10.00% 2.00% 3.00% 4.00% 5.00% Slope of pipe in feet per 100ft (%slope) 1cfs = m 3 /s 1ft/s = m/s 1% = 0.01 ft/ft Note: Based on a design Manning s n described in Table 3-1 for respective diameter. Pipe may not be available in all diameters shown. Solid lines indicate pipe diameters. Dashed lines indicate approximate average velocity.

7 ADS, Inc. Drainage Handbook Hydraulics Figure 3-3 Discharge Rates for ADS TripleWall and Smoothwall Sewer & Drain Pipe Flow capacity (cfs) fps (2.4m/s) 7fps (2.1m/s) 6fps (1.8m/s) 10 fps (3.0m/s) (150mm) 9 fps (2.7m/s) fps (0.9m/s) 4fps (1.2m/s) 5fps (1.5m/s) fps (0.6m/s) (100mm) 1fps (0.3m/s) 3 (75mm) % 0.02% 0.03% 0.04% 0.05% 0.10% 0.20% 0.30% 0.40% 0.50% 1.00% 2.00% 3.00% 10.00% 4.00% 5.00% Slope of pipe in feet per 100ft (%slope) 1cfs = m 3 /s 1ft/s = m/s 1% = 0.01 ft/ft Note: Based on a design Manning s n of Solid lines indicate pipe diameters. Dashed lines indicate approximate average velocity.

8 ADS, Inc. Drainage Handbook Hydraulics THE CONVEYANCE METHOD Conveyance provides a convenient means of selecting a variety of pipe options that will satisfy a project s flow requirements. Conveyance factors are based on a greatly simplified version of the Manning s equation shown in Equation 3-1 and 3-1 (a). In the following discussion, example problems and subsequent sections, the pipe is assumed to be flowing full. This assumption typically allows for a simplified, yet accurate analysis of the given conditions. Each project should be evaluated on a case-by-case basis to determine the best, most-representative design method. (1.486)(A)(R Q = n 2 / 3 )(S 1/ 2 ) Equation 3-1 Where: Q = pipe capacity, (cfs) n = Manning s n A = cross-sectional flow area of the pipe (ft. 2 ) R = hydraulic radius (ft.): R = A P P = Wetted perimeter (ft); Pipe inside circumference, or (π)(inside diameter) for full flowing pipe conditions S = pipe slope (feet/foot) Or, in metric units: 2 / 3 (A)(R )(S Q = n 1/ 2 ) Equation 3-1(a) Where: Q = pipe capacity, m 3 /s n = Manning s n A = cross-sectional flow-area of the pipe (m 2 ) P = Wetted perimeter (ft); Pipe circumference, or (π)(diameter) for full flowing pipe conditions R = hydraulic radius (m), R = A P S = pipe slope (m/m)

9 ADS, Inc. Drainage Handbook Hydraulics 3-9 For a specific full-flowing pipe installation, the parameters n, A, and R are easily defined constants. The flow-carrying ability, or conveyance factor, of the pipe can then be defined as shown in Equation 3-2 or 3-2(a). (1.486)(A)(R k = n 2 / 3 ) Equation 3-2 Or, in metric units: (A)(R k = n 2 / 3 ) Equation 3-2(a) By substitution, the Manning s formula can then be reduced to the following equation. 2 Q = k S 1/ Equation 3-3 Equation 3-3 can also be written as shown in Equation 3-4. Q k = Equation 3-4 1/ 2 S Direct substitution of design conditions into Equation 3-4 will determine the minimum conveyance factor allowed. Table 3-2 or 3-2 is then used as a guide to select a pipe having a conveyance factor of at least that calculated. Table 3-1 and 3-2 require knowledge of the Manning s n value. These tables can also be used for any materials if the specific Manning s n is known. The Manning s n is a critical value in the conveyance concept. Among pipes of the same diameter and slope, Manning s n will be the only factor that will have an effect on conveyance, and therefore capacity. When comparing identical field conditions, conveyance has a direct relationship to capacity. That is, if the slope is held constant, tripling conveyance will triple the capacity; halving conveyance will halve the capacity. Example problems involving conveyance factors are explained in a subsequent section.

10 ADS, Inc. Drainage Handbook Hydraulics 3-10 Table 3-1 Conveyance Factors (Standard Units) Design Manning s Values for ADS Thermoplastic Pipe * Product Diameter Design Manning s n N-12, MEGA GREEN, N-12 STIB, N-12 WTIB, 4-60 n = HP STORM, SaniTite, SaniTite HP, N-12 Low Head Single Wall Highway and Heavy Duty * n = n = n = n = n = TripleWall and Smoothwall Sewer & Drain 3-6 n = ** Conveyance Equations: k = Q/(s^0.5) Q = k s^0.5 Conveyance Factors for Circular Pipe Flowing Full Manning s "n" Values Dia. (in.) Area (sq. ft.) * Corrugated Polyethylene Pipe Association (2000) Hydraulic Considerations for Corrugated Polyethylene Pipe ** Lingedburg, Michael, Civil Engineer Reference Manual 4 ADS, Inc., July 2010

11 ADS, Inc. Drainage Handbook Hydraulics 3-11 Table 3-2 Conveyance Factors (Metric Units) Design Manning s Values for ADS Thermoplastic Pipe * Product Diameter Design Manning s n N-12, MEGA GREEN, N-12 STIB, N-12 WTIB, mm n = HP STORM, SaniTite, SaniTite HP, N-12 Low Head Single Wall Highway and Heavy Duty * mm mm 250mm 200mm mm n = n = n = n = n = TripleWall and Smoothwall Sewer & Drain mm n = ** Conveyance Equations: k = Q/(s^0.5) Q = k s^0.5 Conveyance Factors for Circular Pipe Flowing Full Manning s "n" Values Dia. (mm) Area (sq. m.) * Corrugated Polyethylene Pipe Association (2000) Hydraulic Considerations for Corrugated Polyethylene Pipe ** Lingedburg, Michael, Civil Engineer Reference Manual 4 ADS, Inc., July 2010

