# LEVEL GAUGES WITH MAGNETIC JOINT L 14 - L 22 - L 34

Size: px
Start display at page:

Download "LEVEL GAUGES WITH MAGNETIC JOINT L 14 - L 22 - L 34"

## Transcription

1 LEVEL GAUGES WITH MAGNETIC JOINT L 14 - L 22 - L 34

2 2 LEVEL GAUGES WITH MAGNETIC JOINT SIZE Ø 140/220/340

3 58 58 TYPE LA TYPE LA S TYPE LA NO. HOLES Ø D2 76 O-RING CENTRE OF THE CONSERVATOR 120 Ø DC = DIAMETER OF THE CONSERVATOR Ø DC R= VARIABLE LENGHT fig. 1 R = (DC/2-10) x 1.15 S = (DC/2-40) x TYPE LB TYPE LB TYPE LB NO. HOLES Ø D2 90 O-RING R= VARIABLE LENGHT Ø DC = DIAMETER OF THE CONSERVATOR Ø DC Ø D1 Ø D L L Ø 60 Ø D1 Ø D Ø 58 PG Ø 60 Ø DC Ø 58 PG 16 fig. 2 R = (DC/2-10) x 1.15 TYPE OF GAUGE Ø D Ø D1 Ø D2 NO. HOLES L O.RING TYPE WEIGHT kg R STANDARD LA O.R. 186 (6362) 1.40 max. 370 LA O.R max. 550 LA O.R. 248 (81000) 6.00 max. 710 LB O.R. 186 (6362) 1.70 max. 370 LB O.R max. 550 LB O.R. 248 (81000) 6.30 max. 710 DIMENSIONS IN MILLIMETERS 3

4 LEVEL GAUGES WITH MAGNETIC JOINT The level gauges with a magnetic joint are composed of a sturdy watertight body of aluminium alloy painted against corrosion. The movement of the float rod and the gauge disk takes place by means of magnetic coupling through an angle of 120. In this way, for every variation in the level of the liquid there is a corresponding rotation of the magnet with consequent variation of the indication on the dial of the gauge. The gauge disk is coloured white and red. The system is closed with a screen-printed polycarbonate disk with reference marks corresponding to the levels that the oil should reach at the following temperatures in degrees Centigrade: -20 C, +20 C, +85 C. Note: special dials may be made on request. READING THE INDICATIONS OF THE VARIOUS LIQUID LEVELS - Minimum level: when the dial shows all red. - Maximum level: when the dial shows all white. - Intermediate indications between MAX and MIN: the dial shows part white and part red. Remember that the amount of red shown indicates, in proportion, the part of the conservator left without liquid. FLOAT MOVEMENT This may be in the radial direction of the conservator (type LA ) or in the axial direction (type LB ), as shown in the drawing (Fig. 1 and 2). FLOAT ROD This is completely threaded. If the length is not specified (distance R in the drawing, fig. 1 and 2), the standard size indicated on the table is supplied. ELECTRIC INDICATION These level gauges are fitted with microswitches for indicating the minimum and maximum oil level. ELECTRIC CHARACTERISTICS - Power supply: 24 to 220 V a.c. or d.c. - Interruption power: 3 A 125/250 V ac (resistive) 0.5 A 125 V dc for inductive load L/R = 40 ms 0.25 A 250 V dc for inductive load L/R = 40 ms INDICATING INTERVENTION The electric microswitches intervene with an advance angle of 5 with respect to the indications of the minimum or maximum oil level in the conservator. When there is a double contact on MIN and/or MAX, the second contact intervenes about 5 after the first contact. After installation of the gauges it is possible to check the correct operation of the microswitches and, in general, good operation of all the internal parts of the gauge by proceeding as follows: - Remove the cap situated in the centre of the dial on the front of the level gauge, unscrewing it in an anticlockwise direction. - Insert a screwdriver in the slot provided and turn the gauge disk until the electric circuit connected to it switches on or off. - Close the cap again, being particularly careful to position the O-ring (O.R.) correctly under the cap and to screw the cap on quite firmly. RESISTANCE TO VIBRATIONS ON THE ELECTRIC CONTACTS Tests have been carried out according to the procedures illustrated below in graph (10 cycles), with an amplitude of oscillation of 2 mm and in normal working conditions. No contacts gave any sign of closing or opening. NOTES External nuts and bolts made of stainless steel. External painting in grey RAL Degree of protection: IP 54. Working temperature. All the level gauges are suitable for working with: - Oil temperature between: -25 C and +120 C - Environment temperature between: -25 C and +60 C 4

