Heat Exchangers. Heat Exchanger Types. Heat Exchanger Types. Applied Heat Transfer Part Two. Topics of This chapter


 Abraham Thornton
 2 years ago
 Views:
Transcription
1 Applied Heat Transfer Part Two Heat Excangers Dr. Amad RAMAZANI S.A. Associate Professor Sarif University of Tecnology انتقال حرارت کاربردی احمد رمضانی سعادت ا بادی Autumn, 1385 (2006) Ramazani, Heat Excangers 1 Topics of Tis capter Introduction of Heat Excangers (HEXs) Te Overall Heat Transfer Coefficient Fouling Factor Types of Heat Excangers Te Log Mean Temperature Difference (LMTD) Metod Effectivenessnumber eat transfer unit (NTU) Metod Effectiveness and Heat Transfer Rate Compact Heat Excangers Analysis for Variable Properties Heat Excanger design Consideration Ramazani, Heat Excangers 2 Heat Excanger Types Wat is a eat excanger? An equipment tat permits to transfer eat from a ot fluid to a cold one witout any direct contact of fluids Heat excangers, can be seen in quotidian life, as well as different industries. Heat Excanger Types Heat Excanger can be categorized according to Flow arrangement and Type of Construction Parallel flow (fig. a) and Counterflow (fig. b) in concentric tubes (doublepipe) Almost all Cemical And Petrocemical Plants, Air Conditioning Systems, Power production, Waste Heat recovery, Automobile Radiator, Central Heating System Radiator, Electronic Parts,. Ramazani, Heat Excangers 3 Concentric Tubes: a) parallel flow; b) Counter flow Ramazani, Heat Excangers 4
2 Heat Excanger Types (Con.) Finned and unfinned tubular eat excanger wit cross flow Heat Excanger Types (Con.) Sellandtube eat excanger wit one sell pass and one tube pass (Cross counter flow mode of operation) Cross flow eat excangers a) finned; b) unfinned Ramazani, Heat Excangers 5 Ramazani, Heat Excangers 6 Heat Excanger Types (Con.) Heat Excanger Types (Con.) Oter types of Sellandtube eat excanger One sell pass and two tube passes Two sell passes and four tube passes Ramazani, Heat Excangers 7 Ramazani, Heat Excangers 8
3 Heat Excanger Types (Con.) Heat Excanger Types (Con.) Ramazani, Heat Excangers 9 Ramazani, Heat Excangers 10 Heat Excanger Types (Con.) Compact eat excanger cores Heat Excanger Types (Con.) Core of a plate Compact eat excanger wit counter flow from Aluminum, AKG America Corp. Ramazani, Heat Excangers 11 Ramazani, Heat Excangers 12
4 Heat Excanger Types (Con.) Heat Excanger wit fins on Surface, General Motors Corp., Lockport, NY Heat Excanger Types (Con.) Heat excanger wit fins Ramazani, Heat Excangers 13 Ramazani, Heat Excangers 14 Heat Excanger Types (Con.) Fins deposited on tubes internal surface for increasing eat transfer Heat Excanger Types (Con.) Heat transfer area density (m 2 /m3) for different types of eat excangers Ramazani, Heat Excangers 15 Ramazani, Heat Excangers 16
5 Te Overall Heat Transfer Coefficient Te Overall eat transfer coefficient for walls Te Overall Heat Transfer Coefficient (con.) Te Overall eat transfer coefficient for Dublepipe (HEXs) (U can be determined from Total Termal resistance to eat transfer between two fluid) Ramazani, Heat Excangers 17 Ramazani, Heat Excangers 18 Te Overall Heat Transfer Coefficient (Con.) Table Approximate Values of Overall Heattransfer Coefficient Ramazani, Heat Excangers 19 Te Overall Heat Transfer Coefficient, Example 1. EXAMPLE OVERALL HEAT.TRANSFER COEFFICIENT FOR PIPE IN AIR. Hot water at 98 C flows troug a 2in scedule 40 orizontal steel pipe [k = 54 W/m. o C] and is exposed to atmosperic air at 20 C. Te water velocity is 25 cm/s. Calculate te overall eattransfer coefficient (U) for tis situation, based on te outer area of pipe. Solution. From Appendix A (P. 653) te dimensions of 2in scedule 40 pipe are ID = in = m OD = in = m Te eattransfer coefficient for te water flow on te inside of te pipe is determined from te flow conditions wit properties evaluated at te bulk temperature. Te freeconvection eattransfer coefficient on te outside of te pipe depends on te temperature difference between te surface and ambient air. Tis temperature difference depends on te overall energy balance. First, we evaluate i and ten formulate an iterative procedure to determine o. Te properties of water at 98 o C are p = 960 kg/m3 µ = 2.82*10^4 kg/m.s k = 0.68 W/m. o C Pr = 1.76 Ramazani, Heat Excangers 20
6 Te Overall Heat Transfer Coefficient, Example 1. (Con.) Te Overall Heat Transfer Coefficient, Example 1. (Con.) Te Reynolds number is ρud (960)(0.25)(0.025) Re = = = µ and since turbulent flow is encountered, we may use Eq. (64) For unit lengt of te pipe te termal resistance of te steel is Ramazani, Heat Excangers 21 Ramazani, Heat Excangers 22 Te Overall Heat Transfer Coefficient, Example 1. (Con.) Te Overall Heat Transfer Coefficient, Example 2. EXAMPLE OVERALL HEATTRANSFER COEFFICIENT FOR PIPE IN STEAM. Te pipe and otwater system of Example 101 is exposed to steam at 1 atm and 100 o C. Calculate te overall eattransfer coefficient for tis situation based on te outer area of pipe. Solution. We ave already determined te inside convection eattransfer coefficient in Example 10.1 as i = 1961 W/m 2. o C Te convection coefficient for condensation on te outside of te pipe is obtained by using Eq. (912), were T o is te outside pipesurface temperature. Te water film properties are, Ramazani, Heat Excangers 23 Ramazani, Heat Excangers 24
