1 VFD 101 Lesson 4 Application Terminology for a VFD This lesson covers the application terminology associated with a Variable Frequency Drive (VFD) and describes each term in detail. When applying a Variable Frequency Drive (VFD) to a particular application, a number of terms are involved. This lesson attempts to clarify most of those terms. Here is the basics outline for this lesson. Outline: Application Terminology 1. Application Curves 2. Starting Torque 3. Open or Closed Loop 4. Closed Loop and PID 5. Different Types of VFDs Note: Other names are used for this device, such as Adjustable Frequency Drive (AFD), Variable Speed Drive (ASD), Frequency Converter and Inverter, but Variable Frequency Drive (VFD) or just Drive is used throughout this lesson.
2 Outline Application Terminology 1. Application Curves CT, CP, VT 2. Starting Torque HO, Breakaway, NO 3. Open or Closed Loops 4. Closed Loop & PID Action, Setpoint, Offset, Proportional, Integral, Derivative 5. Different Types of VFDs This module covers some of the application terminology used with VFDs. This terminology becomes very important for selecting the correct VFD and programming the correct settings needed for an application. Applications include terms such as Constant Torque (CT), Constant Power (CP) and Variable Torque (VT). Starting Torque is also covered, which uses High Overload (HO), Breakaway Torque, and Normal Overload (NO). Terms such as open loop and closed loop are also covered. Terms in closed loop, also explore action, setpoint and PID terminology. The last part covers a summary of the different types of VFDs. It shows the Volts/Hz, Voltage Vector, Flux Vector as they compare to a DC Servo in terms of response, accuracy and speed range. A more detailed explanation of each type is scheduled for a later lesson.
3 1. Application Torque Curves This part of the lesson covers the application terminology associated with a VFD, starting with application torque curves. VFD Application Terminology 1. Application Torque Curves a) Constant Torque (CT) b) Constant Power (CP) c) Variable Torque (VT) 2. Starting Torque 3. Open or Closed Loop 4. Closed Loop & PID 5. Different Types of VFDs
4 1. a) Constant Torque (CT) CT used on Reciprocating Compressors Torque stays relatively constant from 5Hz to 60Hz. AC motors have low torque at slow speeds. The graph above shows Torque in relationship to Speed. This graph was made when the VFD and loaded motor, were running at Synchronous Speed, 60 Hz, 1800 rpm on a 4-pole 3- phase AC motor. The speed of the VFD was slowly turned down to 0 Hz. Notice that the torque drops down to its nominal rating on an AC induction motor at the lower speeds, 5Hz or less. Please be aware that this particular CT application, reciprocating compressor, should never run less than 30Hz. Constant Torque applications require a constant level of torque throughout a process regardless of different speeds. The vast majority of constant torque applications are for industry, which involve conveyors, mixers, elevators, feeders, hoists, and bottling machines. In HVAC reciprocating compressors, and positive displacement pumps might be encountered which require CT. Some VFD manufacturers attempt to apply a CT drive to fans and pumps used in HVAC, because they do not make a specific VFD for variable torque applications. More information is given in the pages that follow. On most CT applications, constant torque must be maintained from 1 to 60Hz. Notice that the torque curve drops when the speed is reduce below a minimum of 5Hz. To compensate for this drop, some VFDs can perform Motor Tuning, which matches the VFD settings to a particular motor. This tuning allows for more precise calculations by the VFD giving more torque throughout the CT curve, but particularly noticeable is the torque boost at those slow speeds from 1 to 10Hz. In HVAC, Motor tuning is only a slight advantage for fans and pumps, saving only a small portion of energy. Because of motor cooling, most fans and pumps have a minimum speed of 10Hz or greater.
5 Volts per Hertz Chart Voltage increases as speed increases CT linear relationship between volts and hertz 30Hz = 230V; 60Hz = 460V on 460VAC motor VFDs attempt to generate the correct level of torque needed for its application. Torque is directly related to current. In CT applications, voltage going from the VFD to the motor is increased in a linear manner as the speed increases. In the example above, on a 460Vac motor, 460 Volts is only sent to the motor when the speed reaches 60Hz and higher. The chart above displays the Volts/Hz relationship for a CT application. Constant Torque is achieved because the VFD is increasing the voltage to the motor as it increases the speed. In this chart, when the VFD sends a signal of 30Hz, it is also sending a 230V signal to the motor. When the VFD sends a 60Hz signal, the voltage is at 460V. This relationship keeps the current and in turn the torque to the motor relatively constant. The changes seen in the motor current are based on the load. Notice that when the speed reaches 60Hz, base speed, the voltage going to the motor from the VFD can not go higher, it has reached its limit, 460V. If the speed is increased above base speed, to say 90Hz, the voltage from the VFD stays at 460V, but the current and torque drop. This Volts/Hz chart is different for motors that use different voltages.
