# Explanation of Blower Door Terms and Results. Information taken from TECTITE BUILDING AIRTIGHTNESS TEST by The Energy Conservatory

Save this PDF as:

Size: px
Start display at page:

Download "Explanation of Blower Door Terms and Results. Information taken from TECTITE BUILDING AIRTIGHTNESS TEST by The Energy Conservatory"

## Transcription

1 Explanation of Blower Door Terms and Results Information taken from TECTITE BUILDING AIRTIGHTNESS TEST by The Energy Conservatory AIRFLOW AT 50 PASCALS CFM50: This is the airflow (in Cubic Feet per Minute) needed to create a change in building pressure of 50 Pascals. CFM50 is the most commonly used measure of building airtightness. ACH at 50 Pa: The Air Changes per Hour (ACH at 50 Pa) is another commonly used measure of building airtightness. ACH at 50 Pa is the number of complete air changes that will occur in one hour with a 50 Pascal pressure being applied uniformly across the building envelope. ACH at 50 Pa is a useful method of adjusting (or normalizing) the leakage rate by the size (volume) of the building. If you did not enter the building volume on the Building Information screen, ACH50 will not be calculated. ACH at 50 Pa = (CFM50 x 60) / building volume in cubic feet CFM50/square foot of floor area: This is the CFM50 reading for the building divided by the floor area of the building. CFM50/square foot adjusts (or normalizes) the leakage rate by the size (floor area) of the building. If you did not enter the floor area on the Building Information screen, this variable will not be calculated. CFM50/square foot = CFM50 / floor area in square feet CFM50/square foot of surface area (MLR): Also known as the Minneapolis Leakage Ratio (MLR), this is the measured CFM50 divided by the above grade surface area of the building. MLR is a useful method of adjusting (or normalizing) the leakage rate by the amount of envelope surface through which air leakage can occur. The MLR has been particularly useful for weatherization crews working on wood frame buildings. Experience to date has shown that for buildings with a MLR above 1.0, very large cost-effective reductions in infiltration can often be achieved using blower door guided infiltration and insulation techniques. In buildings with a calculated MLR in the 0.5 to 1.0 range, it is often more difficult to achieve economical improvements in airtightness. If you did not enter an Above Grade Surface Area value into the Building Information screen, MLR will not be calculated. MLR = CFM50 / above grade surface area in square feet LEAKAGE AREAS Page 1 of 6

2 Once the leakage rate for the building has been measured, it is useful to estimate the cumulative size (in square inches) of all leaks or holes in the building's air barrier. The estimated leakage areas not only provide us with a way to visualize the physical size of the measured holes in the building, but they are also used in infiltration models to estimate the building's natural air change rate (i.e. the air change rate under natural weather conditions). The results screen includes two leakage area calculations, based on differing assumptions about the physical shape of the hole, which are compatible with the two most commonly used infiltration models. Equivalent Leakage Area (EqLA):EqLA is defined by Canadian researchers at the Canadian National Research Council as the area of a sharp edged orifice (a sharp round hole cut in a thin plate) that would leak the same amount of air as the building does at a pressure of 10 Pascals. The EqLA is used in the AIM infiltration model (which is used in the HOT2000 simulation program). Effective Leakage Area (ELA): ELA was developed by Lawrence Berkeley Laboratory (LBL) and is used in their infiltration model. The Effective Leakage Area is defined as the area of a special nozzle-shaped hole (similar to the inlet of your Blower Door fan) that would leak the same amount of air as the building does at a pressure of 4 Pascals. Notes on Leakage Areas: When using leakage area calculations to demonstrate physical changes in building airtightness, we recommend using the EqLA measurement. Typically, EqLA more closely approximates physical changes in building airtightness. For example, if you performed a Blower Door test, and then opened a window to create a 50 square inch hole and repeated the test, the estimated EqLA for the building will have increased by approximately 50 square inches from the initial test results. BUILDING LEAKAGE CURVE Coefficient (C) and Exponent (n):once an automated airtightness test sequence (or manual entry of data into the table) has been completed, a best-fit line (called the Building Leakage Curve) is drawn through the collected Blower Door data. The Building Leakage Curve can be used to estimate the leakage rate of the building at any pressure. If you conduct a single point test (i.e. input a single target pressure into the custom pressure list), the program assumes an exponent (n) of 0.65 in its calculation procedures. The Building Leakage Curve is defined by the variables Coefficient (C) and Exponent (n) in the following equation: Q = C x P^n where: Q is airflow into the building (in CFM). Page 2 of 6

