1 Aerobic Digestion, or, It s a Bug eat Bug World Brett Ward Municipal Technical Advisory Service The University of Tennessee
2 Aerobic Digestion Continuation of the Activated Sludge Process Super Extended Aeration No food is added Reduction of Volatile Solids through: Endogenous Respiration Bacterial Cells use their own protoplasm for energy Some cells die and become food for others
3 Biological Chemistry BOD, Bug Food, Organic Pollution Test of the organic strength of sewage Organic- from plants and animals Protein, carbohydrates, fats Fecal matter, food scrapes, paper, industrial waste of plant or animal origin. Normal Bacteriological Respiration BOD + BOD Bugs + O 2 = More BOD Bugs + CO 2 + H NH 3
4 Respiration / Oxidation Respiration We call it breathing Scientifically it is the release of energy The Bugs want the energy in the BOD Energy to live and grow The Bugs are teeny tiny chemical factories They split complex organic compounds into simple oxidized compounds.
5 Respiration / Oxidation Normal Bacteriological Respiration BOD + BOD Bugs + O 2 = More BOD Bugs + CO 2 + H NH 3 Glucose C 6 H 12 O 6 + BOD Bugs+ O 2 = More BOD Bugs + CO 2 + H 2 0 Protein C 3 H 7 O 2 N + BODBugs+ O 2 = More BOD Bugs + CO 2 + H NH 3
6 Sewage Treatment Sewage, BOD Carbs, Protein, Fats Add air and mix well Bugs grow And Grow And Grow
7 Waste excess Bugs to Digester With out wasting MLSS goes up, up, up and OUT! Waste today what grew today
8 Biological Chemistry Digesters receive no food or BOD Endogenous Respiration BOD Bugs +O 2 = Less BOD Bugs +CO 2 + H 2 O + NH 3 Bugs use stored energy Some die, and become food for others Reduction of Volatile Solids
9 Digestion Goals Thicken Waste Activated Sludge: Decanting Control Odors, Keep it aerobic Reduce Sludge Volume, Endogenous Resp. Meet Disposal Requirements Land Fill Land Application
10 Aerobic Advantages Low Construction Cost Easy to Operate High Quality Supernatant Safer process, no methane
11 Aerobic vs Anaerobic Supernatant Aerobic BOD 500 mg/l TSS mg/l TKN 170 mg/l T.Phos 98 mg/l Anaerobic BOD mg/l TSS mg/L Ammonia mg/L T. Phos mg/L
12 Aerobic Disadvantages High Aeration Costs, electricity Digested Sludge more difficult to dewater Process affected by temperature changes More Sludge produced for disposal
13 Aerobic Digester Design Various Sizes Various Aeration Diffused air Surface Mechanical Various Decant Fixed Valves Moving Arms Telescoping Valves Suspended Pumps
14 Operating Strategy WAS Biosolids Complete Mixed Batch, Fill and Draw Series, Parallel or combination Primary & WAS Primary Biosolids Secondary Digesters Biosolids
15 Digester Operations Operational Strategy Tools you have Basins Decant or supernatant equipment Aeration Personnel Destination Land Fill Land Application Other Facility
16 Digester Monitoring Daily to Weekly Dissolved Oxygen Settleometer ph, Alkalinity Nitrate 503 tests, Prior to use or disposal SOUR Temperature Fecal
17 Digester Monitoring
18 Supernatant Monitoring Monitor for affects on the water treatment system. Flow BOD Ammonia TSS Nitrate (NO 3 ) Phosphorus
19 Land Fill Special Waste Permit Division of Solid Waste Management No Free Water, AKA paint filter test No Toxic Lecheate, TCLP, Toxic Characteristics Lecheate Proceedure
20 Land Fill Primary Concerns Odor Control, too little O2, too much feed Sludge Oxygen Maintain Oxic environment Sacramento Manual, 1-2 mg/l DO What works for you 0.5 mg/l, can be more cost effective >2.0 mg/l» wastes electricity» can cause low ph» can contribute to foaming
21 Land Fill Dewatering Avoid excessive long aeration times Long times decrease floc and particle size Greater than 20 days, Capillary Suction Time (CST) greatly increases Lower CST means better dewatering.
