1 Applying Variable Speed Drives In Industrial Refrigeration Systems Douglas Reindl, Ph.D., P.E. Professor, University of Wisconsin-Madison Director, Industrial Refrigeration Consortium (2012) Reindl, All Rights Reserved
2 High pressure liquid Equalizer line Single Stage Compression System High pressure gas Evaporative Condenser condenser Evaporative Condenser condenser DX evaporator High pressure receiver T King valve (automatic) Flooded evaporator Dry suction 1 4 Wet return Overfed evaporator(s) To HPR Suction trap Refrigerant transfer system Compressor(s) Pumped recirculator 4 4 T Compressor(s)
3 Where Can VFDs Be Applied? Condenser fans o All or none expect 2-3% savings Evaporator fans o 2-4% savings range o Simple paybacks 1-5 years Compressors o At most, one VFD comp per suction level o Simple paybacks 1-4 years
4 VFD Basic Principles Common terms AFD, ASD, VFD, VSD, drive What it is an electronic controller device capable of adjusting speed of electric motor by modulating power being delivered What it can do: o Vary motor speed to match variable load requirement o Soft start to eliminate mechanical, electrical, hydraulic surges/transients o Potentially save energy, energy cost
5 How VFDs Work Rectifier Converts 3 phase AC voltage to pulsating DC voltage Intermediate circuit Stabilizes the pulsating DC voltage Inverter Converts DC voltage to variable voltage, variable frequency AC Source: Ohme Fundamentals of VFDs and Refrigeration Applications, IRC R&T Forum (2009)
6 VFD Basic Principles Rating o Voltage o Required current to motor o Load type o Overload requirements Variable torque required torque increases as speed increases (condenser, evaporator fans) Constant torque required torque independent of speed (compressors)
7 VFDs Condenser Fans A variable torque application.
8 Evaporative Condenser Operating Principles (Induced draft, counter flow) Moist, hot air out Eliminators Spray header High pressure vapor refrigerant, in High pressure liquid refrigerant, out Ambient air Ambient air Remote sump Makeup water Remote pump Local pump Condenser water circuit
9 Condenser Fan Control Options Single speed fan with on/off control o Most common method of head pressure control o Need to set cut-in (e.g. 150 psig), cut-out pressures (e.g. 145 psig) o Simple control method except: Highest energy consumption option Higher maintenance (fan motors, belts) Potential for liquid management problems in multiple condenser systems Two-speed fan control
10 Condenser Fan Control Options (continued) Variable frequency drive o Set target head pressure, modulate fan speed to maintain o Simple to implement: Slightly higher capital cost versus fixed speed Lowest energy consumption control alternative Multiple condenser systems, modulate ALL condensers together Smooth system operation with minimal transients
11 Condenser Fan Control Map Example Strategy Mode 1 Mode 2 Mode 3 Mode 4 Mode Small Motor off on off on Large Motor off off on on Small Motor off off on Large Motor off on on Small Motor off on on on Large Motor off off half-speed on Small Motor off half-speed half-speed on on Large Motor off off half-speed half-speed on Small Motor off variable speed Large Motor off variable speed
12 Comparative Condenser Fan Performance ~44% ~6%
13 Simple Two Condenser System Heat rejection load Fixed speed control # condensers HP Variable speed drive # condensers HP * 100% % 30 75% 1 + 1/ % % % 1.8 Each condenser equipped with 15 HP fan. * Sans drive losses
14 VFDs Condenser Fans Benefits Stable head pressure Reduced maintenance on shafts, bearings, belts Allows ability to optimize head pressure Reduced energy consumption and operating costs Look to achieve optimal/near-optimal performance with a simplified control strategy
15 Questions on VFDs for condenser fans?
16 VFDs Evaporator Fans A variable torque application.
17 Evaporator Fans Opportunity Load variability essential Best choices for modulating evaporator capacity as space load is reduced: o Cycle refrigerant feed, always run fans (normal situation) o Cycle refrigerant feed + cycle fans after period of time with no call for refrigerant feed (duty cycle) o Raise suction pressure, always run fans (often not possible) o Cycle refrigerant feed with VFD control frequency (best practice) Which is best?