6 1. b) Constant Power (CP) CP applications are rare for the VFD, none in HVAC. CP applications are always above base speed. Torque drops significantly above base speed (60Hz). Constant Power applications are run at synchronous speed, 60Hz and higher. On a CT Curve, the area above synchronous speed is known as the Constant Power Curve. As speed continues above 60Hz, torque continues to drop. The few applications that require these high speeds are typically saws, and grinders, and no applications in HVAC. A point of clarification between synchronous speed and base speed is useful. Synchronous speed, in an induction motor, is the RPM of the magnetic field when the motor reaches its nameplate voltage and frequency. The formula for synchronous speed is as follows: Synchronous speed = (Motor frequency) * 120 / (# poles) Example: (60Hz * 120) / 4 poles = 1800RPM Base Speed is the speed in rpm that results when the motor is at its nameplate voltage, frequency and current. Most Asynchronous 4-pole induction motors using 60Hz have a base speed between 1725 to 1770rpm.
7 1. c) Variable Torque (VT) VT applications save a great deal of energy Used with centrifugal pumps and centrifugal fans. Variable Torque (VT) applications almost always involve centrifugal pumps and centrifugal fans. If a VFD manufacturer has an HVAC drive, it is most likely designed and programmed for VT applications only, such as the VLT 6000 from Danfoss. The torque required to operate a pump or fan is very low until it starts to approach its base speed, say 1750rpm at 60Hz. There are formulas that show the relationship of power to rpm. Ideally, assuming no friction losses, the pump at half the speed only requires 1/8 the power. VFDs on VT applications save a great deal of energy and money. Once above base speed, a fan or pump requires a considerable amount of power, so they are rarely run above 60Hz.
8 Automatic Energy Optimization (AEO) VT voltage lower at speeds than CT AEO - Reduces voltage until speed is effected 30Hz = 160V straight VT; 90V with AEO A couple of VFD manufacturers, such as Danfoss, offer Automatic Energy Optimization (AEO). This is used in all VT applications. This function automatically and continuously monitors and adjusts the output voltage to maximize energy savings. After the motor reaches the set speed, say 30Hz, the AEO function reduces the output voltage to the motor, if the load allows. When the load is light, the voltage is reduced perhaps from 160V to 90V. This reduced voltage not only saves energy, but reduces motor heating, motor noise, and increases efficiency.
9 2. Starting Torque Centrifuge This part of the lesson covers the application terminology associated with starting torque. Outline: VFD Application Terminology 1. Application Torque Curves 2. Starting Torque a) High Overload (HO) b) Breakaway Torque c) Normal Overload (NO) 3. Open or Closed Loop 4. Closed Loop & PID 5. Different Types of VFDs
10 2. a) High Overload (HO) High Overload allows 160% starting current for 1 min. Most CT applications require High Overload. If drive exceeds 160% or 1 minute, VFD trips. High Overload (160%) is used to apply the torque to start a load. The inertia to start a reciprocating compressor, a positive displacement pump or in the example above a hoist requires a great deal of starting torque. It can be as high as 160% of the current for 1 minute. Once started the torque drops back to 100% or less. If the load does not move and the drive exceeds 160% or exceeds 1 minute, the drive trips, which means that the VFD does not move the motor. This trip gives an Over-current or Torque Limit alarm and for protection sake a reset button must be pressed to clear the alarm and restart the VFD. Some VFDs have a High Overload limit of 150% for 1 minute. It is possible to use a High Overload or CT Start to get a fan or pump moving, but most HVAC applications do not require High Overload.
11 2. b) Breakaway Torque High Overload has a breakaway torque that allows 180% starting current for 0.5 seconds. If drive exceeds 180% or 0.5 seconds, VFD trips. Breakaway Torque (180%) also known as Starting Torque, usually refers to the first 0.5 seconds after start. In the example a mixer has a very thick substance, perhaps a batch of adhesive. When the VFD starts to turn the motor the resistance of the substance is very high. The VFD increases the current output up to 180% for half a second to get the mixer started. Once it starts, the VFD continues at the High Overload setting of 160% for 1 minute. If it does not move, the VFD trips for protection of the VFD, motor and mixer. This is rarely needed for HVAC applications.