5 INDICATIONS FOR ASSEMBLY The level gauges which have float movement in the radial direction of the container (type LA ) must be fitted offset with respect to the horizontal axis of the conservator (distance S fig. 1) so as to have an exact indication of the minimum and maximum oil level. Those with movement in the axial direction (type LB ) must be fitted in the centre of the conservator. The measurements of the movements (distance S ) and the length of the rod (distance R ) are obtained from the formulae given under fig. 1 and 2. It is good practice to check operation of the gauge after having fitted it on the conservator.for further and more detailed information, see the technical information card supplied. TESTS AND INSPECTIONS The level gauges are subjected to insulation test towards earth as follows: 2.5 kv AC 50/60 Hz for 72 seconds. The bodies of the level gauges, after having passed the dimensional inspection and without their internal parts, are tested for watertightness so as to eliminate those that have leaks. Final testing is carried out when the level gauge is completely assembled. The sensitivity of all the signalling movements and the accuracy of their assembly are scrupulously checked. IDENTIFICATION MARKS The mark that completely identifies the type of level gauge is composed of a series of letters and numbers according to the following pattern: 1 (letter) 2 (letter) 3 & 4 (cifra) 5 (lettera 6 (lettera) 7 (lettera) L A B K Y X W O S N S Level gauge Movement of the radial float (fig. 1) (letter) Movement of the axial float (fig. 2) Size of the level gauge = Ø 140 mm Size of the level gauge = Ø 220 mm Size of the level gauge = Ø 340 mm Wiring diagram with 1 contact on min. Wiring diagram with 2 contacts on min. Wiring diagram with 1 contact on min. + 1 contact on max. Wiring diagram with 2 contacts on min + 2 contacts on max. Ordinary paint Paint for corrosive environments COMEM standard level gauge Specific level gauge for customer Example : LA14XON Level gauge with radial movement, diameter 140 mm, wiring diagram with 1 contact on minimum and 1 contact on maximum, painted for normal environments and with standard COMEM dial and rod length. WIRING DIAGRAMS DIAGRAM TYPE K DIAGRAM TYPE Y 1 CONTACT ON MINIMUM LEVEL 2 CONTACTS ON MINIMUM LEVEL DIAGRAM TYPE X DIAGRAM TYPE W 1 CONTACT ON MIN. LEVEL + 1 CONTACT ON MAX. LEVEL 2 CONTACTS ON MIN. LEVEL + 2 CONTACTS ON MAX. LEVEL 5

6 comem - S.p.A Strada Statale 11, km MONTEBELLO VIC.NO (VI) ITALY Tel Fax Internet edizione 11/01 - Edigraf - 5m cod L2000

### OLI. Oil level indicator

OLI Oil level indicator Oil level indicator Unexpected or accidental oil leakages may occur randomly along transformer s lifetime. Clear indication of oil level inside transformer tank and on load tap

### INSTRUCTION MANUAL Oil level indicator with pointer

INSTRUCTION MANUAL Oil level indicator with pointer 5COL868200 REV.01 I II CONTENTS 1. SAFETY... 1 1.1 Safety instructions... 1 1.2 Specified applications... 1 1.3 Safety notes on the equipment operation...

### PPS-PPQ-BT-PIAS RESIN INSULATORS FOR OIL INSULATED ELECTRICAL MACHINES

PPS-PPQ-BT-PIAS RESIN INSULATORS FOR OIL INSULATED ELECTRICAL MACHINES BUSHING WITH PLUG CONNECTION WITH OUTER CONE PPS CHARACTERISTICS The PPS bushing can be used as a fixed section for the entry of medium

### HEAT MONITORING AND CONTROL INSTRUMENTS FOR TRANSFORMERS MB 103 TEMPERATURE CONTROL UNIT PT 100 TEMPERATURE SENSOR

HEAT MONITORING AND CONTROL INSTRUMENTS FOR TRANSFORMERS MB 103 TEMPERATURE CONTROL UNIT PT 100 TEMPERATURE SENSOR 2 MB 103 TRANSFORMER TEMPERATURE CONTROL UNIT WITH CONTROL SIGNAL Recent approval of new

### OUT. The SF2 series suction filter are designed for reservoir side-wall applications. This completely new design of filter allows the filter

D e s c r i p t i o n 250 The SF2 series suction filter are designed for reservoir side-wall applications. This completely new design of filter allows the filter within the filter preventing oil loss from

### Pressure monitoring equipment for oil-sf 6. bushings, type GOEK

Pressure monitoring equipment for oil-sf 6 bushings, type GOEK Installation and maintenance guide 5693 827-6 en, Rev. 3, 2002-01-30 This document must not be copied without our written permission, and

### Cable Plug acc. to DIN EN 175301-803, Form A

Cable Plug acc. to DIN EN 175301-803, Form A Complete program Contact form 18 mm Also available with LED indicator Optional 4-pin version for pressure switch or impulse valves respectively Versions with

### Contactless Encoder RI360P0-QR24M0-INCRX2-H1181

Compact, rugged housing Many mounting possibilities Status displayed via LED Immune to electromagnetic interference 1024 pulses per revolution (default) 360, 512, 1000, 1024, 2048, 2500, 3600, 4096, parametr.