18 Hours per Year Good Applications For Evaporator Fan VFDs Larger fan motors High hours/year operation Frequent part-load operation 1,500 Good VFD Candidate Poor VFD Candidate 1, Percent of Design Load
19 First Principles Applicable fan laws N N full load CFM CFM full load hp hp full load CFM CFM full load 3 Limitations typical minimum motor speeds between Hz Heat exchange impact Capacity Capacity full load CFM CFM full load 0.76
20 Speed Control Impact On Fan Power hp / hp full-load hp hp full load Capacity Capacity full load 3.95 PLR PLR 20-Hz 30-Hz
21 Evaporator Fan VFD Savings Example Evaporator TD* = 12 o F for cooler and 8 o F for freezer VFD costs o Assume 3 HP VFD for each evaporator o Installation 15 hours/vfd by $65/hour Energy costs o Blended $0.08/kWh * TD = Temperature difference (T room T refrigerant )
22 Hours per Year Comparative Load Profiles Cooler 1,500 35F cooler 1, Percent of Design Load
23 Hours per Year Comparative Load Profiles Freezer 2,000-20F Freezer 1,500 1, Percent of Design Load
24 Control Options Fan Speed Control Suction Pressure Control #1 Fixed Fixed #2 Fixed Variable #3 Duty Cycle Fixed #4 Variable Fixed #5 Variable Variable
25 Compressor + Evaporator Efficiency (kw/ton) Comparative Energy Performance Cooler Fixed Speed // Fixed Suction Fixed Speed // Variable Suction T s p a c e = 3 5 [ F ] N e v a p = Duty Cycling / Fixed Suction Variable Speed / Fixed Suction Variable Speed / Variable Suction T D d e s i g n = [ F ] Refrigeration Load (%)
26 Compressor + Evaporator Efficiency (kw/ton) Comparative Energy Performance - Freezer Fixed Speed // Fixed Suction Fixed Speed // Variable Suction Duty Cycling / Fixed Suction T s p a c e = [ F ] N e v a p = 7 T D d e s i g n = 8. 5 [ F ] 2.6 Variable Speed / Fixed Suction Variable Speed / Variable Suction Refrigeration Load (%)
27 Economic Analysis Results From always on fan control to VFD Cooler (35 o F) Freezer (-20 o F) Savings per ton $72 $96 Capital cost per ton $65 $95 Installation cost per ton $48 $71 Simple payback 1.6 years 1.7 years From cycling fan control to VFD Savings per ton $48 $64 Simple payback 2.4 years 2.6 years Assumes single drive operates all fan motors (4) on individual evaporators
28 VFDs Evaporator Fans Reduced system power o Evaporator fan power drastically reduced at part-load o Compressor power reduced due to lower parasitic space refrigeration loads attributable to lower fan energy use (5 HP = 1 ton of refrigeration) More stable suction pressure Increased motor life o Less motor cycling, inherently soft-start Improved power factor Decreased noise, wind-chill
29 VFD Heads Up Drive losses (~3-6%, losses increase at low loads) Evaporator throw loss Typical systems have large number of small evaporator fan motors (cost) Additional equipment to maintain Resonance of equipment (natural frequency) Power quality Siting the drives Minimum fan speed/drive frequency Requires low temperature bearing lubrication/grease
30 Questions on VFDs for evaporator fans?
31 VFDs Compressors A fixed torque application.
32 Compressor Capacity Control Reciprocating o Start/stop individual compressors (rack system) o Discrete cylinder unloaders o Hot gas bypass (not preferred) o Variable speed drive? o Screw single, twin o Continuous slide valve, poppet valves, etc. o Hot gas bypass (not preferred) o Variable speed drive?
33 Percent Full Load BHP Screw Compressor Part-load Characteristics Screw Compressor V i = 5. 0 V i = 3. 6 V i = (Condensing Temperature > 75 F) compressor-only Percent Capacity
34 Efficiency [BHP/ton] Inefficient Part-load Operation! F Suction; 90 F Condensing compressor-only Capacity [%]
35 Percent Full-Load Capacity Compressor Capacity Control Twin Screw Compressor Compressor capacity is directly proportional to shaft speed Percent Compressor Speed
36 Efficiency [BHP/ton] Speed Control Efficiency Benefit Twin Screw Fixed Speed (slide valve) Single Stage 15 psi suction 181 psi discharge thermosiphon oil cooling VFDs perform well at partload conditions! 1.7 Variable Speed Part-Load Capacity [%]
37 % of Run Hours Screw Compressor Field Retrofit Compressors operation on -30 F suction level Comp 1 Comp 2 Slide Valve Position Ref: Campbell, VFDs in Industrial Refrigeration - Lesson's Learned, IRC R&T Forum (2006).