12 2. c) Normal Overload (NO) Normal Overload has a starting torque that allows 110% starting current for 1 minute. Most VT applications require Normal Overload. VT VFDs are sized differently 200Hp for CT; 250Hp for VT Normal Overload (110%) is almost always used with HVAC applications basically with centrifugal fans and pumps. When a centrifugal fan is started it takes very little starting torque to turn the fan against air, so the 110% limit is adequate. If the 110% for 1 minute is exceeded, the VFD trips. Since the current output on starting is less for VT applications, smaller VFDs can operate slightly larger motors. If a 200Hp VFD which is normally Constant Torque (CT) has a VT setting, the VFD could be used to operate a 250Hp motor with little difficulty.
13 3. Open or Closed Loop All applications fall into 2 categories Open Loop or Closed Loop Closed loop has additional settings which include controller action, setpoint, and PID settings Outline: VFD Application Terminology 1. Application Torque Curves 2. Starting Torque 3. Open or Closed Loop a) Open Loop b) Closed Loop 4. Closed Loop & PID 5. Different Types of VFDs A quick definition for Open and Closed Loop is shown here. Open Loop control does NOT have a direct feedback signal. Closed Loop has a direct feedback signal coming into the VFD.
14 3. a) Open Loop The VFD is programmed for open loop, because there is NO feedback signal going to the VFD but the system is closed loop. Open Loop control does NOT have a direct feedback signal. In the example above, a static pressure sensor is wired to a Direct Digital Controller (DDC). Because the feedback signal, pressure, goes to the Controller, a closed loop must be setup in it to control the static pressure. This closed loop inside the Controller monitors the pressure comparing it against a setpoint and then calculates a reference signal. The Controller then sends this reference signal to the VFD for proper modulation of the fan. The reference signal is sent to the VFD, which in turn controls the motor and fan. In this example, the VFD is programmed for Open Loop and it receives a reference command from the Controller. If the pressure sensor were wired directly into the VFD, then the drive would need to be programmed for Closed Loop in order to have proper control of the fan. The system is a closed loop system because it senses its own action, its feedback, but because the feedback signal does not go directly to it, the VFD is programmed for open loop.
15 4) Closed Loop Sensor monitors the feedback signal. Controller, the VFD, gives the sensor a desired value, action and PID settings and calculates a response. Controlled Device, the fan, responds to the signal from the controller, increasing or decreasing in speed. Closed Loop is where the controller inside the VFD can be used to modulate the speed of a motor to maintain a process. It is the job of the sensor or transmitter to measure a variable, in the example above, this is static pressure. This sensor sends a signal (usually a 4-20mA) to the controller over a particular range, in this example from 0 to 5 wc. The sensor is wired to the current input of the VFD, the controller. This signal is programmed in the VFD as the feedback signal. This feedback signal must be given engineering units, from our example, inches of water column ( wc) or Pascals. Inside the VFD the feedback signal must also be given the range that matches the sensor. When the sensor sees 4mA it is 0 wc (0 Pascals) and when the sensor sees 20mA, the reading is 5 wc (1250 Pascals). The VFD, controller, has a setpoint, action and PID settings (explained later) to calculate the response necessary to maintain the desired value seen at the sensor. The VFD sends a signal to the fan to speed up or slow down to maintain a certain level. The fan, controlled device, responds to match the signal from the VFD, controller. It speeds up when the level of the static pressure decreases and slows down when the level of the static pressure is too high.
16 4. a) Control Action Normal Control incoming signal increases; VFD speed decreases. Inverse Control incoming signal increases; VFD speed increases. In closed loop applications, such as controlling pressure by monitoring the volume of return air, shown above, the VFD must always be programmed for the correct action. There are 2 choices: Normal Control (also know as Reverse Acting). In the top return fan example, when the CFM Transmitter sends a signal that indicates it is above the setpoint, the output from the VFD decreases. The action is correct if the sensor is down stream from the controlled device, the return fan. As the CFM sees an increase, the signal to the fan decreases, slowing the fan down. As the CFM transmitter sees a drop, the speed of the fan increases. Inverse Control (also know as Direct Acting). In the bottom return fan example, when the signal from the CFM Transmitter increases above the setpoint the output from the VFD increases. This action is correct if the CFM transmitter is upstream from the return fan. If the wrong action (Inverse) were programmed in the VFD on the top return fan, it would speed up as the CFM in the duct rose higher. Eventually the speed of the return fan would go to its maximum. This could put a major stress on the ductwork. If the incorrect action is programmed in an application the VFD ends up locked at minimum or at maximum speed.