### Ferrostat Speed Sensor Series DSF Explosion Proof Versions EEx

Ferrostat Speed Sensor Series DSF Explosion Proof Versions EEx DSF..10.**.HV Ex ATEX Operating Instructions 374E-64368 Valid from lot nr. 0103 General Function Use in potentially explosive environment

### HERZ-Thermal Actuators

HERZ-Thermal Actuators Data Sheet 7708-7990, Issue 1011 Dimensions in mm 1 7710 00 1 7710 01 1 7711 18 1 7710 80 1 7710 81 1 7711 80 1 7711 81 1 7990 00 1 7980 00 1 7708 11 1 7708 10 1 7708 23 1 7709 01

### FLOAT SWITCHES FLOW SWITCHES FOR LIQUIDS PRESSURE SWITCHES

01D351-GB FLOAT SWITCHES FLOW SWITCHES FOR LIQUIDS PRESSURE SWITCHES DOLOMIT FLOAT SWITCHES The DOLOMIT float switches find application in liquid level control in tanks and wells; they require connection

### Thermometer in stainless steel with capillary and switch contacts

Design Type Case diameter Thermometer in and switch contacts 7308 = back flange for wall mounting 7312 = front flange for panel mounting 7310 = mounting bracket for wall mounting Dim 100 mm or 160 mm Accuracy

### The SF2 series are designed for reservoir side-wall mounting applications, suitable for flow rates to 850 l/min and filtration from 25 to 250 micron.

D e s c r i p t i o n 500 The SF2 series are designed for reservoir side-wall mounting applications, suitable for flow rates to 850 l/min and filtration from 25 to 250 micron. A major feature of these

### ATL Fuel Level Sender Probes

T E C H N I C A L S P E C I F I C A T I O N The ATL EL-AD-151 (Resistance Output) and EL-AD-152 (Voltage Output) Fuel Level Senders are highly advanced sensors for continuously measuring the contents of

### SITEMA PowerStroke. Technical Information TI-P11. 1 Function. 2 Applications. Mould Closing Devices series FSK. Contents

English translation of German original Technical Information TI-P11 SITEMA PowerStroke Mould Closing Devices series FS drive system for powerful forces on a short stroke hydraulic actuation closing force

### Mounting Instructions. Torque Transducer. A0329 3.2 en

Mounting Instructions Torque Transducer T5 T5 Contents 3 Page Safety instructions.............................................. 4 1 Measuring characteristics..................................... 7 2 Mounting.....................................................

### Tubular Analog model resolution: 0,5 mm (SLOW mode), 1 mm (FAST mode) Right angle Repeatibility: 0,7 mm Vdc

Ultrasonic sensors for high precision detection of clear and transparent objects Clear object detection, inspection on transparent or highly reflective film and liquid level measurement Standard M18 tubular

### Vacuum Gate Valve DN 100 and DN 150

Vacuum Gate Valve DN 100 and DN 150 WER Dok.E.02.050_02.051 1. Introduction/Safety Instructions 2. Description 3. Technical Data 4. Installation 5. Operation 6. Maintenance Instructions 7. Spare Parts

### Fluid Level Gauge Fluid Level Sensor Temperature Switch FSA / FSK / TS

Fluid Level Gauge Fluid Level Sensor Temperature Switch FSA / FSK / TS up to size 381; to PN 0.5; to T = 80 C 1. Description 1.1. General FSA fluid level gauges, FSK fluid level sensors and TS temperature

AB-5361-U Specifications/Instructions Radiant Temperature TY7321 General TY7321 Radiant Temperature s are designed to measure infrared radiation from perimeter windows and walls and provide a proportional

### Proportional pressure regulators VPPE

Proportional pressure regulators VPPE Proportional pressure regulators VPPE Product range overview Function Version Pneumatic connection Proportional pressure regulator Nominal size for pressurisation/

