1 VFD 101 Lesson 4 Application Terminology for a VFD This lesson covers the application terminology associated with a Variable Frequency Drive (VFD) and describes each term in detail. When applying a Variable Frequency Drive (VFD) to a particular application, a number of terms are involved. This lesson attempts to clarify most of those terms. Here is the basics outline for this lesson. Outline: Application Terminology 1. Application Curves 2. Starting Torque 3. Open or Closed Loop 4. Closed Loop and PID 5. Different Types of VFDs Note: Other names are used for this device, such as Adjustable Frequency Drive (AFD), Variable Speed Drive (ASD), Frequency Converter and Inverter, but Variable Frequency Drive (VFD) or just Drive is used throughout this lesson.
2 Outline Application Terminology 1. Application Curves CT, CP, VT 2. Starting Torque HO, Breakaway, NO 3. Open or Closed Loops 4. Closed Loop & PID Action, Setpoint, Offset, Proportional, Integral, Derivative 5. Different Types of VFDs This module covers some of the application terminology used with VFDs. This terminology becomes very important for selecting the correct VFD and programming the correct settings needed for an application. Applications include terms such as Constant Torque (CT), Constant Power (CP) and Variable Torque (VT). Starting Torque is also covered, which uses High Overload (HO), Breakaway Torque, and Normal Overload (NO). Terms such as open loop and closed loop are also covered. Terms in closed loop, also explore action, setpoint and PID terminology. The last part covers a summary of the different types of VFDs. It shows the Volts/Hz, Voltage Vector, Flux Vector as they compare to a DC Servo in terms of response, accuracy and speed range. A more detailed explanation of each type is scheduled for a later lesson.
3 1. Application Torque Curves This part of the lesson covers the application terminology associated with a VFD, starting with application torque curves. VFD Application Terminology 1. Application Torque Curves a) Constant Torque (CT) b) Constant Power (CP) c) Variable Torque (VT) 2. Starting Torque 3. Open or Closed Loop 4. Closed Loop & PID 5. Different Types of VFDs
4 1. a) Constant Torque (CT) CT used on Reciprocating Compressors Torque stays relatively constant from 5Hz to 60Hz. AC motors have low torque at slow speeds. The graph above shows Torque in relationship to Speed. This graph was made when the VFD and loaded motor, were running at Synchronous Speed, 60 Hz, 1800 rpm on a 4-pole 3- phase AC motor. The speed of the VFD was slowly turned down to 0 Hz. Notice that the torque drops down to its nominal rating on an AC induction motor at the lower speeds, 5Hz or less. Please be aware that this particular CT application, reciprocating compressor, should never run less than 30Hz. Constant Torque applications require a constant level of torque throughout a process regardless of different speeds. The vast majority of constant torque applications are for industry, which involve conveyors, mixers, elevators, feeders, hoists, and bottling machines. In HVAC reciprocating compressors, and positive displacement pumps might be encountered which require CT. Some VFD manufacturers attempt to apply a CT drive to fans and pumps used in HVAC, because they do not make a specific VFD for variable torque applications. More information is given in the pages that follow. On most CT applications, constant torque must be maintained from 1 to 60Hz. Notice that the torque curve drops when the speed is reduce below a minimum of 5Hz. To compensate for this drop, some VFDs can perform Motor Tuning, which matches the VFD settings to a particular motor. This tuning allows for more precise calculations by the VFD giving more torque throughout the CT curve, but particularly noticeable is the torque boost at those slow speeds from 1 to 10Hz. In HVAC, Motor tuning is only a slight advantage for fans and pumps, saving only a small portion of energy. Because of motor cooling, most fans and pumps have a minimum speed of 10Hz or greater.
5 Volts per Hertz Chart Voltage increases as speed increases CT linear relationship between volts and hertz 30Hz = 230V; 60Hz = 460V on 460VAC motor VFDs attempt to generate the correct level of torque needed for its application. Torque is directly related to current. In CT applications, voltage going from the VFD to the motor is increased in a linear manner as the speed increases. In the example above, on a 460Vac motor, 460 Volts is only sent to the motor when the speed reaches 60Hz and higher. The chart above displays the Volts/Hz relationship for a CT application. Constant Torque is achieved because the VFD is increasing the voltage to the motor as it increases the speed. In this chart, when the VFD sends a signal of 30Hz, it is also sending a 230V signal to the motor. When the VFD sends a 60Hz signal, the voltage is at 460V. This relationship keeps the current and in turn the torque to the motor relatively constant. The changes seen in the motor current are based on the load. Notice that when the speed reaches 60Hz, base speed, the voltage going to the motor from the VFD can not go higher, it has reached its limit, 460V. If the speed is increased above base speed, to say 90Hz, the voltage from the VFD stays at 460V, but the current and torque drop. This Volts/Hz chart is different for motors that use different voltages.