17 4. b) Setpoint, Error & Gain Setpoint or reference is the desired value for a controlled variable; example: 2.00 wc (500pa). Error (offset) is the amount the feedback is from setpoint at any given time, example: 0.15 wc (38pa) Proportional Gain is a multiplier times the error (offset). Example above the Gain starts at 0.3 Setpoint is the desired value or reference of the controlled variable for a closed loop application. In controlling static pressure, shown above, 2.00 wc (500pa) is the desired setpoint or reference. Error is a difference between the setpoint, 2.00 wc (500pa) and the actual feedback pressure, 1.85 wc (462pa) for this system. This difference is also known as Offset (or off the setpoint). Proportional Gain is multiplied by the error to create an output. The larger the proportional gain, the larger the output change for a given error. If the proportional gain is too small (0.01) this multiplier times the error has no effect on the speed of the VFD. If the proportional gain is too large (3.00 or higher) the system can become unstable, modulating between minimum speed and maximum speed which is called hunting. A good starting place for the Proportional Gain is about 1.00 but changes depending on the application. If Proportional Gain is only used, without I or D (explained on the next slide), the output is relatively close to setpoint but there is always an error.
18 4. c) Integral & Derivative Integral checks the offset over a period of time and makes corrections. Derivative checks the offset and corrects for the speed of the integral correction. Integral Gain is based on the history of the error. The integral function maintains a running total of the error and creates an output based on this total. The lower the number used for the integral gain the more frequently the error is checked and the larger its influence. If the integral time is too low (less than 5 seconds), the system can become unstable and starts to hunt. A good place to start is 10 seconds, but again this can vary based on the application. Integral gain eliminates the steady error inherent to proportional control. As pictured above, integral gain adds overshoot every time the load changes, but eventually settles close to setpoint. Integral is used frequently in HVAC applications. Derivative or differential is based on the rate of change of the error. It is used to limit overshoot and dampen system oscillation. The larger the derivative time, the larger the influence. If the derivative time is too large, the system becomes unstable. Derivative is very sensitive to noise on the feedback signal and historically seldom used in HVAC closed loop systems.
19 4. b) PID Summary: There are many different PID algorithms. All contain these 3 features, Proportional Gain, Integral, and Derivative. The ways these terms are combined may be different. In some implementations the 3 values operate independently of each other and in others, changing one value effects the others. Proportional Gain contributes to the output in a direct relationship to the error between the feedback and setpoint. Integral contributes to the output based on the history of the error. Derivative contributes to the output based on the rate of change to the error. Setpoint is the desired value for the variable being controlled. Feedback is the actual value of the variable being controlled. Error (offset) is the difference between the setpoint and feedback Hunting is an unstable condition which causes the speed of the motor to continuously vary from maximum to minimum.
20 5) Different Types of VFDs There are different types of VFDs, which are briefly covered here. They include Volts/Hz, Voltage Vector, Voltage Vector +, Flux Vector and Servo. Volts/Hz drives also known as a Basic Scalar drives, are the least expensive drive with the least features. This drive is usually setup for CT and Open Loop only. Voltage Vector drives also known as Space Vector drives have more features and may have the ability to do both CT/VT and Open/Closed Loop. Voltage Vector Plus drives have more features than the others and therefore have more cost than previously mentioned drives. They can calculate motor characteristics without spinning the shaft of the motor. These last 3 types of VFD account for 95% of all applications. There are a few that need greater accuracy which follow. Flux Vector drives have more calculations which makes them more expensive and more accurate. Some Flux vector drives require special motors. Servo drives are DC and do not operate with AC induction motors. They are expensive in comparison to VFDs. They are the most responsive to dynamic changes. These drive types are explored in greater detail in a later lesson.
21 5) Different Types of VFDs Summary: Type Response Accuracy Speed Range V/Hz ms 10% + 10:1 180rpm Voltage Vector ms 2% - 8% 50:1 36rpm Voltage Vector ms 0.2%-2% Open 100:1 18rpm Closed 900:1 2rpm Flux Vector 5 60ms 0.02% - 0.1% 1400:1 1.3rpm Servo 2 8ms 0.007% % 1800:1 1rpm As a comparison above, each type of motor control shows, Response to dynamic changes Accuracy and Speed Range. Speed Range indicates how slow the motor can turn but still have proper operation. Speed Range is always indicated as a ratio. The higher the ratio the better control at slow speeds. The minimum rpm for each type has been calculated, assuming 1800 base speed. Voltage Vector Plus has 2 values, one for open loop and the other for closed loop. This completes this lesson. There are Review Questions in the Post-Test section.