12 ADS, Inc. Drainage Handbook Hydraulics MINIMUM VELOCITY CONSIDERATIONS Sediment can reduce the capacity of a stormwater pipe over time. In some installations, it may render the pipe useless until the system can be cleaned. This is an expensive, time-consuming undertaking so preventative measures should be taken during design. Sedimentation is of great concern in sewer applications since large, heavy grit may be present. To minimize potential problems, flow should be maintained at a minimum, or self-cleansing, velocity. A commonly accepted selfcleansing velocity for storm and sanitary sewers is 3 fps (0.9 m/s). In each design, a final check should be performed to compare the expected velocity with the self-cleansing velocity. The design velocity for fullflowing pipes can be approximated with Equation 3-5: Q V = A Equation 3-5 The potential for settling is determined by the specific gravity and diameter of particle, its cohesive properties, flow velocity, and the roughness of the pipe interior. For further discussion on the complexities and variables associated with determining the self-cleansing velocity for a specific pipe diameter and material, refer to ASCE publication No. 60, Gravity Sanitary Sewer Design and Construction. In some specialized installations where sediment is a known problem it may be wise to perform a soil analysis prior to final drainage design. 3-5 MAXIMUM VELOCITY CONSIDERATIONS High flow velocity can also create problems if not properly taken into consideration. High velocity is usually considered to be approximately 12 fps (3.7 m/s) but can vary depending on the specific site conditions. The preferred method of contending with high velocity is to look for opportunities to minimize it, such as reducing the slope of the pipe. If that is not feasible, and many times it is not, the velocity must simply be managed the best way possible. High velocity, especially if it carries an abrasive effluent, can present durability problems. Over time, the invert of the pipe can wear prematurely. Thermoplastics resist the effects of these rigorous conditions better than many other traditional pipe materials. Additional information specific to the effects of abrasives on many types of pipe materials is provided in the Durability section (Section 4) of the Drainage Handbook. Special consideration should also be given to the conditions at the pipe outlet. High flow velocity can erode the channel where the flow is deposited. Erosion management methods, such as rip-rap, should be considered in these areas. ADS, Inc., July 2010

13 ADS, Inc. Drainage Handbook Hydraulics 3-13 Another consideration in high velocity applications is managing the momentum of the flow. Changes in flow direction will result in large forces that can cause pipe movement, especially if the pipe size is large, velocity is very high, and the native soil has a low bearing strength. Concrete thrust blocks positioned at areas of flow direction change and sized specifically for the site conditions can be used to control the effects of momentum. Anchoring systems may also need to be considered when the velocity is high or the slope that the pipe is installed is fairly steep. Anchors keep the pipe from moving down the slope while it is being installed and later due to the energy of the flow. They are an especially important consideration if the native soil is subject for movement or instability. ADS does not produce anchoring systems, but can provide additional information on companies who are experts in this area. For further discussion of steep slope applications, refer to Steep Slope Installations in the Installation section (Section 5) of the Drainage Handbook. 3-6 LONG TERM PRESSURE CONSIDERATIONS Most ADS pipe products are intended for gravity flow applications only. Storm drainage products are not recommended for long-term pressure or intermittent pressure flow, including constant head and pumping applications. N-12 Low Head pipe may be suitable for longterm and intermittent pressure flow applications where constant pressure does not exceed 5psi and surge pressure does not exceed 10psi. Contact an ADS sales representative for assistance in selecting a product suitable for the project application. ADS, Inc., July 2010

14 ADS, Inc. Drainage Handbook Hydraulics CULVERT CONSIDERATIONS Culverts are typically short relative to a storm sewer system and are classified according to which of the ends controls the discharge capacity. Laboratory tests and field observations indicate two primary culvert flow control conditions: (1) inlet control and (2) outlet control. While inlet or outlet control conditions typically do not exist in storm sewer systems, where a system is controlled by the inlet or outlet, hydraulic head loss due to the entrance or outlet must be taken into account. For this reason, the Manning s formula cannot be the sole method of pipe sizing and selection. While the theory of energy conservation will closely affect culvert design, no single formula or procedure has been developed to design all culverts, due to the numerous variables involved. True culvert design is, therefore, often an empirical, trial-and-error process. One common variable used in culvert design, is the Entrance Loss Coefficient (k e ). Entrance Loss Coefficients are highly dependant on the size and shape of the interface between the culvert material and the fluid. For example, a square cut abrupt culvert edge will result in a greater loss coefficient than a culvert with a beveled or rounded edge. In the absence of test data for corrugated polyethylene or polypropylene pipe, corrugated metal pipe with a similar profile and structure can be used to estimate the entrance loss coefficients for ADS thermoplastics. Table 3-3 provides Entrance Loss Coefficients based on available data for common pipe materials and end treatments. Ultimately, the design engineer shall determine the most appropriate value for the entrance loss coefficient to use for the application. Table 3-3 Entrance Loss Coefficients a,b (Outlet Control, Full or Partially Full Flow) Type of Structure and Design of End Treatment k e Pipe, Concrete a Projecting from fill, square cut end 0.5 Square cut with headwall 0.5 Mitered to conform to fill slope 0.7 Beveled edges, 33.7 bevels 0.2 Socket end of pipe 0.2 Pipe, Corrugated Metal a, ADS Thermoplastic b Projecting from fill (no headwall) 0.9 Square cut with headwall 0.5 Mitered to conform to fill slope 0.7 End-Section conforming to fill slope 0.5 Beveled edges (33.7 o or 45 0 bevel) 0.2 a) Data obtained from U.S. Department of Transportation Federal Highway Administration Hydraulic Charts for the Selection of Highway Culverts 5 b) ADS thermoplastic pipe is estimated to have coefficients in the range of those found for corrugated metal pipe. ADS, Inc., July 2010