6 1. b) Constant Power (CP) CP applications are rare for the VFD, none in HVAC. CP applications are always above base speed. Torque drops significantly above base speed (60Hz). Constant Power applications are run at synchronous speed, 60Hz and higher. On a CT Curve, the area above synchronous speed is known as the Constant Power Curve. As speed continues above 60Hz, torque continues to drop. The few applications that require these high speeds are typically saws, and grinders, and no applications in HVAC. A point of clarification between synchronous speed and base speed is useful. Synchronous speed, in an induction motor, is the RPM of the magnetic field when the motor reaches its nameplate voltage and frequency. The formula for synchronous speed is as follows: Synchronous speed = (Motor frequency) * 120 / (# poles) Example: (60Hz * 120) / 4 poles = 1800RPM Base Speed is the speed in rpm that results when the motor is at its nameplate voltage, frequency and current. Most Asynchronous 4-pole induction motors using 60Hz have a base speed between 1725 to 1770rpm.
7 1. c) Variable Torque (VT) VT applications save a great deal of energy Used with centrifugal pumps and centrifugal fans. Variable Torque (VT) applications almost always involve centrifugal pumps and centrifugal fans. If a VFD manufacturer has an HVAC drive, it is most likely designed and programmed for VT applications only, such as the VLT 6000 from Danfoss. The torque required to operate a pump or fan is very low until it starts to approach its base speed, say 1750rpm at 60Hz. There are formulas that show the relationship of power to rpm. Ideally, assuming no friction losses, the pump at half the speed only requires 1/8 the power. VFDs on VT applications save a great deal of energy and money. Once above base speed, a fan or pump requires a considerable amount of power, so they are rarely run above 60Hz.
8 Automatic Energy Optimization (AEO) VT voltage lower at speeds than CT AEO - Reduces voltage until speed is effected 30Hz = 160V straight VT; 90V with AEO A couple of VFD manufacturers, such as Danfoss, offer Automatic Energy Optimization (AEO). This is used in all VT applications. This function automatically and continuously monitors and adjusts the output voltage to maximize energy savings. After the motor reaches the set speed, say 30Hz, the AEO function reduces the output voltage to the motor, if the load allows. When the load is light, the voltage is reduced perhaps from 160V to 90V. This reduced voltage not only saves energy, but reduces motor heating, motor noise, and increases efficiency.
9 2. Starting Torque Centrifuge This part of the lesson covers the application terminology associated with starting torque. Outline: VFD Application Terminology 1. Application Torque Curves 2. Starting Torque a) High Overload (HO) b) Breakaway Torque c) Normal Overload (NO) 3. Open or Closed Loop 4. Closed Loop & PID 5. Different Types of VFDs
10 2. a) High Overload (HO) High Overload allows 160% starting current for 1 min. Most CT applications require High Overload. If drive exceeds 160% or 1 minute, VFD trips. High Overload (160%) is used to apply the torque to start a load. The inertia to start a reciprocating compressor, a positive displacement pump or in the example above a hoist requires a great deal of starting torque. It can be as high as 160% of the current for 1 minute. Once started the torque drops back to 100% or less. If the load does not move and the drive exceeds 160% or exceeds 1 minute, the drive trips, which means that the VFD does not move the motor. This trip gives an Over-current or Torque Limit alarm and for protection sake a reset button must be pressed to clear the alarm and restart the VFD. Some VFDs have a High Overload limit of 150% for 1 minute. It is possible to use a High Overload or CT Start to get a fan or pump moving, but most HVAC applications do not require High Overload.
11 2. b) Breakaway Torque High Overload has a breakaway torque that allows 180% starting current for 0.5 seconds. If drive exceeds 180% or 0.5 seconds, VFD trips. Breakaway Torque (180%) also known as Starting Torque, usually refers to the first 0.5 seconds after start. In the example a mixer has a very thick substance, perhaps a batch of adhesive. When the VFD starts to turn the motor the resistance of the substance is very high. The VFD increases the current output up to 180% for half a second to get the mixer started. Once it starts, the VFD continues at the High Overload setting of 160% for 1 minute. If it does not move, the VFD trips for protection of the VFD, motor and mixer. This is rarely needed for HVAC applications.
