# Hydraulics in building systems. Answers for infrastructure and cities.

Save this PDF as:

Size: px
Start display at page:

## Transcription

1 Hydraulics in building systems Answers for infrastructure and cities.

2

3 Contents 1 Hydraulic circuits Key components of a hydraulic plant Different hydraulic circuits Consumers with their basic hydraulic circuits Hydraulic circuits with variable and constant flow Control of flow and control of mixing Basic hydraulic circuits Throttling circuit Diverting circuit Mixing circuit Mixing circuit with fixed premixing Injection circuit Injection circuit with three-port valve Injection circuit with two-port valve Components in the consumer circuit Controlling element Balancing throttle Circulating pump Distribution circuits Combinations of distribution and consumer circuits Low-pressure distribution Pressurized distribution at constant flow Pressurized distribution at variable flow Hydraulic characteristics Heat exchanger characteristic and a-value Heat exchanger characteristic a-value Valve characteristic k V -values and k VS -value Rangeability S V and smallest controllable flow value k Vr Different valve characteristics Characteristic of the controlled system Valve operating characteristic and valve authority P V Oversized valves Controlling in the low load range Plant characteristics, pump characteristics and operating point Plant characteristic (piping network characteristic) Pump characteristic Operating point The operation of pumps The operation of uncontrolled pumps The operation of controlled pumps

4 3 Sizing the controlling elements Piping sections with variable volumetric flow in different hydraulic circuits Valve sizing example Sizing the valve (controlling element) Impact of valve authority P V on total volumetric flow with three-port valves Example of hot water charging control Example of air cooling coil control Appendix: Calculating the a-value Definition of the a-value: Formulas used for calculating the a-value: Subject index

5 Introduction Heating, ventilation and air conditioning (HVAC) plants are used to create comfortable environmental conditions for human beings. To satisfy this requirement in our climatic zone, heat but also cooling energy must be generated, adequately regulated and delivered to the right place at the right time. Hydraulic systems are designed to integrate the required plant components in the circuit between the heating / cooling source and the consumer in a way that optimum operating conditions can be reached for the: heating / cooling source (temperature, flow of water) transportation of the heating / cooling energy carrier such as water or steam (temperature, flow of water) integrated control equipment Training program "Hydraulics in building technology" The training program "Hydraulics in building technology" offers fundamental training in hydraulics and is aimed at conveying the knowledge required for more advanced hydraulics courses and other training courses in the field of control engineering. The program is designed primarily for experts in the heating and air conditioning sector who deal with hydraulic plants and who want to enhance their knowledge. The training program "Hydraulics in building technology" and this documentation especially focus on hydraulics on the consumer side. This does not mean, however, that the knowledge of heating / cooling sources is less important the contrary is the case. As a result of the continued technical development of the heating / cooling sources, hydraulic considerations on that side are becoming more and more important as well. However, it is not the purpose of the present training program to cover those aspects in detail. But much of the knowledge gained about the hydraulics behavior of the consumer can also be applied to the heating / cooling source. This documentation contains key information out of the training modules from the training program Hydraulics in building technology. It is designed as a supporting documentation for and a reference to the training program. In addition, this document contains examples on dimensioning control valves. These examples are not part of the training program, but are content of a separate class room training. The majority of the graphs and illustrations are taken from the training program. Many of them are animated in the training program and interactive, so you can try for yourself how hydraulic circuits and components behave under different operating conditions. Training program If you are interested in the training program Hydraulics in building technology, please contact your Siemens sales office. 5

6 1 Hydraulic circuits 1.1. Key components of a hydraulic plant controller (with sensor) radiator (heat consumer) actuator controlling element (threeport valve) heating boiler (heat generation) circulating pump supply pipes balancing throttle return pipes Key components of a hydraulic plant Circulation in a hydraulic plant (valve fully closed) Circulation in a hydraulic plant (valve fully open) 6

7 1.2. Different hydraulic circuits The hydraulic circuits shown so far are easy to understand. For the expert, however, they are not common practice because they are not suited to explain plant-related interrelationships. For this reason, schematic diagrams are used in the HVAC field. All the essential elements of an HVAC plant can be shown there and technical processes and interrelationships are easier to understand. heat consumer supply pipes circulating pump controlling element heat producer balancing throttle return pipes Pictorial diagram of a plant Schematic diagram of a plant From the pictorial to the schematic plant diagram There are two different kinds of schematic plant diagrams: geographic diagram synoptic diagram flow supply consumer return Geographic diagram Geographic and synoptic diagram of a basic plant Synoptic diagram Geographic diagram Often, the schematic diagram shown above is used for basic plants. It is called a geographic diagram and is closely related to the actual design of the plant. 7

8 Example of a geographic diagram showing a heating plant with several consumers However, the geographic diagram is less suited for larger plants, because it becomes more and more difficult to understand, especially when interrelationships between consumers and heating / cooling sources are getting complex. For example in the case of a ground water heat pump with storage tank and additional heating boiler that delivers heat to several distributed consumers. For this reason and due to the extensive use of CAD systems, the kind of diagram frequently used today is a more structured one the synoptic diagram. Synoptic diagram The synoptic diagram shows the schematic representation of complex and extensive hydraulic plants in a clearly structured and easy-to-understand manner. With the synoptic diagram, a number of important rules are typically considered: The supply is shown at the top, the return at the bottom Heating / cooling source and consumers are shown parallel in the direction of flow between supply and return Note on the representation of controlling elements In the schematic diagrams of hydraulic circuits, it is also important that the correct symbols of the plant components are used. Especially important is the correct use of the symbol for the three-port controlling element (stroke or slipper valve). The two triangles representing the ports with variable flow are shown filled while the triangle representing the port with constant flow is shown empty. Schematic representation of the valve ports triangle filled = variable flow triangle empty = constant flow 8

9 In a large number of the schematic diagrams used in the training program Hydraulics in building technology and in this documentation, controlling elements are shown without their actuators. Thus the diagrams are easier to understand. In addition, the assumption is made that the controlling element is always a valve. Examples of geographic and synoptic diagrams: Geographic diagrams Synoptic diagrams 9

10 1.3. Consumers with their basic hydraulic circuits Hydraulic circuits with variable and constant flow The output of a heating / cooling source or consumer (amount of heating or cooling power) is proportional to the product of mass flow and temperature differential across the heating / cooling source or consumer. Q = V T c ρ For our considerations and for the standard applications in building technology plants, we consider the density r and the specific heat capacity c to be constant. This means that the output of a heating / cooling source or consumer is proportional to the product of volumetric flow and temperature differential. Q ~ V T Hence, in hydraulic circuits, the following variables can be used for adjusting the output: The volumetric flow is changed while the temperature is maintained at a constant level. Þ Operation with variable volumetric flow Þ Control of the flow The temperature is changed while the volumetric flow is maintained at a constant level. Þ Operation with constant volumetric flow Þ Control of mixing temperature 10

11 Control of flow and control of mixing Both control of flow (variable volumetric flow) and control of mixing (constant volumetric flow) use two different basic hydraulic circuits. Control of flow With control of flow (variable volumetric flow), the following hydraulic circuits are used: Throttling circuit Diverting circuit Throttling circuit Diverting circuit Both hydraulic circuits adjust their outputs by varying the volumetric flow passing through the consumer. Control of mixing With the control of mixing (constant volumetric flow) the following hydraulic circuits are used: Mixing circuit Injection circuit (with a three- or two-port valve) Mixing circuit Injection circuit (with three-port valve) Both hydraulic circuits adjust their outputs by delivering different fluid temperatures to the consumer. Each hydraulic circuit possesses an own pump to push the fluid through the consumer. 11

12 1.4. Basic hydraulic circuits Throttling circuit Mode of operation When the valve is adjusted, the volumetric flow will change both in the heating / cooling source section and in the consumer section of the hydraulic circuit. As a result, pressure conditions will vary considerably throughout the system. Valve fully closed Valve fully open Throttling circuit Characteristics Low return temperatures in part load operation Variable volumetric flow throughout the entire plant On startup, the correct fluid temperature will reach the consumer with a certain delay (dead time, depending on the length of the pipe and the cooling down effect) When the valve is fully closed, the pump can reach excessive temperatures (Þ use of speed-controlled pumps) Field of use Air heating coils where there is no risk of freezing Air cooling coils with dehumidification Hot water storage tank charging District heat connections Storage tank charging and discharging Plants using condensing boilers Types of diagrams Geographic diagram Synoptic diagram Throttling circuit 12