7 Te Overall Heat Transfer Coefficient, Example 2. Te Overall Heat Transfer Coefficient, Example 2 (Con). Ramazani, Heat Excangers 25 Ramazani, Heat Excangers 26 Te Overall Heat Transfer Coefficient, Example 2 (Con). Ramazani, Heat Excangers 27 Te Overall Heat Transfer Coefficient (Fouling Factor) After a period of operation, eat transfer surfaces of HEXs may become Coated wit various deposits present in te flow systems Corroded Or, in general, deteriorated because of use Resulting in decreased performance because of additional resistance(s) to eat flow Te overall effect of tis deterioration is represented by a Fouling Factor R f R f 1 = U dirty 1 U clean Ramazani, Heat Excangers 28
8 Te Overall Heat Transfer Coefficient (Fouling Factor Con.) Te Overall Heat Transfer Coefficient Example 3. (Fouling Factor Con.) From previous example clean = 1961 W/m 2. o C and so from above equation we can obtain i Ramazani, Heat Excangers 29 Ramazani, Heat Excangers 30 Liquid Temperature Profile in Counterflow HEXs Liquid Temperature profile in a Counterflow double pipe HEXs (Oil is ot fluid in tube and water is cold one in sell) Liquid Temperature Profile in Crossflow HEXs Fluid Temperature profile in a Crossflow Heat Excangers (Steam is ot fluid and water is te cold one, Steam condense on te tube at a constant temperature) Ramazani, Heat Excangers 31 Ramazani, Heat Excangers 32
9 Te Log Mean Temperature Difference (LMTD) Metod Fluid Temperature Profile in Double Pipe Heat Excangers Te Log Mean Temperature Difference (LMTD) Calculation Parallel Flow Counter Flow Heat balance on an element of HEX Q = UA T m T = Suitable mean temperature difference across HEX m Ramazani, Heat Excangers 33 Mixing two above relations Ramazani, Heat Excangers 34 Te Log Mean Temperature Difference (LMTD) Calculation (Con.) Te Log Mean Temperature Difference (LMTD) Calculation (Con.) Heat excanges at lengt an element of HEXs Putting values of m C and m c C c in relation obtained for ln of temperatures differences Ramazani, Heat Excangers 35 Ramazani, Heat Excangers 36
10 Correction Factors for LMTD Metod Correction Factors for LMTD Metod (Con.) Fig Correction Factor for HEX wit one Sell and two, four, or any multiple of tube passes Ramazani, Heat Excangers 37 Fig Correction Factor for HEX wit Two Sell and four, eigt, or any multiple of tube passes Ramazani, Heat Excangers 38 Correction Factors for LMTD Metod (Con.) Correction Factors for LMTD Metod (Con.) Fig Correction Factor for Singlepass Crossflow Ramazani, Heat Excangers 39 HEXs, bot fluid unmixed Fig Correction Factor for Single pass Crossflow Ramazani, Heat Excangers 40 HEXs, one fluid mixed, te oter unmixed
11 Use of te LMTD for calculation excanger performance. EXAMPLE CALCULATION OF HEAT EXCHANGER SIZE FROM KNOWN TEMPERATURE. Water at te rate of 68 kg/min is eated from 35 to 75 O C by an oil aving a specific eat of 1.9 kj/kg. o C. Te fluids are used in counterflow double pipe eat excanger, and te oil enters te excanger at 110 o C and leaves at 75 o C. Te overall eattransfer coefficient is 320 W/m 2. o C. Calculate te eat excanger area. Solution. Te total eat transfer is determined from te energy absorbed by te water Use of te LMTD metod for calculation excanger performance. (Con.) Since all te fluid temperatures are known, te LMTD can be calculated by using te temperature sceme in Fig. 107b: Ramazani, Heat Excangers 41 Ramazani, Heat Excangers 42 Use of te LMTD for calculation HEXs performance. (Con.) Use of te LMTD for calculation excanger performance. (Con.) So, Using Fig Correction factor is F=0.81 Ramazani, Heat Excangers 43 Ramazani, Heat Excangers 44
12 Use of te LMTD for calculation excanger performance. Example Design of Sell and tube HEXs: Water at te rate of 30000lbm/ [3.783 kg/s] is eated from 100 to 130 o F [37.78 to C] in a selland tube eat excanger. On te sell side one pass is used wit water as te eating fluid, 15,000 1b. m [1.892 kg/s], entering te excanger at 200 o F [93.33 o C]. Te overall eattransfer coefficient is 250 Btu/. ft 2. o F [1419 W/m 2. o C], and te average water velocity in te 3/4in [1.905cm] diameter tubes is 1.2 ft/s[ m/s]. Because of space limitations te tube lengt must not be longer tan 8 ft [2.438 m]. Calculate te number of tubes per passes, and te lengt of te tubes. consistent wit tis restriction. Solution: We first assume one tube pass and ceck to see if it satisfies te conditions of tis problem. Te exit temperature of te ot water is calculated from q = m& C T T c c c = m& C T T (30000 )(1)( ) = (15000 )(1) = 60 m& ccc T = m& C o O Ramazani, Heat Excangers 45 F = C Use of te LMTD for calculation excanger performance. (Con.) Ramazani, Heat Excangers 46 Use of te LMTD for calculation excanger performance. (Con.) Use of te LMTD for calculation excanger performance. (Con.) Ramazani, Heat Excangers 47 Ramazani, Heat Excangers 48
13 EffectivenessNTU Metod EffectivenessNTU Metod (Con.) Energy balance for a) parallel flow b) Counterflow Selltube HEXs Ramazani, Heat Excangers 49 Ramazani, Heat Excangers 50 EffectivenessNTU Metod (Con.) EffectivenessNTU Metod (Con.) Ramazani, Heat Excangers 51 Ramazani, Heat Excangers 52
