1 Rev.00 - Pag. 1/19 Installation and use Manual OIL TRANSFORMER
2 Rev.00 - Pag. 2/19 TABLE OF CONTENTS 1 INTRODUCTION Reference standard Electromagnetic compatibility Marking CE GENERAL OUTLINE OF THE TRANSFORMER AND THE ACCESSORIES RECEPTION, HANDLING, STORAGE Reception Handling Storage INSTALLATION Standard installation conditions Ventilation Insulating distances Earthing connections LV and HV connections Regulation of transformation ratio Parallel connection of transformers TRANSFORMER PROTECTIONS Over temperature protection Overloading and short circuit protection Protection against over voltages COMMISSIONING Mechanical checks before the commissioning Electrical checks before the commissioning Insulating fluid level Arcing horns Air dryer Buchholz Relay Thermometer Integrated safety device Operations for commissioning... 19
3 Rev.00 - Pag. 3/19 1 INTRODUCTION 1.1 Reference standard The oil transformer referred to the attached test report, has been designed and manufactured by TESAR in order to meet to Italian CEI and international IEC Standards requirements in force at the moment of its manufacturing (unless different agreement). CEI Standards (Italian) - CEI EN Power transformer part 1 : General - CEI EN Power transformer part 2 : Temperature Rise - CEI EN Power transformer part 3 : Insulation levels, dielectric tests and external clearances in air - CEI EN Power transformer part 4 : Guide to the lightning impulse and switching impulse testing - Power transformers and reactors - CEI EN Power transformer part 4 : Ability to withstand short circuit - CEI EN Power transformer- part 10 determination of sound levels - CEI Marcatura dei terminali dei trasformatori di potenza - CEI Guida di carico per trasformatori immersi in olio IEC Standards (International) - IEC Power transformer part 1 : General - IEC Power transformer part 2 : Temperature Rise - IEC Power transformer part 3 : Insulation levels, dielectric tests and external clearances in air - IEC Power transformer part 4 : Guide to the lightning impulse and switching impulse testing - Power transformers and reactors - IEC Power transformer part 4 : Ability to withstand short circuit - IEC Power transformer- part 10 determination of sound levels - IEC Terminal and tapping markings for power transformers - IEC Loading guide for oil-immersed power transformers 1.2 Electromagnetic compatibility The intensity of low frequency magnetic field emitted by the windings is of a limited value and, however, it is equal or lower than those of the field emitted by the connections and the low voltage bars. Its value quickly decreases by increasing of the distance from the transformer. 1.3 Marking CE TESAR does not affix the marking CE on its transformers as foreseen at paragraph of the Guide to the application of the Directive 89/336/EEC which excludes from the Directive application field: High voltage inductor High voltage transformer 2 GENERAL This publication aims to guide users on the properties of power and distribution transformers insulated with mineral, silicone or vegetable oil. Two types of transformers are considered: - Hermetically sealed total filled (Fig. 1) - Breathing with conservator (Fig. 2)
4 Rev.00 - Pag. 4/19 3 OUTLINE OF THE TRANSFORMER AND THE ACCESSORIES Fig. 1 Hermetically sealed total filled transformer Fig. 2 Breathing with conservator transformer
5 Rev.00 - Pag. 5/19 Standard components and accessories: a. Rating plate (Fig. 3 and Fig. 4) b. HV porcelain bushing (Fig. 4) c. LV porcelain bushing (Fig. 4) d. Off-load tap-changer (Fig. 4) e. N 2 earthing terminals (Fig. 4) f. Tow attachment (Fig. 4) g. Lifting eyes (Fig. 4) h. Truck with rollers for lengthways or sideway travel (Fig. 4) i. Thermometer pocket (Fig. 4) j. Drain valve(fig. 4) k. Arcing horns on HV porcelain bushing, for transformer without HV cable box (Fig. 4) l. Air dehydrating breathers, for breathing transformer (Fig. 4) m. Oil level indicator, for breathing transformer (Fig. 4) Optional components and accessories: I. Plug-in HV terminals (Fig. 5) II. Thermometer, to install on the thermometer pocket (Fig. 5) III. RIS or equivalent for hermetically sealed transformer (Fig. 5) IV. Buchholz Relay for breathing transformer (Fig. 5) V. Safety valve (Fig. 5) VI. PT100 thermo-resistance (to install in the thermometer pocket) (Fig. 5) VII. HV and/or LV cable boxes (Fig. 5) Fig. 3 Rating plate
6 Rev.00 - Pag. 6/19 k i b g f c d a j e h m l Fig. 4 Standard components and accessories
7 Rev.00 - Pag. 7/19 I Plug-in for HV terminals II Thermometer III RIS or equivalent (for hermetically sealed transformer) IV - Buchholz Relay V - Safety valve VI - PT100 thermo-resistance (for breathing transformer) VII - HV and/or LV cable boxes Fig. 5 Optional components and accessories