12 2. c) Normal Overload (NO) Normal Overload has a starting torque that allows 110% starting current for 1 minute. Most VT applications require Normal Overload. VT VFDs are sized differently 200Hp for CT; 250Hp for VT Normal Overload (110%) is almost always used with HVAC applications basically with centrifugal fans and pumps. When a centrifugal fan is started it takes very little starting torque to turn the fan against air, so the 110% limit is adequate. If the 110% for 1 minute is exceeded, the VFD trips. Since the current output on starting is less for VT applications, smaller VFDs can operate slightly larger motors. If a 200Hp VFD which is normally Constant Torque (CT) has a VT setting, the VFD could be used to operate a 250Hp motor with little difficulty.
13 3. Open or Closed Loop All applications fall into 2 categories Open Loop or Closed Loop Closed loop has additional settings which include controller action, setpoint, and PID settings Outline: VFD Application Terminology 1. Application Torque Curves 2. Starting Torque 3. Open or Closed Loop a) Open Loop b) Closed Loop 4. Closed Loop & PID 5. Different Types of VFDs A quick definition for Open and Closed Loop is shown here. Open Loop control does NOT have a direct feedback signal. Closed Loop has a direct feedback signal coming into the VFD.
14 3. a) Open Loop The VFD is programmed for open loop, because there is NO feedback signal going to the VFD but the system is closed loop. Open Loop control does NOT have a direct feedback signal. In the example above, a static pressure sensor is wired to a Direct Digital Controller (DDC). Because the feedback signal, pressure, goes to the Controller, a closed loop must be setup in it to control the static pressure. This closed loop inside the Controller monitors the pressure comparing it against a setpoint and then calculates a reference signal. The Controller then sends this reference signal to the VFD for proper modulation of the fan. The reference signal is sent to the VFD, which in turn controls the motor and fan. In this example, the VFD is programmed for Open Loop and it receives a reference command from the Controller. If the pressure sensor were wired directly into the VFD, then the drive would need to be programmed for Closed Loop in order to have proper control of the fan. The system is a closed loop system because it senses its own action, its feedback, but because the feedback signal does not go directly to it, the VFD is programmed for open loop.
15 4) Closed Loop Sensor monitors the feedback signal. Controller, the VFD, gives the sensor a desired value, action and PID settings and calculates a response. Controlled Device, the fan, responds to the signal from the controller, increasing or decreasing in speed. Closed Loop is where the controller inside the VFD can be used to modulate the speed of a motor to maintain a process. It is the job of the sensor or transmitter to measure a variable, in the example above, this is static pressure. This sensor sends a signal (usually a 4-20mA) to the controller over a particular range, in this example from 0 to 5 wc. The sensor is wired to the current input of the VFD, the controller. This signal is programmed in the VFD as the feedback signal. This feedback signal must be given engineering units, from our example, inches of water column ( wc) or Pascals. Inside the VFD the feedback signal must also be given the range that matches the sensor. When the sensor sees 4mA it is 0 wc (0 Pascals) and when the sensor sees 20mA, the reading is 5 wc (1250 Pascals). The VFD, controller, has a setpoint, action and PID settings (explained later) to calculate the response necessary to maintain the desired value seen at the sensor. The VFD sends a signal to the fan to speed up or slow down to maintain a certain level. The fan, controlled device, responds to match the signal from the VFD, controller. It speeds up when the level of the static pressure decreases and slows down when the level of the static pressure is too high.
16 4. a) Control Action Normal Control incoming signal increases; VFD speed decreases. Inverse Control incoming signal increases; VFD speed increases. In closed loop applications, such as controlling pressure by monitoring the volume of return air, shown above, the VFD must always be programmed for the correct action. There are 2 choices: Normal Control (also know as Reverse Acting). In the top return fan example, when the CFM Transmitter sends a signal that indicates it is above the setpoint, the output from the VFD decreases. The action is correct if the sensor is down stream from the controlled device, the return fan. As the CFM sees an increase, the signal to the fan decreases, slowing the fan down. As the CFM transmitter sees a drop, the speed of the fan increases. Inverse Control (also know as Direct Acting). In the bottom return fan example, when the signal from the CFM Transmitter increases above the setpoint the output from the VFD increases. This action is correct if the CFM transmitter is upstream from the return fan. If the wrong action (Inverse) were programmed in the VFD on the top return fan, it would speed up as the CFM in the duct rose higher. Eventually the speed of the return fan would go to its maximum. This could put a major stress on the ductwork. If the incorrect action is programmed in an application the VFD ends up locked at minimum or at maximum speed.