22 Land Application 503 Requirements Metal accumulation Nitrogen management Pathogen Destruction Class A or B Vector Requirements 38% Red. of V.S. SOUR Bench top test Time and Temp.
23 Land Application Concerns Odors Pathogen Reduction Vector Attraction Red.
24 Land Application Class B Geometric Mean of seven samples is less than 2,000,000 cfu/g Requires Total Solids Test for Calculations Natural Die off in Digester Intestinal organisms Air Off cycles appear to assist in reduction.
25 Land Application Class B, PSRP Aerobic Digestion MCRT, 40 days at 20 C 60 days at 15 C
26 Land Application Vector Attraction Reduction 38% Reduction of VS, Van Kleeck Equation Works best where there is Primary Sludge feed Bench Top Aerobic Digestion SOUR Test, don t thicken above 2% TS All are tests to document Sludge Stability Low BOD (food), Low energy, highly oxidized
27 Sludge Stabilization Requires Time and Air Low Temperature Slows the process High Temps speed the process TN Design Criteria Hydraulic detention time at 20 C should be days depending on type
28 Sludge Stabilization This may not be enough. Variables Feed Sludge, WAS, Primary, Combination We all have Winter Temperatures Design for 20 C guarantees failure in Winter Aeration equipment and location can warm your digester in the winter.
29 Aerobic Digester Tips Low Temperature Slows Pathogen Reduction Slows Volatile Solids Reduction High Temperature Speeds Pathogen Reduction Speeds Volatile Solid Reduction
30 Aerobic Digester Tips Low DO does not slow pathogen reduction does not slow volatile solids reduction High DO Will cause ph to decrease Will waste electricity
31 Digester ph Management Endogenous Respiration BOD Bugs +O 2 = Less BOD Bugs +CO 2 + H 2 O + NH 3 Ammonia is produced
32 Digester ph Management Where there is Ammonia, There is sure to be nitrification Elements of Nitrification Ammonia Present Old Sludge Age Adequate Oxygen Adequate Temperature Adequate Alkalinity
33 Digester ph Management NH 3 +NH 3Bugs + O 2 + Alk.= More NH 3 Bugs + NO 3 1 Part 4 Parts 7 Parts Nitrification is an expensive process If you aerate continuously for long times, alkalinity may drop and ph drop.
34 Digester ph Management If ph drops, If nitrates are present Turn the aeration Off and Denitrify!
35 Oxygen Usage Hierarchy Free Dissolved Oxygen Aerobic or Oxic Treatment Little or No free Oxygen, but NO 3 present Anoxic Treatment Sulfate, SO 4 is the next choice of the Bugs Anaerobic conditions are beginning. ODORS fm. H 2 S 12
36 Denitrification Normal Bacteriological Respiration BOD + BOD Bugs + O 2 = More BOD Bugs + CO 2 + H NH 3 1 Part 1.25 Parts BOD + BOD Bugs + O 2 = More BOD Bugs + CO 2 + H NH 3
37 Denitrification NH 3 +NH 3Bugs + O 2 + Alk.= More NH 3 Bugs + NO 3 BOD + BOD Bugs + NO 3 = More BOD Bugs + CO 2 + H N 2 + Alk Nitrogen gas 1 Part 0.3 Parts 3.5 Parts Denitrifying returns alkalinity to the basin and stops ph drop
38 Agronomic Loading Rates Nitrogen Fertilizer value of the Biosolids The lower the nitrate the more can be applied per acre.
39 Agronomic Loading Rates
40 Agronomic Loading Rates
41 Agronomic Loading Rates Nitrate Levels Digester #1, 5700 mg/l Digester #2, 22,000 mg/l Digester #2 Sludge requires 30% more land for application.
42 Actual Land Application Case Biosolids Nitrate mg/l Not enough land to apply at the present Agronomic Loading Rate Initiated Off- On aeration 8 hours ON, 16 hours OFF Biosolids Nitrate mg/l, % reduction Application rates up and no need for more land.
43 Benefits of Denitrification Prevent ph drops by recycling Alkalinity Save money by recycling Oxygen Apply Biosolids at higher rates Improved Dewatering characteristics Reduce sludge volume Select against filaments
44 Denitrification reduces the Aerobic Digester Disadvantages High Aeration Costs, electricity, Reduced Digested Sludge more difficult to dewater, Improved Process affected by temperature changes More Sludge produced for disposal, Improved
45 Digester Case Study Two Stage Aerated 24/7, odors, odors, odors First Stage, primary and WAS Stage Two Low ph, as low as 6.0 s.u. and under, What would you do?