8 Rev.00 - Pag. 8/19 4 RECEPTION, HANDLING, STORAGE 4.1 Reception The transformer is generally supplied totally assembled and ready to be connected to the medium and low voltage line. According to the specification, the transformer is shipped with a polythene protection, or packed into wooden cage, for protection against dust and little shocks, or finally packed into a wooden case for over-sea shipments. On receipt of the transformer, both at the client's plants or at site, it is necessary to carry out the following checks: Check there are no signs of damage on the packing or on the transformer occurred during the transport. The characteristics of the transformer detailed on the rating plate must correspond to those of the shipping documents and with those of the test report, which is attached to the transformer. Check each transformer is complete with the accessories foreseen in the contract (wheels, bushing, etc.). IMPORTANT: In case any anomalies are found, please contact immediately the manufacturer. If within 5 days there will be no notification of anomalies or defects, it can be considered that the transformer has been delivered in perfect conditions. The manufacturer, therefore, cannot be considered responsible neither for what could happen to the transformer during service nor for the eventual consequences.
9 Rev.00 - Pag. 9/ Handling During the transport or the handling, it is recommended to use only the special lifting eyes and tow attachments (see g and f letter in the Fig. 4). IMPORTANT: The transformer cannot be moved pushing the cooling fins or radiators or tank. Ropes must be arranged so as not to interfere with the radiators or cooling fins. Lifting can be made using the appropriate hooks remembering to use ropes long enough so that H is never less than L (Fig. 6). Always use all the existing hooks and not only one of them. Fig. 6 Lifting transformer
10 Rev.00 - Pag. 10/19 Example of handling Fig. 7 Handling by means of bridge crane and forklift truck Fig. 8 Manual handling Fig. 9 Wrong handling
11 Rev.00 - Pag. 11/ Storage Transformer for indoor installation The transformer must be stored in a sheltered, clean and dry ambient maintaining the packing up to the installation Transformer for outdoor installation The transformer may be stored outdoor until the installation time. IMPORTANT: The storage temperature must not be lower than -25 C. 5 INSTALLATION 5.1 Standard installation conditions The maximum height of installation must not exceed 1000 m above sea level. When the transformer is in service, the ambient temperature of the room must be within the following limits: Minimum temperature: -25 C Yearly average temperature: +20 C Monthly average temperature: +30 C Maximum temperature: + 40 C In case the height of the place of installation and/or the ambient temperature values are higher than the ones specified above, it is necessary to specify it at the ordering stage since a particular dimensioning of the transformer depends upon these values. 5.2 Ventilation The electric current passing through the windings, and the effect of the core magnetising current produce electrical losses resulting in localised heating of the windings and core. The transformer is designed in such a way that natural cooling maintains the transformer temperature under the maximum values foreseen by the standards. In order to avoid temperature accumulation in the room where the transformer is installed, it is necessary to provide suitable ventilation. Each TESAR transformer is equipped with a thermometer pocket where a thermometer with contacts may be installed (optional accessory). The suggested values for setting the contacts are following (oil temperature): Description Alarm C Trip C Oil 90 C 100 C
12 Rev.00 - Pag. 12/19 Dimensioning of air louvers Natural cooling In the room where the transformer is installed, it is necessary to install air louvers sufficient to dissipate the heat generated by transformer during service, in order to guarantee the standard service conditions and to prevent exceed the over temperature limits of the transformer. Therefore the room must be provided with a louver on the lower part S, in order to guarantee an appropriate fresh air flow; and a louver S on the upper part of the opposite wall, in order to extract the hot air (see Fig. 10). To calculate the surface of the louvers for air incoming and outgoing, for a nominal annual ambient temperature of 20 C, the following formula may be used: S P S' S H where: P = Sum of the transformer no-load losses and the load losses at 120 C [kw] (if the losses are at 75 C, they must be multiply for 1.15) S = Surface of the incoming louver [m 2 ] S = Surface of the outgoing louver [m 2 ] H = Height between the two louvers [m] Fig. 10 Natural cooling In order not to obstruct cooling is necessary that the transformer is installed at a distance not less than 30 cm from the walls and not less than 60 cm from other transformers. Forced cooling Forced cooling is necessary in the following cases: Frequent overloading Low-dimensioned room Room scarcely ventilated Medium daily temperature higher than 30 C. The forced cooling can be realized by means of installation of air extractor located in the upper part of the room controlled by a suitable thermostat or directly by a transformer thermal protection relay, with a suggested flow of approx. 3,5 4 m 3 /min for each kw of total losses at 120 C (if the losses are at 75 C, they must be multiplied by 1.15). ATTENTION: an insufficient air circulation, besides reducing the nominal life of the transformer, causes over heating which, in the worst cases, can determine the intervention of the thermal protection relay.