Drives 101 Lesson 1 Functions of an Adjustable Frequency Drive (AFD) This lesson covers the basic functions of an Adjustable Frequency Drives (AFD). Outline: 3-phase AC Motor 1. Bi-Directional Operation
Technical Guide No. 100 High Performance Drives -- speed and torque regulation Process Regulator Speed Regulator Torque Regulator Process Technical Guide: The illustrations, charts and examples given in
INTRODUCTION: Baldor Electric Company has prepared this Specifiers Guide to help you cover all the bases when you are specifying electric motors. It will cover in a generic way most of the subjects which
Unidrive M Energy Savings Why is this important? Some Data: Money, Lots of Money >13.5m electric motors 1Hp or greater installed in US industrial process operations. Industry spends >$33b annually on electricity
MAKING MODERN LIVING POSSIBLE VLT APPLICATION NOTE VLT AutomationDrive for Marine winch applications This Application note is meant to be a guideline for using Danfoss VLT AutomationDrive in winch applications.
VLT HVAC Drive FC 02 Application Note Temperature Derating Guide Temperature Derating Guide.. Abstract This paper provides detailed data regarding the operation of the VLT HVAC Drive FC02 at varying ambient
Servo Drive Current Loop Tuning Procedure (intended for Analog input PWM output servo drives) The standard tuning values used in ADVANCED Motion Controls drives are conservative and work well in over 90%
NX Series Inverters HVAC Pocket Programming Guide HVAC Pocket Programming Guide HVAC Pocket Programming Guide / Contents This guide provides a single reference document for the user of NXL HVAC (product
..OR How To Protect your 3-Phase Equipment Investment with 3-Phase Monitors from Time Mark... TIME MARK CORPORATION 11440 EAST PINE STREET TULSA, OK 74116 USA tel 918 438-1220 fax 918 437-7584 www.time-mark.com
8 Speed control of Induction Machines We have seen the speed torque characteristic of the machine. In the stable region of operation in the motoring mode, the curve is rather steep and goes from zero torque
CPW Current Programmed Winder Application Handbook Copyright 2002 by Eurotherm Drives, Inc. All rights strictly reserved. No part of this document may be stored in a retrieval system, or transmitted, in
Contents Introduction Safety...3 Safety Guidelines...3 Warnings Against Unintended Start...3 Introduction...4 About this manual...4 Assumptions...4 References...4 Trademarks...5 Programming the VLT 6000
ENERGY TRANSFER SYSTEMS AND THEIR DYNAMIC ANALYSIS Many mechanical energy systems are devoted to transfer of energy between two points: the source or prime mover (input) and the load (output). For chemical
SED-635 Digital Excitation System SED-635 is a complete excitation system capable of adapting to control synchronous generators of any size. The integration of the TOUCH SCREEN operator interface and a
Mode Enable Sensor Options Variable Air Volume - VAV The temperature of this sensor will determine if the unit is in heating, cooling or vent mode during occupied operation. The following options are available:
MSF SOFT STARTERS BIG SAVINGS FOR A LOT MORE APPLICATIONS Soft Starters from Emotron Unique features built into Emotron MSF Soft Starters reduce costs significantly for many more applications when compared
EnVisioneering As a world leader in components and solutions, Danfoss meets our customers challenges through EnVisioneering. This approach expresses our views on engineering innovation, energy efficiency,
Motor selection guide 1. Introduction As you know it probably, there exists several types of electrical motors and therefore several technologies are available to make variable speed regulation. This guide
FlexPak 3000 Digital DC Drive Software Reference Manual Version 4.3 Instruction Manual D2-3405-2 The information in this manual is subject to change without notice. Throughout this manual, the following
Ground-Fault Protection with VFDs How to use a Sensitive Relay to Find Hard-to-Spot Ground Faults in VFDs on Resistance-Grounded Systems White Paper Mervin Savostianik P. Eng. Littelfuse, Inc. How to Use
