Elimination & Mitigation of Sag & Swell Using a New UPQC-S Methodology & Fuzzy Logic Controller

Save this PDF as:

Size: px
Start display at page:

Download "Elimination & Mitigation of Sag & Swell Using a New UPQC-S Methodology & Fuzzy Logic Controller"

Transcription

1 RESEARCH ARTICLE OPEN ACCESS Elimination & Mitigation of Sag & Swell Using a New UPQC-S Methodology & Fuzzy Logic Controller 1 Kanaka Raju Kalla, 2 Suneelgoutham Karudumpa 1 Assistant Professor, EEE Department, AITAM, Tekkali, 2 Assistant Professor, EEE Department, AITAM, Tekkali Abstract This paper presents the enhancement of voltage sags, harmonic distortion and low power factor using Unified Power Quality Conditioner (UPQC) with Fuzzy Logic Controller in distribution system, The series inverter of UPQC is controlled to perform simultaneous 1) voltage sag/swell compensation and 2) load reactive power sharing with the shunt inverter. Since the series inverter simultaneously delivers active and reactive powers, this concept is named as UPQC-S (S for complex power) in this paper; a detailed mathematical formulation of PAC for UPQC-S is carried out. In this paper details are carried out on both series inverter & shunt inverter, and fuzzy logic controller is applied to shunt inverter in order to dc fluctuations and to compensate reactive power. The feasibility and effectiveness of the proposed UPQC-S approach are validated by simulation in using MATLAB software. Keywords power quality, active filters, facts, upqc, fuzzy. I. INTRODUCTION An increasing demand for high quality, reliable electrical power and increasing number of distorting loads may leads to an increased awareness of power quality both by customers and utilities. The most common power quality problems today are voltage sags, harmonic distortion and low power factor. Voltage sags is a short time (10 ms to 1 minute) event during which a reduction in r.m.s voltage magnitude occurs [4]. It is often set only by two parameters, depth/magnitude and duration. The voltage sags magnitude is ranged from 10% to 90% of nominal voltage and with duration from half a cycle to 1 min. Voltage sags is caused by a fault in the utility system, a fault within the customer s facility or a large increase of the load current, like starting a motor or transformer energizing [2, 3].Voltage sags are one of the most occurring power quality problems. For an industry voltage sags occur more often and cause severe problems and economical losses. Utilities often focus on disturbances from end-user equipment as the main power quality problems [5]. Harmonic currents in distribution system can cause harmonic distortion, low power factor and additional losses as well as heating in the electrical equipment. It also can cause vibration and noise in machines and malfunction of the sensitive equipment. The development of power electronics devices such as Flexible AC Transmission system(facts) and customs power devices have introduced and emerging branch of technology providing the power system with versatile new control capabilities [1].There are different ways to enhance power quality problems in transmission and distribution systems. Among these, the UPQC is one of the most effective devices. A new PWMbased control scheme has been implemented to control the electronic valves in the UPQC. The UPQC has additional capability to sustain reactive current at low voltage, and can be developed as a voltage and frequency support by replacing capacitors with batteries as energy storage. [6, 7] In this paper, the configuration and design of the UPQC-S are analyzed. It is connected in shunt or parallel and series to distribution system. It also is design to enhance the power quality such as voltage sags, harmonic distortion and low power factor in distribution system. II. FUNDAMENTALS OF PAC CONCEPT A UPQC is one of the most suitable devices to control the voltage sag/swell on the system. The rating of a UPQC is governed by the percentage of maximum amount of voltage sag/swell need to be compensated [19]. However, the voltage variation (sag/swell) is a short duration power quality issue. Therefore, under normal operating condition, the series inverter of UPQC is not utilized up to its true capacity. The concept of PAC of UPQC suggests that with proper control of the power angle between the source and load voltages, the load reactive power demand can be shared by both shunt and series inverters without 117 P a g e

2 affecting the overall UPQC rating [15]. The phasor representation of the PAC approach under a rated steady-state condition is shown in Fig. 1 [15]. According to this theory, a vector VSr with proper magnitude VSr and phase angle ϕsr when injected through series inverter gives a power angle δ boost between the source VS and resultant load V_L voltages maintaining the same voltage magnitudes. This power angle shift causes a relative phase advancement between the supply voltage and resultant load current I_L, denoted as angle β. In other words, with PAC approach, the series inverter supports the load reactive power demand and thus, reducing the reactive power demand shared by the shunt inverter. For a rated steady-state condition To compute the phase of _VS_r -7,8,9 Fig. 1 Detailed phasor diagram to estimate the series inverter parameters for the proposed UPQC- S approach under voltage sag condition The voltage fluctuation factor kf which is defined as the ratio of the difference of instantaneous supply voltage and rated load voltage magnitude to the rated load voltage magnitude is represented as Therefore, Let us define Equations (9) and (10) give the required magnitude and phase of series inverter voltage of UPQC-S that should be injected to achieve the voltage sag compensation while supporting the load reactive power under PAC approach A. Series Inverter Parameter Estimation under Voltage Sag: In this section, the required series inverter parameters to achieve simultaneous load reactive power and voltage sag compensations are computed. Fig. below shows the detailed phasor diagram to determine the magnitude and phase of series injection voltage. III. UPQC-S CONTROLLER A detailed controller for UPQC based on PAC approach is described in [15]. In this paper, the generation of reference signals for series inverter is discussed. Note that, as the series inverter maintains the load voltage at desired level, the reactive power demanded by the load remains unchanged (assuming load on the system is constant) irrespective of changes in the source voltage magnitude. Furthermore, the power angle δ is maintained at constant value under different operating conditions. Therefore, the reactive power shared by the series inverter and hence by the shunt inverter changes as given by (47) and (54). The reactive power shared by the series and shunt inverters can be fixed at constant values by allowing the power angle δ to vary under voltage sag/swell condition. A. Series controller: The control block diagram for series inverter operation is shown in Fig. below. The instantaneous power angle δ is determined using the procedure give in [15]. Based on the system 118 P a g e