13 Rev.00 - Pag. 13/ Insulating distances The transformer supplied for service without HV/LV cable-box (IP00) must be installed in the room respecting the insulating distances specified in the national standard (in Italy, CEI 11-1). The transformer, also with plug-in bushing, must be protected against direct contacts. 5.4 Earthing connections Tesar is not responsible for the transformer installation. The installation must be carried out according to the standards in force, to the applicable laws and to the present instructions. The following points must be taken into consideration when the installation is carried out: connect the earthing conductors to the relative earth points on the metallic parts of the transformer and cable boxes. connect the low voltage neutral to earth when required or when required by the protection system to earth. 5.5 LV and HV connections Execution without cable boxes (IP00) The cables and the bus bars which are connected to the transformer must be duly fixed to avoid any mechanical stress on the LV and HV transformer terminals. Both upper and bottom cable connections can be performed, being sure, however, to respect the configuration showed in the drawings. In case the connections arrive from the bottom please ensure that there is sufficient depth for the bending of the cables. Execution with cable boxes The cables and/or the bus bars which are connected to the transformer must enter in the cable boxes only through suitable flanges specified at the ordering stage. In any case the cables and/or the bus bars must be duly fixed outside the cable boxes to avoid any mechanical stress on the LV and HV terminals of the transformer and also on the cable boxes. After the installation please check the correct degree of protection is maintained near the passageway of the cables and/or the bus bars. HV cable box: cables coming only from the bottom LV cable box: cables coming from the bottom or from the top Fig. 11 Cables coming from the bottom (left) and from the top (right)
14 Rev.00 - Pag. 14/ Regulation of transformation ratio The variation of the primary voltage is obtained by changing the position of the voltage off-load tapchanger located on the cover of the tank. Ensure always that the position of the tap-changer is properly inserted and not in an intermediate position. In case the primary voltage of the system does not correspond exactly to the voltage of the central tap, it is necessary to modify the position of the tap duly positioning it on one of the other taps in order that the secondary obtained is the no-load voltage shown on the rating plate. Note: At the time of shipping, the position of the voltage off-load tap-changer are located on the central tap. In case of transformers with double ratio, please be sure that the position corresponding to the voltage of the system feeding the transformer is properly connected. Note: At the time of shipping, the position of the voltage off-load tap-changer are connected on the position of the higher primary voltage. Important A) In case of transformers with double ratio, please be sure the tap corresponding to voltage of the system feeding the transformer it-self, is duly connected. B) In case the position of the tap-changer has to be changed after the transformer has been put into service the first time, it is recommended to put the transformer out of service and to connect to ground the LV and HV circuits before approaching the transformer. 5.7 Parallel connection of transformers If the transformer must be connected in parallel with other transformers, please verify the total compatibility of the voltage ratio and of the conditions stated by the IEC standards, and particularly: Identical voltage ratio Identical frequency of functioning Identical vector group Identical short circuit voltage (Tolerance ± 10%) The rated power (kva) of the biggest transformer should not be larger than twice the smallest transformer The LV connections must be the same length from the LV terminals (of two different units) to the switch junction.