14 EffectivenessNTU Metod (Con.) EffectivenessNTU Metod (Con.) Ramazani, Heat Excangers 53 Ramazani, Heat Excangers 54 EffectivenessNTU Metod (Con.) EffectivenessNTU Metod (Con.) Ramazani, Heat Excangers 55 Ramazani, Heat Excangers 56
15 EffectivenessNTU Metod (Con.) EffectivenessNTU Metod (Con.) Ramazani, Heat Excangers 57 Ramazani, Heat Excangers 58 EffectivenessNTU Metod (Con.) EffectivenessNTU Metod (Con.) Ramazani, Heat Excangers 59 Ramazani, Heat Excangers 60
16 EffectivenessNTU Metod (Con.) Example: Application of EffectivenessNTU Metod P. 578 P. 573 Ramazani, Heat Excangers 61 Ramazani, Heat Excangers 62 Example: Application of EffectivenessNTU Metod (Con.) Example: Application of EffectivenessNTU Metod (Con.) Effectiveness can be calculated using Eq , P.573, to be Ramazani, Heat Excangers 63 Ramazani, Heat Excangers 64
17 Example: Application of EffectivenessNTU Metod Example: Application of EffectivenessNTU Metod (Con.) Fig Te eat transfer is ten q = m& C T = (2.887 )(1006 )(29.44 c c c = kw [ Btu/] 15.55) Ramazani, Heat Excangers 65 Ramazani, Heat Excangers 66 Example: Application of EffectivenessNTU Metod (Con.) Example: Application of EffectivenessNTU Metod (Con.) We sould assume values for te water flow rate until we could matc te performance of HEX according to Fig or table Te selected iterations to approac to correct values are as follow: Fig ; and q = m& C T Ramazani, Heat Excangers 67 q= We tus estimate te water o m& C = 645 W/ C T and Te w, exit 645 m& = = kg/s [1221 lb /] m 4180 exit water temperatu re is accordingl y = flow = rate O Ramazani, Heat Excangers 68 C as about
18 Boilers and Condenser (HEXs) Compact Heat Excangers Ramazani, Heat Excangers 69 Tese eat excangers are best for gases and low cases Ramazani, Heat Excangers 70 Compact Heat Excangers Compact Heat Excangers For tese types of eat excangers driving matematical relation can be difficult, owever some correlation are presented to able us to calculate eat transfer and Pressure drop values for tem. Tese correlations are based on Stanton and Reynolds dimensionless numbers Wic are written based on te mass velocities in te minimum flow crosssectional area and ydraulic diameter stated in Mass Velocity f is friction inside te tubes and v 1 and v 2 are specific volume at entrance and exit and v m is its average at HEXs Ratio of te freeflow = area to frontal area Ramazani, Heat Excangers 71 Ramazani, Heat Excangers 72
19 Compact Heat Excangers Fig Heat transfer and friction factor for finned circulartube HEX Example: Compact Heat Excangers St Pr 2/3 or f Ramazani, Heat Excangers 73 Ramazani, Heat Excangers 74 Analysis for Variable Properties Analysis for Variable Properties (Con.) (1033) Were, (1034) Ramazani, Heat Excangers 75 Ramazani, Heat Excangers 76
20 Analysis for Variable Properties (Con.) Analysis for Variable Properties (Example) Solution Metod: Te numericalanalysis procedure is clear wen te inlet temperatures and flows given: 1) Coose a convenient value of A j for te analysis. 2) Calculate te value of U for te inlet conditions and troug te initial A increment. 3) Calculate te value of Q for tis increment From Eq. (1032). 4) Calculate te values of T, T c, and T  T c, for te next increment, using Eqs and )Repeat te foregoing steps until all increment in A are employed Ramazani, Heat Excangers 77 Ramazani, Heat Excangers 78 Analysis for Variable Properties (Example) Analysis for Variable Properties (Example) Fig A rockbed termalenergy storage unit scematic Ramazani, Heat Excangers 79 Ramazani, Heat Excangers 80
21 Analysis for Variable Properties (Example) Analysis for Variable Properties (Example) Ramazani, Heat Excangers 81 Ramazani, Heat Excangers 82 Analysis for Variable Properties (Example) HeatExcanger Design Considerations Stored energy wit time for te rockbed termalenergy storage unit of figure Ramazani, Heat Excangers 83 Ramazani, Heat Excangers 84
22 HeatExcanger Design Considerations Ramazani, Heat Excangers 85
FREESTUDY HEAT TRANSFER TUTORIAL 3 ADVANCED STUDIES
FREESTUDY HEAT TRANSFER TUTORIAL ADVANCED STUDIES This is the third tutorial in the series on heat transfer and covers some of the advanced theory of convection. The tutorials are designed to bring the
More informationLESSON 1. HEAT EXCHANGERS
LESSON 1. HEAT EXCHANGERS 1 Contents (I) Definition. Classification. Regenerators. Mixers or direct contact heat exchangers. Packed bed heat exchangers (Intercambiadores de lecho compacto). Direct flame
More informationNatural Convection. Buoyancy force
Natural Convection In natural convection, the fluid motion occurs by natural means such as buoyancy. Since the fluid velocity associated with natural convection is relatively low, the heat transfer coefficient
More informationInternational Journal of ChemTech Research CODEN (USA): IJCRGG ISSN: 09744290 Vol.7, No.6, pp 25802587, 20142015
International Journal of ChemTech Research CODEN (USA): IJCRGG ISSN: 09744290 Vol.7, No.6, pp 25802587, 20142015 Performance Analysis of Heat Transfer and Effectiveness on Laminar Flow with Effect of
More informationSheet 5:Chapter 5 5 1C Name four physical quantities that are conserved and two quantities that are not conserved during a process.