### Floating Switch FTS 20 Füllstandgrenzschalter Level Limit Switch Détecteur de niveau

KA 180F/00/en/06.01 (a) 52010984 Floating Switch FTS 20 Füllstandgrenzschalter Level Limit Switch Détecteur de niveau Safety instructions The FTS 20 floating switch may only be used as a level limit switch

### Valve series MN-06 acc. to NAMUR, 3/2-way G1/4 750 Nl/min (0.762 Cv)

Valve series MN-06 acc. to NAMUR, 3/2-way G1/4 750 Nl/min (0.762 Cv) Order code Series and function 1) Plug socket see page 5.042. MN-06-310-HN-442 Standard coil 1) 441 = 12 V DC, 4.2 W 442 = 24 V DC,

### SENSORS. Miniature Sensors - S3Z. Advanced line of miniature Asian style of photoelectric sensors. 40-300 mm background suppression

Advanced line of miniature Asian style of photoelectric sensors 4-3 background suppression.7 m proximity, 15 with narrow beam 4 m polarized retroreflective 3 m LASER through beam Standard 3-wire output

### DiwiTherm, Resistance Thermometers Model TR75, with digital Display Battery or Solar Powered

Electrical Temperature Measurement DiwiTherm, Resistance Thermometers Model TR75, with digital Display Battery or Solar Powered WIKA Data Sheet TE 60.75 Applications Machinery, plant and tank construction

### CONTENTS. 1. CE DECLARATION OF CONFORMITY FOR MACHINES pag.11. 2. DESCRIPTION pag.12. 3. TECHNICAL SPECIFICATIONS pag.13. 4. INSTALLATION pag.

CONTENTS 1. CE DECLARATION OF CONFORMITY FOR MACHINES pag.11. DESCRIPTION pag.1 3. TECHNICAL SPECIFICATIONS pag.13 4. INSTALLATION pag.13 5. TESTING THE AUTOMATED SYSTEM pag.19 6. MANUAL OPERATION pag.19

### IntelliChlor Flow-Temperature Switch Replacement Kit Installation Guide

IntelliChlor Flow-Temperature Switch Replacement Kit Installation Guide Technical Support Sanford, North Carolina (8 A.M. to 5 P.M.) Moorpark, California (8 A.M. to 5 P.M.) Phone: (800) 831-7133 Fax: (800)

### Clear Glass Sensor. Ordering Information E3S-CR67/62. Optimum Sensor for Detecting Transparent Glass and Plastic Bottles

Clear Glass Sensor Optimum Sensor for Detecting Transparent Glass and Plastic Bottles E3S-CR67/62 Retroreflective Sensor smoothly detects 5-mm gaps. Detects transparent bottles that have a lens effect.

### Output torques up to 8000 Nm. General features. Protection. External coating. Working temperature range

Type series booklet 8521.15/2--10 ACTELEC 31 to 800 (BERNARD) 1/4 turn electric actuators (irreversible reducer with multi -turn electric actuator ACTELEC 31: screw -nut kinematics ACTELEC 200 to 800:

### PSU-U-24V/AC-6A/10/FTA-TR-MC PSAC 0624

PSU-U-24V/AC-6A/10/FTA-TR-MC PSAC 0624 v.1.0 AC/AC power supply unit Edition: 1 from 24 th October 2008 Supercedes edition: ---------- 10062009 CONTENTS: 1. Technical description. 1.1. General description

### AIR-AIR PRESSURE MULTIPLIER (BOOSTER)

AIR-AIR PRESSURE MULTIPLIER (BOOSTER) The air-air pressure multiplier, or booster, is an automatic device that compresses air to give an outlet pressure that is double the inlet pressure. It is normally

### Turbine Flow Sensor Series VTR

Turbine Flow Sensor Series VTR SIKA Turbine Flow Sensor Series VTR Extra robust, impressively precise SIKA s VTR turbine flow sensor allows you to determine precisely, dependably and easily the flow rates

### PD30ETB20xxIS. Photoelectrics, Background Suppression reflective with IR light. Main features. Description

Photoelectrics, Background Suppression reflective with IR light Main features Description The PD30ET... stainless steel sensors are built with high-quality materials and designed for harsh environments.