13 Diverting circuit Mode of operation The valve distributes the supply flow over the consumer and the bypass. Depending on the position of the valve, more or less water flows through the consumer. The output of the consumer is controlled by adjusting the volumetric flow. When the valve is fully closed, the temperatures of supply and return are approximately equal. Valve fully closed Valve fully open Diverting circuit Characteristics Changes to the volumetric flow varies thermal output at the consumer Variable volumetric flow through the consumer circuit Constant volumetric flow and pressure in the heat / cooling source circuit (advantageous in plants with several zones) Medium to high temperatures in return to the heating / cooling source On startup, the boiler supply temperature reaches the heat consumer with only little delay (provided that the controlling element is rather close to the consumer) Field of use Air cooling coils with dehumidification Air heating coils where there is no risk of freezing Heat recovery systems Hot water heating Not suited for plants with a district heat connection (high return temperatures) Types of diagrams Geographic diagram Synoptic diagram Diverting circuit 13

14 Mixing circuit Mode of operation A three-port valve subdivides the hydraulic circuit into a primary circuit (heating source circuit) and a secondary circuit (consumer circuit). The hot water delivered by the heat source and the cooler return water are mixed to attain the supply temperature required for the consumer, thereby adjusting the output to meet the demand for heat. Valve fully closed Valve fully open Mixing circuit Characteristics Heating: low return temperatures with small loads Cooling: high return temperatures with small loads Variable volumetric flow through the heat source circuit Constant volumetric flow with variable temperatures through the consumer circuit Even temperature distribution across the heat consumer Low risk of freezing with air heating coils The mixing circuit is not suited for plants with distances of more than 20 m between bypass and control sensor. The long transportation time (dead time) makes the control task much more difficult. Field of use Control of radiator systems Air heating coils where there is a risk of freezing Plants with low temperature heat sources or heat pumps Types of diagrams Geographic diagram Synoptic diagram Mixing circuit 14

15 Mixing circuit with fixed premixing Here too, a three-port valve subdivides the hydraulic circuit into a primary circuit (heat source circuit) and a secondary circuit (consumer circuit). Fixed premixing ensures that a certain portion of cooler return water will always be added to the supply flow. This is applicable when, under design conditions, the required supply temperature to the consumer is considerably lower than the supply temperature delivered by the heating producer. Thus, it is made certain that the three-port valve will operate across its entire valve stroke (from the fully closed to the fully open position). Valve fully closed Valve fully open Mixing circuit with fixed premixing Characteristics Generally low return temperatures Variable volumetric flow through the heat source circuit Constant volumetric flow with variable temperatures through the consumer circuit Control across full valve stroke The mixing circuit with fixed premixing is not suited for plants with distances of more than 20 m between bypass and control sensor. The long transportation time (dead time) makes the control task much more difficult. Field of use Consumer circuits where the flow temperature is lower than that of the heat source circuit Control of floor and radiator heating systems with low temperature heat sources or heat pumps Types of diagrams Geographic diagram Synoptic diagram Mixing circuit with fixed premixing 15

16 Injection circuit Injection circuit with three-port valve Mode of operation The pump on the lower left produces the pressure required in the heating source circuit, including the pressure drop across the valve. The pump above produces the pressure in the consumer circuit. The pump in the heat source circuit injects more or less hot supply water into the consumer circuit, depending on the position of the three-port valve. The hot water mixes with cooler return water from the consumer which the consumer s pump sucks in via the bypass. As a result, there is a constant volumetric flow with varying temperatures in the consumer circuit. Valve fully closed Valve fully open Injection circuit with three-port valve Characteristics constant volumetric flow in both the heat source and the consumer circuit Variable volumetric flow through the bypass Relatively high return temperatures (corresponding to the heating source supply temperature when load = 0 %, and the consumer return temperature when load = 100 %) Even temperature distribution across the heat consumer Small risk of freezing with air heating coils Field of use Radiator and floor heating systems Air heating coils where there is a risk of freezing Air cooling coils without controlled dehumidification Hot water storage tank charging Not suited for plants with district heat connection (high return temperatures) Types of diagrams Geographic diagram Synoptic diagram Injection circuit with three-port valve 16

17 Injection circuit with two-port valve Mode of operation The pump in the heating source circuit injects more or less hot supply water into the consumer circuit, depending on the position of the two-port valve. As a result, there is a constant volumetric flow with varying temperatures in the consumer circuit. In the heating source circuit, by contrast, the volumetric flow and pressure vary significantly, a fact to be taken into consideration in the case of plants with several consumer circuits. Valve fully closed Valve fully open Injection circuit with two-port valve Characteristics Relatively low return temperatures (cold consumer return temperature at 100 % load) Even temperature distribution across the heat consumer Constant volumetric flow in the consumer circuit Variable volumetric flow in the source circuit Small risk of freezing with air heating coils With a fully closed valve, the pump in the heating source circuit can reach excessive temperatures (Þ use of speed-controlled pumps) Field of use Heat storage tanks and heat pumps Low temperature boiler plants (condensing boilers) Direct district heat connections Not suited for air cooling coils with dehumidification control Radiators and floor heating Types of diagrams Geographic diagram Synoptic diagram Injection circuit with two-port valve 17

18 1.5. Components in the consumer circuit In practical applications, the hydraulic circuits discussed above operate only accurately if a number of components are used and installed in the right locations. The following plant components are discussed here: Controlling element (valve) Circulating pump Balancing throttle actuator controlling element (three-port valve) circulating pump balancing throttle Major components in the consumer circuit Controlling element The task of the controlling element is to control the volumetric flow from the heat source to the consumer in such a way that the supply of heat can be varied between 0 and 100 %. Every controlling element has a controlled port that can be more or less open, or fully open or fully closed. The controlling elements used in hydraulic circuits are slipper valves (rotary movement) or seat valves (linear movement). The seat valves are divided into: Two-port valves Three-port valves The actuating device consists of controlling element and actuator. 18

19 Two-port valve With the two-port valve, the cross-sectional area for the flow is increased or decreased by a change of stroke so that the volumetric flow can be varied to satisfy the demand for heating / cooling. Flow control Two-port valve (cross-section) Three-port valve The three-port valve has a port with a constant volumetric flow. Depending on the use of the valve - mixing or diverting the change of stroke is different. Mixing: The delivered volumetric flow remains constant. It is the result of two variable volumetric flows. Diverting: The incoming constant volumetric flow is divided into two variable outlet flows. (Note: not all types of three-port valves are suited for use as diverting valves). Mixing control Three-port valve with designation of ports (cross-section) Designation of ports Valve ports can be designated differently, e.g. I, II, III (see illustration above) or A, B, AB. 19

20 Balancing throttle Balancing throttles in the sections of hydraulic circuits with a constant volumetric flow are used during commissioning to adjust the calculated nominal volumetric flow. Hydraulic balancing The procedure is called hydraulic balancing. It is an important prerequisite for ensuring the correct functioning of the plant. balancing throttle Heating groups with balancing throttles (in the piping sections with constant volumetric flow) Circulating pump A hydraulic circuit operates correctly only if the circulating pump: is correctly sized is correctly installed and connected operates at the right speed Also, in certain types of hydraulic circuits, there is a risk of excessive pump temperatures, especially when the pump works against a fully closed valve (also refer to throttling circuits). In such situations, it is recommended to use speed-controlled pumps or to install a small, adjustable bypass which ensures minimum circulation when the valve is fully closed. Also, a pump can be deactivated via an end switch when the valve closes or when a minimum opening position is reached (e.g. < 2 %). 20

21 1.6. Distribution circuits In typical plants, one generation generally supplies multiple consumers. A distribution is the link between the heating / cooling generation and multiple consumers. Medium from the generation supply is distributed to various consumer circuits; the return medium from all consumer circuits is collected and returned to the generation. Distributor as the connecting element between heating generation and consumer side Requirements Consumers and generation place certain requirements on distributions e.g. pressure conditions, constant or variable flow, required flow and return temperatures, etc. Þ Various types of distribution circuits are needed to meet all these requirements. Suitable combinations A distribution cannot be considered on its own. It is important to use the generation and consumer circuits suitable for the distribution type. From the distribution s point of view, all the properties listed above must be the same (or similar) for all connected consumers. Therefore we will consider the distribution as part of the overall hydraulic setup. Hydraulic circuit model (example: heating plant) 21