15 ADS, Inc. Drainage Handbook Hydraulics EXAMPLE PROBLEMS The following example problems demonstrate use of conveyance factors in sizing application, basic velocity checks, and optional designs. Example 1 Given: Field conditions stipulate a pipe capacity of 2 cfs and a slope of 0.5%. Find: The ADS pipe product providing the optimum hydraulic solution. Solution: It is necessary to use Equation 3-4 to determine the required conveyance for the given conditions. Before substituting the values into the equation, first convert the slope into a value with units of feet/foot as follows: 0.5% = ft/ft Now substitute values directly into Equation 3-4. Q k = 1/ 2 S 2 = ( ) 1/ = 28.3 Refer to Table 3-1 to select the appropriate pipe product having a minimum conveyance of 28.3, based on the respective Manning s n value. The most practical solutions are as follows: 12-inch corrugated, smooth interior pipe k = inch single wall pipe k = 38.2 The optimum solution would be the pipe with conveyance most near that calculated. Both the 12-inch corrugated, smooth interior and 15-inch single wall pipes will function in about the same manner because their conveyances are relatively close to that required. Final selection of pipe size and material is made in Example 2. Example 2 Substituting data from tentatively selected solutions from Example 1 into the velocity formula (Equation 3-5), 12-inch corrugated, smooth interior pipe and 15-inch single wall pipe will yield velocities of 3.5 fps and 2.2 fps, respectively. Therefore, the 12-inch corrugated, smooth interior pipe should be selected to attain a self-cleansing velocity. ADS, Inc., July 2010

16 ADS, Inc. Drainage Handbook Hydraulics 3-16 Example 3 Given: Field conditions stipulate a pipe capacity of 2 cfs and a slope of 0.5%. Find: The ADS pipe product providing the optimum hydraulic solution. Solution: It is necessary to use Figure 3-1 and Figure 3-2 to determine the pipe products 0.5% = ft/ft Refer to Figure 3-1 to select the corrugated, smooth interior pipe diameter. The intersection of the 0.50% and 2 cfs lines is above the 10 line but below the 12 therefore 12 corrugated, smooth interior pipe products are practical. Refer to Figure 3-2 to select the single wall pipe product diameter. The intersection of the 0.50% and 2 cfs lines is above the 12 line but below the 15, therefore 15 single wall pipe products are practical. The optimum solution would be the pipe with the flow capacity at least as great as the required. Both, the 12-inch corrugated, smooth liner and 15-inch single wall pipes will function in about the same manner because their flow capacities are greater than that required. Final selection of pipe size and material is made in Example 4. Example 4 Substituting data from tentatively selected solutions from Example 4 into Figure 3-1 and Figure 3-2, 12-inch corrugated, smooth interior pipe and 15-inch single wall pipe will yield velocities of approximately 3.6 fps and 2.8 fps, respectively. Therefore, the 12-inch corrugated, smooth interior pipe should be selected to attain a self-cleansing velocity. ADS, Inc., July 2010

17 ADS, Inc. Drainage Handbook Hydraulics FOOTNOTES 1 Federal Highway Administration, Hydraulic Design of Highway Culverts (HDS 5), 2 nd Edition, 2001, Pg Federal Highway Administration, Design Charts for Open- Channel Flow (HDS 3), August 1961, Chapter 5. 3 Clyde, Calvin G., Manning Friction Coefficient Testing of 4-, 10-, 12- and 15-inch Corrugated Plastic Pipe. Utah Water Research Laboratory, Report No. 36, May Lingedburg, Michael P.E. Civil Engineer Reference Manual. Belmont, CA: Professional Publications, Inc. 5 Federal Highway Adminstration, Design Charts of Highway Culverts (HDS 5), 2 nd Edition, 2001, Pg ADS, Inc., July 2010

### Hydraulics Guide. Table 1: Conveyance Factors (English Units)... 7 Table 2: Conveyance Factors (Metric Units)... 8

Table of Contents 1.1 Index of Tables... 1 1. Index of Figures... 1 1.3 Overview of Hydraulic Considerations... 1.4 Discharge Curves... 1.5 Conveyance Method... 5 1.6 Flow Velocity Considerations... 9

### CHAPTER 2 HYDRAULICS OF SEWERS

CHAPTER 2 HYDRAULICS OF SEWERS SANITARY SEWERS The hydraulic design procedure for sewers requires: 1. Determination of Sewer System Type 2. Determination of Design Flow 3. Selection of Pipe Size 4. Determination

### City of Quinte West Storm Flow Management Section 7.0 Engineering Design Page 7-1 Standards January 2012

Engineering Design Page 7-1 1.0 Storm Flow Management The objective of Storm Flow Management is to provide: The safe conveyance of stormwater to legal and adequate outlets Water quality control Flooding

### CHAPTER 3 STORM DRAINAGE SYSTEMS

CHAPTER 3 STORM DRAINAGE SYSTEMS 3.7 Storm Drains 3.7.1 Introduction After the tentative locations of inlets, drain pipes, and outfalls with tail-waters have been determined and the inlets sized, the next

### Module 7: Hydraulic Design of Sewers and Storm Water Drains. Lecture 7 : Hydraulic Design of Sewers and Storm Water Drains

1 P age Module 7: Hydraulic Design of Sewers and Storm Water Drains Lecture 7 : Hydraulic Design of Sewers and Storm Water Drains 2 P age 7.1 General Consideration Generally, sewers are laid at steeper