3 C is the Coefficient. P is the pressure difference between inside and outside of the building. n is the Exponent. Example: Use the Building Leakage Curve to estimate the exhaust fan airflow in a building needed to create a 5 Pa negative pressure. From our Blower Door test we determined the following Building Leakage Curve variables. C = n = From the equation above: Airflow (at 5 Pa) = x 5^.702 = 341 CFM. In other words, we estimate from the Building Leakage Curve that it would take exhaust fans with a combined capacity of 340 CFM to cause a 5 Pa pressure change in this building. Correlation Coefficient: The correlation coefficient is a measure of how well the collected Blower Door data fit onto the best-fit Building Leakage Curve. The closer all data points are to being exactly on the Building Leakage Curve, the larger the calculated correlation coefficient (note: the largest possible value for the correlation coefficient is 1.0). Under most operating conditions, the correlation coefficient will be at least 0.99 or higher. Testing in very windy weather can sometimes cause the correlation coefficient to be less than In this case, you may want to repeat the test, or increase the number of Samples Per Station. Achieving a correlation coefficient of 0.99 or higher is particularly important in the estimation of Leakage Areas, or when using the Building Leakage Curve to estimate leakage rates at low building pressures. ESTIMATED ANNUAL INFILTRATION Estimating the natural infiltration rate of a building is an important step in evaluating indoor air quality and the possible need for mechanical ventilation. Blower Doors do not directly measure the natural infiltration rates of buildings. Rather, they measure the building leakage rate at pressures significantly greater than those normally generated by natural forces (i.e. wind and stack effect). Blower Door measurements are taken at higher pressures because these measurements are highly repeatable and are less subject to large variations due to changes in wind speed and direction. In essence, a Blower Door test measures the cumulative hole size, or leakage area, in the building's air barrier (see Leakage Areas above). From this measurement of leakage area, estimates of natural infiltration rates can be made using mathematical infiltration models. TECTITE uses the calculation procedure contained in ASHRAE Standard to estimate the average annual natural infiltration rate of the building. Page 3 of 6

5 ventilation to maintain acceptable indoor air quality. To help evaluate the need for mechanical ventilation in buildings, national ventilation guidelines have been established by ASHRAE. The recommended whole building mechanical ventilation rate presented in this version of TECTITE is based on ASHRAE Standard , and is only appropriate for low-rise residential structures. Recommended Whole Building Mechanical Ventilation Rate: This value is the recommended whole building ventilation rate to be supplied on a continuous basis using a mechanical ventilation system. The recommended mechanical ventilation rate is based on 7.5 CFM per person (or number of bedrooms plus one, whichever is greater), plus 1 CFM per 100 square feet of floor area. This guideline assumes that in addition to the mechanical ventilation, natural infiltration is providing 2 CFM per 100 square feet of floor area. For buildings where the estimated annual natural infiltration rate (based on the Blower Door test) is greater than 2 CFM per 100 square feet of floor area, the recommended mechanical ventilation rate is reduced to provide ventilation credit for excess infiltration. In these cases, the recommended mechanical ventilation rate is reduced by the following amount: 0.5 x (est. annual natural infiltration rate (CFM) minus 0.02 CFM x sq. ft. of floor area) Notes on the Ventilation Guideline: ASHRAE Standard also contains requirements for local kitchen and bathroom mechanical exhaust systems. These local exhaust systems may be incorporated into a whole building ventilation strategy. Consult Standard for more information on ventilation strategies and specific requirements and exceptions contained in the Standard. Compliance with the ventilation guideline does not guarantee that a moisture or indoor air quality (IAQ) problem will not develop. Many factors contribute to indoor air quality including ventilation rates, sources and locations of pollutants, and occupant behavior. Additional testing (including combustion safety testing) is needed to fully evaluate air quality in buildings. In many cases, a combination of pollutant source control and mechanical ventilation will be required in order to ensure adequate indoor air quality. Previous versions of TECTITE used ASHRAE Standard to determine an annual ventilation guideline. The Standard guideline (which was superceded by Standard ) was based on 15 CFM per person or 0.35 Air Changes per Hour (whichever was greater). ESTIMATED COST OF AIR LEAKAGE The program estimates the annual cost associated with air leakage, both for heating and cooling. Because these cost estimates are based on estimated infiltration rates and many other assumptions, actual cooling costs may differ Page 5 of 6

6 significantly from the estimates. The equations used to calculate the annual cost for air leakage are: Annual 26 x HDD x Fuel Price x CFM50 Heating = x 0.6 Cost N x Seasonal Efficiency - HDD is the annual base 65 F heating degree-days for the building location. - The Fuel Price is the cost of fuel in dollars per Btu. - N is the Energy Climate Factor from the Climate Information Screen (adjusted for wind shielding and building height). See Appendix E of the Model 3 Blower Door Operation Manual for more information on this calculation procedure. - Seasonal Efficiency is the AFUE rating of the heating system. Annual.026 x CDD x Fuel Price x CFM50 Cooling = Cost N x SEER - CDD is the base 70 F cooling degree days for the building location. - The Fuel Price is the cost of electricity in dollars per kwh. - N is the Energy Climate Factor from the Climate Screen (adjusted for wind shielding and building height). See Appendix E of the Model 3 Blower Door Operation Manual for more information on this calculation procedure. - SEER is the SEER rating for the air conditioner. Note: The Cooling Cost procedure does not include latent loads. In humid climates, latent loads due to air leakage can be greater than the sensible loads, which are estimated by this procedure. Page 6 of 6