15 Rev.00 - Pag. 15/19 6 TRANSFORMER PROTECTIONS 6.1 Over temperature protection The protection can be realized with: - thermometer (optional accessories) - RIS or equivalent equipment (optional accessories for hermetically sealed transformer) The thermometer is generally installed in the thermometric pocket on the cover of the tank. The thermometer may be equipped with two settable contacts, one for alarm, the other for trip. The suggested values are written at paragraph 5.2. The integrated safety device for hermetically sealed transformer (RIS or equivalent) provides: - two settable contacts for temperature, one for alarm and the other for trip. The suggested values are written at paragraph one settable trip contact for pressure (The suggested value is 0.3 bar) - one trip contact for oil level 6.2 Overloading and short circuit protection According to the parameters of the standards shown at point 1.1, the transformer is designed and manufactured in such a way to withstand limited abnormal situation of over-voltages, overloading and short circuit. Therefore, the transformer must be protected against thermal and dynamic effects caused by continuous overloading and secondary short circuits by means of an automatic switch or suitable fuses, able to disconnect the transformer in case of current flow higher than the one fixed by the protection. The protections setting and/or the choice of fuses HV and LV side, must be carried out taking into consideration the primary and secondary rated currents stated in the transformer rating plate, taking also into consideration that when we feed the transformer, a very high magnetizing current is established on the primary, by means of variable starting from a minimum of 10 times the rated current (in the worst conditions of insertion depending from the instant when the feeding circuit is closed, from the electric characteristics of the feeding network, from the reactance and resistance values of the circuit network-transformer, the insertion current can reach also 20 times the rated current), even if the automatic switch located on the secondary is open and therefore without loading. Therefore, it is necessary to duly set the relay of maximum current HV side, in current and time value, by introducing a little delay (approx. some tens of ms), in such a way that the protection relay will not operate. Furthermore, we suggest limiting the number of connections and disconnection of the transformer on the network. 6.3 Protection against over voltages In order to protect the transformers against over-voltages at industrial frequencies or the ones due to atmospheric origin, it is recommended that voltage surge arrester with variable resistance are used. The characteristics of the surge arresters depend on the transformer insulation level and from the characteristics of the distribution system line. It is recommended to install the surge arresters when the transformer is connected, directly or through a short cable, to the main networks.
16 Rev.00 - Pag. 16/19 7 COMMISSIONING 7.1 Mechanical checks before the commissioning Check the earth connections Check of the insulating distance of the parts under voltage towards ground as shown at paragraph 5.3 Check the tightening of HV and LV terminals applying the following values of the tightening torque. Bushing On the central conductor LV/HV in copper or brass Bolts M8 M12 M20 M30x2 M42x3 M48x3 M55x3 M75x3 Torque N*m On the fixing stud screw HV insulators Bolts M10 M12 M16 Torque N*m On the pinch bolts connecting flags Bolts M10 M12 M16 Torque N*m Mechanical parts Bolts M8 M10 M12 M14 M16 M18 M20 M22 Torque N*m With torque wrench set in kgm, divide the values by 10
17 Rev.00 - Pag. 17/ Electrical checks before the commissioning Verify that the position of the tap-changer is inserted correctly. In case of double primary voltages, please check the feed to the transformer correspond to the correct position. Check the correct functioning of the switches located as protection of the transformer on HV and LV side. Check the correct setting and functioning of the overloading and short-circuit protection relay. Check the correct setting and functioning of the over-temperature protection relay and of the thermometer. Check the functioning of the fans. Check the general conditions of the transformer and proceed with the measurement of the insulating resistance by means of a Megger at 2500 V. This measurement must be carried out with HV and LV terminals disconnected from the equipment, it means before connecting the cables and/or the bus bars. The values of the measured resistances must be approx. the following: HV terminals / LV terminals grounded 20 MΩ LV terminals / HV terminals grounded 10 MΩ HV terminals - LV terminals / ground terminal 10 MΩ In case the measured values are lower, please contact our after sale service. ATTENTION: In case a transformer is put into service after a long storage period, or after a long de-energised period, it will be necessary: 1) clean the HV/LV bushings from eventual dust and condensation by means of dry compressed air jets and dry cloth. 2) if the transformer has been held in stock far more than six months in normal climates or far more than a month in damp climates, check the dielectric strength of the insulating oil. Using the procedure established by the IEC standard to check the dielectric strength of the insulating oil, if the test is negative proceed to dry the dielectric oil of the transformer, otherwise contact Tesar. It is recommended, finally, to carry out always a visual check of the transformer in order to verify any unlikely presence on the surface the cooling ducts 7.3 Insulating fluid level Check that the reading on the level indicator approximately correspond to ambient temperature (transformer with conservator or RIS for hermetically sealed). If the insulating fluid needs to be topped up, only fluid with the same characteristic and not containing PCBs must be used and with the required dielectric strength. The oil transformer must be topped up according to the manufacters instruction.