Thermo 1 (MEP 261) Thermodynamics An Engineering Approach Yunus A. Cengel & Michael A. Boles 7 th Edition, McGrawHill Companies, ISBN9780073529325, 2008 Sheet 5:Chapter 5 5 1C Name four physical
More informationSECTION 3: CLARIFICATION AND UTILITIES (1)
CHPR4402 Chemical Engineering Design Project The University of Western Australia SECTION 3: CLARIFICATION AND UTILITIES (1) Aaliyah Hoosenally 10428141 TEAM A: ALCOHOLICS ANONYMOUS AALIYAH HOOSENALLY,
More informationDesign,Development and Comparison of Double Pipe Heat Exchanger with Conventional and Annular Baffles
Design,Development and Comparison of Double Pipe Heat Exchanger with and Annular Baffles Mukund B Pandya Asst. Professor, Department of Mechanical Engineering, Babaria Institute of Technology, Varnama
More informationHEAT TRANSFER ANALYSIS IN A 3D SQUARE CHANNEL LAMINAR FLOW WITH USING BAFFLES 1 Vikram Bishnoi
HEAT TRANSFER ANALYSIS IN A 3D SQUARE CHANNEL LAMINAR FLOW WITH USING BAFFLES 1 Vikram Bishnoi 2 Rajesh Dudi 1 Scholar and 2 Assistant Professor,Department of Mechanical Engineering, OITM, Hisar (Haryana)
More informationComparison of Heat Transfer between a Helical and Straight Tube Heat Exchanger
International Journal of Engineering Research and Technology. ISSN 09743154 Volume 6, Number 1 (2013), pp. 3340 International Research Publication House http://www.irphouse.com Comparison of Heat Transfer
More information2 Limits and Derivatives
2 Limits and Derivatives 2.7 Tangent Lines, Velocity, and Derivatives A tangent line to a circle is a line tat intersects te circle at exactly one point. We would like to take tis idea of tangent line
More informationHEAT TRANSFER AUGMENTATION THROUGH DIFFERENT PASSIVE INTENSIFIER METHODS
HEAT TRANSFER AUGMENTATION THROUGH DIFFERENT PASSIVE INTENSIFIER METHODS P.R.Hatwar 1, Bhojraj N. Kale 2 1, 2 Department of Mechanical Engineering Dr. Babasaheb Ambedkar College of Engineering & Research,
More informationIntegration of a fin experiment into the undergraduate heat transfer laboratory
Integration of a fin experiment into the undergraduate heat transfer laboratory H. I. AbuMulaweh Mechanical Engineering Department, Purdue University at Fort Wayne, Fort Wayne, IN 46805, USA Email: mulaweh@engr.ipfw.edu
More informationEXPERIMENTAL ANALYSIS OF HEAT TRANSFER ENHANCEMENT IN A CIRCULAR TUBE WITH DIFFERENT TWIST RATIO OF TWISTED TAPE INSERTS
INTERNATIONAL JOURNAL OF HEAT AND TECHNOLOGY Vol.33 (2015), No.3, pp.158162 http://dx.doi.org/10.18280/ijht.330324 EXPERIMENTAL ANALYSIS OF HEAT TRANSFER ENHANCEMENT IN A CIRCULAR TUBE WITH DIFFERENT
More informationHEAT TRANSFER ENHANCEMENT ON DOUBLE PIPE HEAT EXCHANGER BY WIRE COILED AND TAPER WIRE COILED TURBULATOR INSERTS
HEAT TRANSFER ENHANCEMENT ON DOUBLE PIPE HEAT EXCHANGER BY WIRE COILED AND TAPER WIRE COILED TURBULATOR INSERTS J.Kalil basha 1,G.Karthikeyan 2, S.Karuppusamy 3 1,2 Assistant Professor, Dhanalakshmi Srinivasan
More informationApplied Fluid Mechanics
Applied Fluid Mechanics 1. The Nature of Fluid and the Study of Fluid Mechanics 2. Viscosity of Fluid 3. Pressure Measurement 4. Forces Due to Static Fluid 5. Buoyancy and Stability 6. Flow of Fluid and
More informationEnergy Efficient Process Heating: Insulation and Thermal Mass
Energy Efficient Process Heating: Insulation and Thermal Mass Kevin Carpenter and Kelly Kissock Department of Mechanical and Aerospace Engineering University of Dayton 300 College Park Dayton, OH 454690210
More informationHEAT TRANSFER ENHANCEMENT AND FRICTION FACTOR ANALYSIS IN TUBE USING CONICAL SPRING INSERT
HEAT TRANSFER ENHANCEMENT AND FRICTION FACTOR ANALYSIS IN TUBE USING CONICAL SPRING INSERT Rahul M. Gupta 1, Bhushan C. Bissa 2 1 Research Scholar, Department of Mechanical Engineering, Shri Ramdeobaba
More informationCOIL INPUT SCREENS. ITEM NUMBER: Always use a 1 through? In this field you might also use a dash and place quantity of coils here.
COIL INPUT SCREENS Example of a Water Coil Input Screen: (*please see the appendix for an example of an Evaporator, Steam or Condenser Coil input screen) PHYSICAL DATA ITEM NUMBER: Always use a 1 through?
More informationWaste Heat Recovery through Air Conditioning System
International Journal of Engineering Research and Development eissn: 2278067X, pissn : 2278800X, www.ijerd.com Volume 5, Issue 3 (December 2012), PP. 8792 Waste Heat Recovery through Air Conditioning
More informationCorrugated Tubular Heat Exchangers
Corrugated Tubular Heat Exchangers HEAT EXCHANGERS for the 21st CENTURY Corrugated Tubular Heat Exchangers (CTHE) Corrugated Tube Heat Exchangers are shell and tube heat exchangers which use corrugated
More informationBattery Thermal Management System Design Modeling
Battery Thermal Management System Design Modeling GiHeon Kim, Ph.D Ahmad Pesaran, Ph.D (ahmad_pesaran@nrel.gov) National Renewable Energy Laboratory, Golden, Colorado, U.S.A. EVS October 8, 8, 006 Yokohama,
More informationCHAPTER TWO. f(x) Slope = f (3) = Rate of change of f at 3. x 3. f(1.001) f(1) Average velocity = 1.1 1 1.01 1. s(0.8) s(0) 0.8 0
CHAPTER TWO 2.1 SOLUTIONS 99 Solutions for Section 2.1 1. (a) Te average rate of cange is te slope of te secant line in Figure 2.1, wic sows tat tis slope is positive. (b) Te instantaneous rate of cange
More informationSteady Heat Conduction
Steady Heat Conduction In thermodynamics, we considered the amount of heat transfer as a system undergoes a process from one equilibrium state to another. hermodynamics gives no indication of how long
More informationReview of Heat Transfer Parameters of Serrated Plate Fin Heat Exchanger for Different Materials
Review of Heat Transfer Parameters of Serrated Plate Fin Heat Exchanger for Different Materials Mr. S.V. Jagtap Prof. A.M. Patil Prof. H.M.Dange Abstract The heat transfer and flow friction characteristics
More informationInternational journal of Engineering ResearchOnline A Peer Reviewed International Journal Articles available online http://www.ijoer.