17 4. b) Setpoint, Error & Gain Setpoint or reference is the desired value for a controlled variable; example: 2.00 wc (500pa). Error (offset) is the amount the feedback is from setpoint at any given time, example: 0.15 wc (38pa) Proportional Gain is a multiplier times the error (offset). Example above the Gain starts at 0.3 Setpoint is the desired value or reference of the controlled variable for a closed loop application. In controlling static pressure, shown above, 2.00 wc (500pa) is the desired setpoint or reference. Error is a difference between the setpoint, 2.00 wc (500pa) and the actual feedback pressure, 1.85 wc (462pa) for this system. This difference is also known as Offset (or off the setpoint). Proportional Gain is multiplied by the error to create an output. The larger the proportional gain, the larger the output change for a given error. If the proportional gain is too small (0.01) this multiplier times the error has no effect on the speed of the VFD. If the proportional gain is too large (3.00 or higher) the system can become unstable, modulating between minimum speed and maximum speed which is called hunting. A good starting place for the Proportional Gain is about 1.00 but changes depending on the application. If Proportional Gain is only used, without I or D (explained on the next slide), the output is relatively close to setpoint but there is always an error.
18 4. c) Integral & Derivative Integral checks the offset over a period of time and makes corrections. Derivative checks the offset and corrects for the speed of the integral correction. Integral Gain is based on the history of the error. The integral function maintains a running total of the error and creates an output based on this total. The lower the number used for the integral gain the more frequently the error is checked and the larger its influence. If the integral time is too low (less than 5 seconds), the system can become unstable and starts to hunt. A good place to start is 10 seconds, but again this can vary based on the application. Integral gain eliminates the steady error inherent to proportional control. As pictured above, integral gain adds overshoot every time the load changes, but eventually settles close to setpoint. Integral is used frequently in HVAC applications. Derivative or differential is based on the rate of change of the error. It is used to limit overshoot and dampen system oscillation. The larger the derivative time, the larger the influence. If the derivative time is too large, the system becomes unstable. Derivative is very sensitive to noise on the feedback signal and historically seldom used in HVAC closed loop systems.
19 4. b) PID Summary: There are many different PID algorithms. All contain these 3 features, Proportional Gain, Integral, and Derivative. The ways these terms are combined may be different. In some implementations the 3 values operate independently of each other and in others, changing one value effects the others. Proportional Gain contributes to the output in a direct relationship to the error between the feedback and setpoint. Integral contributes to the output based on the history of the error. Derivative contributes to the output based on the rate of change to the error. Setpoint is the desired value for the variable being controlled. Feedback is the actual value of the variable being controlled. Error (offset) is the difference between the setpoint and feedback Hunting is an unstable condition which causes the speed of the motor to continuously vary from maximum to minimum.
20 5) Different Types of VFDs There are different types of VFDs, which are briefly covered here. They include Volts/Hz, Voltage Vector, Voltage Vector +, Flux Vector and Servo. Volts/Hz drives also known as a Basic Scalar drives, are the least expensive drive with the least features. This drive is usually setup for CT and Open Loop only. Voltage Vector drives also known as Space Vector drives have more features and may have the ability to do both CT/VT and Open/Closed Loop. Voltage Vector Plus drives have more features than the others and therefore have more cost than previously mentioned drives. They can calculate motor characteristics without spinning the shaft of the motor. These last 3 types of VFD account for 95% of all applications. There are a few that need greater accuracy which follow. Flux Vector drives have more calculations which makes them more expensive and more accurate. Some Flux vector drives require special motors. Servo drives are DC and do not operate with AC induction motors. They are expensive in comparison to VFDs. They are the most responsive to dynamic changes. These drive types are explored in greater detail in a later lesson.