### Concrete Pipe Design Manual INDEX OF CONTENTS. FOREWORD... iii. Chapter 1. INTRODUCTION... 1

Concrete Pipe Design Manual INDEX OF CONTENTS FOREWORD...... iii Chapter 1. INTRODUCTION... 1 Chapter 2. HYDRAULICS OF SEWERS Sanitary Sewers... 3 Determination of Sewer System Type... 3 Determination

### Module 9: Basics of Pumps and Hydraulics Instructor Guide

Module 9: Basics of Pumps and Hydraulics Instructor Guide Activities for Unit 1 Basic Hydraulics Activity 1.1: Convert 45 psi to feet of head. 45 psis x 1 ft. = 103.8 ft 0.433 psi Activity 1.2: Determine

### ENERGY DISSIPATION CHAPTER 7

CHAPTER 7 ENERGY DISSIPATION 7.1 Overview... 7-1 7.2 Design Criteria... 7-1 7.2.1 General Criteria... 7-1 7.2.2 Erosion Hazards... 7-1 7.2.3 Recommended Dissipators... 7-1 7.3 Riprap Aprons... 7-2 7.3.1

### SECTION 5 - STORM DRAINS

Drainage Criteria Manual SECTION 5 - STORM DRAINS 5.1.0 GENERAL This The purpose of this section discusses briefly is to consider the hydraulic aspects of storm drains and their appurtenances in a storm

### TECHNICAL NOTE Culvert Sliplining and Lining of Casings with HPPipe

TECHNICAL NOTE Culvert Sliplining and Lining of Casings with HPPipe TN 5.14 February 2010 Introduction It may be at times necessary, in an aging infrastructure, to rehabilitate drainage and sanitary lines

SECTION 08000 STORM DRAINAGE 08010 DESIGN A. Location B. Sizing TABLE OF CONTENTS 08020 MATERIALS A. Pipe Materials B. Structure Materials C. Installation D. Inlets and Outlets 08030 INSPECTIONS AND TESTING

### 1. Carry water under the canal 2. Carry water over the canal 3. Carry water into the canal

Lecture 21 Culvert Design & Analysis Much of the following is based on the USBR publication: Design of Small Canal Structures (1978) I. Cross-Drainage Structures Cross-drainage is required when a canal

### Module1: Open Channel Flow. 1 Classification, types and regimes in Open channel flow. 3 Velocity distribution in open channel, Wide-open channel.

Module1: Open Channel Flow 1 Classification, types and regimes in Open channel flow. 2 Channel geometry. 3 Velocity distribution in open channel, Wide-open channel. 4 Specific energy and Critical flow.

### Land Disturbance, Erosion Control and Stormwater Management Checklist. Walworth County Land Conservation Department

Land Disturbance, Erosion Control and Stormwater Management Checklist Walworth County Land Conservation Department The following checklist is designed to assist the applicant in complying with the Walworth

### Native InDesign 2890 SaniTite Brochure 1/8" 100 300 CMYK April 17, 07

Sanitary Sewer Pipe Tough pipe for a tough environment SaniTite Sanitary Sewer Pipe delivers the features that engineers, contractors and municipalities demand durability, performance, handling, toughness

### DRAINAGE CRITERIA MANUAL (V. 2) CULVERTS CONTENTS

DRAINAGE CRITERIA MANUAL (V. 2) CONTENTS Section Page CU 1.0 INTRODUCTION AND OVERVIEW... 1 1.1 Required Design Information... 3 1.1.1 Discharge... 4 1.1.2 Headwater... 4 1.1.3 Tailwater... 5 1.1.4 Outlet

### HDPE PRODUCTS QUALITY, PERFORMANCE AND ECONOMY COMBINED

QUALITY, PERFORMANCE AND ECONOMY COMBINED LANE S HDPE DRAINAGE PIPE Scan for more information on Lane s HDPE product line. Lane provides the complete product line to meet all your HDPE drainage needs -

### CHAPTER 17: STORM SEWER STANDARDS. 17.00 Introduction. 17.01 Administration. 17.02 Standards 17.1

CHAPTER 17: STORM SEWER STANDARDS 17.00 Introduction 17.01 Administration 17.02 Standards 17.1 17.00 INTRODUCTION The purpose of this chapter is to provide guidance for the design and construction of storm

### HYDRAULIC ANALYSIS OF PIPE LINED WITH MADISON S 100% SOLIDS STRUCTURAL POLYURETHANE COATINGS

HYDRAULIC ANALYSIS OF PIPE LINED WITH MADISON S 100% SOLIDS STRUCTURAL POLYURETHANE COATINGS Shiwei William Guan, Ph.D. Vice President, R&D and International Business Madison Chemical Industries Inc. 490

### Open Channel Flow 2F-2. A. Introduction. B. Definitions. Design Manual Chapter 2 - Stormwater 2F - Open Channel Flow

Design Manual Chapter 2 - Stormwater 2F - Open Channel Flow 2F-2 Open Channel Flow A. Introduction The beginning of any channel design or modification is to understand the hydraulics of the stream. The

### DIVISION 4300 STORM DRAINAGE

DIVISION 4300 STORM DRAINAGE SECTION 4305 STORM SEWER PART 1 - GENERAL 1.01 SCOPE This section covers the construction of storm sewers for the collection and transport of stormwater runoff. 1.02 REFERENCES

### Pressure drop in pipes...

Pressure drop in pipes... PRESSURE DROP CALCULATIONS Pressure drop or head loss, occurs in all piping systems because of elevation changes, turbulence caused by abrupt changes in direction, and friction

### APPENDIX G HYDRAULIC GRADE LINE

Storm Drainage 13-G-1 APPENDIX G HYDRAULIC GRADE LINE 1.0 Introduction The hydraulic grade line is used to aid the designer in determining the acceptability of a proposed or evaluation of an existing storm