3 rated specifications, the value of the desired load voltage is set as reference load voltage k. The instantaneous value of factors kf and n o is computed by measuring the peak value of the supply voltage in real time. The magnitudes of series injected voltage VSr and its phase angle ϕsr are then determined using (15) and (17). A phase locked loop is used to synchronize and to generate instantaneous time variable reference signals v Sr,a, v Sr,b, v Sr,c. The reference signals thus generated give the necessary series injection voltages that will share the load reactive power and compensate for voltage sag/swell as formulated using the proposed approach. The error signal of actual and reference series voltage is utilized to perform the switching operation of series inverter of UPQC-S. The control diagram for the shunt inverter is as given in Fig. 2 Series controller B.Shunt controller: On the other hand, the shunt converter of UPQC is used to filter the active and reactive power pulsations generated Thus, the power injected into the grid from t compensator set will be free from pulsations, which are the origin of voltage fluctuation that can propagate into the system. This task is achieved by appropriate electrical currents injection in PCC. Also, the regulation of the DC bus voltage has been assigned to this converter. Fig. below shows a block diagram of the shunt converter controller. This controller generates both voltages commands Ed shuc and Eq shuc based on power fluctuations _P and _Q, respectively. Such deviations are calculated subtracting the mean power from the instantaneous power measured in PCC. The mean values of active and reactive power are obtained by low pass filtering, and the bandwidth of such filters are chosen so that the power fluctuation components selected for compensation, fall into the flicker band as stated in IEC standard. In turn, Ed shuc also contains the control action for the DC bus voltage loop. This control loop will not interact with the fluctuating power compensation, because its components are lower in frequency than the flicker band. The powers PshuC and QshuC are calculated in the rotating reference frame, as follows: ,12 Ignoring PCC voltage variation, these equations can be written as follows Fig. 3 Shunt controller P a g e

4 Taking in consideration that the shunt converter is based on a VSI, we need to generate adequate voltages to obtain the currents in (6). This is achieved using the VSI model proposed in [10], leading to a linear relationship between the generated power and the controller voltages. The resultant equations are: P and Q control loops comprise proportional controllers, while DC bus loop, a fuzzy controller. In summary, in the proposed strategy the UPQC can be seen as a power buffer, leveling the power injected into the power system grid. The Fig. below illustrates a conceptual diagram of this mode of operation. It must be remarked that the absence of an external DC source in the UPQC bus, forces to maintain zero average power in the storage element installed in that bus. This is accomplished by a proper design of DC voltage controller. Also, it is necessary to note that the proposed strategy cannot be implemented using other CUPS devices like D Statcom or DVR. The power buffer concept may be implemented using a D-Statcom, but not using a DVR. On the other hand, voltage regulation during relatively large disturbances cannot be easily coped using reactive power only from D-Statcom; in this case, a DVR device is more suitable. reference voltage (ΔVref {k}) which is to be added to the previous value of reference voltage (Tref{k-1}). The output fuzzy sets have the same linguistic variables used for input except T is added to indicate the fuzzy sets are used for voltage. A look-up table, in which the relation between the input variables, Δω and Δώ, are defined and the output variable of the fuzzy logic controller was developed and used in the simulation. The look-up table is given in Table-1. The Maximum of Minimum method has been used to find the output fuzzy rules stage, as follow Table-1 IV. Fuzzy logic controller The FLC uses a set of fuzzy rules representing a control decision mechanism to adjust the effect of certain system stimuli. Therefore, the aim of using FLC is to replace a skilled human operator with a fuzzy rules-based system. The fuzzy input vectors are the change in DC voltage deviation ΔV and the voltage V. The fuzzy set for inputs and output membership functions are shown seven linguistic variables (LV) are used for each input variables. These are PL (Positive Large), PM (Positive Medium), PS (Positive Small), Z (Zero), NS (Negative Small), NM (Negative Medium) and NL (Negative Large). The fuzzy output is the change in Fig. 4 Surface viewer 120 P a g e

5 V. SIMULATION RESULTS The performance of the proposed concept of simultaneous load reactive power and voltage sag/swell compensation has been evaluated by simulation. To analyze the performance of UPQC-S, the source is assumed to be pure sinusoidal. Furthermore, for better visualization of results the load is considered as highly inductive. The supply voltage which is available at UPQC terminal is considered as three phase, 60 Hz, 600 V (line to line) with the maximum load power demand of 15 kw + j 15 kvar (load power factor angle of lagging). The simulation results for the proposed UPQC-S approach under voltage sag and swell conditions are given in below Fig. Before time t1, the UPQC-S system is working under steady state condition, compensating the load reactive power using both the inverters. A power angle δ of 21 is maintained between the resultant load and actual source voltages. The series inverter shares 1.96 kvar per phase (or 5.8 kvar out of 15 kvar) demanded by the load. Thus, the reactive power support from the shunt inverter is reduced from 15 to 9.2 kvar by utilizing system (sag last till time t = 0.7 s). Between the time period t = 0.7 s and t = 0.8 s, the system is again in the steady state. A swell of 10% is imposed on the system for a duration of t2 = s. The active and reactive power flows through the source, load, and UPQC are given in Fig. below. The distinct features of the proposed the concept of PAC. In other words, the shunt inverter rating is reduced by 20% of the total load kilovolt ampere rating. At time t1 = 0.6 s, a sag of 10% is introduced on the UPQC-S approach are outlined as follows. 1) From Fig 5. (a) And (b), the load voltage profile is maintained at a desired level irrespective of voltage sag (decrease) or swell (increase) in the source voltage magnitudes. Fig 5.c series inverter voltage Fig 5.d Vdc Fig 5.e power angle b/w Vs,Vl at ST Fig 5.f I s Fig 5.a source voltage with 10%sags & swells Fig 5.g load current Fig 5.b Load voltage 121 P a g e