21 5) Different Types of VFDs Summary: Type Response Accuracy Speed Range V/Hz ms 10% + 10:1 180rpm Voltage Vector ms 2% - 8% 50:1 36rpm Voltage Vector ms 0.2%-2% Open 100:1 18rpm Closed 900:1 2rpm Flux Vector 5 60ms 0.02% - 0.1% 1400:1 1.3rpm Servo 2 8ms 0.007% % 1800:1 1rpm As a comparison above, each type of motor control shows, Response to dynamic changes Accuracy and Speed Range. Speed Range indicates how slow the motor can turn but still have proper operation. Speed Range is always indicated as a ratio. The higher the ratio the better control at slow speeds. The minimum rpm for each type has been calculated, assuming 1800 base speed. Voltage Vector Plus has 2 values, one for open loop and the other for closed loop. This completes this lesson. There are Review Questions in the Post-Test section.
VFD 101 Lesson 2 Control Arrangements for a VFD This training covers the major control arrangements for a VFD, starting with the simplest arrangement then moving to the more complex. Many of the control
VFD 101 Lesson 3 Parts of a Variable Frequency Drive (VFD) This lesson covers the parts that make up the Variable Frequency Drive (VFD) and describes the basic operation of each part. Here is the basics
VFD 101 Lesson 1 Functions of an Variable Frequency Drive (VFD) This lesson covers the basic functions of a Variable Frequency Drive (VFD) as it applies to fans. Here is the basics outline for this lesson.
PID SET UP WITH FRENIC Eco series inverter. 1. Introduction. This document describes briefly how to set up the FRENIC Eco series inverter to implement a PID control, for example, a pressure control with
Drives 101 Lesson 3 Parts of an Adjustable Frequency Drive (AFD) This lesson covers the parts that make up the Adjustable Frequency Drive (AFD) and describes the basic operation of each part. Here is the
VFD 101 Intro Lesson Variable Frequency Drives (VFD) Fundamentals This introduction lesson reviews the reasons for using Variable Frequency Drives (VFD) in water and wastewater treatment. It specifically
Drives 101 Lesson 3 This lesson covers the basic parts and operation of an Adjustable Frequency Drive (AFD). These parts are divided into 4 sections: Rectifier, Intermediate circuit (DC Link), Inverter
Drives 101 Lesson 1 Functions of an Adjustable Frequency Drive (AFD) This lesson covers the basic functions of an Adjustable Frequency Drives (AFD). Outline: 3-phase AC Motor 1. Bi-Directional Operation
VFD 101 Lesson 1 Functions of an Variable Frequency Drive (VFD) This lesson covers the basic functions of a Variable Frequency Drive (VFD) as it applies to fans. 10/2/2003 Here is the basics outline for
Technical Guide No. 100 High Performance Drives -- speed and torque regulation Process Regulator Speed Regulator Torque Regulator Process Technical Guide: The illustrations, charts and examples given in
Purchasing Tips Analyse the System as a Whole Variable Frequency Drives Since the process of converting incoming power from one frequency to another will result in some losses, energy savings must always
. When applying VARIABLE Frequency Drives(VFD), the speed-torque characteristics of an induction motor started at full voltage and operated on utility power should first be reviewed. Figure 1 shows the
5. ENERGY ERFORMANCE ASSESSMENT OF MOTORS / VARIABLE SEED DRIVES 5.1 Introduction The two parameters of importance in a motor are efficiency and power factor. The efficiencies of induction motors remain
Application Note CTAN #293 The Application Note is pertinent to the Commander SK Family Fan and Pump Setup Fans and Pumps ( not reciprocating nor peristaltic pumps- only those that follow Variable Speed/Torque
Small mine hoist type loads In this application note we will size and configure a DURApulse variable frequency drive for a small mine hoist. A mine hoist lifts mineral ore from one level to one up in underground
Basic AC Drives AC drives, inverters, and adjustable frequency drives are all terms that are used to refer to equipment designed to control the speed of an AC motor. The term SIMOVERT is used by Siemens
INTRODUCTION: Baldor Electric Company has prepared this Specifiers Guide to help you cover all the bases when you are specifying electric motors. It will cover in a generic way most of the subjects which
Drives AC Drives Using PWM Techniques Power Conversion Unit The block diagram below shows the power conversion unit in Pulse Width Modulated (PWM) drives. In this type of drive, a diode bridge rectifier
Introduction to Temperature Controllers The Miniature CN77000 is a full featured microprocessor-based controller in a 1 16 DIN package. How Can I Control My Process Temperature Accurately and Reliably?