REVIEW ARTICLE ISSN: 23217758 REVIEW OF HEAT TRANSFER AUGMENTATION TECHNIQUES MANOJ HAJARE, CHETAN DEORE, KAVITA KHARDE, PUSHKAR RAWALE, VIVEK DALVI Department of Mechanical Engineering, SITRC, NASHIK
More informationLesson 23 Condensers & Evaporators. Version 1 ME, IIT Kharagpur 1
Lesson 23 Condensers & Evaporators Version 1 ME, IIT Kharagpur 1 The specific objectives of this lesson are to: 1. Classify refrigerant evaporators as natural convection or forced convection type, flooded
More informationExperimental Study On Heat Transfer Enhancement In A Circular Tube Fitted With U Cut And V Cut Twisted Tape Insert
Experimental Study On Heat Transfer Enhancement In A Circular Tube Fitted With U Cut And V Cut Twisted Tape Insert Premkumar M Abstract Experimental investigation of heat transfer and Reynolds number
More informationSECTION 5 COMMERCIAL REFRIGERATION UNIT 21 EVAPORATORS AND THE REFRIGERATION SYSTEM
SECTION 5 COMMERCIAL REFRIGERATION UNIT 21 EVAPORATORS AND THE REFRIGERATION SYSTEM UNIT OBJECTIVES After studying this unit, the reader should be able to Define high, medium, and lowtemperature refrigeration.
More informationTransient Analysis of Integrated Shiraz Hybrid Solar Thermal Power Plant Iman Niknia 1, Mahmood Yaghoubi 1, 2
Transient Analysis of Integrated Shiraz Hybrid Solar Thermal Power Plant Iman Niknia 1, Mahmood Yaghoubi 1, 2 1 School of Mechanical Engineering, Shiraz University, Shiraz, Iran 1, 2 Shiraz University,
More informationModels RSRM, RSRN and RSRTN
odels RSR, RSR and RSRT 1.6 troug 2l 1 2 1 odel RSR3 2l 1.6 troug 2 1 1 odel RSR3 Outer dimensions dimensions odel o. Heigt idt engt Greasing ole Grease nipple RSR 3 RSR 3 RSR 5 RSR 5 RSR 5T odel
More informationAPPENDIX 11A Thermal Radiation and Vapor Dispersion Calculations for the Oregon LNG Import Terminal; Oregon LNG LNG Vapor Dispersion from Troughs
APPENDIX 11A Thermal Radiation and Vapor Dispersion Calculations for the Oregon LNG Import Terminal; Oregon LNG LNG Vapor Dispersion from Troughs PDX/072550008.DOC Thermal Radiation and Vapor Dispersion
More informationModule 1 : Conduction. Lecture 5 : 1D conduction example problems. 2D conduction
Module 1 : Conduction Lecture 5 : 1D conduction example problems. 2D conduction Objectives In this class: An example of optimization for insulation thickness is solved. The 1D conduction is considered
More informationAn Experimenatl Study on Heat Transfer Behaviors of A Welded  Aluminum Minichannel Heat Exchanger
ISSN (e): 2250 3005 Vol, 05 Issue,02 February 2015 International Journal of Computational Engineering Research (IJCER) An Experimenatl Study on Heat Transfer Behaviors of A Welded  Aluminum Minichannel
More informationComparing Air Cooler Ratings Part 1: Not All Rating Methods are Created Equal
Technical Bulletin By Bruce I. Nelson, P.E., President, Colmac Coil Manufacturing, Inc. Comparing Air Cooler Ratings Part 1: Not All Rating Methods are Created Equal SUMMARY Refrigeration air coolers (evaporators)
More informationTheoretical and Experimental Investigation of Heat Transfer Characteristics through a Rectangular Microchannel Heat Sink
Theoretical and Experimental Investigation of Heat Transfer Characteristics through a Rectangular Microchannel Heat Sink Dr. B. S. Gawali 1, V. B. Swami 2, S. D. Thakre 3 Professor Dr., Department of Mechanical
More informationPRESSURE DROP ANALYSIS OF INLET PIPE WITH REDUCER AND WITHOUT REDUCER USING CFD ANALYSIS
International Journal of Mechanical Engineering (IJME) ISSN(P): 23192240; ISSN(E): 23192259 Vol. 4, Issue 3, Apr  May 2015, 8592 IASET PRESSURE DROP ANALYSIS OF INLET PIPE WITH REDUCER AND WITHOUT
More informationINTERNATIONAL JOURNAL OF RESEARCH IN AERONAUTICAL AND MECHANICAL ENGINEERING
ISSN (ONLINE): 23213051 INTERNATIONAL JOURNAL OF RESEARCH IN AERONAUTICAL AND MECHANICAL ENGINEERING Study of forced convection heat transfer With DAQ & ANSYS First Authors Moopanar karthikeyan 1, Raote
More informationCFD Analysis of Application of Phase Change Material in Automotive Climate Control Systems
CFD Analysis of Application of Phase Change Material in Automotive Climate Control Systems Vijayakumar Nachimuthu 1, Prabhu Mani 2, Muthukumar. P 3 1 Flowxplore, Coimbatore, India., 2 Kathir College of
More informationNATIONAL RESEARCH COUNCIL CANADA. DIVISION OF BUILn ING RESEARCH DESIGN OF EXPOSED SEWER PIPES FOR INTERMITTENT USE UNDER FREEZING CONDITIONS
NATIONAL RESEARCH COUNCIL CANADA DIVISION OF BUILn ING RESEARCH DESIGN OF EXPOSED SEWER PIPES FOR INTERMITTENT USE UNDER FREEZING CONDITIONS D,G, by Stephenson Report No, 166 of the Division of Building
More informationKeywords: Heat transfer enhancement; staggered arrangement; Triangular Prism, Reynolds Number. 1. Introduction
Heat transfer augmentation in rectangular channel using four triangular prisms arrange in staggered manner Manoj Kumar 1, Sunil Dhingra 2, Gurjeet Singh 3 1 Student, 2,3 Assistant Professor 1.2 Department
More informationThis will also provide you with the knowledge to insure long life for your Investment
CONDUIT PIPE DRYING This Presentation will guide you to why systems fail! This will also provide you with the knowledge to insure long life for your Investment Drainable and Dryable System Design Trough
More information2. CHRONOLOGICAL REVIEW ABOUT THE CONVECTIVE HEAT TRANSFER COEFFICIENT
ANALYSIS OF PCM SLURRIES AND PCM EMULSIONS AS HEAT TRANSFER FLUIDS M. Delgado, J. Mazo, C. Peñalosa, J.M. Marín, B. Zalba Thermal Engineering Division. Department of Mechanical Engineering University of
More informationOpen channel flow Basic principle
Open channel flow Basic principle INTRODUCTION Flow in rivers, irrigation canals, drainage ditches and aqueducts are some examples for open channel flow. These flows occur with a free surface and the pressure
More informationHeat Transfer Enhancement in a Heat Exchanger using Punched and Vcut Twisted Tape Inserts
Heat Transfer Enhancement in a Heat Exchanger using Punched and Vcut Twisted Tape Inserts Imran Quazi#1, Prof. V.R.Mohite#2 #1DPCOEMechanical Department, SPP University Pune, India imranqu azi198 7@gmail.com
More informationWhat is Advanced Corporate Finance? What is finance? What is Corporate Finance? Deciding how to optimally manage a firm s assets and liabilities.