46 On More Issue Foaming This looks like nocardiaform foam If it is a problem Microscopic Exam Surface chlorinate 1% Cl 2 liquid spray on the foam when the air is OFF More than once per day is better.
47 More Foam Light smelly foam Primary Sludge Feed Not filaments Microscopic Exam Small solids Paper fibers
Unit 1 Process Control Strategies Exercise Module 16: The Activated Sludge Process - Part II Instructor Guide Answer Key 1. What are the six key monitoring points within the activated sludge process? Ans:
Activated Sludge Design, Startup, Operation, Monitoring and Troubleshooting Ohio Water Environment Association Plant Operations Workshop Columbus, Ohio September 1, 2010 Phil Anderson Operations Specialist
BOD Bio Chemical Oxygen Demand TSS Total Suspended Solids Wastewater Treatment Fecal Coliform ph NH3 Nitrogen Ammonia What is Sewage Pathogens or disease-causing organisms are present in sewage. Sewage
ANAEROBIC DIGESTION OF SEWAGE SLUDGE USING THE ANOXIC GAS FLOTATION (AGF) PROCESS Dennis A. Burke Cyclus Envirosystems, 6007 Hill Road NE, Olympia, WA 98516-9551 ABSTRACT The AGF (Anoxic Gas Flotation)
1.85 WATER AND WASTEWATER TREATMENT ENGINEERING FINAL EXAM DECEMBER 20, 2005 This is an open-book exam. You are free to use your textbook, lecture notes, homework, and other sources other than the internet.
Distributed by: ARM 1010 AMMonia reducing microbes Application Sheet ARM 1010 is a blend of nitrifying bacteria that removes ammonia from wastewater. It is used in a variety of industries that use aerobic
C & EE 255B Prof. M. K. Stenstrom Winter 2015 BALANCING REDOX EQUATIONS Balancing redox (oxidation-reduction) equations is a simple and very useful technique of performing balances from empirical equations
SECONDARY TREATMENT ACTIVATED SLUDGE Activated sludge is another biological process used to remove organics from wastewater. Like the trickling filter, activated sludge processes are used to grow a biomass
Best Practice Guide NO. BPGCS002 Wastewater Treatment Activated Sludge Process The following is intended to provide a first check for those involved in the operation, management and monitoring of the activated
Example: 2 Design low rate trickling filter for secondary treatment of sewage generated from 10000 persons with rate of water supply 170 LPCD. The BOD 5 after primary treatment is 110 mg/l and BOD 5 of
Retrofitting an Aeration Basin with Anoxic Zone to Reduce Operations Cost and Improve Performance Ed Griﬀenberg, Operations Specialist HDR Engineering, Edmonds, WA 2012 PNCWA Conference, Boise, Idaho Case
PULP AND PAPER MAKING WASTES, TREATMENT AND ENVIRONMENTAL EFFECTS BIOPROA Departamento de Ingeniería de Reactores Liliana Borzacconi María Noel Cabrera Facultad de Ingeniería Universidad de la República
Activated Sludge Biological Nutrient Removal Process Variations Western Chapter Spring Wastewater Conference May 17, 2016 Dan Miklos, Senior Associate, Midwest Region, Hazen and Sawyer Activated Sludge
OPTIMIZING BIOLOGICAL PHOSPHORUS REMOVAL FROM AN SBR SYSTEM ABSTRACT MIDDLEBURY, VT Paul Klebs, Senior Applications Engineer Aqua-Aerobic Systems, Inc. The Middlebury Wastwater Treatment Plant, located
Description of the Water Conserv I Facility Introduction The Water Conserv I (WCI) facility has a design capacity of 7.5 mgd and is classified by FDEP as a Class A, Level 1 treatment plant. The facility
Wastewater Nutrient Removal An overview of phosphorus and nitrogen removal strategies Presented by: William E. Brown, P.E. Peter C. Atherton, P.E. Why are nutrients an issue in the environment? Stimulates
Summary ENVIRONMENTAL ISSUES IN THE RENDERING INDUSTRY Gregory L. Sindt, P.E. Environmental Engineer Bolton and Menk, Inc. The rendering industry has a significant positive impact on environmental quality.