### Cross-beam scanning system to detect slim objects. 100 mm 3.937 in

891 Object Area Sensor General terms and conditions... F-17 Related Information Glossary of terms... P.1359~ Sensor selection guide...p.831~ General precautions... P.1405 PHOTO PHOTO Conforming to EMC

### 3/2-way Solenoid Valve, direct-acting, NC or NO

3/2-way Solenoid Valve, direct-acting, NC or NO Electrical connection cable plug, Form A With or without manual override as standard Threaded port and sub-base s Impulse optional Type 6014 can be combined

### DMS 680. Universal length measuring system gauge inspection for»iso 9000«requirements

DMS 680 Universal length measuring system gauge inspection for»iso 9000«requirements Universal length measuring system DMS 680 Wide range of applications For periodic inspection of gauges, reference gauges,

### Rotary actuators Rotary wing drives Series RAK. Brochure

Brochure 2 Rotary wing drives, angle of rotation: 30-270 Rotary wing drive, double-acting axis geometry: single 4 Rotary wing drives, angle of rotation: 90-270 Rotary wing drive, double-acting axis geometry:

### Long sensing range. Most suitable for conveyor lines and parking lot applications. 10 m 32.808 ft (Red LED)

NX SERIES Compact Multi-voltage Photoelectric Power Supply Built-in Multi-voltage photoelectric sensor usable worldwide Conforming to ow Voltage and EMC Directive Multi-voltage The NX series can operate

(for adjustable heads) Part. 209 40 ø,5 ø10,5 2 2,5 115 15 42 5 11 37 72 4 70 Code 209 / 0754 MATERIALS: Bracket made out of reinforced polyamide black colour. FEATURES: To be used with heads Part.221,

### STANDARD MICRO-D CONNECTORS

STANDARD MICRO-D CONNECTORS RECTANGULAR CONNECTORS Pigtail connector - Metal shell.............................. 56 Pigtail connector - Low profile - Metal shell.................... 58 Pigtail connector

### Speed Control Relays SX2

SX2 File 850 CONENS Description.....................................................Page General Information................................................ 2-3 SX2DV General Information...........................................

### Series 8146/5-V37 and Series 8150/5-V37

www.stahl.de > Clear assignment safe technology easy installation > Intelligent structure only one rotary actuator for frequency-controlled drives ) 20 ms leading auxiliary contact for safe motor disconnection

### ONE OF THE SMALLEST SNAP-ACTION SWITCHES IN THE WORLD. FEATURES Superminiature type, light-weight snap action switch PC board terminal type (0.

ONE OF THE SMALLEST SNAP-ACTION SWITCHES IN THE WORLD SWITCHES FEATURES Superminiature type, light-weight snap action switch PC board terminal type (0.2g) Solder terminal type with mounting holes (0.3g)

### INSTALLATION MANUAL. SAILOR 5080 AC Power Supply

INSTALLATION MANUAL SAILOR 5080 AC Power Supply Contents Introduction... 3 General description... 3 Technical data... 3 Installation... 4 Outline and dimension... 4 Installation wiring... 5 Block diagram

### H45 LED - Direct and indirect pendant

RAL 01 10 00 IP 20 230V 50/60Hz Specifications Direct and indirect light pendant linear luminaire. Aluminium profile. Diffusers in frosted polycarbonate profile. Driver included. Supplied with clear base,

### SEISMIC VELOCITY TRANSDUCER T1-40

SEISMIC VELOCITY TRANSDUCER T1-40 Measurement of Omnidirectional Absolute Vibrations Certified according to ATEX 94/9/CE directive OPERATION Transducer T1-40 serves for seismic measurement of the absolute

### WaterMAG. Electromagnetic Flowmeter for Water Applications. Model MCB10A OVERVIEW APPLICATIONS FEATURES. No. SS2-MCB100-0100

WaterMAG Electromagnetic Flowmeter for Water Applications OVERVIEW The WaterMAG is an electromagnetic flowmeter for water measurement applications based on field proven Azbil Corporation's technologies.

### ! WARNING. Before using product, read and understand instructions.

McDonnell & Miller Installation & Maintenance Instructions MM-600G) Series FS8-W General Purpose Liquid Flow Switch OPERATION This control is an independently mounted water flow sensing device that makes

### PC INTERFACE MODULES FOR TOLL-PLAZA CLASSIFICATION SENSORS

PC INTERFACE MODULES FOR TOLL-PLAZA CLASSIFICATION SENSORS FRANCE Head office USA 4 Rue du Bois Chêne le loup Parc d Activité de Brabois 54 500 VANDOEUVRE LES NANCY (33) 0383442413, Fax (33) 0383443797

### T-Series Precision Linear Actuators Installation and Service Manual DW110353GB-1018 - EDITION 5. www.thomsonlinear.com

T-Series Precision Linear Actuators Installation and Service Manual DW110353GB-1018 - EDITION 5 www.thomsonlinear.com Version History Edition Number Edition Date Reason for Revision 1 2004 First edition