6 Fig 5.h Source active and reactive power Fig 5.i series active power and reactive power Fig 5.j shunt active and reactive power VI. CONCLUSION In this paper, a new concept of controlling complex power (simultaneous active and reactive powers) through series inverter of UPQC is introduced and named as UPQC-S. The proposed concept of the UPQC-S approach is mathematically formulated and analyzed for voltage sag and swell conditions. The developed comprehensive equations for UPQC-S can be utilized to estimate the required series injection voltage and the shunt compensating current profiles (magnitude and phase angle), and the overall VA loading both under voltage sag and swell conditions. The simulation studies demonstrate the effectiveness of the proposed concept of simultaneous voltage sag/swell and load reactive power sharing feature of series & shunt part of UPQC-S with fuzzy logic controller. The significant advantages of UPQC-S over general UPQC applications are: 1) the multifunction ability of series inverter to compensate voltage variation (sag, swell, etc.) while supporting load reactive power; 2) better utilization of series inverter rating of UPQC; and 3) reduction in the shunt inverter rating due to the reactive power sharing by both the inverters. REFERENCES [1] Vinod Khadkikar, and Ambrish Chandra UPQC-S: A Novel Concept of Simultaneous VoltageSag/Swell and Load Reactive Power Compensations Utilizing Series Inverter of UPQC. [2] R. C. Dugan, M. F. McGranaghan, and H. W. Beaty, Electrical Power Systems Quality.. New York: McGraw-Hill, 1996, p [3] C. Sankaran, Power Quality. Boca Raton, FL: CRC Press, 2002, p [4] R. A. Walling, R. Saint, R. C. Dugan, J. Burke, and L. A. Kojovic, Summary of distributed resources impact on power delivery systems, IEEE Trans. Power Del., vol. 23, no. 3, pp , Jul [5] L. Gyugyi, Unified power-flow control concept for flexible AC transmission systems, IEE C Gene. Trans. Distr., vol. 139, no. 4, pp , Jul [6] N. G. Hingorani and L. Gyugyi, Understanding FACTS: Concepts and Technology of Flexible AC Transmission Systems. New York: IEEE Press, 2000, p [7] V. K. Sood, HVDC and FACTS Controllers Applications of Static Converters in Power Systems. Boston, MA: Kluwer, 2004, p Power Electron. vol. 13, no. 2, pp , Mar P a g e

TO CONTROL THE CHARACTERISTICS OF AC MOTOR USING FUZZY LOGIC CONTROLLER

TO CONTROL THE CHARACTERISTICS OF AC MOTOR USING FUZZY LOGIC CONTROLLER Sandeep Goyat 1, Dr.Meena Tushir 2 1 Electrical Department, Research Scholar JJT University, Rajasthan, (India). 2 Electrical Department,

COMPARISON OF THE FACTS EQUIPMENT OPERATION IN TRANSMISSION AND DISTRIBUTION SYSTEMS

COMPARISON OF THE FACTS EQUIPMENT OPERATION IN TRANSMISSION AND DISTRIBUTION SYSTEMS Afshin LASHKAR ARA Azad University of Dezfoul - Iran A_lashkarara@hotmail.com Seyed Ali NABAVI NIAKI University of Mazandaran

NEURO-FUZZY BASED POWER QUALITY IMPROVEMENTS IN A THREE PHASE FOUR WIRE DISTRIBUTION SYSTEM USING DSTATCOM

NEURO-FUZZY BASED POWER QUALITY IMPROVEMENTS IN A THREE PHASE FOUR WIRE DISTRIBUTION SYSTEM USING DSTATCOM E.Babu 1,R.Subramanian 2 1, Department of Electrical and electronics engg 2 Department of Electrical

IMPROVEMENT OF POWER QUALITY (PQ) BY UPQC (UNIFIED POWER QUALITY CONDITIONER) IN POWER SYSTEM USING ADAPTIVE NEURO FUZZY (ANFIS) TECHNIQUE

International Journal of Electrical Engineering & Technology (IJEET) Volume 7, Issue 2, March-April, 2016, pp.59 68, Article ID: IJEET_07_02_007 Available online at http:// http://www.iaeme.com/ijeet/issues.asp?jtype=ijeet&vtype=7&itype=2

Enhancement of load balancing for dynamic loads using D-STATCOM Priyanka Upadhyay 1, Baseem Khan 2 1,2 Electrical and Electronics Department, SCOPE College of Engineering Bhopal, M.P., India Abstract In

1733 P a g e. Keywords: PI, Fuzzy controller, DVR, Voltage sags, Voltage swells.

(IJERA) ISS: 2248-9622 www.ijera.com Mitigation Of Voltage Sags/Swells By Dynamic Voltage Restorer Using i And Fuzzy Logic Controller CH SRISAILAM 1,A SREEIVAS 2 Asst.rofessors, Department Of Electrical

Simulation of VSI-Fed Variable Speed Drive Using PI-Fuzzy based SVM-DTC Technique

Simulation of VSI-Fed Variable Speed Drive Using PI-Fuzzy based SVM-DTC Technique B.Hemanth Kumar 1, Dr.G.V.Marutheshwar 2 PG Student,EEE S.V. College of Engineering Tirupati Senior Professor,EEE dept.