### Spreadsheet Use for Partially Full Pipe Flow Calculations

Spreadsheet Use for Partially Full Pipe Flow Calculations Course No: C02-037 Credit: 2 PDH Harlan H. Bengtson, PhD, P.E. Continuing Education and Development, Inc. 9 Greyridge Farm Court Stony Point, NY

### The Most Advanced Name in Drainage Systems. Sanitary Sewer Pipe

The Most Advanced Name in Drainage Systems Sanitary Sewer Pipe SaniTite Sanitary Sewer Pipe delivers the features that engineers, contractors and municipalities demand durability, performance, handling,

### CITY UTILITIES DESIGN STANDARDS MANUAL

CITY UTILITIES DESIGN STANDARDS MANUAL Book 2 (SW) SW9 June 2015 SW9.01 Purpose This Chapter provides information for the design of open channels for the conveyance of stormwater in the City of Fort Wayne.

### STORM DRAINS CHAPTER 7

CHAPTER 7 Chapter 7 - Storm Drains A storm drain is a drainage system that conveys water or stormwater, consisting of two or more pipes in a series connected by one or more structures. Storm drains collect

### Chapter 3 CULVERTS. Description. Importance to Maintenance & Water Quality. Culvert Profile

Chapter 3 CULVERTS Description A culvert is a closed conduit used to convey water from one area to another, usually from one side of a road to the other side. Importance to Maintenance & Water Quality

### Exercise (1): Open Channel Flow Uniform Flow

Exercise (1): Open Channel Flow Uniform Flow 1) Derive expressions for the flow area A, wetted perimeter P, hydraulic radius R, top water surface width B, and hydraulic depth D for the following channel

### Lecture 24 Flumes & Channel Transitions. I. General Characteristics of Flumes. Flumes are often used:

Lecture 24 Flumes & Channel Transitions I. General Characteristics of Flumes Flumes are often used: 1. Along contours of steep slopes where minimal excavation is desired 2. On flat terrain where it is

### TECHNICAL NOTE Lining of Casings with SaniTite HP Pipe

TECHNICAL NOTE Lining of Casings with SaniTite HP Pipe TN 5.18 October 2015 In sanitary sewer, it is often necessary to use trenchless technology methods to install a casing pipe under high volume roads,

### CHAPTER 9 STORM DRAINAGE

CHAPTER 9 STORM DRAINAGE Section Page 9.01 General...1 9.02 Design Standards...1 9.03 Construction Stormwater Pollution Prevention...2 9.04 Department of Ecology Stormwater Permits...4 9.05 Maintenance

### Appendix 4-C. Open Channel Theory

4-C-1 Appendix 4-C Open Channel Theory 4-C-2 Appendix 4.C - Table of Contents 4.C.1 Open Channel Flow Theory 4-C-3 4.C.2 Concepts 4-C-3 4.C.2.1 Specific Energy 4-C-3 4.C.2.2 Velocity Distribution Coefficient

### Plan Preparation Guide. Chapter 9

Plan Preparation Guide Chapter 9 Drainage Structures R.C. Box Culverts Ditches - Gutters - Curbs Section Description Page 1 Plans for Hydrology 9-1 2 Catch Basin Types and Uses 9-2 3 Drop Inlet Types and

### What is the most obvious difference between pipe flow and open channel flow????????????? (in terms of flow conditions and energy situation)

OPEN CHANNEL FLOW 1 3 Question What is the most obvious difference between pipe flow and open channel flow????????????? (in terms of flow conditions and energy situation) Typical open channel shapes Figure

### DESCRIPTION OF STORMWATER STRUCTURAL CONTROLS IN MS4 PERMITS

DESCRIPTION OF STORMWATER STRUCTURAL CONTROLS IN MS4 PERMITS Phase I MS4 permits require continuous updating of the stormwater system inventory owned and operated by the MS4. They also include inspection

### Lecture 22 Example Culvert Design Much of the following is based on the USBR technical publication Design of Small Canal Structures (1978)

Lecture 22 Example Culvert Design Much of the following is based on the USBR technical publication Design of Small Canal Structures (1978) I. An Example Culvert Design Design a concrete culvert using the

### SECTION 300 STORM SEWER AND SUMP PUMP DRAIN SYSTEMS

SECTION 300 STORM SEWER AND SUMP PUMP DRAIN SYSTEMS Section Title Page 301 General................................... 18 302 Materials.................................. 18 303 Design Requirements........................

### Orifices may be constructed on a pipe, tee riser, baffle, or other structure intended for conveyance.

APPENDIX F CONTROL STRUCTURES FOR DETENTION SYSTEMS This appendix presents the methods and equations for the design of flow control structures. It includes illustrations and equations for the design of

### 8.1.3 General Design Guidelines. The following guidelines shall be used when designing inlets along a street section:

. Introduction Presented in this chapter are the criteria and methodology for design and evaluation of storm sewer inlets located in Town of Castle Rock. The review of all planning submittals will be based

### CHAPTER IX HYDRAULICS AND DRAINAGE

CHAPTER IX HYDRAULICS AND DRAINAGE 9-04.1 GENERAL. Providing for the control of erosion is a necessary part of the complete design of any highway construction project. These provisions must include measures

### M6a: Open Channel Flow (Manning s Equation, Partially Flowing Pipes, and Specific Energy)

M6a: Open Channel Flow (, Partially Flowing Pipes, and Specific Energy) Steady Non-Uniform Flow in an Open Channel Robert Pitt University of Alabama and Shirley Clark Penn State - Harrisburg Continuity

### RIPRAP From Massachusetts Erosion and Sediment Control Guidelines for Urban and Suburban Areas http://www.mass.gov/dep/water/laws/policies.