The cost effective starter for all AC induction motors from 4A 2800A The choice for small to medium industrial applications The XFE Soft Starter range provides a combination of competitive prices, flexible
International Journal of Engineering Inventions e-issn: 78-7461, p-issn: 319-6491 Volume 3, Issue 5 (December 013) PP: 36-41 Modelling, Simulation and Performance Analysis of A Variable Frequency Drive
EET272 Worksheet Week 9 answer questions 1-5 in preparation for discussion for the quiz on Monday. Finish the rest of the questions for discussion in class on Wednesday. Question 1 Questions AC s are becoming
COOLING or HEATING ANALOG or PWM Art. 119914 631001A TOTAL AUTOMATION GENERAL TRADING CO. LLC SUITE NO.506, LE SOLARIUM OFFICE TOWER, SILICON OASIS, DUBAI. UAE. Tel. +971 4 392 6860, Fax. +971 4 392 6850
g Digital Energy ITI Instrument Transformer Basic Technical Information and Application Table of Contents DEFINITIONS AND FUNCTIONS CONSTRUCTION FEATURES MAGNETIC CIRCUITS RATING AND RATIO CURRENT TRANSFORMER
Motor Protection Principles Craig Wester GE Multilin Craig.Wester@GE.com Motor History & Facts The first U.S. patent for a motor was issued to Thomas Davenport in 1837. Today in North America, more than
Phase locked loop fundamentals The basic form of a phase locked loop (PLL) consists of a voltage controlled oscillator (VCO), a phase detector (PD), and a filter. In its more general form (Figure 1), the
PowerAmp Design COMPACT HIGH VOLTAGE OP AMP Rev G KEY FEATURES LOW COST SMALL SIZE 40mm SQUARE HIGH VOLTAGE 200 VOLTS HIGH OUTPUT CURRENT 10A PEAK 40 WATT DISSIPATION CAPABILITY 200V/µS SLEW RATE APPLICATIONS
EDUMECH Mechatronic Instructional Systems Ball on Beam System Product of Shandor Motion Systems Written by Robert Hirsch Ph.D. 998-9 All Rights Reserved. 999 Shandor Motion Systems, Ball on Beam Instructional
For Distribution ENGINEERING BULLETIN No. EB 039 Product: Cooling Towers, Closed Circuit Coolers & Evaporative Condensers Date: June 2003 Purpose: Variable Frequency Drives The purpose of this Engineering
ACS800 Master/Follower Application Guide Supplement to Firmware Manual for ACS800 Standard Application Program Master/Follower Application Guide Supplement to Firmware Manual ACS800 Standard Application
Energy Saving systems for Induction motors. Are they a sham? Do they work? There seems to be a resurgence in interest in the Nola energy saving algorithm for induction motors, with a number of manufacturers
Basics Of UltraVolt HVPS Output Voltage Control Application Note on Remote Control of UltraVolt HVPS By varying the voltage at the Remote Adjust Input terminal (pin 6) between 0 and +5V, the UV highvoltage
IDEAL INDUSTRIES, INC. TECHNICAL MANUAL MODELS: 61-763 61-765 The Service Information provides the following information: Precautions and safety information Specifications Performance test procedure Calibration
ADVANCED ENGINEERING 3(2009)1, ISSN 1846-5900 KINETIC ENERGY RECOVERY SYSTEM BY MEANS OF FLYWHEEL ENERGY STORAGE Cibulka, J. Abstract: This paper deals with the design of Kinetic Energy Recovery Systems
GPD 506/P5 Start-up Procedure and Checklist Preparation for GPD506/P5 Drive Start-Up...2 HVAC Start-Up Procedure for GPD 506/P5 WITH Bypass Option:...4 HVAC Start-Up Procedure for GPD 506/P5 WITHOUT Bypass
Moog Components Group manufactures a comprehensive line of brush-type and brushless motors, as well as brushless controllers. The purpose of this document is to provide a guide for the selection and application
ENERGY-SAVINg DRIVE PACKAGE SPriPM Motor & YASKAWA V1000 Inverter Drive EN DE ES FR IT Overview - Super Premium IPM Motor & YASKAWA V1000 Inverter Drive The Motor-Inverter Package was developed to support
Reliance Electric GV3000/SE Industrial AC Drive Multi-Purpose variable speed control of 1-400 HP three-phase motors, with Volts/Hertz or Vector mode operation as standard FLEXIBLE Control Whether you need
SLIM LINE FUME HOOD MONITOR Phoenix Controls FHM420 Fume Hood Monitor is sized to fit any fume hood and includes icons for simple and universal operation. The FHM420 slim line monitor works in conjunction