The design and performance of Static Var Compensators for particle accelerators

CERN-ACC-2015-0104 Karsten.Kahle@cern.ch The design and performance of Static Var Compensators for particle accelerators Karsten Kahle, Francisco R. Blánquez, Charles-Mathieu Genton CERN, Geneva, Switzerland,

Three phase circuits

Three phase circuits THREE PHASE CIRCUITS THREE-PHASE ADVANTAGES 1. The horsepower rating of three-phase motors and the kva rating of three-phase transformers are 150% greater than single-phase motors

IJESRT. Scientific Journal Impact Factor: 3.449 (ISRA), Impact Factor: 2.114 [633] [Choudhary, 3(12): December, 2014] ISSN: 2277-9655

IJESRT INTERNATIONAL JOURNAL OF ENGINEERING SCIENCES & RESEARCH TECHNOLOGY Performance of Capacitor Supported SRF based DSTATCOM in Three-Phase Four-Wire Distribution System under Linear and Non-Linear

Design a Phase Interleaving PFC Buck Boost Converter to Improve the Power Factor

International Journal of Innovation and Scientific Research ISSN 2351-8014 Vol. 11 No. 2 Nov. 2014, pp. 445-449 2014 Innovative Space of Scientific Research Journals http://www.ijisr.issr-journals.org/

Harmonic Distortion of the AC Power Line

Introduction Adjustable frequency drives have become the standard method of control for heating, ventilating and air conditioning (HVAC) systems due to precise control and very significant energy savings.

PQ03. Using Test Equipment to Detect and Measure Power Quality Issues

PQ03 Using Test Equipment to Detect and Measure Power Quality Issues Power Quality Related Presentations: PQ01 Harmonic Solutions for VFD s PQ02 - Power Quality and Monitoring with isense/igrid/dysc &

Neutral Current compensation in three phase four wire DSTATCOM using Three Leg VSC and a Zig Zag Transformer

Neutral Current compensation in three phase four wire DSTATCOM using Three Leg VSC and a Zig Zag Transformer 1 Ramya A R, 2 T.M.Vasantha Kumar, 3 K.R.Mohan 1,2,3 Dept. of Electrical and Electronics Engineering

Rectifying Power Quality Problems Using a Static Compensator in Wind Energy System

Rectifying Power Quality Problems Using a Static Compensator in Wind Energy System G. Boaz M.Tech (Electrical Power Systems), Department of EEE, Balaji Institute of Technology and Science, Laknepally,

Role of Interline Power Flow Controller for Voltage Quality

International Journal of Advances in Electrical and Electronics Engineering 271 Available online at www.ijaeee.com ISSN: 2319-1112 Role of Interline Power Flow Controller for Voltage Quality Rajshekar

Implementation of A Novel Switch-Mode DC-To-AC Inverter with Non- Linear Robust Control Using MATLAB

Implementation of A Novel Switch-Mode DC-To-AC Inverter with Non- Linear Robust Control Using MATLAB Mr. Damodhar Reddy Asst.Prof K. PavanKumar Goud Asst.Prof K. Pradeep Kumar Reddy Asst.Prof Department

Simulation of wind power with front-end converter into interconnected grid system

Simulation of wind power with front-end converter into interconnected grid system Sharad W. Mohod 1 ; Mohan V. Aware 2 1 Meghe Institute of Technology & Research, Badnera-(INDIA); 2 Visvesvaraya National

Grid Interconnection of Renewable Energy Sources Using Modified One-Cycle Control Technique

Grid Interconnection of Renewable Energy Sources Using Modified One-Cycle Control Technique NKV.Sai Sunil 1, K.Vinod Kumar 2 PG Student, GITAM University, Visakhapatnam, India. Asst.Professor, Department

Harmonic Reduction and Load Balancing of Three Phase Four Wire DSTATCOM using Three Leg VSC and a Zig Zag Transformer

IJSRD - International Journal for Scientific Research & Development Vol. 3, Issue 05, 2015 ISSN (online): 2321-0613 Harmonic Reduction and Load Balancing of Three Phase Four Wire DSTATCOM using Three Leg

MODELING AND SIMULATION FOR VOLTAGE SAGS/SWELLS MITIGATION USING DYNAMIC VOLTAGE RESTORER (DVR)

MODELING AND SIMULATION FOR VOLTAGE SAGS/SWELLS MITIGATION USING DYNAMIC VOLTAGE RESTORER (DVR) 1 ROSLI OMAR, 2 NASRUDIN ABD RAHIM, 3 MARIZAN SULAIMAN 1 Rosli Omar.,Faculty Of Electrical, UTeM, Malacca,

Power Quality Issues in Railway Electrification

International Journal of Computer Sciences and Engineering Open Access Survey Paper Volume-4, Issue-1 E-ISSN: 2347-2693 Power Quality Issues in Railway Electrification Rajshree S Thorat 1*, M. M. Deshpande

SPEED CONTROL OF INDUCTION MACHINE WITH REDUCTION IN TORQUE RIPPLE USING ROBUST SPACE-VECTOR MODULATION DTC SCHEME

International Journal of Advanced Research in Engineering and Technology (IJARET) Volume 7, Issue 2, March-April 2016, pp. 78 90, Article ID: IJARET_07_02_008 Available online at http://www.iaeme.com/ijaret/issues.asp?jtype=ijaret&vtype=7&itype=2

DIRECT torque control (DTC) of induction motors has

76 IEEE POWER ELECTRONICS LETTERS, VOL. 3, NO. 2, JUNE 2005 Constant and High Switching Frequency Torque Controller DTC Drives C. L. Toh, N. R. N. Idris, Senior Member, IEEE, and A. H. M. Yatim, Senior

SABBATICAL REPORT. Submitted to. The Office of Provost. cc: The Improvement of Learning Committee. By Dr. X. Kou. Associate Professor

SABBATICAL REPORT Submitted to The Office of Provost cc: The Improvement of Learning Committee By Dr. X. Kou Associate Professor Electrical Engineering Department University of Wisconsin Platteville Sep.