18 Rev.00 - Pag. 18/ Arcing horns If the transformer is equipped with arcing horns, check that the position of the spark gap rods mounted on HV porcelain bushings corresponds to the insulation class, as shown in the following chart. Insulation Class [kv] A [mm] B [mm] Air dryer Fig. 12 Arcing horns If the transformer is equipped with air dryer (transformer with conservator), check that the salts of silicagel are orange. If they are neutral colour, they have already picked up moisture and do not fulfil their function as dehydrating air. It is necessary to remove the salts and regenerate the dryer by placing them in an oven at 150 C until they are come back to orange colour. 7.6 Buchholz Relay If the transformer is equipped with Buchholz relay (transformer with conservator) to avoid unnecessary activation, proceed carefully with the leaking operation of the relay, acting on the taps (see instruction relay). If during commissioning or in the first hours of the energization the Buchholz relay should signal the formation of gas, in small quantities, first to believe that there is a fault in the transformer and repeat the leaking operation. 7.7 Thermometer If the transformer is equipped with the thermometer check the threshold of the alarm and trip are set at the operating conditions. The setting temperature are provided to the manufacturers in according to transformer type and the insulation class. 7.8 Integrated safety device If the transformer is equipped with the integrated safety device (RIS or equivalent) check the setting of the alarm and trip of the thermometer and the values of pressure shown are matched to operating conditions. For more additional information, consult the operating manual supplied with the integrated security device, you must be careful not to change the orientation fixing RIS or equivalent (the exact position should be required before delivery).
19 Rev.00 - Pag. 19/ Operations for commissioning Closing of HV switch When the switch is closed the transformer gives out a sharp noise, which decreases in few ms until it stabilises. Check of secondary voltages Before closing the low voltage switch or make additional checks for parallel operation with other transformers, it is necessary: Check by means of a voltmeter the proper value between each two phases and of the three wye-connected voltage. Check the proper phases displacement and the correct vector group. In case the values correspond to those stated in the rating plate, it is possible to proceed and complete the commissioning or to carry out the checks for the parallel service. Run in parallel service with other transformer In case the transformer has to run in parallel with another, it is also necessary: Check the compatibility of the rating plates of both transformers Verify the concordance of the phases by measuring the voltage between the phase "one" of the transformer already in service and the phase "one" of the transformer to be connected in parallel by means of a voltmeter. The value of this result must be zero. Continue in the same way for phase 2 and phase 3 Closing of LV switch Complete the commissioning of the transformer closing the LV switch. IMPORTANT We remind you that qualified technical personnel must carry out the operation, commissioning and energization. Furthermore, during the voltage measurements and the phase displacement checks on the upper terminals of the LV switches, you are recommended to use suitable instruments and suitable insulating gauntlets. For more accurate and complete checks, please contact our Assistance Service Phone (+39) Fax (+39)
E N G L I S H Dry type transformers with air insulated MV windings TTR TTO OTN, OTR, OTF reactors TTH Technology Magnetic Core The core is made of grain oriented magnetic sheets characterized by high permeability
ARCO Electric Products Installation and Maintenance Manual Low Voltage Automatic Power Factor Correction Capacitor Systems 2013 READ CAREFULLY These instructions are intended to cover good practices in
to 1250 kva Page 1/10 Technical Specification for Oil insulated Transformers U m < 24 kv up to 1250 kva This technical specification is valid for the business unit E.ON Sweden of the market unit E.ON Nordic.