Wat is? Spring 2008 Note: Slides are on te web Wat is finance? Deciding ow to optimally manage a firm s assets and liabilities. Managing te costs and benefits associated wit te timing of cas in and outflows
More informationCASLU20130193000
L3:THM.CFD.P7.06 Implementation and validation of the new RPI boiling models using STARCCM+ as CFD Platform Victor Petrov, Annalisa Manera UMICH September 30, 2013 EXECUTIVE SUMMARY This milestone is
More informationCFD SIMULATION OF SDHW STORAGE TANK WITH AND WITHOUT HEATER
International Journal of Advancements in Research & Technology, Volume 1, Issue2, July2012 1 CFD SIMULATION OF SDHW STORAGE TANK WITH AND WITHOUT HEATER ABSTRACT (1) Mr. Mainak Bhaumik M.E. (Thermal Engg.)
More informationKONRAD. Hybrid Fancoil Series
KONRAD Hybrid Fancoil Series Konrad is an innovative radiator which cools you down and warms you up. Indeed, it cools in summer and heats in winter; but it makes it with an incomparable quietness. Thanks
More informationA MTR FUEL ELEMENT FLOW DISTRIBUTION MEASUREMENT PRELIMINARY RESULTS
A MTR FUEL ELEMENT FLOW DISTRIBUTION MEASUREMENT PRELIMINARY RESULTS W. M. Torres, P. E. Umbehaun, D. A. Andrade and J. A. B. Souza Centro de Engenharia Nuclear Instituto de Pesquisas Energéticas e Nucleares
More information1D STEADY STATE HEAT
D SEADY SAE HEA CONDUCION () Pabal alukda Aociate Pofeo Depatment of Mecanical Engineeing II Deli Email: pabal@mec.iitd.ac.in Palukda/MecIID emal Contact eitance empeatue ditibution and eat flow line
More informationNumerical Investigation of Heat Transfer Characteristics in A Square Duct with Internal RIBS
merical Investigation of Heat Transfer Characteristics in A Square Duct with Internal RIBS Abhilash Kumar 1, R. SaravanaSathiyaPrabhahar 2 Mepco Schlenk Engineering College, Sivakasi, Tamilnadu India 1,
More informationJournal bearings/sliding bearings
Journal bearings/sliding bearings Operating conditions: Advantages:  Vibration damping, impact damping, noise damping  not sensitive for vibrations, low operating noise level  dust tight (if lubricated
More informationUNIFORM FLOW. Key words Uniform flow; most economical crosssection; discharge; velocity; erosion; sedimentation
Capter UNIFORM FLOW.. Introduction.. Basic equations in uniform opencannel flow.3. Most economical crosssection.4. Cannel wit compound crosssection.5. Permissible velocity against erosion and sedimentation
More informationCalculating Heat Loss by Mark Crombie, Chromalox
Calculating Heat Loss by Mark Crombie, Chromalox Posted: January 30, 2006 This article deals with the basic principles of heat transfer and the calculations used for pipes and vessels. By understanding
More informationMaximizing Boiler Plant Efficiency. Presenter: Dan Watkins, LEED BD+C Sales Engineer Bornquist, Inc.
Maximizing Boiler Plant Efficiency Presenter: Dan Watkins, LEED BD+C Sales Engineer Bornquist, Inc. Efficient Boiler Design Boiler Types Efficiency Definition NonCondensing Condensing Maximizing Efficiency
More informationRusty Walker, Corporate Trainer Hill PHOENIX
Refrigeration 101 Rusty Walker, Corporate Trainer Hill PHOENIX Compressor Basic Refrigeration Cycle Evaporator Condenser / Receiver Expansion Device Vapor Compression Cycle Cooling by the removal of heat
More informationSound pr. (db(a)) Phone: +90 216 394 12 82 Pressure hpa 960.075. Fax: +90 216 394 12 87 Capacity kw 1200.000
HybridReCooler V2x8  Offer no. 1328 Sound power (db(a)) Sound pr. (db(a)) Company Schenkel & Partner GmbH 1 Branch Ingenieurbüro Street Bahnhofstrasse 44 Country/ZIP/City 8 Zürich Installation Credit
More informationCFD ANALYSES OF FLUID FLOW AND HEAT TRANSFER IN PATTERNED ROLLBONDED ALUMINIUM PLATE RADIATORS
Third International Conference on CFD in the Minerals and Process Industries CSIRO, Melbourne, Australia 1012 December 2003 CFD ANALYSES OF FLUID FLOW AND HEAT TRANSFER IN PATTERNED ROLLBONDED ALUMINIUM
More informationPerformance Test of Solar Assisted Solid Desiccant Dryer
Performance Test of Solar Assisted Solid Desiccant Dryer S. MISHA 1,2,*, S. MAT 1, M. H. RUSLAN 1, K. SOPIAN 1, E. SALLEH 1, M. A. M. ROSLI 1 1 Solar Energy Research Institute, Universiti Kebangsaan Malaysia,
More informationCO 2 41.2 MPa (abs) 20 C
comp_02 A CO 2 cartridge is used to propel a small rocket cart. Compressed CO 2, stored at a pressure of 41.2 MPa (abs) and a temperature of 20 C, is expanded through a smoothly contoured converging nozzle
More informationReview on Experimental Analysis and Performance Characteristic of Heat Transfer In Shell and Twisted Tube Heat Exchanger
Review on Experimental Analysis and Performance Characteristic of Heat Transfer In Shell and Twisted Tube Heat Exchanger Nitesh B. Dahare Student, M.Tech (Heat power Engg.) Ballarpur Institute of Technology,
More informationHeat Transfer Analysis of Corrugated Plate Heat Exchanger of Different Plate Geometry: A Review
Heat Transfer Analysis of Corrugated Plate Heat Exchanger of Different Plate Geometry: A Review Jogi Nikhil G. 1, Assist. Prof. Lawankar Shailendra M. 2 1 M.Tech student, 2 Assistant Professor, Government
More informationENHANCEMENT OF HEAT TRANSFER USING WIRE COIL INSERTS WITH CHORD RIBS
ENHANCEMENT OF HEAT TRANSFER USING WIRE COIL INSERTS WITH CHORD RIBS 1 P.S.Desale, 2 N.C.Ghuge 1 PG Student, Heat Power, MCERC, Nasik (India) 2 Asst. Prof., Mech. Dept., MCERC,Nasik(India) ABSTRACT From