### Linear Luminaire with LED Series EXLUX 6402/2

> Latest LED technology with a high luminous efficacy and a long service life > As pendant light fitting or side entry lamp > Central locking > All-pole disconnection by means of an N/C switch when the

### T R A N S F O R M E R A C C E S S O R I E S SAM THERMOMETERS

THERMOMETERS BIMETA THERMOMETERS (DIN 1 1 - PART 2) TYPE: MBT 7 2 4 8 1 12 C APPICATION This thermometer is designed for indication of oil temperature in both transformers with epansion conservator or

### INSTRUCTION MANUAL HYDRAULIC GATE TRANSMISSION SYSTEM ECO240-ECO360

INSTRUCTION MANUAL HYDRAULIC GATE TRANSMISSION SYSTEM ECO240-ECO360 IMPORTANT SAFETY INSTRUCTIONS WARNING! To reduce the risk of injury or death it is important to closely follow all of the following instructions.

### XUSL4E4BB091NS2 XUSL type 4 - Slave2 - For body protection - 4 Beams, Hp = 910 mm

Characteristics XUSL type 4 - Slave2 - For body protection - 4 Beams, Hp = 910 mm Complementary Detection system Kit composition [EAA] effective aperture angle Emission Main Range of product Product or

### 1ZSE 2750-105 en, Rev. 8. Transformer bushings, type GOE and GOE(2) Technical guide

1ZSE 2750-105 en, Rev. 8 Transformer bushings, type GOE and GOE(2) Technical guide Original instruction The information provided in this document is intended to be general and does not cover all possible

### Proﬁle rail guides LLR

Proﬁle rail guides LLR Content The SKF brand now stands for more than ever before, and means more to you as a valued customer. While SKF maintains its leadership as the hallmark of quality bearings throughout

### Displacement encoders

Displacement encoders Analogue and digital For measuring and positioning For use with pneumatic components 1 Displacement encoders Key features Analogue displacement encoders MLO-POT- -TLF Conductive plastic

### Series 6000 Torque measured metal bellow coupling

Properties Free of float metal bellow coupling with integrated torque measurement Non-contact measurement system, high robustness High torsional stiffness Limited torque of inertia Performance Measurement

### LUCCI AIRFUSION QUEST II CEILING FAN

LUCCI AIRFUSION QUEST II CEILING FAN WITH IR REMOTE INSTALLATION OPERATION MAINTENANCE WARRANTY INFORMATION CAUTION READ INSTRUCTIONS CAREFULLY FOR SAFE INSTALLATION AND FAN OPERATION. V1.0 QUEST II IR

### T1-40 T1-40BF T1-40V T1-38 T1-38BF T1-38V

Transducers T1-40 T1-40BF T1-40V T1-38 T1-38BF T1-38V Velocity transducers B A L A N C I N G M A C H I N E S B A L A N C I N G M A C H I N E S Principle of operation A voltage proportional to the velocity

### Type 3353 Angle Seat Valve

Type 3353 Angle Seat Valve Application On/off valve with pneumatic piston actuator Nominal size DN 15 to 50 (NPS ½ to 2) Nominal pressure PN Temperature range 10 to 180 C Globe valve with an angle seat

### Supplementary instructions. Connection cable IP 66/IP 68 (1 bar) Retrofitting set/accessory for instruments of the plics family. Document ID: 34107

Supplementary instructions Connection cable IP 66/IP 68 (1 bar) Retrofitting set/accessory for instruments of the plics family Document ID: 4107 Contents Contents 1 For your safety 1.1 Appropriate use...

### SMARTY 160 POWER page 4-5 SMARTY 180 / 220 XL page 4-6 SMARTY TX 250 page 4-7. SMARTY TX 160 Alu page 4-8 SMARTY TX 220 Alu page 4-9

CHAPTER TIG welding Introduction pages - & - WELDING POWER SOURCES DC power sources SMARTY 60 POWER page -5 SMARTY 80 / 0 XL page -6 SMARTY TX 50 page -7 AC/DC power sources SMARTY TX 60 Alu page -8 SMARTY

### MEDIUM VOLTAGE CE-BF SWITCHBOARDS. UP TO 40.5 kv. CE - BF - C - en - REV.00 2012.4

CE - BF - C - en - REV.00 2012.4 APPLICATION CE-BF Switchbords up to 40.5 kv are designed for use in public and industrial distribution system up to 40,5KV for the operation and protection of lines, transformers,

### SICONT Limit Switches Type 3SE3 upto 500 VAC, 600 VDC, 10A

s SICONT Limit Switches Type 3SE3 upto 500 VAC, 600 VDC, 10A Introduction The technical and descriptive information on the function, construction and selection of the new types of 3SE3 limit switches is