July, 2012 This goal for this month s paper is to provide a basic understanding of tests performed on each liquid filled transformer. The following standards detail the general construction requirements
High efficiency air/water reversible heat pumps type Geyser Mini Technical information manual 2 GEYSER MINI Reversible heat pump Index Technical features 120 Basic version general technical data 124 Basic
THE ECONOMICS OF A TRANSFORMER DESIGNED WITH A LOW CURRENT, RESISTANCE BRIDGING LTC AND SERIES TRANSFORMER VERSUS A HIGH CURRENT, REACTANCE BRIDGING LTC AND NO SERIES TRANSFORMER By Steve Moore, SPX Transformer
BIS PRESENTATION ON STANDARDS- DISTRIBUTION TRANSFORMERS PRAKASH BACHANI Scientist E (Electrotechnical) BUREAU OF INDIAN STANDARDS STANDARDIZATION IS 1180 (PART 1) OUTDOOR TYPE OIL IMMERSED DISTRIBUTION
www.kosgeb.gov.tr Tasarım ve Baskı: AJANSBRAND A 15.09.2014 THE ENERGY TRANSFERRED TO NATURE www.atstrafo.com ABOUT Having been founded in Adıyaman Organized Industrial District in 2003, ATS Trafo carries
CE - BF - C - en - REV.00 2012.4 APPLICATION CE-BF Switchbords up to 40.5 kv are designed for use in public and industrial distribution system up to 40,5KV for the operation and protection of lines, transformers,
M T E C o r p o r a t i o n DRIVE ISOLATION TRANSFORMER TYPE: T USER MANUAL PART NO. INSTR - 017 REL. 031112 Instructions for the Safe Handling, Installation, Operation and Maintenance of Ventilated Dry-Type
TRANSFORMATORY OLEJOWE OIL IMMERSED TRANSFORMERS POL ENG Informacje Ogólne General features Our oil immersed transformers are among TRAFO ELETTRO s first products and they are available with conservator,
PPS-PPQ-BT-PIAS RESIN INSULATORS FOR OIL INSULATED ELECTRICAL MACHINES BUSHING WITH PLUG CONNECTION WITH OUTER CONE PPS CHARACTERISTICS The PPS bushing can be used as a fixed section for the entry of medium
Power Voltage Transformers for Air Insulated Switchgear Introduction Trench Power Voltage Transformers (Power VTs) combine the attributes of an inductive voltage transformer with the application of a small
DESIGN OF TRANSFORMER Classification of transformer Depending upon the type of construction used: I. Core type II. Shell type 2 Comparison of core type and shell type transformers:- I. Construction:- Core
Type: DILM115(RAC240) Article No.: 239548 Sales text Contactor,55kW/400V,AC operated Ordering information Connection technique Description Description Rated operational current Screw terminals 3 pole AC
g Digital Energy ITI Instrument Transformer Basic Technical Information and Application Table of Contents DEFINITIONS AND FUNCTIONS CONSTRUCTION FEATURES MAGNETIC CIRCUITS RATING AND RATIO CURRENT TRANSFORMER
Fundamentals of Modern Electrical Substations Part 1: Mission of Electrical Substations and their Main Components Course No: E02-010 Credit: 2 PDH Boris Shvartsberg, Ph.D., P.E., P.M.P. Continuing Education
SPECIFICATION FOR LOW VOLTAGE SWITCHBOARD SEN I N D E X Description 10 STANDARD TECHNICAL REQUIREMENTS 11 Standards 12 General Operating Conditions 13 General Description Of Switchboard 131 Structure 132
Scope This guideline defines the standard tests that all electrical systems and equipment must pass prior to final acceptance by the University. These tests are in addition to acceptance tests specified
MLK Low Voltage Switchboard System New Switchboard MLK Wide Range of Applications The MLK switchboard is designed mainly for electrical distribution in real estate and industrial buildings, and its nominal
011: 2008 CEB SPECIFICATION MEDIUM VOLTAGE SURGE ARRESTERS CEYLON ELECTRICITY BOARD SRI LANKA Specification for MEDIUM VOLTAGE SURGE ARRESTERS CEB Specification - 011: 2008 CEYLON ELECTRICITY BOARD No.
AC Electrical System Tests Hot Skin Test Prepare Documentation? Make sure shore line is plugged into 120VAC source? Set VOM to AC voltage scale? Place one probe on a bare metal surface of the RV (i.e.,
Current Transformers ZIEGLER CURRENT TRANSFORMER SERIES Ziegler Instruments, leader in measuring instruments unveils its world class plastic cased Square and Round Current Transformers. Ziegler Current
14 SWITCHGEAR Secondary Unit Substations Overview Siemens offers a wide variety of unit substation designs to meet customer requirements. A unit substation consists of one or more transformers mechanically
Type XPI-III Surge Arresters Maximum System Voltage 2 to 48 kv XPI-III Metal Oxide Surge Arrester XPI-III Metal Oxide Surge Arresters are for protection of switchgear, transformers, and other equipment
32/1091 32 Testing a metalenclosed bus system Contents 32.1 Philosophy of quality systems 32/1093 32.1.1 Quality assurance 32/1093 32.1.2 Purpose of testing 32/1093 32.2 Recommended tests 32/1093 32.2.1
Yadav Measurements Pvt. Ltd. Instrument Transformers By: Kiran Kelapure A specifically designed programme for Da Afghanistan Breshna Sherkat (DABS) Afghanistan 1 Electricity Metering technologies and systems
White paper 3D Modeling in transformer design Power transformers 1ZUL000101-TEE Status of document Final Issued by department: Power transformers Project name: NA Date: 10.3.2013 Doc. Type: White paper
Product brochure ABBACUS Metal Enclosed Capacitor Banks The ABB comprehensive solution for low voltage automatic power factor correction ABB LV capacitor banks The most comprehensive solution for automatic
PRODUCT LEAFLET TRANSFORMER TSA TYPE Transformers for 950 V network (from 3 to 16 kva) 1 60 20752-01/06/2012 Transformers for supplying equipments away Type TSA transformers are used to power the receivers
Trouble 1: The air conditioner can t be turned on at all. Check to see if there is power supply to the air conditioner. If there's no power supply to the unit, insure the fuse or circuit breaker is ok.