Product Overview The HYUNDAI N700E Series High Performance Drives offer powerful control solutions with exceptional speed control and torque response which provides superior vector performance. The N700E
Starter Ratings Starter contactors are rated according to size and type of load they handle. The National Electrical Manufacturers Association (NEMA) and the International Electrotechnical Commission (IEC)
Understanding Variable Speed Drives April 1, 1997 Solomon S. Turkel, Solomon S. When applied properly, the variable frequency drive (VFD) is the most effective motor controller in the industry today. Modern
AC drive with PID control loop In this application note we will configure a DURApulse variable frequency drive for a fan that has to maintain the air flow by means of a PID control loop. In this case we
Control Technologies Manual PWM AC Drives Revision 1.0 Pulse Width Modulated (PWM) Figure 1.8 shows a block diagram of the power conversion unit in a PWM drive. In this type of drive, a diode bridge rectifier
EFFICIENCY COMPARISON OF MODERN VARIABLE SPEED DRIVE TECHNOLOGIES JUNE 1993 BY EDWARD C. LEE POWERTEC INDUSTRIAL CORPORATION Abstract: Brushless D.C. technology is new to the general industrial maketplace
Variable Speed Drive Specification Part 1 General 1.01 Description A. This specification describes an AC variable speed Direct Torque Control or sensorless vector equivalent drive used to control the speed
SINPAC Switches: Brief Operating Description For over 75 years, single-phase motors have utilized a mechanical centrifugal switch to switch the start circuit. Inherent characteristics of a mechanical device
Fans and Pumps are sized to meet the maximum flow rate required by the system. System conditions frequently require reducing the flow rate. Throttling and bypass devices dampers and valves are installed
Specifying a Variable Frequency Drive s Put on by Bruce Reeves and Jeremy Gonzales Dykman Electrical Covering the Western US For all of your VFD and Soft Start and Motor Needs How To Specify a Variable
SINPAC Switches: Brief Operating Description For over 75 years, single-phase motors have utilized a mechanical centrifugal switch to switch the start circuit. Inherent characteristics of a mechanical device
Understanding a Universal Testing Machine Motor Control System An Experimental PID Gain Tuning Procedure By: Richard Gedney, ADMET, Inc. 1.0 PID Controller Basics The mechanical properties of a material
Exercise 2 Open Loop Servo Motor Static Characteristics EXERCISE OBJECTIVE When you have completed this exercise, you will be familiar with the various mechanical and electrical components of a brush-type
Control of the Process Open Loop Control Closed Loop Control Open Loop Control Limited uses No feedback from the output Predicted outcomes Block Diagram Controller Final Control Element Process Optional
Tension Controls VERSATEC Versatile Tension Control Unwind Rewind Dancer Free Loop Ranger VTC-E US-2 VTC The VERSATEC Versatile Tension Control is a multi-function automatic tension or process controller.
MAKING MODERN LIVING POSSIBLE VLT APPLICATION NOTE VLT AutomationDrive for Marine winch applications This Application note is meant to be a guideline for using Danfoss VLT AutomationDrive in winch applications.
Alternating Current Motors AC induction motor is the most widely used type of electric motor in the modern world. AC motors are primarily used as a source of constant-speed mechanical power but are increasingly
AC Motor Basics Topics Motor Basics Motor Construction Application of Variable Speed Motors Motor Basics Magnetism and Induction Motor Speed Relationship Motor Performance Motor Nameplate Information Motor
Data Bulletin 88DB126 Applying the Altivar 61 AC Drive in Constant Torque Applications Retain for future use. Introduction Definitions: Variable Torque and Constant Torque; Normal Duty and Heavy Duty The
VLT Drives and Controls WINDER AND TENSION CONTROL OPTION VLT Series 5000 Introduction... page 3 Parameters... page 5 This manual is to be used for the Winder and Tension Control Option installed in all
Overload Relay Tables of Elements for Overload Relays Use only when motor full load current is not known. Motor amps will vary depending on the type and manufacturer of the motor. These average values,
SMC-50 Offers New Control Advances, Including Sensorless Linear Acceleration Rockwell Automation Given increasing costs and environmental awareness, energy conservation is a growing concern, and the need
MA7200 Sensorless Vector AC Inverter Features and Benefits Sensorless Vector The MA7200 has precise speed and torque control for the most demanding system performance and simple set-up through an auto-tuning
MANUAL ECM Motor ECM / ECM-DX Series v100 Issue Date: 07/17/15 2015 Price Industries Limited. All rights reserved. ECM MOTOR TABLE OF CONTENTS ECM Motor Background...1 ECM Motor Power and Control Connectors...2