38 Compressor VFD Retrofit Installed 500 HP VFD on -30 suction level (trim machine) Implemented 1 st level of capacity control using speed rather than slide valve All other compressors base loaded at 100% 500 HP inverter rated motor (North Ice Cream Plant) Ref: Campbell, VFDs in Industrial Refrigeration - Lesson's Learned, IRC R&T Forum (2006).
39 Compressor VFD Retrofit Positive Results 5% compressor run time reduction 25% booster energy consumption reduction Savings analysis 160 kw peak demand reduction Simple payback 1.2 yr Ref: Campbell, VFDs in Industrial Refrigeration - Lesson's Learned, IRC R&T Forum (2006).
40 Compressor VFD Application Considerations One VFD-equipped compressor per suction level Operating sequence considerations o Base load fixed speed screws at 100% slide valve o Trim with VFD-equipped compressor Use speed as first level of capacity control Use slide valve as second level of capacity control o Monitor, tune PI control to avoid speed cycling
41 Compressor VFD Application Considerations (continued) Not cost effective for medium voltage (4160 V) motors Speed control range essential to field verify compressor is free from excessive vibration at all frequencies/speeds Adhere to minimum speed o Required for adequate oil circulation o Required to maintain rotor tip velocity o May require supplemental fan for motor cooling
42 Questions on VFDs for compressors?
43 Closing Thoughts Condenser fans o All or none expect 2-3% savings Evaporator fans o 2-4% savings range o Simple paybacks range 1-5 years Compressors o At most, one VFD comp per suction level o Simple paybacks range 1-4 years
44 Questions? Douglas Reindl, Ph.D., P.E. Professor, University of Wisconsin-Madison Director, Industrial Refrigeration Consortium Thank you!
45 Additional Resources Industrial Refrigeration Consortium Research and Technology Forum Presentations o Fundamentals of VFDs and Refrigeration Applications Ohme (2009) o VFDs for Evaporators Runsey (2009) o VFDs for Compressors Cosner (2009) o Case Studies of VFD Applications Zanutto (2009) o VFDs in Industrial Refrigeration Lesson s Learned Campbell (2006) Cold Front Newsletters o VFDs for Evaporative Condenser Fans Vol. 4 No. 2 (2004) o VFDs for Screw Compressors Vol. 4 No. 3 (2004) o VFDs for Evaporator Fans Vol. 4 No. 4 (2004) Industrial Refrigeration Energy Efficiency Guidebook, Reindl & Jekel, 2 nd Edition, (2011)
46 Additional Resources (continued) University of Wisconsin-Madison/IRC o Short course Achieving Energy Cost Savings for Ammonia Refrigeration Systems May 22-24, 2012 o Northwest Energy Efficiency Alliance Evaporator Fan VFD Initiative o Baseline Market Evaluation Report, April 1999 o Market Progress Evaluation Report No 2., November 2000 o Market Progress Evaluation Report No 2., June 2002 o Reports available at
Industrial Refrigeration Systems: Floating Head Pressure Control For Peak Energy Performance Douglas Reindl, Ph.D., P.E. Professor, University of Wisconsin-Madison Director, Industrial Refrigeration Consortium
Optimization of Industrial Refrigeration Plants: Including a Case Study at Stonyfield Farm Yogurt Mark D Antonio, Satyen Moray, Brian McCowan and Gary Epstein, Energy & Resource Solutions, Inc. Lisa Drake,
Why and How we Use Capacity Control On refrigeration and air conditioning applications where the load may vary over a wide range, due to lighting, occupancy, product loading, ambient weather variations,
The following article was published in ASHRAE Journal, August 2007. Copyright 2007 American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. It is presented for educational purposes
Chapter 3.4: HVAC & Refrigeration System Part I: Objective type questions and answers 1. One ton of refrigeration (TR) is equal to. a) Kcal/h b) 3.51 kw c) 120oo BTU/h d) all 2. The driving force for refrigeration
Chapter 25 Case of Screw Refrigeration System Design Copy Right By: Thomas T.S. Wan 温 到 祥 著 Sept. 3, 2008 All rights reserved This shall be a simplified version of the example to illustrate the thinking