Basis of Design This section applies to the design and installation of transformers. Design Criteria 13.8kV equipment shall be 15kV class. 4.16KV and 2.4kV equipment shall be 5kV class. 15KV class transformers
1. PURPOSE AND SCOPE The purpose of this Standard Work Practice (SWP) is to standardise and prescribe the method for testing Capacitor Banks including capacitors, tuning reactors and inrush limiting reactors.
GUIDE FOR TESTING POWER TRANSFORMERS Type test & Special test 11/11/02 Pagina 1 di 7 GUIDE FOR TESTING POWER TRANSFORMERS... 1 Type test & Special test... 1 Introduction... 3 1 Type test... 4 1.1 Lightning
SHORT-CIRCUIT CALCULATION INTRODUCTION Designing an electrical system is easy and simple, if only the normal operation of the network is taken into consideration. However, abnormal conditions which are
SA 44-721-1 Sales Aid April, 2000 Power Transformer Replacement Parts ABB Power Transmission CAPABILITIES TAP CHANGERS CONTROLS BUSHINGS COOLING UNITS GAUGES SUDDEN PRESSURE RELAYS MECHANICAL RELIEF DEVICES
SURGE PROTECTIVE DEVICES 1. INTRODUCTION In order to ensure safety of people, protection of equipment and, to a certain extent, continuity of supply, insulation co-ordination aims at reducing the likelihood
Course Outline 1. Introduction to WECC 2. Fundamentals of Electricity 3. Power System Overview 4. Principles of Generation 5. Substation Overview 6. Transformers 7. Power Transmission 8. System Protection
Type: DILM50(230V50HZ,240V60HZ) Article No.: 277830 Ordering information Rated operational current AC 3 400 V I e A 50 Max. rating for three phase motors, 50 60 Hz AC 3 230 V Max. rating for three phase
Technical Data Distribution Transformers and Oil-immersed and three-phase distribution transformers Standard: DIN 00 Rated : 0 00 kva Rated frequency: 0 Hz HV rating: up to kv Taps on ±. % or ±. % HV side:
Oil and Coolant Circulating Heating System Model - OCSM Installation & Operation Manual 216280-000 REV 2 Identifying Your System The HOTSTART heating system is designed to heat fluids for use in marine
DRY TYPE Trafotek transformers are made to meet customer requirements in demanding applications. We are specially focused on manufacturing transformers for different types of frequency converters and special
DRY TYPE Trafotek transformers are made to meet customer requirements in demanding applications. We are specially focused on manufacturing transformers for different types of frequency converters and special
Powertrain Systems Chassis Systems Safety Security Body Driver Information Convenience Description Features Limiting continuous current 70 A Dimensional characteristics and the functional allocation of
Thermistor motor protection CM-E Range Thermistor motor protection Thermistor motor protection relays Benefits and advantages Selection table Operating principle and fields of application for thermistor
FAMILY OF EARTH SHORT-CIRCUIT TRANSFORMERS TYPE IO Operating Manual Gliwice, May 2004 Solutions contained within this design may be copied and distributed only as a whole. Copying and/or use part of this
Type: DILM9 10(24VDC) Article No.: 276705 Ordering information Rated operational current AC 3 400 V I e A 9 Max. rating for three phase motors, 50 60 Hz AC 3 230 V Max. rating for three phase motors, 50
INSTALLATION MANUAL EKRTR EKRTETS 1 2 1 2 3 60 87 170 161 ±1.5 m >0.2 m 3 5 4 34 125 4 5 28 50 EKRTR EKRTETS Contents Read this manual attentively before starting up the unit. Do not throw it away. Keep
Type: DILM32 10(24V50HZ) Article No.: 277247 Ordering information Rated operational current AC 3 400 V I e A 32 Max. rating for three phase motors, 50 60 Hz AC 3 230 V Max. rating for three phase motors,
ebr Buchholz Relay Buchholz Relay type ebr COMEM s ebr is equipped with a digital interface for easy connection to the smart grid and it can be integrated into a single system via a central control unit.