22 Combinations of distribution and consumer circuits The overview includes a number of possible generators and consumers (list not conclusive). Not all generators can be combined with every type of consumer though. We will focus on three types of distribution and suitable consumer circuits that can be combined with selected generators and consumers to provide appropriate solutions. The solutions vary in regard to energy efficiency. Overview generation, distribution and consumer 22

23 Low-pressure distribution Valve closed Distribution between wood-fired boiler and room heating group Valve fully open Characteristics High return temperature to generation Constant volume flow in generation Clear hydraulic separation between generation and consumer Important for trouble-free use Generously size distribution and above all the bypass (short circuit) Connected consumer groups with constant or year round heat demand at the start of distribution (prevent unneeded flow through distribution) Field of use Generation requiring a high return temperature Energy efficiency There is only limited energy efficiency in this combination of distribution and consumer circuits. Reasons: Volumetric flow drawn by the distribution from the generation is constant and runs with high temperature. The temperature differential between distribution supply and return is very low at zero load and small at partial load. This results in significant losses of thermal energy in the generation and distribution. The volumetric flow provided continuously by the distribution pump is only needed at full load. The loss of pump energy is also significant. 23

24 Pressurized distribution at constant flow Valve closed Pressurized distribution at constant flow Valve fully open Characteristics High return temperature to generation Constant volumetric flow in generation Primary pump must assume pressure loss across consumers when using diverting circuits Hydraulic balancing is a challenge Important for trouble-free use Correctly sized controlling elements (valves) for the consumer groups Only recommended, if with regard to pump output, key consumers can be operated without a group pump Generation must be suitable for high return temperatures Field of use Generation requiring return minimum limitation Energy efficiency The level of energy efficiency is unsatisfactory in this combination of distribution and consumer circuits. Reasons: Nominal flow runs continuously throughout distribution as well as inlet and outlet of all consumer circuits. The temperature differential between distribution supply and return is very low at zero load and small at partial load. This results in considerable losses in thermal energy in the generation, distribution and connecting lines to consumer circuits. Distribution pump must be operated continuously at nominal flow. The required additional expense in pump transport energy is also considerable. 24

25 Pressurized distribution at variable flow Valve closed Valve fully open Pressurized distribution at variable flow, e.g. cold water storage tank, cooling coil and chilled ceilings Characteristics Cooling: High return temperature to generation Heating: Low return temperature to generation Variable volumetric flow in distribution Important for trouble-free operation Controlling elements (valves) for the consumer circuits must be properly sized Variable speed control pump or adjustable bypass for minimum circulation (The variable speed control reduces the use of energy or shuts down at zero low to prevent damage to the pump. The bypass is mounted at the beginning of the distribution.) Field of use Chilled water supply for cooling coils and chilled ceilings (example). (consider different working temperatures) Supply in district heating network (e.g. community heating supply) Energy efficiency This combination of distribution and consumer circuits is highly energy efficient. It represents a future-oriented approach! Reasons: The volumetric flow in the distribution is variable. It corresponds to the sum of all variable volume flows from all connected consumer circuits. As a result, the distribution only draws as much medium from the storage tank as is actually needed by the consumers. The temperature differential between distribution supply and return is sufficiently high at nominal load and increases with decreasing load (corresponding to return temperatures from variable volume consumer circuits). The temperature differential built up by generation (thermal energy) in the storage tank remains quite high and is used by this hydraulic circuit in an energy-efficient manner. 25

26 2 Hydraulic characteristics Parts of the hydraulic circuit also constitute part of the controlled system. To provide comfortable conditions for the occupants of the building while ensuring low wear and tear during the operation of the plant, the hydraulic circuits must also satisfy the requirements of control technology. The combination of characteristics and properties of valves, heat exchangers and pumps in the hydraulic circuit determines whether or not the actuating device (controlling element and actuator) is capable of adequately controlling the plant s heating / cooling output. The actuator converts the positioning signal from the controller to a linear or rotary movement of the controlling element so that the volumetric flow passing through it can be adjusted between 0 and 100 %. Goal is optimal controllability The aim is to achieve a linear relationship between valve travel and heating (cooling) output. In other words, when the valve position reaches 50 % of the stroke range, the heat output should be 50 % of the nominal output. Desired characteristic: 50 % heat output at 50 % valve opening In practice, however, this characteristic cannot be fully achieved. It is affected by a number of factors that are described in the following chapters Heat exchanger characteristic and a-value Heat exchanger characteristic The ratio of volumetric flow of the heat exchanger and heat output is dependent on the following factors: Design of the heat exchanger Temperature differential of water inlet and outlet Temperature differential between the heat-absorbing and heat-delivering medium which, as a rule, is not linear In the case of a small volumetric flow, the majority of heat exchanger characteristics are extremely steep. One consequence, for example, is the significant increase of the temperature of a heating coil for an air handling unit, even if the amount of hot water passing through it is relatively small. 26

27 Examples: 10 % volumetric flow Þ 27 % heat output Change from 60 % to 100 % volumetric flow Þ 18 % more heat output Typical heat exchanger characteristic (examples: radiators or cooling/heating coils for air handling units) a-value The a-value is the measure for the nonlinearity of a heat exchanger characteristic. The calculation is based on the temperature conditions at the heat exchanger and is dependent on the type of hydraulic circuit (see calculating the a-value in the Appendix). Conclusion: To attain the desired controllability of the plant the flexion (nonlinearity) of the heat exchanger characteristic must be offset by an appropriate valve characteristic. Heat exchanger characteristic with different a-values Ranges of typical heat exchanger characteristics: top: air cooling coil, variable flow middle: radiator heating bottom: heat exchanger water / water The following applies: a-value = 1 Þ linear characteristic a-value < 1 Þ upward inflection a-value > 1 Þ downward inflection 27

28 2.2. Valve characteristic The following parameters are important to determine the valve size: Required flow rate Pressure drop across the path with variable flow k V -values and k VS -value k V -value: flow value at a certain valve position (stroke) The k V value corresponds with the flow rate of water through a valve at a constant differential pressure of 1 bar across the controlled port. The unit is m 3 /h or l/min. The k V value of a valve is dependent on the valve s position (stroke). k VS -value: flow value when the valve is fully open The k V value of the fully open valve (nominal stroke H 100 ) is called the k VS -value. The manufacturers of seat valves and throttling valves specify this design-dependent variable k VS for every type of valve. To be able to compare different makes and types, all valves are specified in a uniform manner: k V values in relation to the k VS -value: k V / k VS = Stroke H in relation to the nominal stroke H 100 : H / H 100 = If k V / k VS is shown as a function of the stroke range , then this is called valve characteristic (or basic valve characteristic). Typical valve characteristic 28

29 Rangeability S V and smallest controllable flow value k Vr The rangeability S V of a valve is the ratio of the nominal flow value k VS to the smallest controllable flow value k Vr. Rangeability S V = k VS / k Vr Typical values of the S V reach from 50 to >150 The rangeability is an important characteristic that is used to assess the controllable range of a valve and is mainly dependent on the design of the valve plug and valve body. Smallest controllable flow value k Vr The smallest controllable flow value k Vr is the volumetric flow at the point where the valve suddenly opens, that is, where the valve s characteristic suddenly drops. The k Vr is either described in ratio to the k VS (k Vr /k VS ) or in m 3 /h. k Vr /k Vs H/H 100 Smallest controllable flow value k Vr of a valve Modulating control below k Vr is not possible because the valve only permits volume surges to pass (on / off operation) Different valve characteristics A distinction is made between: the basic form of the characteristic which is determined mathematically (that is, theoretically) the basic characteristic which represents the flow rate under standard conditions (1 bar, 25 C), ascertained at each valve position The most common basic forms of characteristics are briefly described next: Linear characteristic The same change of stroke produces the same change of k V -value. Equal-percentage characteristic The same change of stroke produces the same percentage change of the relevant k V -value, that is, the greater the stroke (the more open the valve), the greater the impact of the stroke change on the volumetric flow. In the lower stroke range, the characteristic is flat. In the upper stroke range, it becomes steeper and steeper. Equal-percentage/linear characteristic Basic form of the characteristic that is linear in the lower stroke range and that adopts an equalpercentage characteristic from about 30 % of stroke. 29