II. PROBLEMS ASSOCIATED WITH ARC FURNACES

Electric Arc Furnace Flicker Mitigation in a Steel Plant Using a Statcom P.M.Sarma, Dr.S.V.Jayaram Kumar Professor in Electrical and Electronics Engineering, Gokaraju Rangaraju Institute of Engineering

Wave Shaping Of Current Using PWM Rectifiers

International Journal of Engineering and Technical Research (IJETR) Wave Shaping Of Current Using PWM Rectifiers Mahasweta Bhattacharya, Ashish Srivastava Abstract The paper presents the modeling and analysis

Voltage Stability Improvement using Static Var Compensator in Power Systems

Leonardo Journal of Sciences ISSN 1583-0233 Issue 14, January-June 2009 p. 167-172 Voltage Stability Improvement using Static Var Compensator in Power Systems Department of Electrical/Computer Engineering,

POWER QUALITY IMPROVEMENT USING AC- DC BOOST CONVERTER

Volume: 03 Issue: 12 Dec -2016 www.irjet.net p-issn: 2395-0072 POWER QUALITY IMPROVEMENT USING AC- DC BOOST CONVERTER Ankita A. Yeotikar 1, Swapnil B. Mohod 2 1PG Student, Electrical and Electronics Engg.,

An Experimental Study on Power Quality of Wind Turbines

An Experimental Study on Power Quality of Wind Turbines Joaquín Mur Ángel Antonio Bayod Roberto Zapata Samuel Ortiz Universidad de Zaragoza Dpto. Ingeniería Eléctrica CIRCE joako@posta.unizar.es Abstract

Mathematical Modeling and Dynamic Simulation of a Class of Drive Systems with Permanent Magnet Synchronous Motors

Applied and Computational Mechanics 3 (2009) 331 338 Mathematical Modeling and Dynamic Simulation of a Class of Drive Systems with Permanent Magnet Synchronous Motors M. Mikhov a, a Faculty of Automatics,

Chapter 12. RL Circuits. Objectives

Chapter 12 RL Circuits Objectives Describe the relationship between current and voltage in an RL circuit Determine impedance and phase angle in a series RL circuit Analyze a series RL circuit Determine

Fuzzy Logic based Reactive Power Control System in Radial Feeder

Fuzzy Logic based Reactive Power Control System in Radial Feeder Bijaya Lubanjar Pursuing B.E. Degree in Electrical Chandra Khatri Received B.E. Degree in Electrical Pradip Neupane Received B.E. Degree

Power Quality Analysis and Evaluation at Water Pumping Station Supplied by Medium Voltage

Power Quality Analysis and Evaluation at Water Pumping Station Supplied by Medium Voltage Mustafa SEKKELI 1,*, Süleyman EROL 2 1 Sutcu Imam University, Faculty of Engineering, Electrical and Electronics

CHAPTER 3 ANALYSIS OF SWITHCHED MODE PWM INVERTER

31 CHAPTER 3 ANALYSIS OF SWITHCHED MODE PWM INVERTER 3.1 INTRODUCTION Fixed DC power can be converted into AC power at desired output voltage and frequency by using a power electronics circuit, called

Power Quality & Custom Power

Day-3 Power Quality & Custom Power Arindam Ghosh Dept. of Electrical Engineering Indian Institute of Technology Kanpur,, India E-mail: aghosh@iitk iitk.ac.in Power Quality (PQ) The term electric power

Chapt ha e pt r e r 12 RL Circuits

Chapter 12 RL Circuits Sinusoidal Response of RL Circuits The inductor voltage leads the source voltage Inductance causes a phase shift between voltage and current that depends on the relative values of

Part IV Modern Rectifiers and Power System Harmonics

Part IV Modern Rectifiers and Power System Harmonics Chapter 15 Chapter 16 Chapter 17 Chapter 18 Power and Harmonics in Nonsinusoidal Systems Line-Commutated Rectifiers The Ideal Rectifier Low Harmonic

Sajith Shaik *, I.Raghavendar **

Power Quality Improvement Of Three Phase Four Wire Distribution System Using VSC With A Zig-Zag Transformer Sajith Shaik *, I.Raghavendar ** *(Department of Electrical Engineering, Teegala Krishna Reddy

A MULTILEVEL INVERTER FOR SYNCHRONIZING THE GRID WITH RENEWABLE ENERGY SOURCES BY IMPLEMENTING BATTERY CUM DC-DC CONERTER

A MULTILEVEL INVERTER FOR SYNCHRONIZING THE GRID WITH RENEWABLE ENERGY SOURCES BY IMPLEMENTING BATTERY CUM DC-DC CONERTER 1 KARUNYA CHRISTOBAL LYDIA. S, 2 SHANMUGASUNDARI. A, 3 ANANDHI.Y 1,2,3 Electrical

A Low Cost Power Quality and Energy Savings Laboratory for Undergraduate Education and Research

Session #3133 A Low Cost Power Quality and Energy Savings Laboratory for Undergraduate Education and Research Abdullatif Bagegni, Vance Poteat Merrimack College Abstract This paper describes the design

Transient analysis of integrated solar/diesel hybrid power system using MATLAB Simulink

Transient analysis of integrated solar/diesel hybrid power system using ATLAB Simulink Takyin Taky Chan School of Electrical Engineering Victoria University PO Box 14428 C, elbourne 81, Australia. Taky.Chan@vu.edu.au

Renewable Energy Interconnection at Distribution Level to Improve Power Quality

Research Inventy: International Journal Of Engineering And Science Issn: 2278-4721, Vol. 2, Issue 5 (February 2013), Pp 39-48 Www.Researchinventy.Com Renewable Energy Interconnection at Distribution Level

Manjari Mehrotra, Dr. A.K Pandey

ISO 91:28 Certified Volume 2, Issue 5, November 212 Harmonics Analysis of VSI Fed Induction Motor Drive Abstract- This paper mainly focus on harmonics analysis of three phase AC supply available from three