### Air Leakage and Blower Door Basics

Air Leakage and Blower Door Basics New River Center for Energy Research and Training A Division of Community Housing Partners Air Leakage Requires All of the Following: Air Hole Pressure Difference (Driving

### The Need for Ventilation and Moisture Control for Health, Comfort and Sustainability Nikki Kruger Industry Manager

The Need for Ventilation and Moisture Control for Health, Comfort and Sustainability Nikki Kruger Industry Manager ANTITRUST POLICY STATEMENT FOR SPRAY POLYURETHANE FOAM ALLIANCE MEETINGS It is and shall

### Return Fan and Exhaust Fan Economizers and Building Pressurization APPLICATION GUIDE OUTSIDE AIR

Return Fan and Exhaust Fan Economizers and Building Pressurization APPLICATION GUIDE Supersedes: Nothing Form 100.00-AG3 (104) OUTSIDE AIR One of the primary functions of a packaged rooftop unit (RTU)

### Measurement and simulations of air pressure in a two-storey detached house and in a five-storey apartment building

Annex 41 MOIST-ENG, Working meeting, 16-18 April 2007, Florianopolis, Brazil Measurement and simulations of air pressure in a two-storey detached house and in a five-storey apartment building Targo Kalamees

### Blower Door Testing. Introduction. The blower door system. What can blower door testing do for me? The Pennsylvania Housing Research Center

The Pennsylvania Housing Research Center Blower Door Testing Builder Brief BB0201 Bill Van der Meer Introduction Have you ever had to deal with call-backs from home owners who complain that they aren t

### Home Energy Evaluation Report

Home Energy Evaluation Report Nate Begeman, 1550 Saint Francis Dr San Jose, CA 95125 Air Infiltration Current Air Leakage 2,852 Current Air Changes Per Hour 0.91 Recommended Air Changes Per Hour 0.35 Percent

### BEFORE YOU VENTILATE

READ THIS BEFORE YOU VENTILATE Healthy and Affordable Housing: Practical Recommendations for Meeting Your Ventilation Requirements BEFORE YOU VENTILATE Residential Ventilation: Too Little, Too Much, or

### Blower Door Training

Blower Door Training Presenter: Mark Rogers!! Mark is the Quality Assurance Manager and Lead Trainer for Lightly Treading. He performs energy audits, ratings, and design consulting in new and existing

### Makeup Air For Exhaust Systems In Tight Houses. Tony Jellen Engineering Projects

Makeup Air For Exhaust Systems In Tight Houses Tony Jellen Engineering Projects PA Housing & Land Development Conference February 23, 2012 Effects of Kitchen Ventilation on Residential Dwellings Anthony

### Whole House Dehumidification for Occupant Comfort and Energy Savings

Downloaded from www.rsrews.com. Since 1968, RS Andrews has proudly served Atlanta's Heating, Air Conditioning & Plumbing Needs. Whole House Dehumidification for Occupant Comfort Energy Savings June 2009

### ENERGY STAR v3.0 Home Report

ENERGY STAR v3.0 Home Report Normalized, Modified End-Use Loads (MMBtu/yr) ENERGY STAR As Designed Heating 22.1 15.4 Cooling 7.2 3.8 Water Heating 11.8 10.7 Lights and Appliances 19.4 19.2 Total 60.5 49.1

### RosevilleProject. LoE _ 2 Glass Products. You can reduce your cooling energy usage by 25% or more. Here is the proof.

RosevilleProject Glass Products You can reduce your cooling energy usage by 25% or more. Here is the proof. Hot-Button Issues Residents of California, Arizona, and Nevada don t need a weather forecast

### Keys to Efficient Dehumidification

Keys to Efficient Dehumidification Jeff Ihnen for Engineered Systems Magazine, May 2009 p 608.785.1900 400 Main Street, Suite 200 La Crosse, WI 54601 Contents Keys to efficient dehumidification... 1 Relative

### FLORIDA SOLAR ENERGY CENTER

FLORIDA SOLAR ENERGY CENTER Creating Energy Independence Since 1975 Impact of Energy-Efficiency Parameters on Home Humidity Rob Vieira Florida Solar Energy Center A Research Institute of the University

### Mechanical and Natural Ventilation

BBSE3006: Air Conditioning and Refrigeration II http://www.hku.hk/bse/bbse3006/ Mechanical and Natural Ventilation Dr. Sam C. M. Hui Department of Mechanical Engineering The University of Hong Kong E-mail:

### about your house How to Get the Ventilation That You Need in Your House Figure 1 Infiltration and exfiltration of air in a house

about your house CE 64 How to Get the Ventilation That You Need in Your House Canadian houses are relatively airtight, and have been for years. The old farmhouses where people lived several generations

### Glossary of Heating, Ventilation and Air Conditioning Terms

Glossary of Heating, Ventilation and Air Conditioning Terms Air Change: Unlike re-circulated air, this is the total air required to completely replace the air in a room or building. Air Conditioner: Equipment

### Ventilation: Effective Strategies and Lessons Learned. Douglas McCleery, PE, CEM; MaGrann Associates

Ventilation: Effective Strategies and Lessons Learned Douglas McCleery, PE, CEM; MaGrann Associates Let s Review A house has got to breathe, right? Why? o Fresh indoor air o Outdoor air quality/allergies

### Residential HVAC Load Sizing Training October 14, 2015. David Kaiser Green Code Plan Reviewer

Residential HVAC Load Sizing Training October 14, 2015 David Kaiser Green Code Plan Reviewer DCRA - Green Building Division Regulations of green codes including: Green Building Act Green Construction Code

### Parking and the ENERGY STAR Score in the United States and Canada

and the ENERGY STAR Score in the United States and Canada OVERVIEW The ENERGY STAR score provides a fair assessment of the energy performance of a property relative to its peers, taking into account the

### ENERGY STAR Qualified Homes, Version 3 (Rev. 03) National Program Requirements

Qualifying Homes ENERGY STAR Qualified Homes, Version 3 (Rev. 03) The following homes are eligible to earn the ENERGY STAR: Single-family homes; Units in multi-family buildings that are three stories or

### Public Review Draft. ASHRAE Standard

BSR/ASHRAE Addendum s to ANSI/ASHRAE Standard 62.2-2007 Public Review Draft ASHRAE Standard Proposed Addendum s to Standard 62.2-2007, Ventilation and Acceptable Indoor Air Quality in Low- First Public

### INFORMED MECHANICAL DESIGN THROUGH TESTED AIR LEAKAGE RATES. Jeff Speert, AIA MAIBC LEED AP

INFORMED MECHANICAL DESIGN THROUGH TESTED AIR LEAKAGE RATES Jeff Speert, AIA MAIBC LEED AP Background Move towards more energy efficient structures Collaborative approach promoted by LEED, 2030 Challenge,

### An energy and economic modeling study of exhaust ventilation systems compared to balanced ventilation systems with energy recovery

7th Annual North American Passive House Conference - 2012 John Semmelhack www.think-little.com An energy and economic modeling study of exhaust ventilation systems compared to balanced ventilation systems

### Energy Analysis for Internal and External Window Film Applications for Existing Homes in Florida

Energy & Environmental Solutions Energy Analysis for Internal and External Window Film Applications for Existing Homes in Florida PREPARED FOR: INTERNATIONAL WINDOW FILM ASSOCIATION P.O. BOX 3871 MARTINSVILLE,

### New Homes EPS Modeling Frequently Asked Questions. Developed by Energy Trust of Oregon

New Homes EPS Modeling Frequently Asked Questions Developed by Energy Trust of Oregon 1 General Questions 3 REM/Rate questions 4 -Creating custom entries 4 -Modeling Heat Pumps 5 -Modeling HRV/ERV 7 -Modeling

### ECHO System for Basements

ECHO System for Basements Homeowners looking for more space are all too familiar with the cold, damp and dingy basement. Now, the Enclosure Conditioned Housing (ECHO) System TM, winner of the Ottawa-Carleton

### SYNOPSIS. Improve Indoor Air Quality and Reduce Costs With Demand Controlled Ventilation. In this issue...

VOLUME THREE NUMBER FOUR SYNOPSIS A N H V A C N E W S L E T T E R F O R B U I L D I N G O W N E R S A N D M A N A G E R S In this issue... Demand Controlled Ventilation How CO2-based DCV effectively maintains

### Analysis of Energy Consumption, Rating Score, and House Size

Analysis of Energy Consumption, Rating Score, and Duncan Prahl, Registered Architect Innovation Programs Leader, Research and Development, IBACOS, Inc., Phone: + 1 412 325 1523. Fax: + 412 765 3738. E-mail:

### ALASKA HOUSING FINANCE CORPORATION AHFC-BD1.97. Blower Door Test

ALASKA HOUSING FINANCE CORPORATION AHFC-BD1.97 Blower Door Test DETERMINING AIR FLOW THROUGH A BUILDING AIRTIGHTNESS BOUNDARY BY THE FAN DEPRESSURIZATION METHOD August 23, 2010 DETERMINING AIR FLOW THROUGH

### Below are detailed instructions for using the EMS load calculator.

Introduction The EMS load calculator is designed to make load calculating as painless as possible. For sizing the equipment, only the first three tabs (Steps 1, 2 & 3) need to be completed. This process