Data Realty Colocation Data Center Ignition Park, South Bend, IN Owner: Data Realty Engineer: ESD Architect: BSA LifeStructures Project Overview Data Realty is a data center service provider for middle
WHAT IS THE OPTIMUM COMPRESSOR DISCHARGE PRESSURE SET POINT FOR CONDENSERS? Dr Richard J. Love, Prof. Don J. Cleland, Dr Inge Merts, Mr Brett Eaton Centre for Postharvest and Refrigeration Research Massey
COMMERCIAL HVAC CHILLER EQUIPMENT Air-Cooled Chillers Technical Development Programs (TDP) are modules of technical training on HVAC theory, system design, equipment selection and application topics. They
This article was published in ASHRAE Journal, February 2011. Copyright 2011 American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. Posted at www.ashrae.org. This article may not
Condenser November 2009 Published by the International Institute of Ammonia Refrigeration as a service to its members and the Industrial Refrigeration Industry INDUSTRIAL HEAT PUMPS The Renewing of Rejected
COMPRESSED AIR STORAGE Storage can be used to control demand events (peak demand periods) in a compressed air system by reducing both the amount of pressure drop and the rate of decay. Storage can be used
Energy Efficiency - Innovation, Technology & Experience Workshop Oil-Free Magnetic Bearing Compressors for Air-Conditioning Plants 19 November 2008 1 Disclaimer All the technical details in this presentation
ASHRAE Boston Chapter Meeting Designing AC Refrigeration Systems Lessons Learned February 11, 2014 Explanation of the refrigeration cycle. Compressors. Benefits and operating characteristics. -Reciprocating
An Industrommercial CO 2 System Joe Sanchez BITZER US, INC 6/26/2015 What does Industrommercial mean? [in-duhs-truh-mur-shuh l] noun 1. of, relating to, industrial and commerical markets 2. of, pertaining
Chapter 6 Screw Compressors Copy Right By: Thomas T.S. Wan 温 到 祥 著 Sept. 3, 2008 All rights reserved Screw compressors are the most widely used compressors for industrial refrigeration application in the
COMMERCIAL HVAC EQUIPMENT Condensers and Cooling Towers Technical Development Programs (TDP) are modules of technical training on HVAC theory, system design, equipment selection and application topics.
SECTION 5 COMMERCIAL REFRIGERATION UNIT 22 CONDENSERS UNIT OBJECTIVES After studying this unit, the reader should be able to explain the purpose of the condenser in a refrigeration system. describe differences
Refrigeration Pressure Vessel Basics Presented by John Murdaugh Apex Refrigeration & Boiler Co. Phoenix Arizona Pressure Vessel: A container designed to hold liquid and or vapor at a pressure greater than
ICE THERMAL STORAGE IN AIR CONDITIONING APPLICATION FUNDAMENTALS By: T. S. Wan Date: April 19, 1994 (1st draft 3/7/86) Copyright 1994 by T. S. Wan (All rights reserved) ABSTRACT: The technology of energy
FINDINGS OF A DETAILED ENERGY AUDIT AT A CHEMICAL PLANT IN SINGAPORE Main Energy Consuming Systems Process chiller system Brine chiller system Process cooling tower water system Air Compressors Boilers
Fans and Pumps are sized to meet the maximum flow rate required by the system. System conditions frequently require reducing the flow rate. Throttling and bypass devices dampers and valves are installed
Purchasing Tips Analyse the System as a Whole Variable Frequency Drives Since the process of converting incoming power from one frequency to another will result in some losses, energy savings must always
Life Cycle Costing Analysis of Water-cooled Chillers Chillventa Nuremburg, Germany Spring 2012 Description Life Cycle Cost Analysis is a method of determining and comparing the total costs of investment
compressors compressors C O M P R E S S O R S compressors C O M P R E S S O R S compres Compressed air systems hold one of the keys to greater productivity, efficiency and profitability. This is the sixth