Direct Current Motors DC MOTORS The DC machine can operate as a generator and as a motor. Chap 5. Electrical Machines by Wildi, 6 e Lecturer: R. Alba-Flores Alfred State College Spring 2008 When a DC machine
Stereoscopic 3D Digital Theater System Operator Manual (MI-2100) -1- All information contained in or disclosed by this document is confidential and propriety to masterimage Co., Ltd. (hereinafter referred
UCRL-CONF-206108 Active Vibration Isolation of an Unbalanced Machine Spindle D. J. Hopkins, P. Geraghty August 18, 2004 American Society of Precision Engineering Annual Conference Orlando, FL, United States
Simulation and Analysis of PWM Inverter Fed Induction Motor Drive C.S.Sharma, Tali Nagwani Abstract Sinusoidal Pulse Width Modulation variable speed drives are increasingly applied in many new industrial
GENERATOR SELECTION Generators must be sized to handle their load based on the continuous KW, kilowatt load, and KVA, kilovoltamp load, and the worst case starting load KW + KVA. They must be derated for
Documenting Results to Validate Energy Savings Projects: Case Study of Direct Drive Cooling Tower Installations: Before and After Roman Wajda, Baldor Electric Company ABSTRACT Documenting the actual energy
LIFT CONTROL SYSTEMS CATALOGUE 2007 All Your Needs For Elevators INDEX 1. Lift Control Cards... 3 2. Speed Control Units... 7 3. Emergency Rescue Cards... 8 4. Lift Control Panels... 10 5. Photocells...
Instruction Manual BEFORE USING THE POWER SUPPLY UNIT Pay attention to all warnings and cautions before using the unit. Incorrect usage could lead to an electrical shock, damage to the unit or a fire hazard.
CASE STUDY ULTRA-EFFICIENT HVAC DESIGN AND CONTROL MAJOR HEATING, VENTILATING AND AIR- CONDITIONING REPLACEMENT AT THE COUNTY OF SAN DIEGO CRIME LAB December 30, 2005 8520 Tech Way, Suite 110 San Diego,
2015 VFD Rebate Section A: MEMBER INFORMATION Member Name Electric Account Number Rate Number Facility Address City State Zip Code Service Location Identification Email Mailing Address (if different from
WHITE PAPER WYE-DELTA AND SOLID STATE STARTER APPLICATION GUIDE EXPLANATION AND ASSISTANCE FOR APPLYING SOLID STATE SOFT STARTERS IN TRADITIONAL REDUCED VOLTAGE APPLICATIONS Introduction..............................................................2
R22. K Control. Indoor Unit. Nomenclature. PL H 3 G K H B Compatibility Unit style Heat Pump Horse Power Control Boost Heaters R22. K Control. Outdoor Unit. Nomenclature. PU H 3 Y K A Compatibility Outdoor
Contents Introduction to HVAC 4 Software version 4 Safety regulations 5 Warning against unintended start 5 Introduction to the Design Guide 7 Available literature 8 Fire mode 11 Star/delta starter or soft-starter
NXL Series Inverters HVAC Inverters made simple Honeywell s Voice Of the Customer process unveils a range of requirements expressed by specifiers and installers, that are ideally covered by the NXL inverter
F4 Process Controller Installation and Operation Guide SAFETY ALERTS The symbols below are used on the equipment and throughout this document to draw the user s attention to important operational and safety
Properties Free of float metal bellow coupling with integrated torque measurement Non-contact measurement system, high robustness High torsional stiffness Limited torque of inertia Performance Measurement
Construction and operation 8.03.00 Instructions for installation 8.03.00 Types of stress 8.04.00 Diagrams for static deformation of the coupling ring 8.05.00 Coupling size 8.07.00 Examples of combinations
Motor Specifications Nameplate The nameplate of a motor provides important information necessary for selection and application. The following drawing illustrates the nameplate of a sample 30 horsepower
What Is Regeneration? Braking / Regeneration Manual Regeneration Overview Revision 1.0 When the rotor of an induction motor turns slower than the speed set by the applied frequency, the motor is transforming
BALDOR ELECTRIC COMPANY SERVO CONTROL FACTS A HANDBOOK EXPLAINING THE BASICS OF MOTION MN1205 TABLE OF CONTENTS TYPES OF MOTORS.............. 3 OPEN LOOP/CLOSED LOOP..... 9 WHAT IS A SERVO..............