### Adjustment functions for both span and shift have been incorporated

SENSORS FOR SERIES LED Type Wafer Alignment Sensor FX-0-F FT-F9 FD-F7 EX-F70/F60 M SH-7 FD-L4 M-DW The use of a safe LED light beam now allows for high precision detection with a resolution of 0!m (.8

### DryLin ZLW Belt Drive

Belt Drive +50º 0º DryLin toothed belt drives have been developed for the fast positioning of small loads. The linear units with toothed belt drive are corrosion resistant, light and compact, besides having

### Magnetic and Hydraulic-Magnetic Circuit Breaker 8340-G2...

Magnetic and Hydraulic-Magnetic Circuit Breaker 840-G2... Description Single, two and three pole magnetic circuit breakers with trip-free mechanism and push/pull on/off manual actuation. A choice of fast

### How To Read A Pipe From A Sensor

Liquid Level Sensor Installation on pipes. Sensing by means electrostatic capacity and is not influenced by the color of the pipe or liquid. Available in 8 to mm dia. and to mm dia. models to enable sensing

### OUTDOOR DISCONNECTORS A division of ACTOM (Pty) Ltd

OUTDOOR DISCONNECTORS A division of ACTOM (Pty) Ltd ACTOM OUTDOOR DISCONNECTORS Single Side Break (SSB) Disconnector 22-132 kv, 800-1 A, 25 ka - 3s Typical bearing assembly. Voltage range 11 kv to 132

Flow switches Flow switch and indicator for liquids and gases Suitable for clear, opaque or turbid liquids (series AD & VH), and for gases (series AD) Flow switching by means of magnetic coupling, watertight,

### Givare NC-SRS 280 och 880

Givare NC-SRS 280 och 880 Aratron AB/Nordic Control, 02 03 SRS280SEALED ROTARY SENSOR PERFORMANCE ±2 Resistance ±20% Hysteresis (repeatability) Accuracy Applied voltage maximum Resolution Output smoothness

### Solid-State Timer H3G

ASH & ALAIN INDIA PVT LTD S-100, F.I.E.E., Okhla Industrial Area, Phase-ii, New Delhi-11000(India) Tel : 011-43797575 Fax : 011-43797574 E-mail : sales@ashalain.com Solid-State Timer Low-Cost, Plug-In

### Power Supply and Indicator Unit Type 5024-1. Fig. 1 Type 5024-1. Mounting and Operating Instructions EB 9539 EN

Power Supply and Indicator Unit Type 5024-1 Fig. 1 Type 5024-1 Mounting and Operating Instructions EB 9539 EN Edition October 2003 Application 1 Application The Type 5024-1 Power Supply and Indicator Unit

### MEMBRANE VACUUM MINI PUMPS

MEMBRANE VACUUM MINI PUMPS The mini pumps described in this page are membrane-type. They can be used both as vacuum pumps and compressors. In the latter version they can supply compressed air 100% oil-free

### RoHS. Shock / vibration resistant. Magnetic field proof. Many variants

Sendix 5000 / 500 (Shaft / Hollow shaft) Push-Pull / RS4 ue to their sturdy bearing construction in Safety-ock esign, the Sendix 5000 and 500 offer high resistance against vibration and installation errors.

### Machine Safety Switches

Machine Switches SI-LS31H Series 31 mm Limit-Switch-Style with Hinged Lever Actuators Features Limit switch design (EN 50047) For use on doors or flaps Positive opening safety contacts (IEC 60947-5-1)

### D.C. Motors. Products and specifications subject to change without notice.

D.C. Motors Order/Technical Support - Tel: (8) 677-5 / FAX: (8) 677-865 / www.crouzet-usa.com / DC Motors Selection guide Gearbox Speed Torque max (Nm).5. Type of Gearbox 8 8 8. Power usable (w) Torque

### Self-aligning ball bearings

Self-aligning ball bearings Designs... 470 Basic design... 470 Sealed bearings... 470 Bearings with an extended inner ring... 472 Bearings on sleeves... 473 Self-aligning ball bearing kits... 474 Appropriate

### Specifications. Model Flow type Pressure type. Air Maximum operating pressure. 1.0 MPa Ambient and fluid temperature. 3% F.S.