Basic Nutrient Removal from Water Beta Edition Presented by Paul Krauth Utah DEQ Salt Lake Countywide Watershed Symposium October 28-29, 2008 Presentation Outline Salt Lake County waters / 303(d) listings
Department of Civil Engineering-I.I.T. Delhi CEL 212: Environmental Engineering Q1. An anaerobic reactor, operated at 35 o C, treats wastewater with a flow of 2000m 3 /d and a biological soluble COD (bscod)
WATER TREATMENT PROCESSES Effluent Primary treatment Secondary Treatment runoff Tertiary treatment Water Treatment Processes PRIMARY TREATMENT to prepare the wastewater for biological treatment Purpose
Wastewater Treatment Plant Operator Certification Training Module 17: The Activated Sludge Process Part III Revised October 2014 This course includes content developed by the Pennsylvania Department of
Phosphorus Removal In Wastewater Treatment by Derek Shires (512) 940-2393 Derek.Shires@ett-inc.com Why do we care? Eutrophication of surface water - Especially reservoirs Maximum agronomic uptake - Limiting
II. PROCESS OVERVIEW Provided below is a description of the processes generating wastewater in a poultry plant and a typical pretreatment and full treatment system. II.1. Wastewater Generation A typical
Activated Sludge Treatment and SBRs ATUs Pre-class questions Name 4 components necessary to have an activated sludge system for wastewater treatment. Aeration tank Sludge recycle Clarification tank Oxygen
WASTEWATER TREATMENT OBJECTIVES The student will do the following: 1. Define wastewater and list components of wastewater. 2. Describe the function of a wastewater treatment plant. 3. Create a wastewater
AP ENVIRONMENTAL SCIENCE 2007 SCORING GUIDELINES Question 1 Read the Fremont Examiner article below and answer the questions that follow. (a) Identify ONE component of the sewage that is targeted for removal
Glossary of Wastewater Terms Activated Sludge Sludge that has undergone flocculation forming a bacterial culture typically carried out in tanks. Can be extended with aeration. Advanced Primary Treatment
ABSTRACT Sludge Stabilization Sustainability of Aerobic Digestion Processes Bryen Woo EGCE 597: Research Paper Treating wastewater is very important to protect the quality of human life and preserve water
CITY OF BARRIE WATER POLLUTION CONTROL CENTRE The City of Barrie owns and operates its own wastewater treatment facility which receives domestic, commercial and industrial wastewater and provides a level
Arkea : A Green Technology for Wastewater Treatment, Residuals Management, and Pathogen Reduction OWEA ANNUAL MEETING JUNE 20, 2012 1 Michael H. Gerardi, Wastewater Biologist, ArchaeaSolutions, Inc. Steve
The Corporation of the Municipality of Wawa Prepared by: Water & Sewer Department Infrastructure Services February 2016 2015 Annual Sewage Performance Report Table of Contents Signature Page... (i) Table
The Islamic University of Gaza- Civil Engineering Department Advanced Sanitary Engineering- ECIV 5325 Unit 1. Physical, chemical and biological Characteristics of Wastewater Based on Dr. Fahid Rabah lecture
ECM Solutions for Waste Water Treatment Plants Analytic solutions for waste water treatment pant help to increase effectivity of the process and significant saving of the cost of plant operation. Large
CHAPTER 14 WASTEWATER TREATMENT PONDS 14-1, Background. A wastewater stabilization pond is a relatively shallow body of wastewater contained in an earthen basin which is designed to treat wastewater. (