30 The basic form of the characteristic represents the basis for designing the valve plug which then determines the valve s basic characteristic. Linear characteristic Equal-percentage characteristic Equal-percentage / linear characteristic Comparison of valve characteristics 30

31 2.3. Characteristic of the controlled system When a valve is installed in a plant, the valve characteristic should offset the heat exchanger characteristic. The resulting output of the heat exchanger can also be shown in the form of a graph, the so-called characteristic of the controlled system or control characteristic. Heat exchanger characteristic curve Valve basic characteristic curve, equal-percentage Controlled system characteristic as the result of heat exchanger characteristic and valve with an equal-percentage basic characteristic A suitable valve characteristic was chosen here. The resulting control characteristic is almost linear. The controlled system can be controlled in a stable manner. 31

32 Heat exchanger characteristic curve Valve basic characteristic curve, linear Controlled system characteristic as the result of heat exchanger characteristic and valve with a linear basic characteristic With the selection of a linear valve characteristic it is not possible to compensate the a-value of the heat exchanger characteristic. The controlled system cannot be controlled in a stable manner. The graphs above reveal that through adequate selection of the valve characteristic the overall performance will be improved, but this is not yet enough to achieve a fully linear characteristic Valve operating characteristic and valve authority P V The characteristic of the controlled system is determined not only by the basic valve characteristic and the heat exchanger characteristic but also by the pressure drop across the valve. The valve s operating characteristic shows the correlation between stroke and volumetric flow of a valve installed in a hydraulic circuit. The operating characteristic is different from the valve s basic characteristic since the pressure differential across the valve s entire stroke range is not constant. 32

33 The extent of deviation is called the valve authority P V : Valve authority P V = Dp V100 / Dp total Dp total Dp V100 The valve authority P V is determined by Dp V100 and Dp total Impact of valve authority on the valve s basic characteristic Valve operating characteristics as a function of P V (example with a linear basic characteristic, that is, P V = 1.0) 33

34 The operating characteristics shown above (example with a linear basic characteristic) show the impact of the valve authority P V < 1 on the basic characteristic: The smaller the pressure drop Dp V100 across the valve in comparison with the affected piping with variable flow, the smaller the valve authority P V The smaller the valve authority P V, the greater the deformation of the basic characteristic If the valve authority P V = 1, the operating characteristic corresponds to the valve s basic characteristic consumer consumer controlling valve P V = 0.1 P V = 0.5 P V = 0.8 heat exchanger characteristic, a = 0.3 controlling valve P V = 0.1 P V = 0.1 P V = 0.5 P V = 0.5 P V = 0.8 P V = 0.8 basic characteristic valve operating characteristics resulting characteristic of the controlled system Heat exchanger characteristic, valve operating characteristics and the resulting characteristic(s) of the controlled system The graph shows which system characteristic results from a heat exchanger characteristic (a-value = 0.3) in combination with different valve operating characteristics. In the example above, a valve authority of P V = 0.8 produces a nearly linear system characteristic. 34

35 Oversized valves valve oversized valve correctly sized System characteristic with correctly and oversized valve Consequences of incorrect dimensioning Oversizing: The minimum controllable output Q min increases. Since the control limits the stroke according to the required nominal output, the usable correcting span of the valve will be restricted. Due to these effects the plant will become more difficult to control. Undersizing: The required volumetric flow cannot pass through the valve In the system an unnecessarily high pressure drop occurs and a more powerful pump is needed. Benefits resulting from a correctly sized valve: Smaller initial flow surge V min, therefore the minimum controllable output Q min will be smaller Higher valve authority P V Valve stroke of % can be fully used The controllability will be considerably improved 35

36 Controlling in the low load range Initial flow surge V min = smallest volumetric flow through a valve that can be controlled in modulating mode Initial flow surge as a function of valve authority P V and rangeability S V Initial output surge Q min = smallest possible output of a consumer (e.g. of a radiator) that can be controlled in modulating mode The initial output surge becomes the smaller, the larger the rangeability S V of the valve the higher the valve authority P V the greater the a-value of the heat exchanger (that is, smaller temperature differentials of heat source and consumer circuit) 36

37 2.4. Plant characteristics, pump characteristics and operating point The plant characteristics and the pump characteristics are needed to determine the operating point of the pump. The correct operating point is essential to reach a stable and energy efficient system. n = constant Plant characteristic (piping network characteristic) Pump characteristic with constant speed n operating point Operating point Plant characteristic (piping network characteristic) Plant characteristic The plant characteristic shows the pressure drop p of the whole piping network. The pressure drop depends, among others, on the following parameters: temperature speed of water volumetric flow friction local situation (piping characteristics such as quality, number of bends, nominal size, lengths, etc) plant elements (heat meters, balancing throttles, etc) medium (glycol, viscosity, heat transfer oil, steam, etc) 37

38 Hydraulic resistances in HVAC plants Each part in an HVAC plant contributes to the differential pressure and thus to the hydraulic resistance to the water flowing in a pipe. Therefore it is mandatory to know the parts with high differential pressures in the piping network. Dp supply Dp valve Dp [kpa] Dp generation Dp return Dp consumer Dp consumer Dp plant Dp valve Dp supply Dp generation Dp return V [m 3 /h] Hydraulic resistances in HVAC plants Added resistances p of the individual components In the example shown above these resistances are: generation consumer valves pipes Possible values of the different elements of the plant boiler: p generation = kpa pipes ( l/h): p pipes = Pa/m consumers: p consumer = kpa All elements of the plant in this example are connected in series. Law of proportionality In hydraulic systems in HVAC plants the 2 nd law of proportionality applies: p 1 = V 1 p 2 V 2 2 The resistance changes with the square to the volumetric flow in the piping network. The elements of a given plant can be considered as a constant C (simplification). Hence the plant characteristic can be determined with the formula: 2 Pressure drop p = C V Calculation of a plant characteristic (piping network characteristic) Plant design data: volumetric flow: 10 m 3 /h differential pressure: 3 mwc 30 kpa = 0.3 bar (mwc: meter water column) 38

39 With this data, the constant C for this plant characteristic can be determined. 2 Differential pressure: p = C V converted with respect to C: C = p 2 V Many pump suppliers specify the pressure head of the pump as pump head in meters. The unit is mwc, meter water column. This corresponds with the hydrostatic pressure. Thus, it is easier to calculate with H instead of p. H p C = H 2 V Þ C = 3 mwc (10 m 3 /h) = 3 mwc mwc = (m 3 /h) 2 (m 3 /h) 2 Determination of the pump head, using C (e.g. volumetric flow: 4 m 3 /h): 2 H = C V Þ H = 0.03 mwc (m 3 /h) 2 4 m3 / h = 0.48 mwc Further data of this plant characteristic are determined the same way. volumetric flow V [m 3 /h] pump head (differential pressure) H [mwc] With this data, the plant characteristics can be outlined. pump head H [m] plant characteristic Resulting plant characteristic outlined in a pump diagram [m 3 /h] 39

40 Pump characteristic Determination of the pump pressure The differential pressure across the pump is supposed to be equal to the sum of all other partial resistances in the plant. p pump = p generation + p supply + p valve + p consumer + p return Dp supply Dp valve Dp [kpa] plant characteristic Dp generation Dp pump pump characteristic n = constant Dp pump Dp consumer Dp return Dp plant HVAC plant with outlined hydraulic resistances in all parts of the plant p pump = p plant V [m 3 /h] The total resistance corresponds to the sum of all partial resistances in the plant (without pump). The pump needs to build up the same pressure to overcome this total resistance. The pressure provided by the pump corresponds to the pump head of the pump. Þ p plant = p pump pump head in mwc Dependency of the pressure difference across the pump and the volumetric flow The increase of the pressure in the pump and the volumetric flow through the pump depend on each other. The pump characteristic shows this fact. There is a different pump characteristic for each speed of the pump. Dp [kpa] n = constant V [m 3 /h] Pump characteristic at constant speed n Pump characteristics at different speeds (n 1 n 3) 40