A Hybrid Multilevel Converter for Medium and High Voltage Applications

A Hybrid Multilevel Converter for Medium and High Voltage Applications G.P. Adam, K.H. Ahmed,.K. Singh *, S.J. Finney and B.W. Williams University of Strathclyde, Glasgow, UK Email: grain.adam@eee.strath.ac.uk,

HARMONICS ISSUES THAT LIMIT SOLAR PHOTOVOLTAIC GENERATION ON DISTRIBUTION CIRCUITS

HARMONICS ISSUES THAT LIMIT SOLAR PHOTOVOLTAIC GENERATION ON DISTRIBUTION CIRCUITS Ketut Dartawan Pterra Consulting, LLC 4 Automation Lane, Ste 250 Albany, NY 12205 USA Email: ketutdartawan@pterra.us Le

DEVELOPMENT OF ON-LINE SINGLE PHASE UNINTERRUPTIBLE POWER SUPPLY (UPS) FOR LOW POWER APPLICATION

International Seminar on the Application of Science & Mathematics 2011 ISASM 2011 DEVELOPMENT OF ON-LINE SINGLE PHASE UNINTERRUPTIBLE POWER SUPPLY (UPS) FOR LOW POWER APPLICATION Asmarashid Ponniran 1,

EE 221 AC Circuit Power Analysis. Instantaneous and average power RMS value Apparent power and power factor Complex power

EE 1 AC Circuit Power Analysis Instantaneous and average power RMS value Apparent power and power factor Complex power Instantaneous Power Product of time-domain voltage and time-domain current p(t) =

ELECTRICAL ENGINEERING Vol. I - Direct Current and Alternating Current Systems - N. Rajkumar DIRECT CURRENT AND ALTERNATING CURRENT SYSTEMS

DIRECT CURRENT AND ALTERNATING CURRENT SYSTEMS N. Rajkumar, Research Fellow, Energy Systems Group, City University Northampton Square, London EC1V 0HB, UK Keywords: Electrical energy, direct current, alternating

EN 206: Power Electronics and Machines

EN 206: Power Electronics and Machines Inverters Suryanarayana Doolla Department of Energy Science and Engineering Indian Institute of Technology Bombay email: suryad@iitb.ac.in March 15, 2013 Prof. Doolla

Harmonics and Noise in Photovoltaic (PV) Inverter and the Mitigation Strategies

Soonwook Hong, Ph. D. Michael Zuercher Martinson Harmonics and Noise in Photovoltaic (PV) Inverter and the Mitigation Strategies 1. Introduction PV inverters use semiconductor devices to transform the

Applications of Multilevel Inverter in Grid Connected PMSG Based Wind Power Generation System

International Journal of Electronic and Electrical Engineering. ISSN 0974-2174 Volume 7, Number 8 (2014), pp. 867-872 International Research Publication House http://www.irphouse.com Applications of Multilevel

Power Quality Analysis and Evaluation at Water Pumping Station Supplied by Medium Voltage

Power Quality Analysis and Evaluation at Water Pumping Station Supplied by Medium Voltage *1 Mustafa SEKKEL, 2 Süleyman EROL 1 Sutcu mam University, Faculty of Engineering, Electrical and Electronics Depart.,

Product Data Bulletin

Product Data Bulletin Power System Harmonics Causes and Effects of Variable Frequency Drives Relative to the IEEE 519-1992 Standard Raleigh, NC, U.S.A. INTRODUCTION This document describes power system

Designing of Phase Angle control and ON-OFF Triggering circuit for SVC reactive Power Compensator.

International Conference on Electrical, Electronics, and Optimization Techniques (ICEEOT) - 2016 Designing of Phase Angle control and ON-OFF Triggering circuit for SVC reactive Power Compensator. Mohammed

Eðlisfræði 2, vor 2007

[ Assignment View ] [ Pri Eðlisfræði 2, vor 2007 31. Alternating Current Circuits Assignment is due at 2:00am on Wednesday, March 21, 2007 Credit for problems submitted late will decrease to 0% after the

The Grid Interconnection of Renewable Energy at Distribution Level with the Features of High Power-Quality Improvement

The Grid Interconnection of Renewable Energy at Distribution Level with the Features of High Power-Quality Improvement Surendar Nagarapu 1, Shaik Khamuruddin 2, and Durgam. Kumara Swamy 3 1 M.Tech, Scholar

DEVELOPMENT OF THE SIGNAL GENERATOR APPLIED TO TESTING OF INSTRUMENTS FOR ELECTRICAL POWER QUALITY MEASUREMENT

FACTA UNIVERSITATIS Ser: Elec. Energ. Vol. 25, N o 3, December 2012, pp. 193-201 DOI: 10.2298/FUEE1203193S DEVELOPMENT OF THE SIGNAL GENERATOR APPLIED TO TESTING OF INSTRUMENTS FOR ELECTRICAL POWER QUALITY

Control Strategy for Three Phase Shunt Active Power Filter with Minimum Current Measurements

International Journal of Electrical and Computer Engineering (IJECE) Vol.1, No.1, September 2011, pp. 31~ 42 ISSN: 2088-8708 31 Control Strategy for Three Phase Shunt Active Power Filter with Minimum Current

TSTE19 Power Electronics

TSTE19 Power Electronics Lecture 7 Tomas Jonsson ISY/EKS 2015-11-24 2 Outline DC-AC switching inverters Switch-mode principle Single-phase inverter PWM switching Current ripple and commutation 2015-11-24

Modified Cascaded Five Level Multilevel Inverter Using Hybrid Pulse Width Modulation

International Journal of Computer Sciences and Engineering Open Access Research Paper Volume-4, Special Issue-2, April 2016 E-ISSN: 2347-2693 Modified Cascaded Five Level Multilevel Inverter Using Hybrid

EDEXCEL NATIONAL CERTIFICATE/DIPLOMA UNIT 5 - ELECTRICAL AND ELECTRONIC PRINCIPLES NQF LEVEL 3 OUTCOME 4 - ALTERNATING CURRENT

EDEXCEL NATIONAL CERTIFICATE/DIPLOMA UNIT 5 - ELECTRICAL AND ELECTRONIC PRINCIPLES NQF LEVEL 3 OUTCOME 4 - ALTERNATING CURRENT 4 Understand single-phase alternating current (ac) theory Single phase AC

KEYWORDS: Direct torque control (DTC), Induction motor (IM), Inverter.