Electro-Pneumatic Proportional Valve Series /VEP Electro-pneumatic proportional valve: Flow type () Controls the flow rate steplessly according to current. (It is a / port valve that has an electrical

### 3 Port Solenoid Valve

Port Solenoid Valve Series V00 Rubber Seal Power consumption 0. W (with power saving circuit) VV0 VV00 V00 -V F VS temperature rises: C (with power saving circuit) Sonic conductance Series Standard Large

### Ball valve C 16 valve ball completely moulded in place, extremely low clearance volume, high k v value

Ball valve C valve ball completely moulded in place, extremely low clearance volume, high k v value Advantage maximum safety due to valve ball completely moulded in place - ball and ball seat cannot be

### Customer: Cardiff Hospital NHS (United Kingdom) Machine:

Customer: Cardiff Hospital NHS (United Kingdom) Machine: Bench for leak test Model: Easy TS Page 1 of 7 Date: 6 th March 2012 1. Introduction. Easy TS is a compact and reliable table top bench designed

### K17.12 Door closers K17. Doors 01.09.2013

K17 Doors K17.12 01.09.2013 Waregemstraat 5-9870 Zulte - Belgium - T. +32 9 388 88 81 - F. +32 9 388 88 21 - commercial@sobinco.com - www.sobinco.com Contents 1. OPTIC door closer TS40(V) with scissor

### Tool Turrets and Tool Discs

Our other products Automatic Tool Changer Chucking Cylinders Tool Discs Indexing Tables Tool Turrets and Tool Discs Pragati Automation Pvt. Ltd. 1, IV Phase, 11th Cross, Peenya Industrial Area Bangalore

### Analogue Input, 4-fold, MDRC AE/S 4.1, GH Q605 0054 R0001

Analogue Input, -fold, MDRC, GH Q605 005 R0001 The analogue input is a DIN rail mounted device for insertion in the distribution board. It is connected to the EIB via the bus connecting terminal supplied.

### Air damper actuators

4 634 OpenAir TM Air damper actuators GDB...1 GLB...1 Rotary version, / AC 230 V Electronic motor driven actuators for three-position and modulating control Nominal torque 5 Nm (GDB), 10 Nm (GLB) Mechanically

### Waterproof Connectors for Outdoor Use

Waterproof Connectors for Outdoor Use HR41A Series Mated condition diagram Nut-tightening rear mount type (panel thickness=mm) 70.5 Features 1. Waterproof connector designed for outdoor use Light-weight

### MILLENIUM INSTALLATION MANUAL NTR 735 A. Simple Automation Control Module (MAS)

MILLENIUM Table of contents 1. INTRODUCTION 1 2. HARDWARE DESCRIPTION 2 3. INSTALLATION 5 4. CONNECTION 6 5. USER SAFETY AND PROTECTION OF EQUIPMENT 8 1. Introduction The MILLENIUM series has been designed

### OEM Manual MODEL 2350 ELECTRONIC DUAL CYLINDER SCALE

OEM Manual MODEL 2350 ELECTRONIC DUAL CYLINDER SCALE Scaletron Industries, Ltd. Bedminster Industrial Park 53 Apple Tree Lane P.O. Box 365 Plumsteadville, PA 18949 USA Toll Free: 1-800-257-5911 (USA &

### Compact pressure switch Flameproof enclosure Ex d Model PCA

Mechatronic pressure measurement Compact pressure switch Flameproof enclosure Ex d Model PCA WIKA data sheet PV 33.31 for further approvals see page 4 Process Compact Series Applications Pressure monitoring

### Operating Instructions. Room temperature controller

Operating Instructions 1. Area of application The room temperature controller is used to regulate the temperature in closed rooms such as flats, schools, function suites, workshops, etc. Safety instructions

### SOLENOID VALVES AND PNEUMATIC VALVES

2 A S E R I E S Catalogue 2005-2006 Directly operated solenoid valves Series A 2/2 way, 3/2 way monostable, bistable (with magnetic memory) Ports M5,, cartridge ø4 The Series A solenoid valves are of the

### Electro-pneumatic control valves

Electropneumatic control valves 7 Miniature solenoid valves for alternating current Conform to the Low Voltage Directive or mounting on subbase or footprint in accordance with CNOMO recoendation E 066120N

### How To Use A Flowmeter

INLINE flowmeter for continuous flow measurement Economic integration in pipe systems without any additional piping 3-wire frequency pulse version to directly interface with PLC s (both PNP and NPN) Connection

### 3-Component Measuring System

Force 3-omponent Measuring System for utting Force Measurement During Turning Modular system for measurement of cutting forces when turning outside and inside diameters on turret lathes. Machine adapters

### Explosion proof enclosures

1 of 7 Explosion proof enclosures DE8 C 2 of 7 The Ex d enclosures are rugged and designed for harsh environment like: Oil and gas industry Chemical industry Pharmaceutical industry Agribusiness Without