2006 Virotec International plc All rights reserved. A COMMERCIAL APPLICATION OF VIROSEWAGE CASE STUDY: BRISBANE WATER FAIRFIELD WASTE WATER TREATMENT PLANT Significant reductions in and are noticed. The
Brewery Wastewater: Solutions for the Problem By Fred M. Scheer 2010 Water and Wastewater Conference Madison, WI 11.02.2011 Page 1 vr74 What We Will Discuss: Biochemical i Oxygen Demand (BOD): Where does
Squeezing the Most Out of Your Decision for Municipal Solids Handling Dewatering Selection Why dewater anyway? 21,594 Publicly Operated Treatment Works (POTW s) provide wastewater collection, treatment
Cambridge Wastewater Treatment Facility Emergency Situations If you have a water or sewer emergency that relates to the City s utility system call the Public Works office at 763-689-1800 on normal working
Advanced Wastewater Treatment and Disposal Systems Water and Wastewater Utility Operation and Management for Tribes Preliminary Treatment Primary Treatment Secondary Treatment Tertiary Treatment Disinfection
Optimized Nutrient Removal in Waste Water Treatment Plants Activated Return Sludge Process Sille Bendix Larsen, Jeanne Agertved Madsen & Gert Petersen EnviDan East A/S Copenhagen, Denmark firstname.lastname@example.org
NUTRIENT REMOVAL WASTEWATER TREATMENT CLIFFORD W. RANDALL, PHD EMERITUS PROFESSOR VIRGINIA TECH The Impacts of Excess Nutrients Nitrogen and Phosphorus Are the nutrients that cause over fertilization of
ADVANCED LAGOON TREATMENT TECHNOLOGIES FOR WASTEWATER TREATMENT ABSTRACT by Vikram M Pattarkine*, Randall C Chann**, Charles E Tharp** *Brinjac Engineering Inc, 114 North 2 nd Street, Harrisburg, PA 1711
CIBO Focus Group Meeting Biological Treatment for Power Generation Wastewater June 11, 2013 Outline New ELGs for Fossil Fuel Power Generation Biological Treatment Fundamentals Aerobic Treatment Ammonia,
Water Quality 101 Dr. Mike Mallin and Matthew McIver Aquatic Ecology Laboratory UNCW-Center for Marine Science Common Water Quality Sampling Parameters and Analytical Procedures Water temperature Salinity
Fort Wayne Water Pollution Control Plant The Water Pollution Control Plant located on Dwenger Avenue -- provides wastewater treatment for the City of Fort Wayne and surrounding areas. Following the treatment
Holistic Aeration and Chemical Optimization Saves Big Money from 1 MGD to 600 MGD Trevor Ghylin, PE PhD Outline Background Case Study: Sterno, Sweden (~1.8 MGD) 65% Aeration Energy Reduction Case Study:
MBR Pretreatment of Landfill Leachate for the Removal of Ammonia and Potential Future Removal of Total Dissolved Solids Clifford S. Wilkinson 1, *, Jurek Patoczka 1, James Williams 2 and Thomas G. Grau
APPENDIX B EXAMPLE OF A COMPLETED SAMPLING PLAN WORKSHEET This example of a completed sampling plan worksheet has been included to illustrate the information necessary to document a sampling program for
21 st Century Biofilm Reactors High Quality Yet Simple Operations Northport/Leelanau Township Wastewater Treatment Facility Presented by: Rich Grant, PE Carey Bond, PE Date Presented by: Rich Grant, PE
Wastewater Treatment Facility Plan City of Paynesville Minnesota BMI Project No. M21.037315 March 2009 TABLE OF CONTENTS EXECUTIVE SUMMARY... 1 A. GENERAL... 1 B. DESIGN PARAMETERS... 1 C. COST ESTIMATES...