Table V Troubleshooting Checklist for Refrigeration Systems TROUBLE POSSIBLE CAUSE CORRECTIVE MEASURE High condensing pressure. Low condensing pressure. Air or non-condensable gas in system. Inlet water
For Distribution ENGINEERING BULLETIN No. EB 039 Product: Cooling Towers, Closed Circuit Coolers & Evaporative Condensers Date: June 2003 Purpose: Variable Frequency Drives The purpose of this Engineering
Scroll compressors for Low GWP Heat Pumps using R290 natural refrigerant Pierre Ginies, Next Heat Pump Generation 2015 firstname.lastname@example.org Danfoss Commercial Compressors Leading compressor R&D and manufacturing
News in Data Center Cooling Wednesday, 8th May 2013, 16:00h Benjamin Petschke, Director Export - Products Stulz GmbH News in Data Center Cooling Almost any News in Data Center Cooling is about increase
FACILITY ENERGY ASSESSMENT ABC Company Headquarters October 17, 2012 Evansville, Indiana Contact Vectren Energy Delivery 1 N. Main Street Evansville, Indiana 47711 (P) 812-491-1515 (E) email@example.com
Why Compressors Fail Causality eflex Variable Speed Compressors Lower Operating Cost through 10%-15% Improvement in Part Load Efficiency Common Compressor Types Reciprocating compressors with hermetic/semihermetic
Compressor - Loss of oil, Loss of oil pressure, or Cuts off on oil pressure control. Compressor short cycling. Insufficient oil in the system. Oil trapping in the system. Probably in the evaporator. Excessively
Appendix C Minimum Equipment Efficiency Standards Appendix C: Minimum Equipment Efficiency Standards This Appendix is an overview of building and equipment standards in the State of California that have
Refrigeration and Airconditioning Prof. M. Ramgopal Department of Mechanical Engineering Indian Institute of Technology, Kharagpur Lecture No. # 22 Refrigeration System Components: Compressor (Continued)
Drives and motors A guide to using variable-speed drives and motors in retail environments Improving energy efficiency and lowering the carbon footprint Retailers across the UK take their corporate responsibility
Specification SERIES: SyScroll 20-30 Air EVO HP TYPE: Air to water inverter driven heat pump TECHNOLOGY: scroll compressor / inverter driven CAPACITY RANGE: Cool ing 20-35 [kw] Heating 20-34 [kw] 1 1 General
Wet Bulb Temperature and Its Impact on Building Performance By: Kurmit Rockwell, PE, CEM, LEED AP and Justin Lee, PE, LEED, AP BD+C Energy Solution Services, AtSite, Inc. 1 What is Wet Bulb Temperature?
HVAC Systems: Overview Michael J. Brandemuehl, Ph.D, P.E. University of Colorado Boulder, CO, USA Overview System Description Secondary HVAC Systems Air distribution Room diffusers and air terminals Duct
GRF Series Non-Cycling Dryers Why Dry Compressed Air Compressed air is a clean, convenient and versatile energy resource ideal for many industrial, commercial and instrument applications. To optimize a
Efficiency Vermont Guide to Savings Helping Vermont businesses save energy and money Compressed Air Systems 888-921-5990 www.efficiencyvermont.com 1 Save money and optimize system performance Air compressors
3 Energy Efficiency Best Practice Guide Contents 1 Introduction 4 2 The business benefits of efficient refrigeration 5 3 What is your opportunity? 6 4 Solution 1 Improve the efficiency of your existing
This article was published in ASHRAE Journal, June 2010. Copyright 2010 American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. Reprinted here by permission from ASHRAE at www.tiaxllc.com.
Overview When thinking of reducing the energy consumption of the cooling tower-chiller system, many assume that large expenses will be incurred. However, this does not have to always be the case if certain
A TRUE Heat Recovery Water Source Heat Pump System Water Source Heat Pump (WSHP) systems are considered energy efficient since they can move heat from one location within a building to another location.