### Pressure Balancing. Chris Clay The Building Performance Center Brad Turner Southface

Pressure Balancing Chris Clay The Building Performance Center Brad Turner Southface Objectives Understand the problems pressure imbalances can cause in a home Review basic pressure principles Demonstrate

### Get the FACTS about SEER and Deliver Better Customer Value

What is SEER? SEER stands for Seasonal Energy Efficiency Ratio. It s a number that describes how well air-conditioning equipment works. A higher SEER means better efficiency and lower energy bills. SEER

### Multi-Point Blower Door and Duct Blower Testing (Power Regression Analysis)

Instructions for Multi-Point Blower Door and Duct Blower Testing (Power Regression Analysis) Multi-Point Blower Door and Duct Blower Testing for Texas Instruments TI-86, 2004 WxWare Diagnostics 83 INTRODUCTION

### Sensitivity of Forced Air Distribution System Efficiency to Climate, Duct Location, Air Leakage and Insulation

LBNL 43371 Sensitivity of Forced Air Distribution System Efficiency to Climate, Duct Location, Air Leakage and Insulation Iain S. Walker Energy Performance of Buildings Group Indoor Environment Department

### Residential HVAC System Sizing

Residential HVAC System Sizing William P. Goss University of Massachusetts, Amherst, Massachusetts, USA Corresponding email: goss@acad.umass.edu SUMMARY Heating, ventilating and air-conditioning (HVAC)

### HVAC Calculations and Duct Sizing

PDH Course M199 HVAC Calculations and Duct Sizing Gary D. Beckfeld, M.S.E., P.E. 2007 PDH Center 2410 Dakota Lakes Drive Herndon, VA 20171-2995 Phone: 703-478-6833 Fax: 703-481-9535 www.pdhcenter.com An

### Fan Applications & System Guide

Fan Applications & System Guide Airflow for general ventilation can be calculated by; Area Method Air Change Method Occupancy Method Ventilation Calculation Methods Area Method Derives the ventilation

### Minnesota State Residential Energy Code Requirements

Minnesota State Residential Energy Code Requirements The Energy Code provides minimum standards for permitting energy efficient operation, assuring building durability and furnishing quality indoor air.

### Energy Efficiency. Energy Efficient Home Cooling:

Energy Efficiency Energy Efficient Home Cooling: Choosing an air conditioning system is an important decision. A poor choice may be costly to purchase and operate and yet fail to provide the desired cooling

### Residential Zoned Systems It s Different Now

The Energy Training Center Stockton and this training are funded by California utility customers and administered by Pacific Gas and Electric Company under the auspices of the California Public Utility

### Modeling the Impacts of Performance Components in Super Energy Efficient House Designs in Different Climate Zones

Modeling the Impacts of Performance Components in Super Energy Efficient House Designs in Different Climate Zones John Broniek, IBACOS Inc. ABSTRACT As part of Building America work, research has been

### FREQUENTLY ASKED QUESTIONS about HERS and CHEERS Provided by the California Energy Commission Consumer Energy Center

http://www.energy.ca.gov/ FREQUENTLY ASKED QUESTIONS about HERS and CHEERS Provided by the California Energy Commission Consumer Energy Center Relevant Standard The Residential Manual for Compliance with

### 2014 British Columbia Building Code Changes

2014 British Columbia Building Code Changes A City of Kelowna interpretation of the 2014 Building Code Changes for 9.36 & 9.32 The following changes reflect the most notable revisions and staff interpretations.

### CITY OF MERCER ISLAND, WASHINGTON

www.mercergov.org CITY OF MERCER ISLAND, WASHINGTON 9611 S.E. 36th St. Mercer Island, WA 98040-3732 p: (206) 275-7605 f: (206) 275-7725 TDD: (425) 803-1751 Inspection Requests: Online: www.mybuildingpermit.com

### Direct Energy Home Energy Audit Audit Report

Direct Energy Home Energy Audit Audit Report Joe Smith 123 Anywere St Houston Tx. 77046 1 Audit Introduction The Direct Energy Home Energy Audit Team used the Home Energy Rating System (HERS ) to evaluate

### Testing Requirements of the 2012 IECC. Paul Morin The Energy Conservatory

Testing Requirements of the 2012 IECC Paul Morin The Energy Conservatory Duct testing Agenda Blower Door testing Blower door tests on multi family buildings Training? 2012 IECC says: Duct Testing Duct

### Gauges and Fans should be checked regularly for accuracy

Why test the building envelope with a Blower Door? Air leakage is responsible for as much as 30% of all the energy lost in a home. Finding and addressing this leakage is often the least expensive way to

### UNDERSTANDING AND USING THE HVAC DESIGN REVIEW FORM

Page 1 UNDERSTANDING AND USING THE HVAC DESIGN REVIEW FORM Each of the 38 points of requested information is discussed, and references to the supporting manual are given to substantiate the requirement.