More informationConvection heat transfer from tube banks in crossflow: Analytical approach
International Journal of Heat and Mass Transfer 49 (2006) 4831 4838 www.elsevier.com/locate/ijhmt Convection heat transfer from tube banks in crossflow: Analytical approach W.A. Khan a, *, J.R. Culham
More informationXI / PHYSICS FLUIDS IN MOTION 11/PA
Viscosity It is the property of a liquid due to which it flows in the form of layers and each layer opposes the motion of its adjacent layer. Cause of viscosity Consider two neighboring liquid layers A
More informationChapter 11. Limits and an Introduction to Calculus. Selected Applications
Capter Limits and an Introduction to Calculus. Introduction to Limits. Tecniques for Evaluating Limits. Te Tangent Line Problem. Limits at Infinit and Limits of Sequences.5 Te Area Problem Selected Applications
More informationDesign and Cost Optimization of Plate Heat Exchanger
Research Inventy: International Journal Of Engineering And Science Vol.4, Issue 10 (October2014), PP 4348 Issn (e): 22784721, Issn (p):23196483, www.researchinventy.com Design and Cost Optimization
More informationExperimental Investigation on Turbulent Flow Heat Transfer Enhancement in a Horizontal Circular Pipe using internal threads of varying depth
IOSR Journal of Mechanical and Civil Engineering (IOSRJMCE) eissn: 22781684 Volume 5, Issue 3 (Jan.  Feb. 2013), PP 2328 Experimental Investigation on Turbulent Flow Heat Transfer Enhancement in a
More informationInitial Experiments of a Novel Liquid Desiccant Dehumidifier for Industrial and Comfort Air Conditioning Systems
Abstract Initial Experiments of a Novel Liquid Desiccant Dehumidifier for Industrial and Comfort Air Conditioning Systems M. Jaradat, R. Heinzen, U. Jordan, K. Vajen Kassel University (Germany), Institute
More informationHow much do you know about HVAC? Try testing yourself with the following questions and then take a look at the answers on the following page.
Demystifying HVAC Test Your HVAC Knowledge By Ron Prager How much do you know about HVAC? Try testing yourself with the following questions and then take a look at the answers on the following page. 1)
More informationGLOBACON 05 HVAC Systems for Cogen
GLOBACON 05 HVAC Systems for Cogen Track 2, Session 2B Advanced HVAC and Building Systems Date: March 24th, 2005 Gearoid Foley President Integrated CHP Systems Corp. Integrated CHP Systems Corp. Electricity
More informationULTRA.DRY HRE Heat Regenerated Adsorption Dryer
Wy drying compressed air? Compressed air is used in almost all areas of industrial manufacturing as a source of energy or processing. Compressed air needs to be dry, oilfree and clean in order to prevent
More informationTechnical Specification for Model RSK2503 (Z)06A IR Belt Solar Cell Firing Furnace
Technical Specification for Model RSK2503 (Z)06A IR Belt Solar Cell Firing Furnace TECHNICAL SPECIFICATION Model RSK 2503(Z)06A IR Belt Solar Cell Firing Furnace Temperature Range 1. Max Temperature.
More informationOUTCOME 3 TUTORIAL 5 DIMENSIONAL ANALYSIS
Unit 41: Fluid Mechanics Unit code: T/601/1445 QCF Level: 4 Credit value: 15 OUTCOME 3 TUTORIAL 5 DIMENSIONAL ANALYSIS 3 Be able to determine the behavioural characteristics and parameters of real fluid
More informationChapter 3.4: HVAC & Refrigeration System
Chapter 3.4: HVAC & Refrigeration System Part I: Objective type questions and answers 1. One ton of refrigeration (TR) is equal to. a) Kcal/h b) 3.51 kw c) 120oo BTU/h d) all 2. The driving force for refrigeration
More informationHEAT TRANSFER ENHANCEMENT IN FIN AND TUBE HEAT EXCHANGER  A REVIEW
HEAT TRANSFER ENHANCEMENT IN FIN AND TUBE HEAT EXCHANGER  A REVIEW Praful Date 1 and V. W. Khond 2 1 M. Tech. Heat Power Engineering, G.H Raisoni College of Engineering, Nagpur, Maharashtra, India 2 Department
More informationHeat transfer efficiency improvement in highpressure metal hydride by modeling approach
International Journal of Smart Grid and Clean Energy Heat transfer efficiency improvement in highpressure metal hydride by modeling approach Nur Aisyah Jalalludin a*, Noboru Katayama b, Sumio Kogoshi
More informationLesson. 11 Vapour Compression Refrigeration Systems: Performance Aspects And Cycle Modifications. Version 1 ME, IIT Kharagpur 1
Lesson Vapour Compression Refrigeration Systems: Performance Aspects And Cycle Modifications Version ME, IIT Kharagpur The objectives of this lecture are to discuss. Performance aspects of SSS cycle and
More informationDiffusion and Fluid Flow
Diffusion and Fluid Flow What determines the diffusion coefficient? What determines fluid flow? 1. Diffusion: Diffusion refers to the transport of substance against a concentration gradient. ΔS>0 Mass
More informationCooling and Heat Exchanger Solutions
Cooling and Heat Exchanger Solutions We are proudly South African and passionate about delivering world class solutions to all industries, from power generation and petrochemical, steel and aluminium to
More informationExperimental test preparation, performance and data processing
Chapter 4 Experimental test preparation, performance and data processing 4.1 Introduction This chapter is dedicated to the experimental test preparation, performance, and data processing and analysis.