POWER QUALITY SOLUTIONS Automatically Switched Low Voltage Capacitor and Harmonic Filterbank Assemblies Installation, Operating and Maintenance Manual 250 Hogan Lane Conway, AR 72034 Phone 501.327.6456
Magnetic and Hydraulic-Magnetic Circuit Breaker 840-G2... Description Single, two and three pole magnetic circuit breakers with trip-free mechanism and push/pull on/off manual actuation. A choice of fast
V.L. LINE AND SUBSTATION OPERATION AND MAINTENANCE 1.0 GENERAL REQUIREMENTS 1.1 Preventive maintenance shall be performed at a level that assures that the unscheduled outage performance of Customer owned
Presentation of the France Transfo factories France Transfo's internationally recognised and highly esteemed expertise is today exported to more than 80 countries throughout the world. Over the past 15
NATUS NES / NES-H Draw-out Type Medium Voltage Switchgear Systems Safe energy distribution that meets the highest industrial requirements NATUS switchgear systems your advantages minimal use of insulant
GE Energy Industrial Solutions Ground Fault Protection Digital Specification Program Latin America Ground Fault. I. Introduction In the electrical systems always exists the possibility of having shutdowns
INSTALLATION INSTRUCTIONS FOR MINI MAKE-UP AIR MODEL FER May 2012 VERSION 1.3 Please read instructions carefully before installation. This unit is a complete fresh air make-up package with an integrated
1 2 INTRODUCTION / TABLE OF CONTENTS Step One Offered in small and large sizes, the compact junction box is ideal for sensor wiring and conduit termination. The junction box is universally compatible with
LOAD BANK PART NUMBER 2004297/2004298 OPERATIONS AND MAINTENANCE MANUAL Prepared by: 5455 N River RD W Geneva, OH 44041 Phone: 1-800-969-8527 TechSupport@get-psi.com HDT 1 TM-2004297/2004298 TABLE OF CONTENTS
Data sheet Three-phase monitoring relay CM-PE The three-phase monitoring relay CM-PE monitors the phase parameter phase failure as well as over- and undervoltage in three-phase mains. 2CDC 251 006 S0012
ALTERNATIVE METHODS FOR INTERNAL ARC TESTS ON 12 KV AND 24 KV METAL-ENCLOSED SWITCHGEARS WITH COMPACT RMU George CURCANU, Constantin ILINCA, Ilie SBORA ICMET Craiova, Romania, Calea Bucuresti 144, phone:
Art.S001-S002 SOLAR MODULE WITH DELIVERY AND RETURN CONNECTIONS Technical Information sheet 0001/07/Rev01 ENG FUNCTION Series S001 and S002 circulation units are applied to the primary circuit of solar
CONSIDERATIONS WHEN SPECIFYING Application A TRANSFORMER Configuration Internal Construction Dielectric Fluid Accessories APPLICATION Distribution Running lights, HVAC, Office Motor Control Center Dedicated
Issued: July 1998 Status: Updated Version: D/25.04.2006 Data subject to change without notice Features Comprehensive voltage regulation for power transformers with on-load tapchangers in distribution substations
Electrical Distribution Transformers Dielectric Liquid immersed Transformers ermetically sealed completely filled type Up to 36 kv Contents Electrical Distribution Transformers Specialisation 3 The Transformer
Data TECHNICL DT Technical data UNIBLOCK UBSF 80 6 Output data Type UBSF 80 UBSF 0 UBSF 00 UBSF 6 Output power 80 kv 0 kv 00 kv 6 kv Output voltage 80/77 V 0/ V 0/ V 0/ V Output current 7 8 66 80 Power
Type: EASY719 DC RC Article.: 274119 Ordering information Relay outputs Quantity 6 Power supply V DC 24 V DC Description 12 digital inputs (4 inputs available as analog inputs) 6 relay outputs LCD display
Application guide for power factor testing of power & distribution transformers Introduction The transformer is probably one of the most useful electrical devices ever invented. It can raise or lower the
eoli Oil level indicator Oil level indicator eoli Unexpected or accidental oil leakages may occur randomly along transformer s lifetime. Clear indication of oil level inside transformer tank and on load