41 Operating point The operating point is characterized by: V plant p plant = V pump p pump Thus, the operating point is at the intersection of the pump characteristic and the plant characteristic (e.g. at the state of design) Requirement: V plant = V pump and hence as well p plant = p pump In the operating point the pump head of the pump is equal to the total resistance of the plant at the pumped volumetric flow. Dp [kpa] plant characteristic ccharacteristic Dp operating point pump characteristic V [m 3 /h] Operating point DV 2 If the volumetric flow changes, the operating point changes as well ( p = C V ). To design the optimal operating point, it is important to understand the interaction of pump characteristic and plant characteristic. Undesired consequences may result, if the condition V plant p plant = V pump p pump is not met. Consequences of an operating point that is not properly designed Volumetric flow too high: pump delivers more than needed output too high room temperature too high Volumetric flow too low: pump head is smaller than the differential pressure required from the system output too low room temperature too low 41

42 Pump head As mentioned above the differential pressure of the pump corresponds to the pump head in the state of design: p pump pump head in mwc If the pump head is higher than the required differential pressure to overcome the resistance of the piping network a throttling (balancing) valve will be mounted (see page 19, hydraulic balancing). 42

43 2.5. The operation of pumps The behavior of uncontrolled and controlled pumps will be shown in the following chapters The operation of uncontrolled pumps If the valve closes, the resistance increases and the volumetric flow V decreases. Hence, the plant characteristic becomes steeper. Due to the higher resistance in the piping network the pump needs to provide a higher pressure. With uncontrolled pumps the speed n remains constant and the operating point follows the pump characteristic to the left. The example shown below demonstrates the shifting of the operating point at part load 50 % and as a result, the related changes in the energy consumption of the pump. Dp [kpa] Dp [kpa] V [m 3 /h] V [m 3 /h] V design V part load Operating point at full load Operating point at part load 50 % P [kw] P [kw] V [m 3 /h] V [m 3 /h] V design V part load Power consumption at full load Power consumption at part load 50 % 43

44 The operation of controlled pumps Constant pump pressure Controlled pump with constant pump pressure At part load the pressure across the pump is kept constant. This can be controlled either electronically in the pump itself or with a pressure dependent control and a variable speed drive at the pump. Þ The operating point follows the line of constant pressure horizontally to the left. The example shown below demonstrates the shifting of the operating point at part load 50 % and as a result, the altered energy consumption of the pump. Dp [kpa] Dp [kpa] Dp constant V [m 3 /h] V [m 3 /h] V design V part load Operating point at full load Operating point at part load 50 % P [kw] n 1 n 2 P [kw] n 1 n 2 V [m 3 /h] V [m 3 /h] V design V part load Power consumption at full load Power consumption at part load 50% 44

45 Constant differential pressure across the end of the plant Controlled pump with constant differential pressure (Dp 0) at the end of the plant The differential pressure Dp 0 is held constant across the end of the plant. There are two possibilities to achieve this constant pressure at the end: a measuring point at the end of the plant, connected to a pressure control and a variable speed drive (VSD) at the pump an electronic control in the pump itself ( Dp variable control) Þ The operating point follows the control slope that runs towards Dp 0 near V = 0 m 3 /h The example shown below demonstrates the shifting of the operating point at part load 50 % and as a result, the related changes in the energy consumption of the pump. Dp [kpa] Dp [kpa] n 1 n 2 n 3 V [m 3 /h] n 1 n 2 n 3 V [m 3 /h] V design V part load Operating point full load Operating point part load 50 % P [kw] n 1 P [kw] n 1 n 2 n 2 n 3 n 3 V design V [m 3 /h] V part load Power consumption at full load Power consumption at part load 50 % V [m 3 /h] The plant characteristic is steeper at part load (50 %). Due to the reduced volumetric flow the resistance in the plant is reduced as well. The controlling across the end of a plant ensures that the necessary differential pressure there is still maintained. With a controlled pump with the measuring point at the end, the energy consumption of the pump is even further reduced. Energy savings with controlled pumps For plants with variable volumetric flows, controlled pumps save energy very efficiently. The selection of the control system depends on the situation on site (distances, investments, etc.) As shown in the chart below, controlled pumps consume less power. Thus, energy and costs can be saved. A pump with constant differential pressure across the end of the plant is more efficient than a controlled pump with a constant pump pressure. 45

46 The chart below shows the saving capacity on the basis of a data sheet of a pump. pump head H b c a Dp pump constant Dp across end point of plant d V power consumption P B C A D V V part load V design Operating points and power consumption in comparison a: operating point, design b: operating point, part load, uncontrolled c: operating point, part load, controlled Dp pump d: operating point, part load, controlled Dp end A: power consumption, design B: power consumption, part load, uncontrolled C: power consumption, part load, controlled Dp pump D: power consumption, part load, controlled Dp end 46

47 3 Sizing the controlling elements The previous chapters covered hydraulic circuits, controlling elements and the physical fundamentals of a plant. In this chapter you will find a detailed description of how to size a controlling element. Before the sizing of actuating devices (controlling elements and actuators) can be started and before they can be selected, all important data about the plant must be available: The basic diagrams of the hydraulic circuits of both the heat source and consumer side (either geographic or synoptic diagrams) The thermal power provided by the heat source and consumer side with the associated temperature differentials The designations of the heat sources and consumers e.g. Heating group West, Floor heating new building, Air heating coil, etc. Þ These sometimes provide information on crucial plant issues. It is also important to know whether the subject hydraulic circuits or control loops (e.g. floor heating systems) are standard or whether special hydraulic circuits are used, making it necessary to gather special detailed information about the plant, such as: start-up control of a heat pump hot water charging with controlled charging temperature district heat substations plant sections with high network pressures etc. When sizing controlling elements, the different hydraulic circuits and their properties must be taken into account. It is also of utmost importance to know the pressure drops in the part of the piping with variable volumetric flow and across the individual plant components in the hydraulic circuits, such as air heating coils, heat meters, etc. (also refer to section 3.1.1). Once all this information is available, the controlling element can be straightforwardly and accurately sized to satisfy plant conditions Piping sections with variable volumetric flow in different hydraulic circuits When sizing controlling elements, it is very important to identify network sections with variable flow of water (in operation) correctly, because the pressure drop in these sections (with the installed plant components) is an important factor. 47

### Why and How we Use Capacity Control

Why and How we Use Capacity Control On refrigeration and air conditioning applications where the load may vary over a wide range, due to lighting, occupancy, product loading, ambient weather variations,

Frequently Asked Questions System and Valve Basics: 1. Q: What is good cooling coil performance? A: The temperature range is controlled within +/- 0.5 F (0.28 C) off the cooling coil at set point or below.

### SUBJECT: HYDRAULIC CHECK VALVES AND FLOW CONTROL VALVES

SUBJECT: HYDRAULIC CHECK VALVES AND FLOW CONTROL VALVES ABOUT THE SESSION This session deals with check valves, flow control valves, its functions, operations and application. INTRODUCTION Check Valve:

### HVAC Processes. Lecture 7

HVAC Processes Lecture 7 Targets of Lecture General understanding about HVAC systems: Typical HVAC processes Air handling units, fan coil units, exhaust fans Typical plumbing systems Transfer pumps, sump

### Module 6. Actuators. Version 2 EE IIT, Kharagpur 1

Module 6 Actuators Version 2 EE IIT, Kharagpur 1 Lesson 25 Control Valves Version 2 EE IIT, Kharagpur 2 Instructional Objectives At the end of this lesson, the student should be able to: Explain the basic

### VAV BOX REHEAT SELECTION

VAV BOX REHEAT SELECTION KRUEGER EXCELLENCE IN AIR DISTRIBUTION Page # 1 VAV terminals provide a measured quantity of conditioned air to a space, in response to a control signal from a thermostat or room

### Applying Pressure Independent Control Valves in H.V.A.C. Systems. A Presentation to: Orange Empire ASHRAE Santa Ana Nov. 17, 2009

Applying Pressure Independent Control Valves in H.V.A.C. Systems A Presentation to: Orange Empire ASHRAE Santa Ana Nov. 17, 2009 1 Introduction I know, as building design consultants, so much of your effort

### UNIT 2 REFRIGERATION CYCLE

UNIT 2 REFRIGERATION CYCLE Refrigeration Cycle Structure 2. Introduction Objectives 2.2 Vapour Compression Cycle 2.2. Simple Vapour Compression Refrigeration Cycle 2.2.2 Theoretical Vapour Compression