More informationICE FOOD DEPOT COOLED WITH A HEAT PUMP: A PREFEASIBILITY STUDY
ICE FOOD DEPOT COOLED WITH A HEAT PUMP: A PREFEASIBILITY STUDY S.A. Guly, G.Z. Perlstein NortEastern Researc Station o Permarost Institute, Siberian Branc o Russian Academy o Sciences. 12, Gagarin St.,
More informationCharacteristics of Evaporators
Characteristics of Evaporators Roger D. Holder, CM, MSME 10282003 Heat or Energy In this paper, we will discuss the characteristics of an evaporator coil. The variance of the operational condenses of
More informationINTERNATIONAL JOURNAL OF MECHANICAL ENGINEERING AND TECHNOLOGY (IJMET)
INTERNATIONAL JOURNAL OF MECHANICAL ENGINEERING AND TECHNOLOGY (IJMET) International Journal of Mechanical Engineering and Technology (IJMET), ISSN 0976 ISSN 0976 6340 (Print) ISSN 0976 6359 (Online) Volume
More informationHeat Exchanger Thin Film Foul Release Applications Corrosion Resistant Protective Coatings Grit Blast Surface Prep of Tubular Equipment
Heat Exchanger Thin Film Foul Release Applications Corrosion Resistant Protective Coatings Grit Blast Surface Prep of Tubular Equipment NonDestructive Examination Heat Exchanger Mechanical Repair Services
More informationTangent Lines and Rates of Change
Tangent Lines and Rates of Cange 922005 Given a function y = f(x), ow do you find te slope of te tangent line to te grap at te point P(a, f(a))? (I m tinking of te tangent line as a line tat just skims
More informationDSRQ  DSRSQ  DSRSQTHERM
DSRQ  DSRSQ  DSRSQTHERM Specification item: Variable geometry diffuser on 597x597 mm panel developed for rooms with high ceilings where a long throw and a high induction ratio are required. Made up
More informationTUTORIAL No. 1 FLUID FLOW THEORY
TUTORIAL No. FLUID FLOW THEORY In order to complete tis tutorial you sould already ave completed level or ave a good basic knowledge of fluid mecanics equivalent to te Engineering Council part examination
More informationHYDRAULIC ANALYSIS OF PIPE LINED WITH MADISON S 100% SOLIDS STRUCTURAL POLYURETHANE COATINGS
HYDRAULIC ANALYSIS OF PIPE LINED WITH MADISON S 100% SOLIDS STRUCTURAL POLYURETHANE COATINGS Shiwei William Guan, Ph.D. Vice President, R&D and International Business Madison Chemical Industries Inc. 490
More informationSECTION 5 COMMERCIAL REFRIGERATION UNIT 22 CONDENSERS
SECTION 5 COMMERCIAL REFRIGERATION UNIT 22 CONDENSERS UNIT OBJECTIVES After studying this unit, the reader should be able to explain the purpose of the condenser in a refrigeration system. describe differences
More informationThermal Management in SurfaceMounted Resistor Applications
VISHAY BEYSCHLAG Resistive Products 1. INTRODUCTION Thermal management is becoming more important as the density of electronic components in modern printed circuit boards (PCBs), as well as the applied
More informationHybrid Modeling and Control of a Power Plant using State Flow Technique with Application
Hybrid Modeling and Control of a Power Plant using State Flow Technique with Application Marwa M. Abdulmoneim 1, Magdy A. S. Aboelela 2, Hassen T. Dorrah 3 1 Master Degree Student, Cairo University, Faculty
More informationEarthAir Heat Exchanger Design for Achieve Energy Saving in HVAC System
EarthAir Heat Exchanger Design for Achieve Energy Saving in HVAC System Farivar Fazelpour (1), Reza Asnaashari (2) (1) Department of Energy System Engineering Faculty of Engineering, Islamic Azad University
More informationLecture 5 Hemodynamics. Description of fluid flow. The equation of continuity
1 Lecture 5 Hemodynamics Description of fluid flow Hydrodynamics is the part of physics, which studies the motion of fluids. It is based on the laws of mechanics. Hemodynamics studies the motion of blood
More informationSection 2.3 Solving Right Triangle Trigonometry
Section.3 Solving Rigt Triangle Trigonometry Eample In te rigt triangle ABC, A = 40 and c = 1 cm. Find a, b, and B. sin 40 a a c 1 a 1sin 40 7.7cm cos 40 b c b 1 b 1cos40 9.cm A 40 1 b C B a B = 90  A
More informationHVAC Systems: Overview
HVAC Systems: Overview Michael J. Brandemuehl, Ph.D, P.E. University of Colorado Boulder, CO, USA Overview System Description Secondary HVAC Systems Air distribution Room diffusers and air terminals Duct
More informationDynamic Process Modeling. Process Dynamics and Control
Dynamic Process Modeling Process Dynamics and Control 1 Description of process dynamics Classes of models What do we need for control? Modeling for control Mechanical Systems Modeling Electrical circuits
More informationHeat Transfer Analysis of Cylindrical Perforated Fins in Staggered Arrangement
International Journal of Innovative Technology and Exploring Engineering (IJITEE) ISSN: 22783075, Volume2, Issue5, April 203 Heat Transfer Analysis of Cylindrical Fins in Staggered Arrangement Amol
More informationCE 6303 MECHANICS OF FLUIDS L T P C QUESTION BANK PART  A
CE 6303 MECHANICS OF FLUIDS L T P C QUESTION BANK 3 0 0 3 UNIT I FLUID PROPERTIES AND FLUID STATICS PART  A 1. Define fluid and fluid mechanics. 2. Define real and ideal fluids. 3. Define mass density
More informationThe Heat Transfer Characteristics of an Insulated Circular Duct Considering and Neglecting the Influence of Heat Radiation
Proceedings of the International MultiConference of Engineers and Computer Scientists 29 Vol II IMECS 29, March 82, 29, Hong Kong The Heat Transfer Characteristics of an Insulated Circular Duct Considering
More information