INDUSTRIAL process water chillers ch series Industrial process water chillers LEADING THE WAY IN liquid COOLING TECHNOLOGY In many industrial applications cold water is used to keep the productivity of
Chapter 4.9: HVAC System Short type questions 1. Define tons of refrigeration?. One ton of refrigeration is the amount of cooling obtained by one ton of ice melting in one day. It is equivalent to kcal/h,
Printing and Publishing Energy Savings Guide Oregon printing and publishing plants face challenges of rising operating costs, environmental and other regulations, outdated equipment and customer demand
Designing a Grocery Store Refrigeration System from Scratch Presented by Nick Shockley, PE Founded 1970 Locations Kansas City Bentonville Dallas Houston Las Vegas New York Metro Philadelphia Metro Phoenix
VACUUM PUMPS Section IV Equipment used to generate vacuum, as noted earlier, is similar to air compressors. It's even possible to generate compressed air or vacuum with the same machine, depending on how
2. OUTDOOR UNIT OPERATION CONTROL 2. OUTDOOR UNIT 2-1 INPUT / OUTPUT LIST I N P U T O UT P U T Input / output or kind of detail Control range Discharge pressure sensor Pressure sensor Measure range 0.0
CASE STUDY ULTRA-EFFICIENT HVAC DESIGN AND CONTROL MAJOR HEATING, VENTILATING AND AIR- CONDITIONING REPLACEMENT AT THE COUNTY OF SAN DIEGO CRIME LAB December 30, 2005 8520 Tech Way, Suite 110 San Diego,
LIQUID PROCESS CHILLERS SUPERIOR COOLING SYSTEMS PRESENTS The Benefits of Process Fluid Chillers Save Water and Money Running city or well tower water through your equipment and down the drain is a tremendous
SECTION 5 COMMERCIAL REFRIGERATION UNIT 21 EVAPORATORS AND THE REFRIGERATION SYSTEM UNIT OBJECTIVES After studying this unit, the reader should be able to Define high-, medium-, and low-temperature refrigeration.
VFD 101 Intro Lesson Variable Frequency Drives (VFD) Fundamentals This introduction lesson reviews the reasons for using Variable Frequency Drives (VFD) in water and wastewater treatment. It specifically
VFD 101 Lesson 4 Application Terminology for a VFD This lesson covers the application terminology associated with a Variable Frequency Drive (VFD) and describes each term in detail. When applying a Variable
DRY MECHANICAL BOOSTERS REPLACE STEAM EJECTOR Steam ejectors find wide use in vacuum pumping applications so called dirty application such as in Vapour extraction, Chemical processing, Evaporative Cooling,
03 Reliable and consistent cooling water is essential for the efficient manufacture of plastics. Energy is needed to reduce water temperature to the required level using cooling or chilling plant, often
Drives and motors A guide to using variable speed drives and motors in data centres Meeting your Carbon Reduction Commitment (CRC) The power behind the data Private and public businesses, from banks to
TECHNICAL STANDARDS & SAFETY AUTHORITY TRAINING, EXAMINATION AND CERTIFICATION REFRIGERATION OPERATOR CLASS B CERTIFICATION & EXAMINATION GUIDE REVISED EDITION 2 CERTIFICATIONS PERSUANT TO THE OPERATING
HVAC Efficiency Definitions Term page EER - 2 SEER - 3 COP - 4 HSPF - 5 IPLV - 6 John Mix May 2006 Carrier Corporation 1 Energy Efficiency Ratio (EER) The energy efficiency ratio is used to evaluate the
Fluid Power Systems Conference November 19-21, 2013 Industrial Heat Exchangers Mel Arent Agenda Introduction Basic Heat Exchanger Design Overview of Air Cooled Products Available Overview of Water Cooled
MAKING MODERN LIVING POSSIBLE Data sheet Temperature Control Type KP KP temperature controls are temperaturecontrolled electrical switches. All KP temperature controls have a single pole double throw (SPDT)
Reprinting this proof for distribution or posting on web sites is not permitted. Authors may request permission to reprint or post on their web site once the fi nal version has been published. A reprint
Commissioning - Construction Documents (Page 1 of 6) A. General Information Climate Zone: Building Type: Conditioned Area (sf): Reviewer's Name: Reviewer's Agency: Note: Design Review for each system/subsystem
TECNAC COALESCENT OIL SEPARATORS TECNAC Reduction of energy consumption and increase the capacity of commercial refrigeration systems. TECNAC The Installation of TECNAC Coalescent Oil Separators in commercial
Energy Conservation Opportunities in Carbonated Soft Drink Canning/Bottling Facilities Ahmad R. Ganji, Ph.D., P.E. + Bryan Hackett and Sandra Chow BASE Energy, Inc. San Francisco, CA 94103 Industrial Energy
Chapter 9 Open Cycle Refrigeration System Copy Right By: Thomas T.S. Wan 温 到 祥 著 Sept. 3, 2008 All rights reserved An open cycle refrigeration system is that the system is without a traditional evaporator.