RIPRAP From Massachusetts Erosion and Sediment Control Guidelines for Urban and Suburban Areas http://www.mass.gov/dep/water/laws/policies.htm#storm Definition: A permanent, erosion-resistant ground cover

### X Planning X Quality X Maintenance & Operations

Delaware Department of Transportation Division of Transportation Solutions Design Guidance Memorandum Memorandum Number 1-20 Revised 1. Road Design Manual 2. Bridge Design Manual 3. Utilities Design Manual

### Chapter 9. Steady Flow in Open channels

Chapter 9 Steady Flow in Open channels Objectives Be able to define uniform open channel flow Solve uniform open channel flow using the Manning Equation 9.1 Uniform Flow in Open Channel Open-channel flows

### CHAPTER 4 DESIGN OF CULVERTS

CHAPTER 4 DESIGN OF CULVERTS 4.8 HY8 Culvert Analysis Microcomputer Program The HY8 culvert analysis microcomputer program will perform the calculation for the following: Culvert analysis (including independent

### CHAPTER 9. Outlet Protection

CHAPTER 9 Outlet Protection General Considerations Not an ABACT, but should be used in all watersheds to prevent erosion due to concentrated discharges For channel or swale, use guidance for pipe with

### Chapter 11 Outfall Systems

Chapter 11 Outfall Systems This section presents the methods, criteria and details for analysis and design of outfall systems. Properly designed outfalls are critical to reducing the chance of adverse

### Riprap-lined Swale (RS)

Riprap-lined Swale (RS) Practice Description A riprap-lined swale is a natural or constructed channel with an erosion-resistant rock lining designed to carry concentrated runoff to a stable outlet. This

### Instructions for the Installation of Driveway Entrances

Instructions for the Installation of Driveway Entrances 1 Step 1 - Permits Complete the Work Within Highway Right-of-Way Permit. A representative from the Department of Transportation and Infrastructure

### CHAPTER II UNIFORM FLOW AND ITS FORMULAS MODULE 1. This experiment was designed to observe the characteristics of uniform flow in

CHAPTER II UNIFORM FLOW AND ITS FORMULAS MODULE 1 2.1 Introduction and Objective This experiment was designed to observe the characteristics of uniform flow in the teaching flume and to utilize the common

### SECTION 02720 SANITARY SEWER AND STORM DRAIN SYSTEMS

SECTION 02720 SANITARY SEWER AND STORM DRAIN SYSTEMS PART 1 GENERAL 1.01 SECTION INCLUDES A. The requirements for pipe material and installation in sewer and drainage collection systems. All materials

### CLEANING, INSPECTION, AND TESTING OF SEWERS

CLEANING, INSPECTION, AND TESTING OF SEWERS PART 1 - GENERAL 1.01 SECTION INCLUDES A. Cleaning, Inspecting, and Testing Sanitary Sewers B. Cleaning, Inspecting, and Testing Storm Sewers C. Cleaning and

### Travel Time. Computation of travel time and time of concentration. Factors affecting time of concentration. Surface roughness

3 Chapter 3 of Concentration and Travel Time Time of Concentration and Travel Time Travel time ( T t ) is the time it takes water to travel from one location to another in a watershed. T t is a component

### Use of Corrugated HDPE Products

Chapter 3 Use of Corrugated HDPE Products Orin Bennett USE OF CORRUGATED HDPE PRODUCTS Corrugated HDPE Pipe Characteristics High-density polyethylene (HDPE) is a versatile material and has some ideal characteristics

### SECTION 6A STORM DRAIN DESIGN Mar. 2002 S E C T I O N 6A STORM DRAIN - DESIGN

S E C T I O N 6A STORM DRAIN - DESIGN 6A.l Scope 6A.2 Storm Water Quantity 6A.3 Storm Drain Hydraulics 6A.4 Depths 6A.5 Locations 6A.6 Curved Storm Drains 6A.7 Manholes 6A.8 Catch basins 6A.9 Storm Drain

### SaniTite HP Sanitary Sewer Pipe 12 60

SaniTite HP Sanitary Sewer Pipe 12 60 TM The Most Advanced Name in Water Management Solutions Sanitite HP pipe 12 60 FOR SANITARY SEWER Meets ASTM F2736 and F2764 SaniTite HP (High Performance) couples

### Index. protection. excavated drop inlet protection (Temporary) 6.50.1 6.51.1. Block and gravel inlet Protection (Temporary) 6.52.1

6 Index inlet protection excavated drop inlet protection (Temporary) 6.50.1 HARDWARE CLOTH AND GRAVEL INLET PROTECTION Block and gravel inlet Protection (Temporary) sod drop inlet protection ROCK DOUGHNUT

### BEST PRACTICE GUIDELINES FOR CULVERT LINER SELECTION

BEST PRACTICE GUIDELINES FOR CULVERT LINER SELECTION GENERAL Rehabilitation of culverts with pipe liners is one of several methods available for extending the life of an existing culvert. It is often cost

### CHAPTER 5. Storm Sewer

CHAPTER 5 Storm Sewer A. Introduction All proposed developments shall have a properly designed and constructed storm water conveyance system. This chapter deals only with the conveyance system. Storm water

### CLARK COUNTY REGIONAL FLOOD CONTROL DISTRICT HYDROLOGIC CRITERIA AND DRAINAGE DESIGN MANUAL SECTION 800 STORM SEWER SYSTEMS TABLE OF CONTENTS

CLARK COUNTY REGIONAL FLOOD CONTROL DISTRICT HYDROLOGIC CRITERIA AND DRAINAGE DESIGN MANUAL SECTION 800 STORM SEWER SYSTEMS TABLE OF CONTENTS 801 INTRODUCTION 803 802 DESIGN PARAMETERS 804 802.1 - Allowable