### 2-way control valves VEFS 2

Data sheet 2-way control valves VEFS 2 Description/Application VEFS 2 valves are a range of 2 port high specification flanged valves for chilled water, LPHW, MPHW, HPHW (low, medium or high pressure hot

### Variable-flow water systems Design, installation and commissioning guidance

APPLICATION GUIDE AG 16/2002 Variable-flow water systems Design, installation and commissioning guidance By Arnold Teekaram and Anu Palmer Supported by PREFACE There are significant benefits to variable

### UNDERSTANDING SCHEMATICS. Introduction

UNDERSTANDING SCHEMATICS Introduction When hydraulic systems are designed, whether on paper or computer, the layout of the system is expressed in what is called a schematic. A schematic is a line drawing

### COPPER TUBES IN DOMESTIC HEATING SYSTEMS

Copper Development Association COPPER TUBES IN DOMESTIC HEATING SYSTEMS Pipe Sizing: Basic Principles Introduction Tube diameters for central heating circuits should be selected so that there is sufficient

### FLUID POWER GRAPHIC SYMBOLS

FLUID POWER GRAPHIC SYMBOLS ANSI Y32.10 GRAPHIC SYMBOLS 1. Introduction 1.1 General Fluid power systems are those that transmit and control power through use of a pressurized fluid (liquid or gas) within

### Industrial Steam System Process Control Schemes

Industrial Steam System Process Control Schemes This paper was developed to provide a basic understanding of the different process control schemes used in a typical steam system. This is however a fundamental

### Eurocondense three. Working towards a cleaner future. Floor Standing Condensing Boilers 125 to 300kW. heating specialists

Eurocondense three Floor Standing Condensing Boilers 125 to 300kW Working towards a cleaner future heating specialists Eurocondense three Floor Standing Condensing Boilers 125 to 300kW Maximum Output on

### VARIABLE VOLUME / VARIABLE SPEED SYSTEMS APPLICATIONS

Bulletin D-120B Pages D120-115 to D120-118 VARIABLE SPEED PRIMARY CHILLED WATER PUMP CONTROL WITH TWO WAY VALVE DIRECT RETURN SYSTEM DESCRIPTION: The volume of water supplied to the system is varied in

### Acvatix well-designed combi valves for high energy efficiency

Acvatix well-designed combi valves for high energy efficiency Increased flexibility and simplicity for planning, installing, and commissioning HVAC plants Answers for infrastructure. Acvatix combi valves

### Objective - Determining characteristic curve of a four-stroke Diesel engine - Calculating thermal efficiency of the engine

Objective - Determining characteristic curve of a four-stroke Diesel engine - Calculating thermal efficiency of the engine Apparatus The experimental setup, shown in Fig. 1, has three main parts: engine,

### HEAT INTERFACE UNITS (Modular)

HEAT INTERFACE UNITS The Rhico T Fire Modular is probably the most versatile HIU available, the basic unit is a indirect heating only module incorporating a circulation pump on the secondary circuit. (A

### 3-Way Temperature Control Valve

3-Way Temperature Control Valve l G, Version G and Accessories Charge air cooling Secondary cooling systems Fuel and lube oil preheating Co-generation Engine jacket water GG valve Waste heat boilers Product

### DN [mm] [m 3 /h] Characterizing disk Dimensions / Weights see Â«Dimensions and weightsÂ», page 3 Motorizing

Technical data sheet R5.. Characterized control valves, 3-way, with external thread for open and closed cold and warm water systems for modulating control on the water side of air-handling and heating

### Example. Fluid Power. Circuits

Example Fluid Power Circuits To Enhance Symbol Reading Skills To Work On Circuit Reading Skills With Answers HI LO Pump Circuit 18 A1 B1 17 16 15 13 Set 14 2,000 PSI PG2 Set 500 PSI 12 11 7 8 10 PG1 9

### TECH TIP # SEER and the TEV Removing the Mystery of the Thermostatic Expansion Valve

TECH TIP # 28 One of a series of dealer contractor technical advisories prepared by HARDI wholesalers as a customer service. 13 SEER and the TEV Removing the Mystery of the Thermostatic Expansion Valve

### Example Retrocommissioning Measure: Opening Throttled Discharge Valves

Opening Throttled Discharge Valves This 21-story building, constructed in 1997, is located in Oregon and contains 589,000 gross square feet of mostly office occupancy. The HVAC system includes six large

### Pneumatic Transmission of Energy. How a Positive Displacement Compressor Works

neumatic Transmission of Energy The reason for using pneumatics, or any other type of energy transmission on a machine, is to perform work. The accomplishment of work requires the application of kinetic

### RVL470. Heating Controller. Building Technologies HVAC Products. Series B

2 522 Heating Controller Series B RVL470 Multifunctional heating controller for use in residential and non-residential buildings; suitable for weather-dependent flow temperature control of heating zones

### BRAVA small size, big performance

BRAVA small size, big performance www.sime.it BRAVA: small size, big performance Brava Slim and Brava One are part of a new generation wall hung boilers, particularly compact and functional. They represent

### Fundamentals of HVAC Control Systems

ASHRAE Hong Kong Chapter Technical Workshop Fundamentals of HVAC Control Systems 18, 19, 25, 26 April 2007 2007 ASHRAE Hong Kong Chapter Slide 1 Chapter 3 Control Valves and Dampers 2007 ASHRAE Hong Kong

### Centrifugal Fans and Pumps are sized to meet the maximum

Fans and Pumps are sized to meet the maximum flow rate required by the system. System conditions frequently require reducing the flow rate. Throttling and bypass devices dampers and valves are installed

### Building Controls Training Courses from the BCIA

Building Controls Training Courses from the BCIA BCO Introduction to building controls and HVAC This introductory course is designed for those who either do not require the full technical detail of the

### Motorized valves 2 and 3 way up to 150 C BR216RA - BR316RA + Electric actuators MC55(Y) - MC100 - MC161

3-way valve BR316RA + actuator MC(Y) 2-way valve BR216RA + actuator MC0 1. CaractÃ©ristiques Suitable for the control of hot and chilled water (0 C... +10 C) in HVAC systems control of heating plants. Above

### MANUAL. for installation and start up of cooling hydraulic module HMC30 MkI

MANUAL for installation and start up of cooling hydraulic module HMC30 MkI IM HMC30MkI EN 02 2014 Table of Contents General information Main parts of hydraulic module........3 Overall and mounting dimensions..4

### Your tool for designing efficient balancing solutions for heating and cooling systems

Application guide Your tool for designing efficient balancing solutions for heating and cooling systems 18 applications Our recommended applications for heating and cooling systems will improve comfort

### Heating Controller. Building Technologies HVAC Products

2 474 Heating Controller RVP300 Multifunctional heating controller for use in residential and non-residential buildings; suitable for weather-dependent flow temperature control of heating zones with or

### Commissioning - Construction Documents (Page 1 of 6)

Commissioning - Construction Documents (Page 1 of 6) A. General Information Climate Zone: Building Type: Conditioned Area (sf): Reviewer's Name: Reviewer's Agency: Note: Design Review for each system/subsystem

### Overview. Introduction Cooling Tower Basics Principles of Operation Types of Cooling Towers Common Applications Design Considerations

Stephen Lowe ASHRAE Hampton Roads Chapter Past President AECOM Design Mechanical Engineering Discipline Manager, Virginia Beach Division Professional Engineer Commonwealth of Virginia, NCEES BSME University

### Energy consumption and heat recovery of refrigeration system in modern Arena

Energy consumption and heat recovery of refrigeration system in modern Arena By Alexander Cohr Pachai Johnson Controls Building Efficiency Christian X s Vej 201 8270 Hoejbjerg Denmark alexander.c.pachai@jci.com

### TA-COMFORT-W. Prefabricated units Heating interface unit for hot water services

TA-COMFORT-W Prefabricated units Heating interface unit for hot water services IMI TA / Control valves / TA-COMFORT-W TA-COMFORT-W All in one design with thermostatic mixing valve and/or temperature maintaining

### Powermite 599 Series MT Series Terminal Unit Three-way Valves

Document No. 155-197P25 VF 599-6 Powermite 599 Series MT Series Terminal Unit Three-way Valves Description The Powermite Series ANSI Class 250 MT Series three-way valves are designed to work with any MT

### Carnegie Mellon University School of Architecture, Department of Mechanical Engineering Center for Building Performance and Diagnostics

Carnegie Mellon University School of Architecture, Department of Mechanical Engineering Center for Building Performance and Diagnostics A Presentation of Work in Progress 4 October 2006 in the Intelligent

### The main steam enters the building in the basement mechanical room; this is where the condensate line also leaves the building.