The International Journal Of Engineering And Science (IJES) ISSN (e): 9 8 ISSN (p): 9 8 Pages - Direct Torque Controlled Four-Quadrant Induction Motor Drive, Dayakar Reddy B,, Chandra Sheker V, Department

New Pulse Width Modulation Technique for Three Phase Induction Motor Drive Umesha K L, Sri Harsha J, Capt. L. Sanjeev Kumar

New Pulse Width Modulation Technique for Three Phase Induction Motor Drive Umesha K L, Sri Harsha J, Capt. L. Sanjeev Kumar Abstract In this paper, various types of speed control methods for the three

Modeling and Simulation of a Novel Switched Reluctance Motor Drive System with Power Factor Improvement

American Journal of Applied Sciences 3 (1): 1649-1654, 2006 ISSN 1546-9239 2006 Science Publications Modeling and Simulation of a Novel Switched Reluctance Motor Drive System with Power Factor Improvement

HARMONIC DISTORTION IN THE ELECTRIC SUPPLY SYSTEM

Technical Note No.3 March 2000 HARMONIC DISTORTION IN THE ELECTRIC SUPPLY SYSTEM This Technical Note discusses harmonic distortion, its causes and adverse effects, what levels are unacceptable and how

POWER SYSTEM HARMONICS. A Reference Guide to Causes, Effects and Corrective Measures AN ALLEN-BRADLEY SERIES OF ISSUES AND ANSWERS

A Reference Guide to Causes, Effects and Corrective Measures AN ALLEN-BRADLEY SERIES OF ISSUES AND ANSWERS By: Robert G. Ellis, P. Eng., Rockwell Automation Medium Voltage Business CONTENTS INTRODUCTION...

Ripple Control in AC to DC Converter

IOSR Journal of Engineering (IOSRJEN) e-issn: 22-321, p-issn: 2278-8719 Vol. 3, Issue 1 (Jan. 213), V5 PP 26-3 Ripple Control in AC to DC Converter Sudeep Pyakuryal 1, Mohammad Matin 3 Department of Electrical

International ejournals

ISSN 2249 5460 Available online at www.internationalejournals.com International ejournals International Journal of Mathematical Sciences, Technology and Humanities 113 (2014) 1221 1227 NEUTRAL CURRENT

SYNCHRONOUS MACHINES

SYNCHRONOUS MACHINES The geometry of a synchronous machine is quite similar to that of the induction machine. The stator core and windings of a three-phase synchronous machine are practically identical

A Review on Basic Concepts and Important Standards of Power Quality in Power System

A Review on Basic Concepts and Important Standards of Power Quality in Power System M. Ramachandran Renganayagi Varatharaj College of Engineering, Sivakasi, India A. Mariya Chithra Mary M. Muthukumaran

Voltage Regulation by Distributed Generation

Voltage Regulation by Distributed Generation Supported by the NSW Government Energy Efficiency Training Program Kashem Muttaqi Overview Understanding the concept of voltage regulation by a DG system Method

615xx, 616xx, 617xxx, 646x, 64xx, 65xx Series Programmable AC source

Chroma Systems Solutions, Inc. AC Power Definitions 615xx, 616xx, 617xxx, 646x, 64xx, 65xx Series Programmable AC source Keywords: Peak, RMS, Phase, Inrush Current, Power Factor, Crest Factor, Apparent

Line Reactors and AC Drives

Line Reactors and AC Drives Rockwell Automation Mequon Wisconsin Quite often, line and load reactors are installed on AC drives without a solid understanding of why or what the positive and negative consequences

Design and Analysis of Switched Reluctance Motors

Design and Analysis of Switched Reluctance Motors İbrahim ŞENGÖR, Abdullah POLAT, and Lale T. ERGENE Electrical and Electronic Faculty, İstanbul Technical University, 34469, Istanbul, TURKEY sengoribrahim@gmail.com,

MULTI PULSE RECTIFIER USING DIFFERENT PHASE SHIFTING TRANSFORMERS AND ITS THD COMPARISON FOR POWER QUALITY ISSUES

MULTI PULSE RECTIFIER USING DIFFERENT PHASE SHIFTING TRANSFORMERS AND ITS THD COMPARISON FOR POWER QUALITY ISSUES Komal Gamit 1, Khushbu Chaudhari 2 1 Assistant Professor, Electrical Engineering Department,

Measurement & Analysis of Harmonics & Flicker Part 1: Harmonics Mandatory Requirements and Premises

Measurement & Analysis of Harmonics & Flicker Part 1: Harmonics Mandatory Requirements and Premises Tom Moyer Amplifier Research tmoyer@amplifiers.com 1. Origin and Effects 1.1 Definition: HARMONICS Harmonics

Fundamentals of Power Electronics. Robert W. Erickson University of Colorado, Boulder

Robert W. Erickson University of Colorado, Boulder 1 1.1. Introduction to power processing 1.2. Some applications of power electronics 1.3. Elements of power electronics Summary of the course 2 1.1 Introduction

INDUCTION MOTOR PERFORMANCE TESTING WITH AN INVERTER POWER SUPPLY, PART 2

INDUCTION MOTOR PERFORMANCE TESTING WITH AN INVERTER POWER SUPPLY, PART 2 By: R.C. Zowarka T.J. Hotz J.R. Uglum H.E. Jordan 13th Electromagnetic Launch Technology Symposium, Potsdam (Berlin), Germany,