### Topic 8: Open Channel Flow

3.1 Course Number: CE 365K Course Title: Hydraulic Engineering Design Course Instructor: R.J. Charbeneau Subject: Open Channel Hydraulics Topics Covered: 8. Open Channel Flow and Manning Equation 9. Energy,

### Rational Method Hydrologic Calculations with Excel. Rational Method Hydrologic Calculations with Excel, Course #508. Presented by:

Rational Method Hydrologic Calculations with Excel, Course #508 Presented by: PDH Enterprises, LLC PO Box 942 Morrisville, NC 27560 www.pdhsite.com Calculation of peak storm water runoff rate from a drainage

### CLARK COUNTY REGIONAL FLOOD CONTROL DISTRICT HYDROLOGIC CRITERIA AND DRAINAGE DESIGN MANUAL SECTION 1100 ADDITIONAL HYDRAULIC STRUCTURES

CLARK COUNTY REGIONAL FLOOD CONTROL DISTRICT HYDROLOGIC CRITERIA AND DRAINAGE DESIGN MANUAL SECTION 1100 ADDITIONAL HYDRAULIC STRUCTURES TABLE OF CONTENTS Page 1101 INTRODUCTION 1102 1102 CHANNEL DROPS

### A perforated conduit such as pipe, tubing or tile installed beneath the ground to intercept and convey ground water. or structures.

BMP: SUBSURFACE DRAIN Definition A perforated conduit such as pipe, tubing or tile installed beneath the ground to intercept and convey ground water. PurRoses 1. To prevent sloping soils from becoming

### SECTION 5: SANITARY SEWER SYSTEM DESIGN

SECTION 5: SANITARY SEWER SYSTEM DESIGN 5.01 GENERAL Sanitary sewer improvements shall be designed to serve the ultimate level of City development as defined in the General Plan and the Wastewater Facilities

### SANITARY SEWER SPECIFICATIONS

SANITARY SEWER SPECIFICATIONS OCTOBER 2003 HARVEST-MONROVIA WATER, SEWER, AND FIRE PROTECTION AUTHORITY SECTION 1.00 1.10 Purpose The purpose of this document is to assemble the sewer specifications, policies,

### APPENDIX A FORMULAE AND SAMPLE CALCULATIONS

APPENDIX A FORMULAE AND SAMPLE CALCULATIONS Pipe Installation (Fused) The fused polyethylene (PE) pipe can be pulled by a cable attached to a pulling head fastened to the pipe. This prevents damage to

### Experiment (13): Flow channel

Introduction: An open channel is a duct in which the liquid flows with a free surface exposed to atmospheric pressure. Along the length of the duct, the pressure at the surface is therefore constant and

### TENNESSEE GAS PIPELINE COMPANY, L.L.C.

TENNESSEE GAS PIPELINE COMPANY, L.L.C. HYDROLOGIC & HYDRAULIC CALCULATIONS FOR WATERBODIES CROSSED BY CONNECTICUT PIPELINE EXPANSION PROJECT CONNECTICUT LOOP Submitted by: Tennessee Gas Pipeline Company,

### Uniform Open Channel Flow and the Manning Equation. Uniform Open Channel Flow and the Manning Equation, Course #501. Presented by:

Uniform Open Channel Flow and the Manning Equation, Course #501 Presented by: PDH Enterprises, LLC PO Box 942 Morrisville, NC 27560 www.pdhsite.com This course is intended for hydrologists, civil engineers,

### Strength and Durability for Life HYDRAULICS. Hydraulic Analysis of Ductile Iron Pipe

Strength and Durability for Life HYDRAULICS Hydraulic Analysis of Last Revised: August 2016 Head Loss Friction head loss or drop in pressure in a pipeline is an everyday concern for the water works engineer.

### SECTION 724 PIPE CULVERTS

SECTION 724 PIPE CULVERTS 724.1 Description. This work shall consist of providing pipe or pipe arch of the diameter or shape designated, laid upon a firm bed and backfilled as specified. Where appropriate

### Viscous Flow in Pipes

Viscous Flow in Pipes Excerpted from supplemental materials of Prof. Kuang-An Chang, Dept. of Civil Engin., Texas A&M Univ., for his spring 2008 course CVEN 311, Fluid Dynamics. (See a related handout

### CHAPTER 11 STORM DRAINAGE

CHAPTER STORM DRAINAGE SECTION PC 0 GENERAL 0. Scope. The provisions of this chapter shall govern the materials, design, construction and installation of storm drainage. Storm water discharge shall be

### City of Shelbyville Site Inspection Checklist

City of Shelbyville Site Inspection Checklist General Information Project Name: KYR10 Permit Number: Date: Project Location: Contractor: Conractor Representative: Inspector's Name: Title: Signature : Weather

### Design Charts for Open-Channel Flow HDS 3 August 1961

Design Charts for Open-Channel Flow HDS 3 August 1961 Welcome to HDS 3-Design Charts for Open-Channel Flow Table of Contents Preface DISCLAIMER: During the editing of this manual for conversion to an electronic

### Green Values Stormwater Calculator Methodology

Green Values Stormwater Calculator Methodology The CNT Green Values Stormwater Calculator (greenvalues.cnt.org) is designed to arrive at a first approximation of the hydrologic and financial conditions

### Infiltration Sump System

Stormwater Management Goals Achieved Acceptable Sizing Methodologies Pollution Reduction.... NA Flow Control. PRES Destination PRES This facility is classified as an Underground Injection Control structure

### Designing Roof Gutters for Horse Barns

Designing Roof Gutters for Horse Barns Equine Water Quality Education Series Roof gutters may be needed on horse facilities to divert clean water from contaminated lot runoff and to prevent uncontrolled