Mobile Climate Control 45 MCC Reference Manual 2014 PN: 89-3069 Rearmount Air Conditioning System Eco RM Capacity, Reliability, and Serviceability MCC Eco RM unit, selected as preferred equipment by leading
Atlas Copco Oil-injected Rotary Screw Compressors 2-7 EP/ 7-11 EL (2-11 kw/3-15 hp) New series: screw compressors built to last Atlas Copco screw compressors have always set the standard for reliability
THERMO KING TRUCK & TRAILER UNIT ALARM CODES THIS DOCUMENT SHOWS ALL CURRENT ALARM CODES FOR THERMO KING TRUCK AND TRAILER UNITS. NOT ALL CODES ARE POSSIBLE ON ANY INDIVIDUAL UNIT. IF THE ALARM APPLIES
If You Can t Take the Heat Utilizing Heat Recovery Effectively 2014 Carrier Corporation Presented by Brent Sigmon Sales Manager Carrier Corporation AGENDA What is Waste Heat? How Waste Heat is captured
RTS/NR Frascold semi-hermetic screw compressors suitable for refrigeration FCOM0.-EN RTS SERIES New compressors characterized by innovative and compact design, suitable for commercial or industrial applications,
32VFD 32VFD Variable Frequency Drives for Centrifugal Chillers ENERGY-SAVING CONTROL FOR CENTRIFUGAL CHILLERS Reduce energy consumption in your existing centrifugal chiller Your chiller was specified to
FinAnswer Express Wyoming Incentive Catalog Effective as of October 1, 2011 Heating, Ventilation & Air Conditioning Equipment Rocky Mountain Power provides incentives for many types of energy efficient
Refrigeration and Air Conditioning Mechanic (Commercial) Level 3 C2 Refrigeration Load Calculations Duration: 30 hours 25 hours 5 hours Upon completion of this unit of instruction the apprentice will demonstrate
Variable Frequency Drives (VFDs): Energy Efficiency Opportunities David Gibson Senior Technical Advisor SAIC, an Ameren Illinois ActOnEnergy Partner Quiz Questions: What do you already know about energy
DX for both cooling and heat pump applications 3 VES Andover offer a comprehensive range of condensing units for both cooling only and heat pump application, designed to match your VES air handling unit.
AIRAH Refrigeration (in HVAC) Back to Basics For the First Time Terms of Reference What this session is NOT about Detailed Refrigeration Design Detailed analysis of various Refrigants properties Comparison
ROTARY SCREW COMPRESSOR RMD - - - 55 kw EN The RMD Coaxial Rotary Compressor high reliability high performance low maintenance is the result of decades of experience in manufacturing design and construction
ROTARY SCREW COMPRESSOR CSD 75-100 - 125 HP EN The CSD Rotary Compressor is the fruit of decades of experience in the design and construction of rotary screw compressors. Soundproofed fairing. Highly efficient
c h i l l e r G l o s s a ry of Te rm s A p p r o a c h Temperature difference between the leaving fluid and the evaporating refrigerant ARI Standard Conditions 54 F. water inlet; 44 F. water out; 35 F.
SECTION 4 ELECTRIC MOTORS UNIT 17: TYPES OF ELECTRIC MOTORS UNIT OBJECTIVES After studying this unit, the reader should be able to Describe the different types of open single-phase motors used to drive
Drives motors A guide to using variable-speed drives motors in data centres The power behind the data Private public businesses, from banks to supermarkets, to telecommunications companies internet providers