UNDERSTANDING POWER FACTOR AND INPUT CURRENT HARMONICS IN SWITCHED MODE POWER SUPPLIES

UNDERSTANDING POWER FACTOR AND INPUT CURRENT HARMONICS IN SWITCHED MODE POWER SUPPLIES WHITE PAPER: TW0062 36 Newburgh Road Hackettstown, NJ 07840 Feb 2009 Alan Gobbi About the Author Alan Gobbi Alan Gobbi

Smart Grid and Renewable Energy Grid Integration. Jian Sun, Professor and Director Department of ECSE & Center for Future Energy Systems

Smart Grid and Renewable Energy Grid Integration Jian Sun, Professor and Director Department of ECSE & Center for Future Energy Systems 1 How Smart Can We Make This Grid? 2 Smart Grid Drivers Need to Use

Direct Torque Control of Brushless DC Motor Using PI and FuzzyController

Direct Torque Control of Brushless DC Motor Using PI and FuzzyController D.Premalatha M.E Power Electronics and Drives(II Year) PA College of Engineering and Technology, Pollachi,Tamil Nadu,India Abstract

USE OF ARNO CONVERTER AND MOTOR-GENERATOR SET TO CONVERT A SINGLE-PHASE AC SUPPLY TO A THREE-PHASE AC FOR CONTROLLING THE SPEED OF A THREE-PHASE INDUCTION MOTOR BY USING A THREE-PHASE TO THREE-PHASE CYCLOCONVERTER

International Journal of Electrical Engineering & Technology (IJEET) Volume 7, Issue 2, March-April, 2016, pp.19-28, Article ID: IJEET_07_02_003 Available online at http:// http://www.iaeme.com/ijeet/issues.asp?jtype=ijeet&vtype=7&itype=2

A COMPARISON ON PERFORMANCE OF TCSC/SSSC FOR A RADIAL SYSTEM

IMPACT: International Journal of Research in Engineering & Technology (IMPACT: IJRET) ISSN(E): 31-8843; ISSN(P): 347-4599 Vol. 3, Issue 9, Sep 015, 7-18 Impact Journals A COMPARISON ON PERFORMANCE OF TCSC/SSSC

Keywords: Fuel Cell, Inverter, PWM, Converter, Parallel, Series. II. SYSTEM DESCRIPTION A. Operation and Topology

Low Cost, High Efficiency Converter for Solid Oxide Fuel Cell Residential Application Afshin Izadian and Parviz Famouri Lane Department of Computer Science and Electrical Engineering, West Virginia University,

Power Quality Standards for Electric Service

Power Quality Standards for Electric Service Effective June 1, 2008 A transition period will exist from June 1 through December 31, 2008 in which installations may be approved and connected as long as

Transformerless UPS systems and the 9900 By: John Steele, EIT Engineering Manager

Transformerless UPS systems and the 9900 By: John Steele, EIT Engineering Manager Introduction There is a growing trend in the UPS industry to create a highly efficient, more lightweight and smaller UPS

Power Quality Issues, Impacts, and Mitigation for Industrial Customers

Power Quality Issues, Impacts, and Mitigation for Industrial Customers By Kevin Olikara, Power and Energy Management Products Rockwell Automation, Inc. Now, more than ever, electronic equipment and computing

Power Quality Centre VOLTAGE FLUCTUATIONS IN THE ELECTRIC SUPPLY SYSTEM. Technical Note No. 7 August 2003

Technical Note No. 7 August 2003 Power Quality Centre VOLTAGE FLUCTUATIONS IN THE ELECTRIC SUPPLY SYSTEM This Technical Note discusses voltage fluctuations, their causes and adverse effects, what levels

Agilent 6800 Series ac Power Source/Analyzers

Agilent 6800 Series ac Power Source/Analyzers Product Note Testing Uninterruptible Power Supplies Using Agilent 6800 Series ac Power Source/Analyzers Includes Dual Power Analyzer option discussion Ensuring

7-41 POWER FACTOR CORRECTION

POWER FTOR CORRECTION INTRODUCTION Modern electronic equipment can create noise that will cause problems with other equipment on the same supply system. To reduce system disturbances it is therefore essential

QA Quality Assurance Reactive Power Primer In this article, I provide an overview of the three types of electrical power in ac circuits: real power, reactive power and apparent power. I also explain how

Chapter 3 AUTOMATIC VOLTAGE CONTROL

Chapter 3 AUTOMATIC VOLTAGE CONTROL . INTRODUCTION TO EXCITATION SYSTEM The basic function of an excitation system is to provide necessary direct current to the field winding of the synchronous generator.

Performance Enhancement of Wound Rotor Induction Motor by VSI with Dynamic Capacitor Controlled Rotor Circuit

Performance Enhancement of Wound Rotor Induction Motor by VSI with Dynamic Capacitor Controlled Rotor Circuit K.Ranjith kumar kumar, Dr.S.Palaniswami K.Priyadharsini, Senior Senior Lecturer Lecturer Professor

98% Efficient Single-Stage AC/DC Converter Topologies

16 POWER CONVERTERS www.teslaco.com 98% Efficient Single-Stage AC/DC Converter Topologies A new Hybrid Switching Method is introduced in this article which for the first time makes possible AC/DC power

DSP based Space Vector Pulse Width Modulation (SVPWM) control for AC Motor Drives

Session 360 DSP based Space Vector Pulse Width Modulation (SVPWM) control for AC Motor Drives Wajiha Shireen, Rahul. A. Kulkarni Universit of Houston I. Abstract: Space Vector Pulse Width Modulation (SVPWM)

Power Quality. Methods for Mitigating Voltage Sag Impact on Variable-Frequency Drives

Power Quality Methods for Mitigating Voltage Sag Impact on Variable-Frequency Drives Background Thanks to the precise controllability of motor speed and to the energy savings potentials, applications of