### DIVISION OF WATER QUALITY CONSTRUCTION GRANTS & LOANS SECTION FAST TRACK AUDIT CHECKLIST

DIVISION OF WATER QUALITY CONSTRUCTION GRANTS & LOANS SECTION FAST TRACK AUDIT CHECKLIST CERTIFICATION 1. Did the engineer submit a certificate of completion utilizing the appropriate page of the issued

### Pacific Pump and Power

Pacific Pump and Power 91-503 Nukuawa Street Kapolei, Hawaii 96707 Phone: (808) 672-8198 or (800) 975-5112 Fax: (866) 424-0953 Email: sales@pacificpumpandpower.com Web: www.pacificpumpandpower.com Pumps

### PVC and HDPE / Pipe Pressure Class ( Example)

DESIGN AND SELECTION OF PLASTIC PRESSURE PIPE TECHNICAL BULLETIN 1. INTRODUCTION Potable water pressure pipes are made from many different materials. The most commonly used pipe materials for municipal

### Nebraska Department of Roads Drainage and Erosion Control Manual December 2011 Appendix C: Pipe Material Policy Page C-1 PIPE MATERIAL POLICY

Appendix C: Pipe Material Policy Page C-1 PIPE MATERIAL POLICY Policy: This policy will replace all previous policies regarding the selection of pipe material for cross drains, drive pipe, drop pipe, storm

### Time of Concentration

Design Manual Chapter 2 - Stormwater 2B - Urban Hydrology and Runoff 2B-3 Time of Concentration A. Introduction Time of concentration (T c ) is the time required for runoff to travel from the hydraulically

### MS-6/2009 Model Specification and Checklist for Polyethylene (PE) Pipe for the Sliplining of Sewers

MS-6/2009 Model Specification and Checklist for Polyethylene (PE) Pipe for the Sliplining of Sewers The Plastics Pipe Institute March 2009 1 DISCLAIMER This guideline has been prepared by the Plastics

### Valve Pressure Loss & Flow

Valve Pressure Loss & Flow The valve coefficient, Cv, is a number which represents the capability of a valve (or any flow component) to flow a fluid. The larger the Cv, the larger the flow at a given pressure

### ITD Pipe Materials Selection & Specification Procedures. July 2011

ITD Pipe Materials Selection & Specification Procedures July 2011 INTRODUCTION: This technical memorandum is written as a guide to the selection of compliant pipe materials and the elimination of non-compliant

### Pipe Flow-Friction Factor Calculations with Excel

Pipe Flow-Friction Factor Calculations with Excel Course No: C03-022 Credit: 3 PDH Harlan H. Bengtson, PhD, P.E. Continuing Education and Development, Inc. 9 Greyridge Farm Court Stony Point, NY 10980

### DESIGN MANUAL CHAPTER 7: Energy Dissipation

DESIGN MANUAL CHAPTER 7: Energy Dissipation 7.0 ENERGY DISSIPATION... 7-1 7.1 SYMBOLS AND DEFINITIONS... 7-1 7.2 DESIGN CRITERIA... 7-2 7.2.1 GENERAL CRITERIA... 7-2 7.2.2 EROSION HAZARDS... 7-2 7.2.3

### SECTION 7- STORM SEWER

SECTION 7- STORM SEWER 7.1. STORM SEWERS.... 7-1 7.2. SUMP DRAINS... 7-3 7.3. CATCH BASINS... 7-3 7.4. MANHOLES... 7-4 7.5. STORM SEWER CALCULATIONS... 7-4 7.6. CULVERTS AND BRIDGES... 7-5 7.7. OPEN CHANNELS...

### TRAPEZOIDAL FLUME. User s Manual. Trapezodidal Flume User s Manual

TRAPEZOIDAL FLUME User s Manual i Trapezodidal Flume User s Manual TABLE OF CONTENTS Introduction to the Trapezoidal Flume... 1 Development... 1 Function... 1 Design... 2 Standards... 3 Accuracy... 3

### STORM DRAIN DESIGN STANDARDS SECTION 4

STORM DRAIN DESIGN STANDARDS SECTION 4 4.100 GENERAL All drainage facilities shall be designed in accordance with accepted engineering principles, and shall conform to these Design Standards. 4.200 SUBMITTAL

### 8-11 Structural Analysis and Fill Height Tables... 42 8-11.1 Pipe Cover... 43 8-11.2 Shallow Cover Installation... 43 8-11.3 Fill Height Tables...

Contents Chapter 8 Pipe Classifications and Materials...1 8-1 Classifications of Pipe... 1 8-1.1 Drain Pipe... 2 8-1.2 Underdrain Pipe... 2 8-1.3 Culvert Pipe... 3 8-1.4 Storm Sewer Pipe... 7 8-1.5 Sanitary

### Storm Drainage Systems 11.9-1

Storm Drainage Systems 11.9-1 11.9 Gutter Flow Calculations 11.9.1 Introduction Gutter flow calculations are necessary in order to relate the quantity of flow (Q) in the curbed channel to the spread of

### SYSTEMS ENGINEERING DATA FOR THERMOPLASTIC PIPING

SYSTEMS ENGINEERING DATA INTRODUCTION In the engineering of thermoplastic piping systems, it is necessary to have not only a working knowledge of piping design but also an awareness of a number of the

### Open Channel Flow. M. Siavashi. School of Mechanical Engineering Iran University of Science and Technology

M. Siavashi School of Mechanical Engineering Iran University of Science and Technology W ebpage: webpages.iust.ac.ir/msiavashi Email: msiavashi@iust.ac.ir Landline: +98 21 77240391 Fall 2013 Introduction

### CHAPTER 11 STORM DRAINAGE

CHAPTER STORM DRAINAGE SECTION GENERAL. Scope. The provisions of this chapter shall govern the materials, design, construction and installation of storm drainage..2 Where required. All roofs, paved areas,