Voltage Influence on Typical Protection and Controls for Motors, Power Electronics, and Other Common Loads Presentation to: WECC Modeling and Validation Work Group March 3, 2011 John Kueck The Study Examines
Servo Drive Current Loop Tuning Procedure (intended for Analog input PWM output servo drives) The standard tuning values used in ADVANCED Motion Controls drives are conservative and work well in over 90%
DC DRIVE FUNDAMENTALS UNDERSTANDING DC DRIVES DC motors have been available for nearly 100 years. In fact the first electric motors were designed and built for operation from direct current power. AC motors
PID for Trim Control GPD515/G5 Software Option (VSG112052) Part Number: CIMR-G5MXXXXXF-012 (1) With this factory-installed FLASH software, the GPD515/G5 has the ability to trim a speed reference with a
ECET 211 Electric Machines & Controls Lecture 9-2 Adjustable-Speed Drives and PLC (2 of 2) Text Book: Electric Motors and Control Systems, by Frank D. Petruzella, published by McGraw Hill, 2015 Paul I-Hai
Synchronous Reluctance Motors Page 1 Synchronous reluctance motor Positioning inside the motor spectrum asynchronous motor reluctance motors permanent magnetized synchronous motor switched reluctance synchronous
Single Phase Motor Starting Pump ED 101 Joe Evans, Ph.D firstname.lastname@example.org http://www.pumped101.com Although there are many different electric motor designs, a characteristic that is common throughout
Siemens STEP 2000 Course AC Drives It's easy to get in STEP! Download any course. Hint: Make sure you download all parts for each course and the test answer form. Complete each chapter and its review section
Tech Note #4: Tuning a Servo Axis For Closed Loop Position Control Application Note by Tim McIntosh September 24, 2001 Abstract: In this Tech Note a procedure for tuning a servo axis for closed loop position
Introduction to Process Control Operating Manual 6/98 Table of Contents Section 1 Process Control Defined.......................................................................... 1-1 Process Control Mode.........................................................................
Exercise 4 Servo Closed Loop Speed Control Steady State Characteristics EXERCISE OBJECTIVE When you have completed this exercise, you will be familiar with servo operation in closed loop speed control.
Unidrive M Energy Savings Why is this important? Some Data: Money, Lots of Money >13.5m electric motors 1Hp or greater installed in US industrial process operations. Industry spends >$33b annually on electricity
VLT HVAC Drive FC 02 Application Note Temperature Derating Guide Temperature Derating Guide.. Abstract This paper provides detailed data regarding the operation of the VLT HVAC Drive FC02 at varying ambient
EELE 354 Lab Assignment 11: DC and AC Motors EELE 354 Lab Assignment 11 1 Lab Overview: Underneath your workbench, there are three electromechanical machines: a three-phase induction machine, a three-phase
Generator Protection Some Review Slids What a Generator looks like Generator Protection 2 Generator 3 Generator Protection Review Abnormal Operating Conditions Loss of Synchronism Abnormal Frequency Over
It s now time to save the world with Efficient Motor Control With Power Drives Systems ALTIVAR Variable Speed Drives Altivar 12 Altivar 212 Altivar 312 Altivar 61 Altivar 71 Charles Nierves Drive Champion
VFD - E700 Series Specifications The cost-effective variable speed control solution for centrifugal pumps. Available in 240V and 480V up to 20HP Advanced Magnetic Flux Vector Control for improved starting
Optidrive Applications Support Library Application Note Title AN-ODE-2-032 Related Products Optidrive E2 Overview Level 2 PI Closed Loop Feedback Control Applications 1 Fundamental - No previous experience
INDUCTION MOTOR TESTS (No-Load Test, Blocked Rotor Test) The equivalent circuit parameters for an induction motor can be determined using specific tests on the motor, just as was done for the transformer.
Drives Flexible, simple, rugged, robust! Our promise Commitment to Price Leadership Price leadership is serious business. It takes continuous life cycle management to make price leadership a sustainable
Introduction The MCI soft starters are designed for soft starting and stopping of 3 phase ac motors, thus reducing the inrush current and eliminating the damaging effects of high starting torque surges.
Sensorless Field Oriented Control (FOC) for AC Induction Motors (ACIM) 2008 Microchip Technology Incorporated. All Rights Reserved. Sensorless FOC for ACIM Slide 1 Welcome to the Sensorless Field Oriented
UNIVERSITY OF WATERLOO ELECTRICAL & COMPUTER ENGINEERING DEPARTMENT ME 269 Electromechanical Devices and Power Processing` Lab Experiment 6: 3-phase induction motors speed control and RMF Objective: 1.