### THE IC Y N E N E AD V A N T A G E

THE IC Y N E N E AD V A N T A G E APP L I C A T I O N CA S E ST U D Y : Insulating a Metal Building for Air Sealing/ Energy Efficiency Synopsis: Twice as effective at air sealing versus conventional insulation

### Building Performance Solutions HVAC Design Guide, 2007

Building Performance Solutions HVAC Design Guide, 2007 HVAC sizing, system design, layout, and installation shall be sized according to (Air Conditioning Contractor of America), ACCA manual J8, 8 th edition,

### Selecting Energy Efficient New Windows in Florida

Selecting Energy Efficient New Windows in Florida www.efficientwindows.org January 06 Zones. Meet the Energy Code & Look for the Windows must comply with your local energy code. Windows that are certified

### Because all SPF-insulated homes are very tightly constructed,

April 2011 Proper Design of HVAC Systems for Spray Foam Homes A report written by Doug Garrett, CEM, ACCA Certified Instructor, Building Performance and Comfort Inc. IntroDuCtIon Spray polyurethane foam

### System Interactions in Forced-Air Heating and Cooling Systems, Part II: Continuous Fan Operation

System Interactions in Forced-Air Heating and Cooling Systems, Part II: Continuous Fan Operation Authors Gu, Lixing Swami, Muthusamy Fairey, Philip Original Publication Lixing Gu, Muthusamy Swami, Philip

### ENERGY STAR Certified Homes, Version 3 Cost & Savings Estimates

November 1, 2013 Contents ENERGY STAR Certified Homes, Version 3 Section 1: Executive Summary... 3 Section 2: Detailed Incremental Cost Estimates... 6 Section 3: Incremental Cost & Savings of the Thermal

### Low-cost Construction for High-energy Savings. Brian J. Wimmer Construction Manager Rochester Area Habitat for Humanity

Low-cost Construction for High-energy Savings Brian J. Wimmer Construction Manager Rochester Area Habitat for Humanity construction@rahh.org Objectives: 1. Control air & moisture in high-performance, low-cost

### CHAPTER 3. BUILDING THERMAL LOAD ESTIMATION

CHAPTER 3. BUILDING THERMAL LOAD ESTIMATION 3.1 Purpose of Thermal Load Estimation 3.2 Heating Load versus Cooling Load 3.3 Critical Conditions for Design 3.4 Manual versus Computer Calculations 3.5 Heating

### SIMULATION OF FtX VENTILATION TECHNIQUE IN A TYPICAL SWEDISH HOUSE

DEPARTMENT OF TECHNOLOGY AND BUILT ENVIRONMENT SIMULATION OF FtX VENTILATION TECHNIQUE IN A TYPICAL SWEDISH HOUSE Adrián Ferreras Pascual June 2010 Master s Thesis in Energy Systems Master Programme in

### A blower door test is used to gauge the rate of air leakage from a building and locate air infiltration points..

Blower Door Tests A blower door test is used to gauge the rate of air leakage from a building and locate air infiltration points.. The blower door is a large fan mounted onto a panel which then seals into

### EPA WaterSense for New Homes Program DOE Zero Energy Ready Home Quality Management Guidelines

22 Harbor Ave Dunhill Companies LTD John S. Rodenhizer 10/28/2014 EPA WaterSense for New Homes Program DOE Zero Energy Ready Home Quality Management Guidelines -7 REM/Rate - Residential Energy Analysis

### Criteria for Obtaining Specified Humidity and Temperature Conditions

Criteria for Obtaining Specified Humidity and Temperature Conditions by Clay Hile, Parameter Generation & Control, Inc. Providing a specified humidity and temperature for testing or process control can

### Northwest ENERGY STAR Homes Program Requirements 1 Oregon Single-Family Homes Effective Date: January 1, 2012

Program Requirements 1 Oregon Single-Family Homes Effective Date: January 1, 2012 Northwest ENERGY STAR BOP 1; Consistent elements for all three pathways listed below: Heating and Cooling Equipment NWBOP

### MODELLING OF MOISTURE CONDITIONS IN A COLD ATTIC SPACE

MODELLING OF MOISTURE CONDITIONS IN A COLD ATTIC SPACE A. Sasic Kalagasidis and B. Mattsson Department of Building Technology, Chalmers University of Technology, Gothenburg, S-41296, SE ABSTRACT This study

### High Performance Diagnostics Blower Doors and Infrared Cameras SPFA Conference Peter V. Burns The Energy Conservatory Minneapolis, MN

High Performance Diagnostics Blower Doors and Infrared Cameras SPFA Conference 2012 Peter V. Burns The Energy Conservatory Minneapolis, MN PV Burns Attic Rat - House Doctor, Insulator, Radon Mitigation

### 2014 Amendments to: 2012 British Columbia Building Code. An interpretation of the 2014 Building Code Changes for 9.36 & 9.32.