Wastewater Stabilization Ponds (Lagoons) Prepared by: Mark Matheson Presented by: Fred Summers NCRWA Introduction to Lagoons Wastewater Treatment Facility Natural Biological Process In Use Since Ancient
Activated Sludge Microbiology Denise L. Seman Youngstown WWTP Activated Sludge Activated sludge is a type of secondary treatment whose primary role is to remove most of the dissolved solids remaining in
BLUE PLAINS - WASHINGTON DC NUTRIENT & ENERGY RECOVERY FACILITY DCWater - Mark Ramirez email@example.com 1 District of Columbia Water and Sewer Authority George S. Hawkins, General Manager Introduction
Wastewater Treatment Aeration We live and breathe aeration What is it that makes our aeration systems the trusted choice the world over? The fact that ITT Water & Wastewater have been designing, installing
Revision Date 6/10/02 9:52 Red Valve Company, Inc. 700 NORTH BELL AVENUE CARNEGIE, PA 15106-0548 PHONE (412) 279-0044 FAX (412) 279-5410 Red Valve Representative Sample Air Diffuser Calcs.xls Input Data
DIGESTERS Sludge digestion is the primary means of stabilizing the volatile organic material in the sludge. Biologically degradable organics account for 60-65% of the total solids in the sludge. The organic
Our Story ISTP2 Building and operating Al Wathba 2 and Allahamah wastewater treatment plants IRAN Our story began in December 2008. The ISTP2 (Independent Sewage Treatment Plant) project is a BOOT project
A NOVEL ION-EXCHANGE/ELECTROCHEMICAL TECHNOLOGY FOR THE TREATMENT OF AMMONIA IN WASTEWATER ABSTRACT Leonard P. Seed, M.Sc., P.Eng., Enpar Technologies Inc. * Daren D. Yetman, A.Sc.T., Enpar Technologies
Integrity. People. Knowledge. WISCONSIN WASTEWATER OPERATORS ASSOCIATION ANNUAL CONFERENCE GREEN BAY Resources. MEETING LOW LEVEL PHOSPHORUS LIMITS BY CHEMICAL ADDITION WHAT IS PHOSPHORUS Atomic # 15 Electron
MBR Wastewater treatment plants Wastewater treatment plants Challenge and a new approach - Sensitive area - Highly developed tourist destination - During summer, population increases even 5 times - Great
Biogas Recovery from Domestic Wastewater with Anaerobic Membrane Bioreactor Jaeho Bae Inha WCU research team INHA University, World Class University Research Team CONTENTS I II III IV Wastewater as Resources
Anaerobic Processes (Chapter 10) Used for treatment of sludges and high strength (usually > 1500 mg/l COD) waste waters Can now be used for dilute strength waste waters if a fixed film system is used 90%
Novel Process for the Treatment of Wastewaters from the Microelectronics Industry IWC 13-34 Authors: Temple Ballard 1, Nabin Chowdhury 2, Bruno Heiniger 4, Denise Horner 2, Antonio Lau 1, Sunil Mehta 2,
THE USE OF MAGNESIUM HYDROXIDE SLURRY FOR BIOLOGICAL TREATMENT OF MUNICIPAL AND INDUSTRIAL WASTEWATER Aileen Gibson Michael Maniocha ABSTRACT In wastewater treatment, microorganisms transform the wastes
THE MARSHALL STREET ADVANCED POLLUTION CONTROL FACILITY (CLEARWATER, FLORIDA) CONVERSION TO 4-STAGE BARDENPHO TO IMPROVE BIOLOGICAL NITROGEN REMOVAL ABSTRACT Timur Deniz, Ph.D., Thomas W. Friedrich, P.E.
PERIODICA POLYTECHNICA SER. CHEM. ENG. VOL. 45, NO. 1, PP. 41 52 (21) TRIAL OPERATION OF A SELECTOR AT THE NORTHPEST WASTEWATER TREATMENT PLANT 1 Andrea JOBBÁGY, Ferenc FARKAS,GY. GARAI, Béla SEVELLA and
2015 YEAR END REPORT WATER/WASTEWATER TREATMENT PLANTS Madison s water and wastewater treatment operations specialists are highly trained professionals who strive to give the citizens of Madison the best
Basics of the Biogas Production Process Stefan Junne, Kozani, 04.06.14 Content Materials and Methods for Biogas Production Background Biogas Process Applicable Substrates Substrate Pre-treatment Monitoring
City of Patterson Waste Water Treatment Plant www.ci.patterson.ca.us Our Mission: To manage and operate safe, cost-efficient, and environmentally sound services for the benefit of the citizens of Patterson.
Science Behind Treatment of Aquatic Systems with TLC Products Introduction TLC Products is located in Cleveland, Ohio, USA., and has been a leading manufacturer of bacterial additives since 1996. The company
Experts Review of Aerobic Treatment Unit Operation and Maintenance Bruce Lesikar Texas AgriLife Extension Service Overview Overview of Aerobic Treatment Units Installing for accessibility to system components
Nitrification and Denitrification William E. Fenner, Jr., P.E. CES Sales/EnviroTech Are a fixed growth process and come in many types Single Pass Sand Filter Recirculating Sand/Gravel filter Single Pass
LAGOONS AND STABILIZATION PONDS One of the oldest means of treating wastewater is the wastewater lagoon or stabilization pond. Although the terms are usually interchangeable, the term lagoon usually refers