MSV: Square Footage: 24,844 No. of Floors: 1 Year Built: 1963 Type of Use: Lounge and dining area open all night for snacks Steam Water-cooled condenser, 50-Ton York unit with a 6 cylinder-reciprocating

### NEBB STANDARDS SECTION-8 AIR SYSTEM TAB PROCEDURES

NEBB STANDARDS SECTION-8 AIR SYSTEM TAB PROCEDURES 8.1 INTRODUCTION Testing, adjusting, and balancing of HVAC systems can best be accomplished by following a series of systematic procedures. The NEBB TAB

### Dynamic Process Modeling. Process Dynamics and Control

Dynamic Process Modeling Process Dynamics and Control 1 Description of process dynamics Classes of models What do we need for control? Modeling for control Mechanical Systems Modeling Electrical circuits

### Refrigerant R410A. Mini SysAqua DCI. 5.5 to 16.0kW. Air-to-Water DCI Heat Pumps Models M.AQA05 DCI to M.AQA16 DCI

Refrigerant R4A Mini SysAqua DCI Air-to-Water DCI Heat Pumps Models M.AQA05 DCI to M.AQA16 DCI 5.5 to 16.0kW Mini SysAqua DCI 1 Strength Points By introducing the variable speed in our packaged heat pump

### Unit 24: Applications of Pneumatics and Hydraulics

Unit 24: Applications of Pneumatics and Hydraulics Unit code: J/601/1496 QCF level: 4 Credit value: 15 OUTCOME 2 TUTORIAL 1 HYDRAULIC PUMPS The material needed for outcome 2 is very extensive so there

### Unit 24: Applications of Pneumatics and Hydraulics

Unit 24: Applications of Pneumatics and Hydraulics Unit code: J/601/1496 QCF level: 4 Credit value: 15 OUTCOME 2 TUTORIAL 3 HYDRAULIC AND PNEUMATIC MOTORS The material needed for outcome 2 is very extensive

### Electromotoric actuators

4 573 SQS35.50, SQS35.53, SQS65.5 with spring return function, without manual adjuster ACVATIX Electromotoric actuators for valves with 5.5 mm stroke SQS35.00, SQS35.03, SQS65, SQS65.2, SQS85.00, SQS85.03

### VE 6.4.0.5: Thermal / Systems Pack. 1. Tabular Room Data editing for thermal properties

VE 6.4.0.5: Thermal / Systems Pack 1. Tabular Room Data editing for thermal properties There is a new button in Apache, UK Part L2, and PRM Tabular Room Data. This tool represents a real productivity enhancement

### Thermal actuators. for radiator valves, small valves and zone valves. 2-position control of heating systems chilled ceilings and terminal units

4 877 Thermal actuators for radiator valves, small valves and zone valves STA21 STA71 STA21 AC 230 V operating voltage, 2-position control signal STA71 AC/DC 24 V operating voltage, 2-position control

### WHAT IS A CONTROL VALVE AND HOW DOES IT AFFECT MY CONTROL LOOP?

1 WHAT IS A CONTROL VALVE AND HOW DOES IT AFFECT MY CONTROL LOOP? Control valves may be the most important, but sometimes the most neglected, part of a control loop. The reason is usually the instrument

### Intelligence down to the last detail.

Intelligence down to the last detail. We question what is already there. That is how we create something new. Those who have developed high-quality products are faced with two options: to declare themselves

### COUNTERBALANCE VALVES

COUNTERBALANCE VALVES Introduction They are modulating valves which allow free flow into the actuator and then block the reverse flow until they feel a pilot pressure inversely proportional to the load

### The Piping System Model a New Life Cycle Document. Elements of the Piping System Model

Piping System Model as a Life Cycle Document White Paper Introduction When designing piping systems, a variety of documents are created providing the details necessary to design, purchase, build, and test

### HEAVY DUTY STORAGE GAS

Multi-Fin flue technology Flue damper saves energy Electronic controls HEAVY DUTY STORAGE GAS Dependability The Rheem heavy duty gas range is the work horse of the industry having proved itself over many

### Water supply in tall buildings: roof tanks vs. pressurised systems

Water supply in tall buildings: roof tanks vs. pressurised s Introduction The use of roof tanks to ensure adequate water pressure in buildings, and especially tall buildings, is very common. The alternative

### Material taken from Fluid Power Circuits and Controls, John S. Cundiff, 2001

Pressure Control Chapter 3 Material taken from Fluid Power Circuits and Controls, John S. Cundiff, 2001 Introduction Pressure control is a key element in the design of any circuit. Used correctly, it can

Laddomat 21-60 Charging unit User and installation instructions NOTE! Diagrams in this brochure only describe connection principles. Each installation must be measured and carried out according to the

### ENERGY EFFICIENT. Water Cooling... Savings of up to 25% of cooling water costs can be easily achieved. Reduce. Optimise Chilled &

03 Reliable and consistent cooling water is essential for the efficient manufacture of plastics. Energy is needed to reduce water temperature to the required level using cooling or chilling plant, often

### Mixing Valves. ARGUS Application Note: Mixing Valves

Mixing Valves Most radiant hot water heating systems in greenhouses use mixing valves to control the temperature of heating pipes. Both 3-way and 4- way valves are commonly used. Mixing valves provide

### CHILLER PLANT CONTROL MULTIPLE CHILLER CONTROLS

CHILLER PLANT CONTROL MULTIPLE CHILLER CONTROLS By: Michael J. Bitondo, Mark J. Tozzi Carrier Corporation Syracuse, New York August 1999 INTRODUCTION In December of 1998, the American Refrigeration Institute

### c h i l l e r G l o s s a ry of Te rm s A p p r o a c h Temperature difference between the leaving fluid and the evaporating

c h i l l e r G l o s s a ry of Te rm s A p p r o a c h Temperature difference between the leaving fluid and the evaporating refrigerant ARI Standard Conditions 54 F. water inlet; 44 F. water out; 35 F.

### 2- and 3-port valves with flanged connections, PN 10

4 402 VVF32.. VXF32.. ACVATIX 2 and 3port valves with flanged connections, PN 10 From the largestroke valve line VVF32.. VXF32.. Performance valves for medium temperatures from 10 150 C Valve body of grey

### Grant Agreement No. 228296 SFERA. Solar Facilities for the European Research Area SEVENTH FRAMEWORK PROGRAMME. Capacities Specific Programme

Grant Agreement No. 228296 SFERA Solar Facilities for the European Research Area SEVENTH FRAMEWORK PROGRAMME Capacities Specific Programme Research Infrastructures Integrating Activity - Combination of

### We have been working in an ideal climate for thirty years.

Underfloor cooling We have been working in an ideal climate for thirty years. A climate that has brought us to a position of leadership in Italy in the field of radiant heating and cooling. RDZ was the

### VARIABLE VANE PUMPS V3

VARIABLE VANE PUMPS V3 (series 30 and 40) Nominal sizes 12; 25; 40; 63 up to p n 100 bar V g 8.5; 19; 32; 47 cm 3 /rev KE 1015 11/02 replaces 07/97 easy commissioning due to automatic bleed facility low

### The Secret of Hydraulic Schematics. BTPHydraulics www.iranfluidpower.com

The Secret of Hydraulic Schematics BTPHydraulics www.iranfluidpower.com www.iranfluidpower.com Table of Contents The Secret to Reading and Interpreting Hydraulic Schematics... 1 Hydraulic System Schematics...