2014 Amendments to: 2012 British Columbia Building Code An interpretation of the 2014 Building Code Changes for 9.36 & 9.32. Prepared by the Building Inspection Services Department The following changes

### Your Personal Home Energy Action Plan

www.centralvalleyenergytuneup.org g Your Personal Home Energy Action Plan 123 Sample Street Fresno, Ca 93710 Home Energy Rater Name Company Evaluation Date Joe Rater Rater Services, Inc. 9/1/2013 This

### IECC Compliance Guide for Homes in Virginia

IECC Compliance Guide for Homes in Virginia Amended Version of 2012 International Energy Conservation Code July 14, 2014 Climate Zone Since the entire state of Virginia falls in the IECC Climate Zone 4,

### Strategy Guideline: HVAC Equipment Sizing

Strategy Guideline: HVAC Equipment Sizing Arlan Burdick IBACOS, Inc. February 2012 This report received minimal editorial review at NREL NOTICE This report was prepared as an account of work sponsored

### HVAC Systems and Indoor Air Quality. Douglas K. Spratt, M.Sc., P.Eng.

HVAC Systems and Indoor Air Quality Douglas K. Spratt, M.Sc., P.Eng. The 5 Senses Architecture Electrical Structural Mechanical Hearing Seeing Smelling Feeling Tasting HVAC Systems are Dynamic Heat Gains

### Home Energy Auditing Standard

Building Performance Institute, Inc. BPI Standards BPI-101 Home Energy Auditing Standard 1 Raising the Bar in Building Performance Contracting May 5, 2010 - Draft Notice BPI standards, bulletins and other

### Verifying & Measuring Ventilation Systems

Verifying & Measuring Ventilation Systems Chip Henderson, AIA, CEM, LEED-Faculty 2012 RESNET Conference Austin, Texas Indoor Air Quality Intent Ventilation System designed to meet ASHRAE 62.2-2007 ASHRAE

### Low-Permeance Materials in Building Envelopes

Construction Technology Update No. 41 Low-Permeance Materials in Building Envelopes by M.K. Kumaran and J.C. Haysom This Update provides guidance on the use of low-permeance materials towards the outside

### A Performance Based ENERGY STAR Homes Program: The Wisconsin ENERGY STAR Homes Perspective

A Performance Based ENERGY STAR Homes Program: The Wisconsin ENERGY STAR Homes Perspective A Performance Based ENERGY STAR Homes Program: The Wisconsin ENERGY STAR Homes Perspective By Carter Dedolph and

### Heating, Ventilation, and Air Conditioning

Chapter 7 Heating, Ventilation, and Air Conditioning One of the most important decisions regarding a new home is the type of heating and cooling system to install. Equally critical is the heating and cooling

### Air Conditioning Contractors of America

Air Conditioning Contractors of America WHO IS ACCA???? Industry Manuals Residential D, J, S, H, RS, T, P A manual J load calculation is a measurement of how much heating and cooling capacity a home will

### Laboratory Performance Testing of Residential Window Mounted Air Conditioners

Laboratory Performance Testing of Residential Window Mounted Air Conditioners Jon Winkler Chuck Booten Dane Christensen Jeff Tomerlin April 29, 2012 NREL is a national laboratory of the U.S. Department

### HVAC Quality Installation for ENERGY STAR Homes (For Version 3)

HVAC Quality Installation for ENERGY STAR Homes (For Version 3) Questar Gas ThermWise Builder Program & Rocky Mountain Power wattsmart New Homes Program ThermWise Builder Program & wattsmart New Homes

### HVAC System Installation & Best Practices in New Construction. Anthony Stamatopoulos ACI New Jersey - 2007

HVAC System Installation & Best Practices in New Construction Anthony Stamatopoulos ACI New Jersey - 2007 This Session Outline: 1. HVAC system Design, Selection and Installation Learn to list the steps

### ATTENTION CONTRACTORS AND HOMEOWNERS JANUARY 1, 2010

2010 CALIFORNIA BUILDING CODE CALIFORNIA RESIDENTIAL CODE 2008 BUILDING ENERGY EFFICIENCY STANDARDS STANDARDS REVIEW WITH REPLACEMENT WINDOW PERMIT APPLICATION ATTENTION CONTRACTORS AND HOMEOWNERS NEW

### Development Services City of Lawrence, KS

Development Services City of Lawrence, KS Building Planning Table R301.2 (1) Climatic & Geographic Design Criteria Building Planning The design criteria for wind speed increased from 90 MPH to 115 MPH.