POWER SAVINGS AND APPLICATION GUIDE For power factor correction and harmonic mitigation techniques Normally, the term Power Factor (PF) is misunderstood. This often results in consumers paying penalties
HITACHI INVERTER SJ/L1/3 SERIES PID CONTROL USERS GUIDE After reading this manual, keep it for future reference Hitachi America, Ltd. HAL1PID CONTENTS 1. OVERVIEW 3 2. PID CONTROL ON SJ1/L1 INVERTERS 3
B Servo Motors Servo Motors B-1 Overview... B-2 Overview Servo Motor and Package NX Series B-10 NX Accessories... B-41 Accessories B-1 B-2 Overview Overview of Servo Motors The servo motor is specialized
BFI Applications Support Library Application Note AN-BEI-P2-038 Title Modbus RTU Control and Register Mapping Related Products Beijer Frequency Inverter P2 Level 3 Overview: 1 Fundamental - No previous
Understanding Pump Curves Presenter: Michael Stroh Application & Project Engineer, June 4th, 2015 OWEA-S: Understanding Pump Curves The Heart of Your Process Understanding Pump Curves The Static Head is
Speed Control s; Servo, AC Induction, or Brushless (BLDC) Too Valuable To Keep Secret: The Power of Brushless s When it comes to speed control, you may think the choice is between an inverter driven three-phase
Bulletin 1365 Startup and Adjustment Only qualified electrical personnel familiar with the construction and operation of this equipment and the hazards involved should install, adjust and/or service this
..OR How To Protect your 3-Phase Equipment Investment with 3-Phase Monitors from Time Mark... TIME MARK CORPORATION 11440 EAST PINE STREET TULSA, OK 74116 USA tel 918 438-1220 fax 918 437-7584 www.time-mark.com
Application of Multi-function Motor Protection Relays to Variable Frequency Drive Connected Motors Tom Ernst GE Digital Energy 4523 Jeremiah Rd Cookeville, TN 38506 715-718-1384 email@example.com Abstract:
PART 1 - GENERAL 1.1 SUMMARY A. This Section includes control sequences for HVAC systems, subsystems, and equipment. B. Related Sections include the following: 1. Division 15 Section "HVAC Instrumentation
AVX-50BL10 50V, 10A Brush / Brushless Power Amplifier Data Sheet and Setup Guide Introduction The AVX-50BL10 amplifier is designed to drive brushless or brush motors at currents up to 10A and 50V. Using
Series Inverter Applications MEH449 Compact inverter Application to Belt Conveyors Advantages of using Fuji inverters (1) Smooth start with a high starting torque of 150% or more Our original simplified
EE 554 FINAL PROJECT DC motor Control of Flexible Shaft TABLE OF CONTENTS 1. INTRODUCTION... 3 2. PHYSICAL SETUP... 4 3. ELECTRICAL SETUP... 5 4. LABVIEW... 7 5. MODELLING... 12 6. TESTING... 16 7. RESULTS...
Electrical Drives 1 Week 1: Introduction to drive systems What Do we mean by Electrical Drive System? It is the study of the electric system involving controlling electric motors in both steady state and
A Project in PID Temperature Control and Loop Tuning Session 2526 Michael Oelschlegel and Rafic Bachnak Texas A&M University-Corpus Christi Corpus Christi, TX 78412 Abstract Automatic temperature control
HVAC Drive Variable Frequency Drive Guide Specification I. PART 1- GENERAL A. DESCRIPTION 1. This specification covers complete a variable frequency drives (VFDs) designated on the drawing schedules to
June 2006 Sheet 17.0-1 Adjustable Frequency Drives Low Voltage Contents Application Guide Basic Motor and Adjustable Frequency Drive Theory..................0-2 AC Motors...................................................0-2
PM Motors operated by V VC PLUS PM 1. Introduction...2 1.1. Scope of Document...2 1.2. Target Group...2 1.3. Discussed Drives...2 2. PM Motors in General...3 2.1. Salient and non salient PM motor constructions...3
Experiment 7 ET 33b No-load and Starting Characteristics of Squirrel-Cage Induction Motors Purpose: Determine the electrical and mechanical characteristics of a squirrel-cage induction motor during no-load