Digital input or output DIO 8.29 Digital input polarity Negative Input or output selection Positive 8.3 Output DIO state 8. Invert 8. Input Digital input or output 2 DIO2 DIO2 state 8.2 Input or output
Programming Circuit White Paper Considerations When Specifying a DC Power Supply By Bill Martin, Sales/Applications Engineer Every automated test system that tests electronic circuit boards, modules or
Application Information Fully Integrated Hall Effect Motor Driver for Brushless DC Vibration Motor Applications By Shaun Milano Vibration motors are used in a variety of applications including mobile phone
Inductance Motors Generators Self-inductance Self-inductance occurs when the changing flux through a circuit arises from the circuit itself. As the current increases, the magnetic flux through a loop due
This article was published in ASHRAE Journal, June 2010. Copyright 2010 American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. Reprinted here by permission from ASHRAE at www.tiaxllc.com.
Power Electronics Prof. K. Gopakumar Centre for Electronics Design and Technology Indian Institute of Science, Bangalore Lecture - 1 Electric Drive Today, we will start with the topic on industrial drive
Basic Op Amp ircuits Manuel Toledo INEL 5205 Instrumentation August 3, 2008 Introduction The operational amplifier (op amp or OA for short) is perhaps the most important building block for the design of
4TTM3-SF-1 Service Facts Split System Cooling 4TTM3018-4TTM3060! CAUTION UNIT CONTAINS R-410A REFRIGERANT! R-410A OPERATING PRESSURE EXCEEDS THE LIMIT OF R-22. PROPER SERVICE EQUIPMENT IS REQUIRED. FAILURE
2 Bosch Rexroth AG Electric Drives and Controls Documentation Brake chopper with up to 30 kw continuous braking power Easy to operate and service (detachable fan, LCD operating panel with copy function)
Zoning with Variable Speed Mini-Split Systems Fujitsu Service Training Welcome - Thank you for attending Did you know? In 1940 only 42% of homes in the US had central heating In 1970 20% of homes had central
LIFT CONTROL SYSTEMS CATALOGUE 2007 All Your Needs For Elevators INDEX 1. Lift Control Cards... 3 2. Speed Control Units... 7 3. Emergency Rescue Cards... 8 4. Lift Control Panels... 10 5. Photocells...
2014 Amplifier - 1 FREQUENCY RESPONSE OF AN AUDIO AMPLIFIER The objectives of this experiment are: To understand the concept of HI-FI audio equipment To generate a frequency response curve for an audio
Safety Requirements Specification Comments on this report are gratefully received by Johan Hedberg at SP Swedish National Testing and Research Institute mailto:email@example.com -1- Summary Safety Requirement
IPB-IB R ELECTRIC ACTUATORS FOR INDUSTRIAL PROCESS CONTROL INDUSTRIAL STEAM BOILERS BECK VIDEO Scan w/ Smartphone 1 Increasing Business Pressures Necessitate Boiler Control Improvements Today s industrial
Solid Core and Split Core Adjustable Current Status Switches CSS-O, CSS-C; CSP-O, CSP-C DESCRIPTION FEATURES PRODUCT DATA Very low operating trip points LED status indication Integral DIN rail mounting
Technical Support Bulletin Nr. 20 Special AC Functions Summary! Introduction! Hot Start Control! Adaptive Control! Defrost Start Temperature Compensation Control! Anti-Sticking Control! Water Free Cooling
SAFETY Industrial DESCRIBE hazards and precautions taken to avoid injury in the workplace. Example #1: All of the following are common PPE used to perform maintenance activities EXCEPT: a. Safety Glasses
AUTOMATED, FULL LOAD MOTOR TESTING AT PRODUCTION SPEEDS Abstract: Revolutionary test method coupled with innovative automation yields superior motor performance measurement data without sacrifice of production
Summary Dually Fed Permanent Magnet Synchronous Generator Condition Monitoring Using Stator Current Joachim Härsjö, Massimo Bongiorno and Ola Carlson Chalmers University of Technology Energi och Miljö,
Adjustable Frequency Drive Instruction Manual VLT Series 3500 Instruction Manual 175R5237 - Document Version 5.00 This manual applies to all VLT Series 3502-3800 Adjustable Frequency Drives with software
Quanser NI-ELVIS Trainer (QNET) Series: QNET Experiment #06: HVAC Proportional- Integral (PI) Temperature Control Heating, Ventilation, and Air Conditioning Trainer (HVACT) Student Manual Table of Contents
Induced voltages and Inductance Faraday s Law concept #1, 4, 5, 8, 13 Problem # 1, 3, 4, 5, 6, 9, 10, 13, 15, 24, 23, 25, 31, 32a, 34, 37, 41, 43, 51, 61 Last chapter we saw that a current produces a magnetic