### Kitchen Ventilation Systems: Part 2 Providing Adequate Makeup Air

The Pennsylvania Housing Research Center Kitchen Ventilation Systems: Part 2 Providing Adequate Makeup Air Builder Brief: April 2012 Anthony C. Jellen, PE & Brian M. Wolfgang, EIT, Michael A. Turns, MS

### PERCENT OUTDOOR AIR CALCULATION AND ITS USE

PERCENT OUTDOOR AIR CALCULATION AND ITS USE APPLICATION NOTE AF-138 (A4 The RH720 calculates Percent Outdoor Air (%OA. In order to take advantage of this feature, it is important to first understand what

### HVAC Basic Science - System Capacity

HVAC Basic Science - System Capacity Btu/hour, btu/h, b/h, btuh. btu?? 1 MBH = 1000 btu/hour 1 KBH = 1000 btu/hour 1 ton of cooling= 12,000 btu/hour 1 watt = 3.414 btu/hour 1 kilowatt = 1000 watts = 3,414

Heating Load Calculation ME 425 Air Conditioning System Design Keith E. Elder, P.E. Heating Load Calculation The heating load calculation begins with the determination of heat loss through a variety of

### Problems Related to Air Handler Leakage

The following article was published in ASHRAE Journal, January 28. Copyright 28 American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. It is presented for educational purposes

### Why and how to save energy at home

Why and how to save energy at home John Irwin, Sierra Club DE, home owner johnirwin@comcast.net Jack Sol-Church, weatherization instructor Presentation will be posted on DE chapter Sierra Club s website

### Temperature Rise Above

Spec-00488 E763.422.2211 763.422.2600 Thermal Management Heat Dissipation in Electrical Enclosures Thermal Management Heat Dissipation in Electrical Enclosures Heat Dissipation in Sealed Electrical Enclosures

### VAV Laboratory Room Airflow The Lowdown on Turndown

Technology Report March, 2003 VAV Laboratory The Lowdown on Turndown Turndown comparison of these two turndown ratios. Note the small actual airflow difference between them. control ranges are normally

### Mississippi. Energy and Cost Savings. for New Single and Multifamily Homes: 2009 and 2012 IECC as Compared to the 2006 IECC

BUILDING TECHNOLOGIES PROGRAM Mississippi Energy and Cost Savings for New Single and Multifamily Homes: 2009 and 2012 IECC as Compared to the 2006 IECC 1 2009 AND 2012 IECC AS COMPARED TO THE 2006 IECC

### 24.301.161 INCORPORATION BY REFERENCE OF INTERNATIONAL. (1) The Department of Labor and Industry adopts and incorporates by

24.301.161 INCORPORATION BY REFERENCE OF INTERNATIONAL ENERGY CONSERVATION CODE (1) The Department of Labor and Industry adopts and incorporates by reference the International Code Council's International

### Air leakage, or infiltration, is outside air that enters uncontrollably through

1 Sealing Air Leaks in Your Home Housing Fact Sheet What is Air Leakage? Air leakage, or infiltration, is outside air that enters uncontrollably through cracks and openings in the walls, ceilings and floors

### Cost Estimation for Materials and Installation of Hot Water Piping Insulation

Cost Estimation for Materials and Installation of Hot Water Piping Insulation Prepared for Pacific Northwest National Laboratory Under Contract Number: 18O9O2 By Gary Klein, Managing Partner Affiliated

### HVAC Code Requirements

one and two family dwellings? Answer: SECTION 2001: GENERAL 2001.1 Air supply. Fuel-burning equipment shall be provided with a supply of air for fuel combustion, draft hood dilution and ventilation of

### A Glossary of HVAC Terms:

Since 1979 TACL A537C Doctor COOL & P rofessor HEA T The Team For All Seasons TM A Glossary of HVAC Terms: Confused by the many terms and acronyms surrounding your indoor comfort system? Don t be! This

### Creating Efficient HVAC Systems

Creating Efficient HVAC Systems Heating and Cooling Fundamentals for Commercial Buildings Heating, ventilating, and air conditioning (HVAC) systems account for nearly half of the energy used in a typical

### Home Performance Guide Heat Pump Installation

Home Performance Guide Heat Pump Installation Something to fully understand about heat pumps is that they are a part of an overall system, the heating, ventilating and air conditioning (HVAC) system. That

### Mechanical ventilation and heat recovery for low carbon retrofitting in dwellings

Mechanical ventilation and heat recovery for low carbon retrofitting in dwellings Phil F. G. Banfill 1*, Sophie A. Simpson 1, Mark C. Gillott 2, Jennifer White 2 1 Heriot-Watt University, Edinburgh, UK

### LEGALETT HVAC DESIGN FEE SCHEDULE (revised April 17, 2012)

LEGALETT HVAC DESIGN FEE SCHEDULE (revised April 17, 2012) Background In the past Legalett has simply supplied warm floors for comfortable living. However, 2012 Building Code changes in Ontario make it