### ACVATIX Modulating control valves with magnetic actuator, PN16

4 454 ACVATIX Modulating control valves with magnetic actuator, PN16 for chilled and low-temperature hot water systems or for systems with media containing mineral oils (M3P..FYP) M3P..FY M3P..FYP Fast

### Zenith Solar thermal 4.5m pump station Installation manual

Zenith Solar thermal 4.5m pump station Installation manual Product code: 20026145 INSTALLATION MANUAL WATER RETURN GROUP This instruction manual is an integral part of the installation and maintenance

### Energy savings in commercial refrigeration. Low pressure control

Energy savings in commercial refrigeration equipment : Low pressure control August 2011/White paper by Christophe Borlein AFF and l IIF-IIR member Make the most of your energy Summary Executive summary

### LG Electronics AE Company, Commercial Air Conditioning

www.lgeaircon.com New concept Ecofriendly Highefficiency Heating solution Total heating & Hot water Solution for MULTI V LG Electronics AE Company, Commercial Air Conditioning 2 Yeouidodong, Yeongdeungpogu,

### 1. INTRODUCTION Internal combustion engines are devices that generate work using the products of combustion as the working fluid rather than as a

1. INTRODUCTION Internal combustion engines are devices that generate work using the products of combustion as the working fluid rather than as a heat transfer medium. To produce work, the combustion is

### Michael Montgomery Marketing Product Manager Rosemount Inc. Russ Evans Manager of Engineering and Design Rosemount Inc.

ASGMT / Averaging Pitot Tube Flow Measurement Michael Montgomery Marketing Product Manager Rosemount Inc. Russ Evans Manager of Engineering and Design Rosemount Inc. Averaging Pitot Tube Meters Introduction

### VAV Reheat Box Control

3. For all except very noise sensitive applications, select VAV boxes for a total (static plus velocity) pressure drop of 0.5 H2O. For most applications, this provides the optimum energy balance (see the

### HERZ-Thermal Actuators

HERZ-Thermal Actuators Data Sheet 7708-7990, Issue 1011 Dimensions in mm 1 7710 00 1 7710 01 1 7711 18 1 7710 80 1 7710 81 1 7711 80 1 7711 81 1 7990 00 1 7980 00 1 7708 11 1 7708 10 1 7708 23 1 7709 01

### Thermal actuators. for radiator valves, small valves and zone valves

4 877 Thermal actuators for radiator valves, small valves and zone valves STA21 STA71 STA21 AC 230 V operating voltage, 2-position control signal STA71 AC/DC 24 V operating voltage, 2-position control

### ASPE Seminar Water Heater Piping Strategies. Presented by Joe Kalarickal, EIT Regional Sales Manager AERCO International

ASPE Seminar Water Heater Piping Strategies Presented by Joe Kalarickal, EIT Regional Sales Manager AERCO International Presentation Overview Water Heater Piping Strategies How to size a water heater?

### Pump Ratio and Performance Charts

Pump Ratio and Performance Charts Concept and Theory Training Table of Contents Introduction... 1 Overview... 1 How to use this Module... 2 Learning Objectives...2 Text...2 Charts, Illustrations...2 Progress

### CGC s Hybrid System Loop Control

verview The CGC Group Hybrid Heat Pump System does NT operate with the same fluid loop temperatures as a conventional reversing Water Source Heat Pump system. The CGC system differs from a WSHP system

### C. starting positive displacement pumps with the discharge valve closed.

KNOWLEDGE: K1.04 [3.4/3.6] P78 The possibility of water hammer in a liquid system is minimized by... A. maintaining temperature above the saturation temperature. B. starting centrifugal pumps with the

### DRY MECHANICAL BOOSTERS REPLACE STEAM EJECTOR

DRY MECHANICAL BOOSTERS REPLACE STEAM EJECTOR Steam ejectors find wide use in vacuum pumping applications so called dirty application such as in Vapour extraction, Chemical processing, Evaporative Cooling,

### Neighbourhood Energy Connectivity Standards

Neighbourhood Energy Connectivity Standards Design Guidelines March 2014 Disclaimer: The following information is provided for general use and the user assumes all responsibility. The information contained

### Electromotoric Actuators

4 554 Electromotoric Actuators for valves with 2 mm stroke SQX32.. SQX82.. SQX62 SQX32.. operating voltage AC 23 V, 3-position positioning signal SQX82.. operating voltage AC 24 V, 3-position positioning

### Indirect passive solar heating systems

3.2.4. Indirect passive solar heating systems Indirect passive solar systems are also combined with the existing elements and structures adding absorption, accumulation and distribution of the received

### HEAT PUMP SIZING. Bard Manufacturing Company, Inc. Bryan, Ohio 43506

HEAT PUMP SIZING Bard Manufacturing Company, Inc. Bryan, Ohio 43506 Since 1914... Moving ahead, just as planned. Manual No.: 2100-057 Rev. A Superseds: 2100-057 File: Volume I, Tab 1 Date: 08/30/95 CONTENTS

### INSTALLATION AND OPERATION MANUAL

INSTALLATION AND OPERATION MANUAL Flow water heaters type POW-LCD 12, 15, 18, 21, 24 Before using the heater, please read the instructions carefully. In the future it will benefit by its failure-free operation

### HYDRAULIC BRAKE SYSTEMS AND COMPONENTS FOR OFF-HIGHWAY VEHICLES AND EQUIPMENT

HYDRAULIC BRAKE SYSTEMS AND COMPONENTS FOR OFF-HIGHWAY VEHICLES AND EQUIPMENT David E. Keyser Applications Coordinator Keith Hogan OEM Sales MICO, Inc. 1911 Lee Boulevard North Mankato, MN U.S.A. 56003-2507

### Refrigeration and Airconditioning Prof. M. Ramgopal Department of Mechanical Engineering Indian Institute of Technology, Kharagpur

Refrigeration and Airconditioning Prof. M. Ramgopal Department of Mechanical Engineering Indian Institute of Technology, Kharagpur Lecture No. # 22 Refrigeration System Components: Compressor (Continued)

### Transient Mass Transfer

Lecture T1 Transient Mass Transfer Up to now, we have considered either processes applied to closed systems or processes involving steady-state flows. In this lecture we turn our attention to transient

### INTERNATIONAL FIRE TRAINING CENTRE

INTERNATIONAL FIRE TRAINING CENTRE FIREFIGHTER INITIAL HYDRAULICS Throughout this note he means he/she and his means his/hers. Areas In bold type are considered to be of prime importance. INTRODUCTION

### Belimo Characterized 6-way Control Valve...

Belimo Characterized 6-way Control Valve...... for Barcol Chilled Ceiling / Chilled Beam Solutions Characterized control valves, 6-way, with internal threads Installation with LR MP/LON Benefits with Chilled

### GESTRA Information C 1.2

Issue Date: 9/06 GESTRA Steam Systems GESTRA Information C 1.2 Utilization of the sensible heat of condensate Examples of effective steam plant design and appropriate equipment 1 Heat content of saturated

### Balancing Variable Flow Hydronic Systems

The following article was published in ASHRAE Journal, October 2002. Copyright 2002 American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. It is presented for educational purposes

### Thermal actuators. for terminal unit valves VVP47..., VXP47... and VMP47... For water-based control of terminal units, heating and cooling zones

4 878 Thermal actuators for terminal unit valves VVP47, VXP47 and VMP47 STP21 STP71 STP21 AC 230 V operating voltage, 2-position control signal STP71 AC/DC 24 V operating voltage, 2-position control signal

### Hydrogen Isotope Separation Using Gas Chromatography

1 Hydrogen Isotope Separation Using Gas Chromatography Aaron Jo Victor Senior High School Advisors: Dr. Walter Shmayda, Neil Redden Dec 2012 2 Abstract A gas chromatograph (GC) system was commissioned

### Process Control and Instrumentation Prof. D. Sarkar Department of Chemical Engineering Indian Institute of Technology, Kharagpur

Process Control and Instrumentation Prof. D. Sarkar Department of Chemical Engineering Indian Institute of Technology, Kharagpur Lecture - 38 Instrumentation: General Principle of Measurement Systems (Contd.)

### HYDRAULIC BRAKE SYSTEMS AND COMPONENTS FOR OFF-HIGHWAY VEHICLES AND EQUIPMENT

HYDRAULIC BRAKE SYSTEMS AND COMPONENTS FOR OFF-HIGHWAY VEHICLES AND EQUIPMENT National Fluid Power Association Technical Paper I92-1.4 David E. Keyser Applications Coordinator Keith Hogan OEM Sales MICO,

### www.klmtechgroup.com TABLE OF CONTENT

Page : 1 of 24 Project Engineering Standard www.klmtechgroup.com KLM Technology #03-12 Block Aronia, Jalan Sri Perkasa 2 Taman Tampoi Utama 81200 Johor Bahru Malaysia S TABLE OF CONTENT SCOPE 2 DEFINITIONS